Cool Air replied promptly to my call for help with my furnace. The technicin, Luis Mendez arrived punctually, was friendly and respectful, and very knowledgeable. He quickly diagnosed the issue with my heating system, ordered the part and returned as soon as they arrived and completely repaired my furnace. The whole experience was very positive.
Cool Air called me as soon as I submitted an email to Angie's List. Their technician, Luis was here first thing the next morning, diagnosed my problem and got repair underway immediateley. The girl on the phone--Ashley--was SO good--professional and friendly, and kept me informed throughout!
Very helpful and knowledgeable.
The service was great. The technician was phenomenal.
I think Michael and Daniel did an amazing job, very thorough. Michael explained everything to where it was easy to follow along with what he was saying. Both of them were kind, courteous, helpful and patient. Cool Air Solutions, Thank you very much!
Jorge was knowledgeable, taking the time to patiently answer my questions, and making recommendations that helped me make an informed decision. I feel like our HVAC system is in good hands with Jorge and Cool Air Solutions. Quick, safe, professional service, and reliable customer service to back it all up.
Hats off to George - top technician. Conscientious, great explainer ,should be valued employee.
On time, informative.
I like cool air solutions that is why I went back to them.
Performed AC maintenance on two systems 2004 Carrier condenserâ€™s. Upon my maintenance there were multiple points of concerns that were addressed with the homeowner. Downstairs condenser- 1. Found the condenser fan motor had significant oil leakage occurring from Bearing and Can Potentially lock up or over heat. Motor already showed signs of failure on start up due to the delay of the motors initial start up. 2.Starter showed signs of burn marks and pitting on contact points this component acts as the brakes for the system. 3. Duel secondary motor control has become weak on fan side terminals. This is initially caused due to the motor using more power than needed 4. System contains R22 refrigerant which was completely phased out January 1, 2020 5. Compressor was also locking out during the stress test which indicates to me that the compressor could potentially be dying. Compressor saver kit Reduce this problem from happening. Upstairs condenser- 1. Condenser fan motor is also leakin
Preformed Ac maintenance on 5 year old Lennox condenser
Upon arrivals performed gas valve replacement. installed and verified system works for heating. Added sediment trap tp system. Also installed indoor and outdoor surge protectors to keep system protected from any power surges. Washed outdoor coils. Re taped insulation that is covering suction refrigerant line. Primary and secondary motor control in range. System was reset tested and fully operational upon departure.
Upon arrival performed air conditioning tune up and sensi predict installation. Replaced both leaking condenser fan motors outside. Replaced with high efficiency slow start up motors. Secondary and primary motor control done. Washed outdoor coils with water and indoor air conditioning unit. Indoor secondary motor controls in range. Sensi predict is in working order. System was reset tested and fully functional.
Upon arrival performed diagnostic found gas valve to be shorted out. Verified and tested with contractor, system did not shut off. Only shuts off when gas valve kicks on. Ordered part from manufacture. Adding 2 surge protectors to keep system protected from any power surges. System is non operational for heat.
Performed AC maintenance on 2017 Lennox system. Checked indoor and outdoor unit electrical and system components. Temperature split is in range and system is producing proper temperature split. Merv filter is dirty and should be replaced. Homeowner has one on order and will replace it when it gets in. Air scrubber bulb is burnt out and should also be replaced. Washed outdoor condenser coil inside and out. Replaced air scrubber catalyst and signed homeowner up on maintenance program. Office gave customer option to sign up and use today as first visit. Cycled system, system is operational upon departure.
Installation of a Lennox Single Stage 16 SEER ML14XC1 Air Conditioner with high performance coil to assist higher SEER rating, including
Installation of a Lennox ML14XC1 Single Stage Air Conditioner with High Performance/Efficiency Coil, including Permits, Electrical, Line Set, and Installation. Total amount will be paid in full by check upon compilation
Quality control check and picked up check
Upon arrival replaced faulty hot surface igniter, system is operational.
Replace existing furnaces and add AC. Swap attic furnaces so upstairs ac is 4-ton and downstairs is 3 Ton. Enlarge upstairs return duct for proper airflow. Existing condenser location meets code requirements. Permits and HERS testing is included. Optional items : High Flow register set X2= $800 Rossi Air balancing dampeners X2= $450 Wifi Thermostat X2= $200 High Flow 5â€ filtration kit X2= $440 Financing available= please contact sales rep Warranty= 10 year parts and compressor, Lifetime heat exchanger, 2 year labor and 1 year maintenance.
Performed furnace maintenance on system. Cycled system for heat. Verified proper heating sequence of operations. Temperature rise across heat exchanger is within range. Recorded indoor motor and inducer motor amp draws. Cleaned blower and heating compartment. Performed 20 point inspection checklist. Removed indoor motor to safety inspect heat exchanger. Went over findings and recommendations. Cycled system, system operational upon departure.
Arrived on site to perform combo tune up on a 2018 lennox unit. Furnace and Evaporator coil located in attic. Condenser located on side of home. Client stated he is familiar with unit and trade but no issues. Client supplies his own filters. Washed. Condenser inside and out. Unit was good slightly dirty and dog had but good. Electrical compartment is good. Primary is good. Amp draws on compressor and fan motor are good. Fan motor is good. System pressure is good and cooling hole at 21 degrees. No protection on unit. Indoor unit good. Filter was good and was replaced by client. Blower assembly is good. Motor is good and amp draws are good. Inducer motor is good and in range of amp draws. Evaporator coil is good. Drain lines good. Temperature rise is good and in range of heating home at 54 degrees. All safety switches are operational. No protection on either unit. Recommend adding a surge protectors that are hard wired in in control board to prevent system getting damaged from electrical
Performed Combo tune up on Lennox system in San Marcos. Tested and verified correct operation of the cooling and heating. No recommendations at this time
Performed AC maintenance on 2020 Goodman condenser. Upon the maintenance everything checked out properly regarding refrigeration cycle and electrical amperages. Home warranty left debris laying everywhere inside of attic and on top of roof from previous system. Also found that secondary drain pan is completely rusted out and can potentially leak water into the Ceiling. Ductwork was also not sealed properly with air leakage occurring all around evaporator coil. Recommending a new pan is added in a seal is done to system to ensure that no dust and debris can enter the airstream of supply air. Upon departure system is fully operational and cooling home