My whole experience was pleasant. Everyone I spoke to was nice and respectful. Jamie included me in the entire tune up process. He explained what he was going to do and why. He was respectful of my space and cleaned up after. The price was very reasonable. I would definitely recommend Cool Air Solutions.
Was able to provide a great price.
Darren was knowledgeable, explained things clearly, and helped us make an informed decision on what was best for us.
Jorge was outstanding in every way. Thorough in his presentation of information and options, quietly efficient and respectful in our home. Very professional and friendly. Good man!!
Michael was very nice and professional. He wore boot covers in my home which was nice. He took the time to explain everything in detail so that I could understand what he was doing. We will definitely be calling back for our AC needs.
Excellent technician. Very courteous and friendly. Informative. Excellent service.
From the very first time I called Cool Air Solutions over 1 year ago, I knew I had found an Air Conditioning/Heating company with a total commitment to their sales and service. From the Sales and Installation of our new system a year ago to the outstanding preventive maintenance service we received today, we know we chose the right company. We are as committed to Cool Air Solutions as they are to us. The technicians are very friendly and always explain everything in complete detail. Thanks to everyone at Cool Air Solutions
Tech arrived on site. Found an old ac with now power. Checked breaker and still no power. System was flat. Cap was low. Fan motor ohmed out bad. Compressor was okay. Homeowners didnâ€™t want to hear options.
Reconnected the thermostat to the hub. Configured the zones for the home. Connected the WiFi and connected the dealer control access.
Arrived on site to perform maintenance on 3 year old Lennox system. Cycled system for cooling. Checked outdoor unit electrical and system components. Amp draws for compressor and condenser fan motor are within range. Primary motor control is in good condition. Secondary motor control is within range. Pulled off condenser fan motor and thoroughly washed out condenser coil inside and out. Condenser was fairly dirty with dust and debris, but is completely clean now. Refrigerant levels are in range and system is producing proper temperature split. Per homeowner request, he would like his visits split up, and would like us to come back to perform furnace maintenance before the next winter season. Advised I would notify office to make the changes. Cycled system, system is fully operational upon departure.
After $1350 Lennox rebate total $24,350 Cash discount applied
Replaced the high limit switches on the furnace. Tested the system in heating mode with the furnace door closed. Recorded temperature rise.
Upon arrival performed maintenance on Goodman furnace. FOund indoor blower wheel to be dirty. One inch filter needs to be replaced a lot more frequently. Secondary motor control is in range. Circuit board is in very good condition/. Dusted and cleaned all burned and inside of heating cabinet. Checked amperages throughout entire system nothing over working. Recommend adding a merv cabinet to upgrade filtration to filter out all the dust that gets through the standard filter. This filter will keep inside of the system clean, filters 90% effective compared to standard filter that does 20%. Temp rise split good. Heat exchanger has some heat spots on tubulars. Gas valve and gas shut off in working order. Heating saftey components in range. System was reset tested and fully functional upon departure. - dirty blower wheel - recommend adding upgraded filtration - replaced air filter
1 Night stay for 2 + Pets at Hilton Home2you suites included. Replace existing system with listed equipment. Professionally clean and sanitize existing ducting. Replace and enlarge existing return duct for proper airflow. (Dirtiest duct inside the home). Install 5â€ Carbon clean Merv 13 filtration for great indoor air quality. Install air balancing dampeners for even airflow through out the home. Replace all air registers and grills with new bar style high flow registers. All permits and HERS testing included. Cash discount applied Optional: Private labeled equipment (Lennox Brand) substitution deduct $533.00 (Total $11,656.00)
Adjusted blower fan speed to keep the furnace internal temperature down during operation. Updated inducer motor programming speed. Opened two supply vents upstairs which were closed. Adjusted gas pressure to 3.0-3.8 inwc. Inspected filter. Measured and recorded temperature rise.
Found unit on high pressure lockout adjusted charge
Tested the heating equipment and measured indoor temperature rise. Recorded supply voltages and motor amp loads. Cleaned flame sensor and tested igniter in ohms. Replaced merv16 hepa filter. Inspected blower wheel integrity and balance. Inspected gas piping. Inspected ducting for leaks and kinks.
Add 5â€ filtration to existing Lennox system After Lennox rebate total $11,434.00 Cash discount applied
Arrived on site to perform combo tune up on a 2018 carrier unit. Condenser located in back yard. Furnace and evaporator coil located in attic. Client stated no issues just has been living here for 2 years and would like to get system serviced. Advised I would be inspecting both unit. Cycled system system operational. Washed condenser coil inside and out. Unit really dirty due to area home is surrounded by. Recommend join Maintenance plan to help keep system operating properly and efficiently. Primary and secondary controls are both good. Fan motor shows some light signs of were due to dirt build up on coil creating a restriction. Fan motor amp drawls are in range after getting coil cleaned. Compressor amp drawls are good on start up and run amp and both in range. Recommend a compressor booster kit to help preserve compressor and run more efficiently and prolong life of unit overall. Refrigerant pressure are good. Cycled system to ensure system operating . Attic and insulation is good.
Found low voltage short and repaired heat pump.
Return to install ignitor and test heating system.
Tested system for heating and diagnosed issue with ignitor