I appreciate Luis and his pleasant demeanor
Michael did a great job. He was on time and got the job done quickly.
Jorge is a great technician with exceptional professionalism, I couldn’t have asked for better service!
Came to do A/C, H/V tuneup, but suggested to wait since ducting needed repairs. Arranged for a senior technician to come out and inspect further. Did not charge.
Had a great experience through the whole process! Jordan was an awesome sales rep. Very professional and knowledgeable! Jordan knew what would work best for our small house and budget. Installers Freddie and Miguel were amazing! Very efficient, clean and professional. Communicated wonderfully through the whole process. I couldn’t be more pleased with my purchase and the installation process. It’s my pleasure to give them a FIVE STAR 🌟🌟🌟🌟🌟 Review! I will highly recommend this company to others I know. Thank you!
NO CHARGE. upon arrival performed diagnostic. This was not a diagnostic, answered customer questions and concerns. Recommended replacing duct work to get a full design of home. System is operational.
Arrived on site to diagnose a (2) 2000 year old system. Upstairs was not cooling or operating. Downstairs is not heating. Spoke with clients they advised heating has not been working since winter. Thermostat upstairs is not working and client canâ€™t get set temperature to go up or down. Inspected upstairs unit. System would not turn on. Checked out connection, voltage and main circuit board. Eliminated thermostat and jumped system and system turn on. Cycled in heating and cooling. Both temp split and rise are good on upstairs unit. Recommend replacing thermostat to get system operating. Inspected downstairs unit. Heating mode would produce hot air. Checked for voltage, connections, Continuity, all good. Sequence of operation will start up till it got to gas value and not flames is created. Checked gas pressure on supply line and gas vale on manifold gas pressure. Was getting gas pressure on supply but valve would not open up. Cycled a few time and showed a gas pressure spike for a co
Upon arrival performed maintenance. Opened up and washed outdoor condensing coils. Amperages on compressor & fan motor in range. Refrigerant levels are in range. Pressure subcooling and superheat in range. Secondary control good. Primary motor control in excellent condition. Condenser fan motor good. Coils were washed. System was reset tested and fully functional upon departure. Filter was given to home owner.
Condenser maintenance and service
Inspected the home for possible air conditioning
Inspection of the outdoor system
Foam spray for lineset cover
Quality control check. We need to return to install a screen on the linset cover
We are adding registers at part of promo but not adding Merv 16 filter. Includes new return and supply plenum. We will straighten supply trunk ducting off the plenum as best as we can
Performed diagnostic on 2000 Carrier. System is not kicking on, error code on thermostat. I cycled system for heat. System initiated heating cycle, but fan never kicked on and system shut off. After carefully troubleshooting system, I found circuit board to be bad as well as indoor blower motor. Both would have to be replaced for it to operate. Went over findings and recommendations. Homeowners are Leaning more towards replacing the system as oppose to repairing it. Repair cost was given to homeowners. Darren will be coming out tomorrow morning to go over replacement options. System is not operational upon departure.
Replace existing furnace with below listed equipment. Unblock downstairs return air duct and fix low wall return duct. Install 5â€ filter rack and new Honeywell thermostat. Replace and redesign all existing ducting with new R-8 Class 1 ducting. Permits and HERS testing included. Asbestos abatement included. After rebate total $9,691.00
Replacement of ducting, return seal and supply can install
Performed heating and Ac tune up and installed Sensi predict kit