Jimmy was friendly and very thorough. He figured out what the problem was with my AC. Thankfully he had it up and running quickly!
Jimmy always does such a great job! He is knowledgeable, professional, and efficient!
Truly satisfied with the service
Very professional and fair!
service was prompt and and the man was very competent.
The crew was extremely professional and made me feel at ease in my home.
Arrived on site to perform spring tune up on a 2004 unit. Unit seems to be original to home. Condenser in back yard and furnace and Evaporator coil located in attic. Spoke over with client and she stated they had system running and was only blowing warm air. They havenâ€™t had maintenance in a while and lack it. cycled unit and found both units not operating and no airflow produced. Advised would inspect both unit to see why unit is not working she stated sheâ€™s had issues in past and husband replaced fan motor and secondary motor control for fan in past himself. Found it not the best connection and recommended rewiring with new good connections and spades. Found no low voltage advised would have to trouble shoot for low voltage to get power to the outdoor unit. Found cooling terminal to have been pulled off or lost connection. Got indoor unit to turn on. Inspected out door unit and found compressor not on. Advised client of findings outside now that we got power to it. Inspected ele
Performed AC diagnostic on 2018 Carrier Condenser. Upon my diagnostic client stated that he is only able to get the fan spinning on the system by pushing it with a twig. Upon arrival I found that the fan motor was not spinning and the compressors was off. During the diagnostic I found multiple points of concerns 1. Duel Secondary motor control has become defective and was mostly caused by the compressor or fan using more power or also by a power outage. 2. Compressor is using high amperage on start up. 3. Both Power disconnect were not supplied with fuses nor surge protection. 4. Outdoor condensing fan motor has oil leakage coming from bearing. This can lead to premature failure and overheating. 5. Recommend maintenance is done twice a year to keep system at standard and full efficiency. Discussed full condition of system with client and he is aware of how it is running at the moment. Presented options regarding repairs and Ronald Chose to go with the premium long-term options. Will n
Arrived on site to diagnose a no cooling 2001 comfort maker system. Spoke to client and he stated just recently system stopped producing airflow but outside unit would still turn on. Cycled unit and no air flow coming out. Advised I would inspect indoor unit. Found board was bad as it would not send 120 to turn on blower motor. By passed unit to check motor and found it pulling 10 amps and max rated at 12 and is going to be failing soon. Secondary motor control for blower is out of range and weak from blower motor over working and going bad. Blower assembly and wheel are really dirty due to the lack of maintenance not done to system in past years. Went over all find and in furnace as unit is not operating properly due to bad board. Went over all repairs and recommendations with client. Client stated they didnâ€™t want to put a lot of money into unit that could fail at any time. As they are considering replacement and would like to get someone out to go over replacement options. Turned
Performed AC maintenance on 2001 Goodman system. Verified refrigerant pressures were in range and cleaned up condenser coil. Found a deal secondary motor control is far o of range on the hermetic side terminal for the compressor. System Contained R22 refrigerant which was completely phase out January 1, 2020. Starter had slight pitting on contact points although itâ€™s still working at this time. Fan motor also was in range for Amperage. Measured compressor amperage and found that it was pouring a total of 22 which is incredibly high for what is designed for a max of 23 this indicates to me that the compressor is beginning to go out and heâ€™s using more power due to the duel secondary motor control being weak as well. Discussed full condition of system with Nick and he understands how old is running at the moment. Upon departure system is fully operational Cooling and swapped out filter that is supplied by client
Found secondary drain switch open on arrival. Removed evaporator panel and pressurized primary drain line with nitrogen. Cleared the debris and tested with a. Title of water to confirm primary line is now draining.
Performed AC maintenance on a carrier system. Units cooling temperature split is 22 degrees. Duct runs are sealed and free of obstruction. Condensate lines are clear but have no overflow switch. Blower motor is clean and amping ok. Outdoor unit was chemically washed. Electrical components are in range at this time. Compressor and fan amp draws are ok. Refrigerant levels are good. Compressor bay and service panel was cleaned. Outdoor unit needs electrical protection. System was running at end of appointment.
Looked through coils and found no signs of leak dye, refrigerant levels are similar to the day of re charge. System is sitting at an 18 degree temp split. Advised client, we will have to do another leak check during fall tune up. Let the system release dye.
Upon arrival found saftey switch to be leaking water. Replaced saftey switch and got system going. Poured 2.5 gallons of water to prime drain. Drain is draining perfectly. Advised client she can run ac.
Found circuit board wiring issue. The blower motor was wired for medium low on cooling mode. Rewired the circuit board and the system delta t was tested and is cooling properly at this time.
Systems qualifies for $500 clean air rebate online
Performed AC diagnostic on 18-year-old Aireflo Condensers. Upon my diagnostic client initially stated that just the other day the condenser fan motor had failed and is no spinning. Performed full diagnostic on system and found multiple points of concerns. 1. Outdoor condensing fan motor has completely failed and is no longer spinning due to it locking up. 2. Starter showed signs of pitting and burn marks on contact points 3. System Contained R22 refrigerant which was completely phased out on January 1 2020. 4. Condenser had a coil Rot 5. Compressor saver kit should be installed to help reduce start up amps 6. Service disconnect was not equipped Surge protection or fuses. Discussed full condition of system with homeowners and they would like to replace everything. No repair was done at the moment and will be returning for a full system installed.
Tech arrived on site. Found the capacitor to be leaking oil and completely failed. Replaced capacitor and found the compressor to be over amping. Also the return is undersized. Client said the room closets to the garage is always hot. Recommend adding a return into the room. Clients are considering replacing the unit do to age and condition. Also possibly adding a mini split in the garage.
Upon arrival performed maintenance on Goodman system. System is about 5 years old. Verified refrigerant levels are in range. Temp splits are very good. Replaced 2 filters that client provided. Dusted off return vents. System does not have a secondary drain pan for emergency back up. Washed out condenser coils. Secondary motor control is in range. Indoor blower wheel is dirty. Amperages are In range. Primary starter is good. System is starting to get dirty inside for blower wheel. Advised client to replace filters more often. 1. Dirty blower wheel 2. Washed coils 3. Refrigerant levels in range 4. Tested components 5. System amperages in range. Client is gonna talk to husband about membership
Technician arrived on site. Condenser was not operational. Found the capacitor to have failed. It was replaced in June 2020 by our company. Fan motor was rusted and not looking good. Installed a tester capacitor. Compressor and fan motor came on. Compressor amps were high but not over amping. Fan motor amps were high. After explaining to the client, we decided it would be best to explore replacement options.
Recharged system 2 and tightened txv bulb. Tested indoor temperatures and verified operation.