Professional and friendly
Checked everything and made reasonable suggestions.
Jimmy was a pro right from the start with the phone call letting me know he was on his way. He explained the maintenance that he would performing. He explained to me what he discovered during his inspection clearly and distinctly. You have an excellent individual representing your company. Kudos to Jimmy.
Jimmy was very helpful.
Performed heating tune up on carrier furnace. Tested both zones and ran heat cycle. Measured temperature rise and monitored operation. Measured voltages and amp draws. Inspected control elements and measured ignitor. Removed foam insulation debris from inside furnace control cabinet. Replaced air filters.
Arrived on site to diagnose a 1998 comfort maker unit. Client stated unit is very old and she been advised unit could fail. But now it dose not turn on. Found unit not operating but to electrical fuse relay popped. Replaced and kept tripping unit and checked all electrical wiring and they stated they tried to replace thermostat and found it wired bad rewired it and replies and stayed running. Advised due to age asked if we could check for a safety inspection. Client approved and inspected heat exchanger and found all 4 chambers compromised. Client did see and is aware and advised unit is not safe to run due to condition. Client is aware and what is going on. Client did not want to repair and Wanted replacement options. Turned call over to darren and he did go over system replacement options at that time. Client is present with client and they did want to go forward with replacement. Advised due to go with replacement would not collect Dx fee today. Left system not operational due cra
Heating tune up and service. Tested heating system and monitored controls. Measured temperature rise. Measured ignitor and blower amps. Tested voltages. Cleaned burner compartment.
Upon arrival performed maintenance on heating systems. Cleaned inside of furnaces and dusted off all electrical connections. Motors are brand new, blower wheels are extremely dirty. Say heat exchanger from blower compartment and saw a lot of discoloration on joints. Temp rise was quite high, advised client we can pull heat exchanger to give a full inspection on heat box, client declined to do that. Did not want me to pull it out. Ducting is very dirty inside of plastic tubing. Standard filtration. Dusted off all return vents. Waxed furnace units. Replaced filters client provided. System is oper Upon departure.
Quality control check and verified loose chamber for a Rheem heater
Performed furnace maintenance on 2003 weather king furnace. Upon arrival Tristan stated that he noticed recently that the thermostat had lost power a few times and adjusted the red wire and it appeared to work although he also got a message informing him that his furnace had unexpectedly shut down. During the maintenance I performed a full safety inspection and found a major fault within the heat exchanger of the furnace. Weather King heater- 1. Pulled and inspected tubular heat exchanger and found multiple heat spots in three loose tubular cells which were found to be defective and confirmed by second opinion. 2. Measured system static pressure and found that it was a total of 0.81 one manufactures design the system for 0.50 which indicates a major Airflow restriction. 3. Evaporator coil was completely plugged up due to previous renter Not swapping filter out enough. Recommend 5 inch filter, Especially of system is to be cleaned and will have a much longer life up to a year before b
Inspected system for faults and offered repair options.
Performed leak Inspection on 2016 Goodman condensing unit. Upon arrival inspected outdoor unit for any signs of refrigerant leakage. All manufacture welds Show no signs of leakage along with the aluminum coil showing no signs of a leakage as well. Inspected evaporator coil in the attic and also found no signs of refrigerant leak. At the moment the client is unsure what he would like to do and would like some time to think about the route he would like to go due to the summer already coming to an end which gives him some time. Client is aware that system has a leak inside of the system and it leaked I need to be injected to help locating pinpointed due to it Being hard to find the leak today. On arrival disconnect is left upside down at condenser
Performed AC Diagnostic 2016 Goodman condensing unit. Upon arrival client sitting in just a couple weeks ago he noticed the system is no longer Cooling to the proper efficiency it had. When they first move-in. Unfortunately today was raining and there was ice formed throughout the system. Refrigerant pressures were measure low on R410a refrigerant charge. This is due to a leak somewhere within the refrigeration cycle. Inspected evaporator coil inside of the attic and found no signs of refrigerant leakage. Inspected condenser coil outside and found oily residue on the bottom of the condenser by the compressor And the aluminum coil. Due to the coil being covered in water it makes it bad to determine where the leak is. will be rescheduling to come back as soon as possible for refrigerant leak search Once ice is melted and rain is no longer present. Upon departure System was left off at the disconnect and recommend not to run until system leak is fixed and is fully charged up.
Technician arrived on site, started AC tune up on systems. Cleaned the condensers with coil cleaning chemicals. Cleaned out the inside of the condensers. Cleaned out electrical. Secured relays inside units as they were loose. Tested out electrical components. Found the following: upstairs condenser fan motor is leaking oil. Is almost consuming more power than itâ€™s rated for. Upstairs motor controller is low. Will fail soon. Compressor is almost consuming more power than itâ€™s rated for. Downstairs ac: low on charge. Made recommendations to client. Will follow up on Monday. Made estimates to relocate condensers as well.
Tech arrived on site. Began demoing the old return duct. Installed new start collars and sealed them up. Installed new 20 in return duct. Went outside to the condenser and installed fan motor, booster kit and capacitor for the fan motor. Tested charge and monitored electrical. Unit is cooling upon departure.
Inspected the mini split and disassembled the head unit to find the issue. Found fan rubbing o the frame inside the unit. The fan can be adjusted but it will slide back down over time. Need to replace the head unit. Awaiting approval from Larry at Acpro tech support. Emailed video on Friday evening.
Arrived on site to perform spring tune up on 2 2007 airflow units. Both condenser unit located in back yard. Furnace and Evaporator coil located in attic. Client stated no issues. Cycled both units. Washed both condenser coils inside and out. Checked all components. Found primary starters burnt up and worn out from normal operation. Recommend replacing. Found secondary control for downstairs was boarder line bad. Upstairs was good. Advised it could fail in future. Would recommend replacing to keep system operating. Checked start up amps on both compressor. Found upstairs to have old design of the compressor booster kit and it good. Downstairs is getting hard start up from age but is in range. Recommend adding a compressor booster kit to help preserve it from hard start up. Fan motor have both leaked in oil in past. Downstairs is pulling 2.0 amps and max rated at 1.4. Upstairs motor was pulling 1.1 and max rated at 0.7. Advised motor are working hard and they could fail in future from o
Estimate is for two variable speed 3 Ton Systems. Estimate includes all of the below items. Full Price - $37,730 After Family / Friends Discount: Price w/ Financing - $23,491 ($273 /mo) Price w/ Cash/Check Discount - $22,739