He was very nice friendly efficient knowledgeable I had no problem whatsoever with him
Very well very informative very kind
Luis found the problem, fixed it!
Very Happy With The Service Of The Service Personal
Luke arrived an hour early! Of course he called to confirm we would be home... Service was friendly, efficient and he had the parts to make the repair on our home AC unit in 30 min. We are once again sitting in cool comfort.
Got a call to set up the appointment and Luke came out on time. He was friendly and professional and really cared about my satisfaction. Everything is fine.
MICHAEL PIERSON DID A GREAT JOB IN SERVICING MY A/C. HE IS HONEST, PROFESSIONAL, POLITE AND PROMPT. I HIGHLY RECOMMEND "COOL AIR SOULUTIONS" FOR YOUR HVAC NEEDS.
Very knowledgable Technician, and was able to explain things in a way I could understand.
Everything was explained in easy to understand language.
Tested both systems and measured indoor temperatures. Replaced filters. Checked outdoor electrical and measured voltages and amps. Leaned condenser coils. Verified refrigerant charge.
Heating and cooling tune up
Install Lennox 16 SEER single speed complete system. Install 5â€ Media filter kit. Relocate and enlarge supply register in living room to 12x12 (customer to take care of patch work). Add new supply register to master bathroom. Seal all cans and install high flow bar style registers. Build catwalk, light and switch, extend gas and electrical add ceiling return air. Permits and HERS testing included.
We will be installing a new Bryant slim line condenser only. This includes a condenser pad with service disconnect. Also includes permits and everything included in the permit process
Performed system operations tune up and maintenance on both heating and cooling systems. Checked all electrical components and controls. Measured airflow and recorded temperatures. Cleaned outdoor coil and indoor blower cabinet. Changed air filter. Cleaned flame sensor and condensate drain.
Upon arrival performed condensate drain box. And brand new venting proper venting
Pressure switch hose was open. System now functional
Upon arrival performed maintenance. Collectors box is cracked & needs to be replaced. Venting is completely wrong needs pvc ran. Have power shut off due to leaking water and could cause damage to system. Coming back out to replace parts. Collected 216, 1945 due upon completion.
Ac check up
Performed performance check and cleaning of the furnace. Checked electrical. Components and temperature rise. Checked heat exchanger for reliability and monitored operation of the heater.
Thermostat replacement in San Marcos, Ca.