Nate was friendly, hardworking and professional. Highly recommended!
Daniel is a very professional and knowledgeable technician who went very ver our system and options without any pressure to do more. Cool Air has already gone above expectations and this is our first visit. Glad we signed up for the maintenance package.
I have been a regular customer for over 5 years...Still here, still pleased.
Michael has come to my house a few times now and has been awesome every time. Friendly, cares, and does a great job explaining his craft. Excellent representation for your company!!!
Jimmy was very thorough and made sure to explain everything in detail, and he gave me all the options available. He was very knowledgeable, and great to work with. Also, there company has the best local advertisement jingle that you’ll definitely be singing after you give them a call. Picked them because they have great reviews on Yelp.
What a rip off. Jimmy, the technician, showed up, only to try to sell me a new furnace, wouldn’t even perform a diagnostic which is why I called, and then charged $100 for nothing. Never call these guys.
Luis showed up promptly, explained everything in detail, and completed his inspection/maintenance on my older Carrier furnace with courtesy and a smile!
The technician was very polite very respectful we discussed Covid protocols and he was able to enter and complete the update of the thermostat. Unfortunately it took maybe five months for the part to come in that was under warranty
We have been using Cool Air Solutions for years. Michael did a great job of making sure that his work was just right! Highly recommended!
Upon arrival performed AC tune ups, refrigerant levels are in range. Replaced filter client provided. Indoor coil is very clean. Dusted off return registers. Washed condenser coils. Checked primary and secondary starter. Circuit board & electrical connections in range. Hardstart kit in working order. System is operational upon completion. Client approved renewal.
Arrived on site and performed AC maintenance on Lennox system.
Arrived on site and performed AC Maintenance on 2001 rheem condenser. Upon arrival Susan stated that sheâ€™s had no issues with the system. Perform system clean out on outdoor condenser coil. All electrical components checked out properly Besides starter with heavily burnt contact points. System contains a phased out refrigerant called R22 which is no longer manufactured as of January 1, 2020. Pressures are in range at this time. Amperage is for compressor Are beginning to get high But OK at this time. Condenser fan motor shows no signs of oil leakage. Cleaned out condenser where it looked like a rat had nested in. Discussed full maintenance with client and she is aware of current condition. She will be buying filters herself and swapping them out. Client would like to renew maintenance plan at this time in systems fully operational upon departure.
Performed AC and heating maintenance on heat pump. Inspected electrical components. Inspected ducting. Clean outdoor condenser coil and remove debris from bottom of the unit. Checked filters customer will change. System does have drain pan and float switch system is zoned. System is operating upon departure
Replaced the thermostat control and wire harness for the ducted mini split system. Tested equipment and ensured proper operation. Replaced the thermostat control and wire harness for the ducted mini split system. Tested equipment and ensured proper operation.
Arrived on site and performed AC/furnace maintenance on 2021 Lenox unit
System totals to $13,181 however client is only liable for payment for $7,181 as Tech Clean California Rebate will cover remaining $6,000 balance. (2) 15 amp breakers w/ 220v circuit 10 gauge required.
Upon arrival gave estimate for replacement of ducting. System has no seals at joints, standard filtration. 2 cut ins would need to be performed for supply. And one cut in for return on dry wall. System is operational, cools, just very little airflow in some vents.
Upon arrival performed AC tune up. Cleaned condenser coils outside. Checked refrigerant levels, everything is in range. Condenser fan motor run amps are in range. Compressor has high start amps, adding a compressor assist kit would help Ampergess start low. System has no protection on. Primary and secondary control in range. System is operational upon completion
Arrived on site to perform AC diagnostic on Lennox system. Upon arrival homeowner states that zone two is no longer active on the S30 thermostat. Proceeded to upstairs to verify the thermostat was an active and found no screen being displayed at this time. Remove thermostat off the wall and tested for power and found 12 V DC present at thermostat. Re-insert thermostat on the wall and it came back online. Verified and tested system and ran it for approximately 20 minutes and no issues occurred. It appears the thermostat may have been loose on the wall or possibly banged causing the imperfect connection were it lost power. Cycled system five times and system ran fine with zone disconnection. Upon departure system is fully operational and cooling
Arrived on site to perform spring tune up on 3 unit. 8 year old good man unit and 2 mini splits. Client stated no issues. Washed condenser coil inside and out on all 3 units. Cleaned and washed and wiped down nothin inside and out side unit. Both unit were cooling at 20 degrees. Found no protection for no protection on either unit. Main home condenser checked electrical compartment and components. Found primary starter to be getting worn out as contact point are burning up from use and age. Secondary motor control is weak and really low and out of range. Fan motor is okay. Checked pressure and are good and holding and cooling home at 20 degrees. No protection on unit. Indoor unit filter was replaced recently by client. Blower we okay and motor is good. Drain lines are clear at this time and draining. All safety switches are operational. Unit is cooling at 20 degrees. No protection on indoor unit. Client signed up for a maintenance plan for 2 unit. She wanted to use today as her first v
Upon arrival performed maintenance. Cleaned entire condenser coils. Dusted off all electrical components. Coil was dirty. Recommended adding surge protectors. Circuit boards have some burnt spots. Refrigerant levels in range. Voltages and amperageâ€™s good. Thermostat in working order. Filter needs to be replaced. System is operational upon completion.
Upon arrival performed maintenance on Lennox AC unit. Refrigerant levels in range . Client has some registers closed. Blower wheel has dust build up, advised cleaning, client said she canâ€™t at the moment but next visit. Washed condenser coil. Checked amperageâ€™s they are in range. Replaced filters client provided. Surge protectors in working order. Circuit board good. System is operational upon completion.
Installed 40 amp breaker for new electrical panel to power condenser. Changed fuses in disconnect to match breaker. Tested equipment and recorded temperature splits. Measured voltages at outdoor unit.
Performed ac maintenance. Checked electrical components. Measured temperature split at 20degree. Changed filter. Cleaned outdoor coil and removed debris from condensor. Checked condensate line. Check safety components. Measured capacitor it is within range. Checked refrigerant levels. Unit is cooling an operational upon departure