The technician was professional polite and courteous
Luke did an outstanding job and was very knowledgeable about his craft. He took the time to answer every question we had. I highly recommend Cool Air Solutions.
Very good worker and professional
Jason and all the Cool Air Solutions staff are outstanding! Never try to push sells on you and they have top notch service. Super friendly and very knowledgeable. Would recommend them to anyone needing any HVAC services.
Upon arrival performed maintenance. Indoor motor is leaking oil. System ignites nut gas valve does not stay open. Gas does not have sediment trap could have possibly flooded gas valve. Spark ignitor is good. Blower wheel is really dirty and needs cleanings. Andrew came out to give replacement options.
Doing a two system heating maintenance out here in Winchester.
Gas valve turned off by installers
Upon inspection looking at ducts and zoning system is performing the way it was designed. Running 2 zones at one time will cut CFMs from one zone due to having to supply whole home. Zone signal box fell of damper holder, reconnected damper signal.System is good, air is coming out at 49.5 degrees. Air flow throughout home is good.
Replace outdoor condensing unit and attic evaporator coil with new secondary drain pan, safety switch, ac pad, 220v disconnect and whip. All permits and HERS testing included.
Heating and cooling maintenance
Upon arrival performed maintenance. Outdoor system was not operational upon arrival. Replaced outdoor fan motor, installed battery cap with compressor hard start kit. Replaced disconnect with whip. Indoor motor is in really good condition. Blower wheel and ducts good. Circuit board and electrical connections good.
Upon arrival performed lowes heating tune up x2.
Performed fau maintenance on 2 2006 Systems. Cycled furnaces for heat. Verified proper heating sequence of operations. Temperature rise across heat exchangers are within range. Blower wheel amp draws are within range, although blower wheel for kitchen side unit is on higher end of allowed range and is starting to leak oil. Highly recommend replacing blower motor. Blower wheel for bedroom unit is extremely dirty. Tested and verified safety components. Neither unit is equipped with condensation safety switches on drain lines. Highly recommend adding switches to secondary drain lines. Shut off valves working accordingly. Went over findings and recommendations with homeowners as well as pricing and pictures. Do not want to take care of any work at this time. Replaced all 3 filters. Cycled systems. Systems are fully operational upon departure.
Upon arrival performed maintenance on 1 year old system. Filter needs to be replaced customer said he will buy himself. Indoor system is working at normal operations. Temp rise good. Washed off outdoor coil with water. Amperages throughout system good. Duct work is good and strapped. System is working at normal operations.
Ac maintenance in Winchester ca
Tune up for both heaters and downstairs Ac, upstairs ac was excluded for this visit per customer. Inspected and measured all electrical components. Checked furnace integrity and functionality. Checked airflow and measured temperature rise for both systems. Changed filter.
Reconfigured drainage hoses on furnace
Commercial heating maintenance in Winchester, Ca.