I think Michael and Daniel did an amazing job, very thorough. Michael explained everything to where it was easy to follow along with what he was saying. Both of them were kind, courteous, helpful and patient. Cool Air Solutions, Thank you very much!
Jorge was knowledgeable, taking the time to patiently answer my questions, and making recommendations that helped me make an informed decision. I feel like our HVAC system is in good hands with Jorge and Cool Air Solutions. Quick, safe, professional service, and reliable customer service to back it all up.
Hats off to George - top technician. Conscientious, great explainer ,should be valued employee.
On time, informative.
I like cool air solutions that is why I went back to them.
I found your staff for sales install and service to be thorough, conscientious, and professional, the installers did a nice clean installation.
He was very nice friendly efficient knowledgeable I had no problem whatsoever with him
Upon arrival performed heating maintenance. Indoor motor is leaking oil, has some dirt and debree build up. Secondary motor control out of range. Blower wheel slightly dirty. Gas valve and shut off in working order. Dusted off all electrical connections. Circuit board and electrical connections good. Amperages throughout system good. Temp split at 50 degrees. Undersized ducting, restricting a lot of airflow system is currently performing at a 2 ton system. Ducts are not sealed at joints, there is a lot of air flow leakage. Could not do maintenance on other systemmas it is not functional, will follow up with client for part replacement. There is no emergency drain pan under coils. Heat exchanger has heat spots. System is operational upon departure.
Perform diagnostics check and found system with no leaks present at this time. System temperature split was 71Â°F return and 50Â°F supply. This is more than a 20Â° split that I am looking for and temperature is good inside. Hooked up refrigerant gages and found the pressures exactly where they need to be to manufacture specs on York condenser outside.
Performed furnace maintenance checks on a Coleman gas furnace. Tested electrical components to determine if they are working within spec.
Installation of a Lennox XP20 Variable Speed A/C with Duel Fuel SL280V Variable Speed Heater. Including PureAir PCO.
Performed routine fall maintenance on Lennox furnace in San Marcos, tested and verified correct operation of system. System is running correctly with no recommendations at this visit.
Post job walk
Install 2 baffles in middle bathroom and middle bedroom to force more air to back bathroom
Performed combo tune up on 1 year old Lennox system. Cycled system through heating and cooling modes. Checked indoor and outdoor unit electrical and system components. Amp draws are all within range. Indoor blower motor is clean and amp draws within range. Temperature rise in heat is within Range. Temperature split in cooling also within range and cooling efficiently. Primary motor control is in good condition. Secondary motor control also in good condition. Pulled off condenser panels as well as condenser fan motor and thoroughly washed out condenser coil. Replaced Merv 16 filter with approval. Also Renewed yearly ESA maintenance program. Cycled system, system is operational upon departure.
Install Secondary Drain Pan under existing air handler in attic. Install safety switch onto the newly installed drain pan and wire to air handler to disable the system in the even water is in the secondary pan.
Replaced a comfort M30 thermostat with new icomfort M30 thermostat. Also saw that the account was never set up in the first place and the WiFi I was never set up as well. Set up the Wi-Fi and the account and the client download the app and hook it up to his phone. Client is very happy at this time but was unable to connect the two system zone on left side of house due to the router being too far away from the thermostat. I let the client know if he can fix the Internet issue towards the left side of the house we will hook up the thermostat to his phone afterwards
Inspected heating system for popping sound during operation. After a call for heat discovered the source of the noise is coming from the flue pipe cooling after operation. Installed some additional set screws to further secure the flue pipe and measured system temperature rise (50F) Raised the 1st and 2nd stage heating blower cfm by 50 to allow for a lower temperature rise.
Installation of 2 SL280V Furnaces with Merv 16 Filtration, Permits, Check Pricing is shown.
Performed furnace maintenance on 2000 comfort maker heaters. Upon my maintenance I came across a few major concerns and safety issues regarding the operation of the heaters. Downstairs- 1. Found that heat exchanger has developed cracks in all four chambers due to overheating. This is left the heat exchanger in a failed condition and is not safe for operation. 2. Inducer draft motor is running at 1.70 A exceeding in specification of 1.60 3. Circuit board has developed heat marks on diodeâ€™s and can lead to intermittent behavior and failure for AC and heating call. 4. Temperature rise on system was 75Â° exceeding the 65Â° limit this is due to low Airflow and ultimately result in damaging the heat exchanger 5. Static pressure on system is the airflow that was recorded at .95 water column which is an indication the air is definitely restricted considering that the specifications should only reach at .50 wc Upstairs 1. Upstairs heat exchangers also developing small fractures and cracks n
Performed diagnostic on new install system not heating. System hasnâ€™t worked in heat since install. Went into attic and found gas valve turned off. After turning gas valve on also found reversed polarity causing system not to heat and only work in cooling. Cycled system for heat, system cycled on and started heated correctly. System is operational upon departure.
After Lennox rebate total $14,037.00