My whole experience was pleasant. Everyone I spoke to was nice and respectful. Jamie included me in the entire tune up process. He explained what he was going to do and why. He was respectful of my space and cleaned up after. The price was very reasonable. I would definitely recommend Cool Air Solutions.
Was able to provide a great price.
Darren was knowledgeable, explained things clearly, and helped us make an informed decision on what was best for us.
Jorge was outstanding in every way. Thorough in his presentation of information and options, quietly efficient and respectful in our home. Very professional and friendly. Good man!!
Michael was very nice and professional. He wore boot covers in my home which was nice. He took the time to explain everything in detail so that I could understand what he was doing. We will definitely be calling back for our AC needs.
Excellent technician. Very courteous and friendly. Informative. Excellent service.
From the very first time I called Cool Air Solutions over 1 year ago, I knew I had found an Air Conditioning/Heating company with a total commitment to their sales and service. From the Sales and Installation of our new system a year ago to the outstanding preventive maintenance service we received today, we know we chose the right company. We are as committed to Cool Air Solutions as they are to us. The technicians are very friendly and always explain everything in complete detail. Thanks to everyone at Cool Air Solutions
Service as good as usual.
Arrived on site to perform combo tune up on a 2018 carrier unit. Condenser located in back yard. Furnace and evaporator coil located in attic. Client stated no issues just has been living here for 2 years and would like to get system serviced. Advised I would be inspecting both unit. Cycled system system operational. Washed condenser coil inside and out. Unit really dirty due to area home is surrounded by. Recommend join Maintenance plan to help keep system operating properly and efficiently. Primary and secondary controls are both good. Fan motor shows some light signs of were due to dirt build up on coil creating a restriction. Fan motor amp drawls are in range after getting coil cleaned. Compressor amp drawls are good on start up and run amp and both in range. Recommend a compressor booster kit to help preserve compressor and run more efficiently and prolong life of unit overall. Refrigerant pressure are good. Cycled system to ensure system operating . Attic and insulation is good.
Found low voltage short and repaired heat pump.
Return to install ignitor and test heating system.
Tested system for heating and diagnosed issue with ignitor
Reprogrammed thermostat for heat pump / electric
Arrived on site to diagnose loud noise on a 2020 Lennox unit. Upon arrival spoke over with client and he started unit running is making loud noise consistently as heat is one on system for upstairs. System Dose heat home up just making loud noise. Had client cycled heating mode on upstairs unit. Inspected unit system was operational. Checked gas pressure and found gas pressure high At 3.9 and adjusted gas pressure down to recommend pressure of 3.4. Cycled system with client twice. System is operational and client was happy noise level was reduce a lot. Cycled system one last time with client to ensure systems operating and that noise level was addressed. Both systems are operational upon departure.
Arrived on site to perform diagnostic on 15 year old Goodman system. Jay was our yesterday to give replacement options. Homeowner is waiting on another company to come out and bid on Tuesday, but has company coming over this weekend and would like to get system running for the time being. System works and cools, but it never shuts off unless homeowner pulls the disconnect. Checked electrical components and found primary motor control had welded itself in the on position, allowing electricity to flow through it at all times even when not calling for cool. Secondary motor control is also out of range for compressor. Due to homeowner wanting to replace system, wants to move forward with the minimum to get system operating normally for now. Replaced primary motor control. Cycled system on and off, unit works accordingly. Refrigerant levels are in range and system is cooling. Amp draws on compressor are very close to going over allowed capacity. Homeowner is aware of system condition which
Replace both systems with listed equipment. Permits/HERS included
PTU. Found system operational upon arrival. Replaced both washable filters with new cut to fit washable filters. Old filters were clean but customer requested to replace them anyway. Customer also had some questions about air quality and running unit with doors or open windows. Customer was under the impression it was better to run the unit with the doors and windows open to bring in fresh air. Advised customer not to do that since it forces the unit to run longer and reduces the unit efficiency. Running the unit on with outdoor air coming would keep the unit running all day. Washed condenser coil. Customer stated he had just done this too a couple weeks ago. Checked electrical. Compressor is running on very high amperage. This number also goes up in higher temperatures. Customer stated that made sense since the unit doesnâ€™t work very well in high temperatures. Checked freon pressures and they are slightly low but advised customer it wasnâ€™t affecting cooling performance. He asked h
Arrived on site to diagnose a no cooling 2013 good and system. Condenser located in back yard. Furnace and evaporator coil located in attic. Spoke to client upon arrival and he stated system was working few days back and recently he noticed house was getting warm instead of cool. She stated both indoor and outdoor systems were operational. Upon arrival had client cycle cooling mode on. Found compressor was not starting up but fan would operate. Advised client I would be checking both indoor and out door units. Inspect all electrical wiring, connections, and components. Check refrigerant pressure and compressor and fan amp drawls. Advised the summary of findings are as followed. Condenser 1. 2013 goodman system. Found not operating properly upon arrival. 2. Primary start control good. 3. Secondary motor control is completely bad and not allowing compressor to turn on. Fan side was weak but able to turn on. Replaced and evaluated full system. 4. Fan is rusted up condition due to spr
Quality control check
Performed AC maintenance on one year old Lennox condensing unit
Inspected system and found extremely high static pressure(1.25â€ w.c.) due to undersized rerun and supply ducting. There is no access to get into the attic. Everything else checked out properly. Coil didnâ€™t have an emergency drain switch.
Performed AC maintenance on seven-year-old lennox condensing unit.
NO COOL. Customer said she cancelled Saturday. Said she spoke with a Travis about 20 minutes ago.