Well I need the copy of the three options so I can review them . I want you to email me or sent me a hard copy. Thank you and God Bless be safe Liz
After 12 years with another company, I decided to give Cool Air Solutions a try. I am glad I did. George was very kind, very knowledgeable and thorough in inspecting both my air conditioner and furnace units. He spent a bit of time explaining things to me, which I really appreciated, not just so I could understand but it also instilled confidence that I went with the right company. George was excellent.
They were very professional,
Very professional and knowledgeable of what he’s doing and explained it clearly
Amazing service! Great price. Extremely honest and genuine technician. Took the time to explain everything, breaking down all the details. If you’re considering a company to contact for your service, trust me, go with Cool Air Solutions. Take advantage of their monthly service plan too.
Very knowledgeable and friendly service.
Very informative about function types ACs
Arrived on site to replace U.v light and catalyst kit in system. No work done on system itself and client is aware we just returned just to replace kit. U.V light is operational and lit. System is operational upon departure.
Upon arrival performed maintenance on 2 airflow heating systems. Cycled systems on and off, verified heating order of operations. Found blower wheels to have dust build up. This can cause blower wheel to go off balance. Indoor motors have slight oil leaking. Amperages throughout system good. Temp rise splits in range. Flame sensors cleaned. No distribution boxes on returns, ducts tapped into caging of furnace. Secondary motor controls low & out of range. - dirty blower wheels - no distribution boxes - heat exchangers have major heat spots Advised client that heat exchangers could be damaged, needed to pull heat exchanger to verify crack, client declined. Recommended to get low level co detectors. Systems both reset tested and fully functional.
Arrived on site to perform fall tune on a 2019 Lennox system. System located in attic. client stated no issues. Cycled thermostat and was good. Found some black flex and some new flex ducting. filter was dirty recommended replacing filtration. As it is over due replacement. and should be doing so every 1-2 years. Blower assembly is good. Motor is good. Amp drawls are good. Inducer motor is good and amp draws are in range. Exchanger is good. Evaporator oil was good. Drain lines was good. All safety switches are operational and good. Temperature rise is good and on range and heating home good. Found on protection on either unit would recommend adding surge protectors on system to prevent and protect system from getting damaged from electrical surges and power outages that can damage or even short out system and components. Cycled system to ensure system operating. Went over all findings And recommendations with and would like to sign up on maintenance plan and replace U.v replacement kit
Performed furnace maintenance on 2006 two system Carrier Heaters. During my maintenance I found a few safety concerns and points of failure that may occur. Downstairs furnace- 1. Inspected heat exchanger and found that stamps have cracked due to Airflow restrictions and over heating temperatures over time. Performed hydrotest to confirm that stamps are cracked and verified that all three cells On the heat exchanger assembly are compromised. Due to the heat exchanger becoming compromised there is a potential chance Combustion gases Could enter the airstream once the blower motor turns on. 2. Measure static pressure and found a total of 0.69wc. Recommended manufacture Airflow is rated at 0.50wc. 3. Temperature rise Measured at 57Â° manufacture specifications rated at 60. 4. Scroll Wheel was covered in dust and debris due to 1 inch filters not being swapped out consistently, recommend to do every one to three months. 5. Indoor blower motor hod oil leakage coming from bearing, The lubrica
Performed furnace maintenance on 9 year old carrier 98 percent system. Met with Marcus, homeowners not present. Cycled both zones for heat. Checked indoor unit electrical and system components. Verified proper heating sequence of operations. Temperature rise across heat exchanger is within range. Ran system through 20 point inspection checklist. Cleaned off filter return register. Furnace exterior is covered in foam insulation that can not be cleaned off. Could not go over findings and recommendations, will be emailing everything to homeowner. Cycled system, system is operational upon departure.
Performed Fau maintenance on 1 year old carrier unit. Cycled system for heat. Verified proper heating sequence of operations. Temperature rise across heat exchanger is within range. Amp draws on indoor and inducer motor are in range. Blower wheel is clean and motor looks healthy. Ductwork is all properly strapped and sealed. Cleaned burner assembly and blower assembly. Cleaned flame sensor. Tested all zoning and heating components, all are working accordingly. Cycled system, system operational upon departure.
Installation of a 20 SEER Lennox Variable Speed XC20 and Variable Speed Furnace with 2 Stage Gas Valve. Rebate of $1050 will be applied towards total amount once received, bringing total to $17,710
Upon arrival performed maintenance on furnace system. Cycled system on and off for heating, went through operations of heat make sure everything was working properly. Found secondary motor control to begin going out of range. Indoor motor is leaking oil with a dirty blower wheel, dirty blower wheel can cause to put weight and make motor work harder then normal. Inducer draft motor is over amping, working harder then what it is specified for. Circuit board and electrical connections good. Evap coil clean. Heat exchanger has a lot of heat marks and weak points, did saftey check to make sure system is not damaged. Did not identify any cracks. Temp rise in range. Return ducting is very undersized. Supply ducting is good. Recommend adding another return ducting to help bring more airflow into system. Client could not go over options due to being at a meeting. Sent over information.
Estimate to reconnect condenser. Deep vacuum for lineset / evaporator coil and compressor. Nitrogen purge and complete recharge.
Arrived on site to perform furnace maintenance on 2 10 year old Bryant furnaces. Cycled systems for heat. Verified proper heating sequence of operations. Tested all heating components and safety equipment. Furnaces do not have sediment traps on gas valves. Cleaned and wiped off furnace exterior as well as blower assemblies and heating compartment. Cleaned flame sensors. Replaced 1 inch filters. Ran systems through 20 point inspection. Indoor blower wheels are both dirty. Secondary motor control for both indoor motors are out of range, and both indoor motors are running hot and have lost a significant amount of oil. Evaporator coils are also both dirty, causing a slight restriction in airflow and causing motors to work harder as well. Pulled off evaporator coil covers to inspect heat exchangers. Heat exchanger chambers do have some hot spots throughout. Went over findings and recommendations with homeowner. Did explain condition of the units, as well as all recommendations. Went over fi
arrived on site to install surge protector on condenser unit. Installed surge protector. Cycled system in cooling and Ac to ensure system operational. System is operational upon departure.
Quality control check and crack verification
Performed furnace maintenance on 2001, 2 system Bryant heater. Upon the maintenance this is turned into a diagnostic duty heaters both being non-operational and tripping on high limit. 1. Found temperature rise was 83Â° which is incredibly high from what it is specified on the data plate 2. Both high limit switches are going bad due to it consistently in the years before being tripped. 3. Heat exchanger from downstairs was verified cracked. Discovered the crack on a dimple due to high temperature rise and low Airflow. 4. Downstairs blower scroll wheel was off-balance creating a screeching noise readjusted and noise is gone Recommendations- 1. Replace heat exchanger if available 2. Increase airflow by cutting in new return intake 3. Replace both high limits to prevent heating problems 4. System replacement options
2nd opinion on cracked heat exchanger. Customer is going to let me know what home warranty is going to do