Luke did a fine job servicing my heater.I appreciated his efforts to abide by the Covid procedures while he was here. Very polite and friendly. Thank you Luke. Jane Gorsky My husband Paul passed away 12/10/2019. Please update your records to my name..
Explaining everything done, and got our unit up and running yay😊
Very prompt. Very professional. Got the job done on the 1st visit. Did not try to upcharge..
Michael, arrived in time as scheduled. I appreciate him calling to confirm if the scheduled time was still good. Very informative and thorough in his diagnostic. Highly professional and courteous. Inspected the heating and a/c unit and fixed or gave recommendations on what will require replacement. Explained every step he was doing to me, which kept me informed and at the same time, made me learn more about the process. I would highly recommend this company again and will continue to do business with them.
Jorge Was very friendly and knowledgeable. I appreciate the job that he did.
Michael was very professional, gave me the straight poop on the condition of the heating system. We talked options, there was no pressure just a factual discussion. I very much appreciated working with him. Plus he likes cats!
We have had Jimmy come out twice now and his professionalism and expertise is blaring. Last night he was here at the end of his day and he was as energetic as if it was the beginning of the day. He walked us through everything he saw with our furnace. We really really appreciate that he was not pushy in selling us on repairs but instead was able to show priority repairs which is great for a layman and the anxiety that come with lacking knowledge in this area. You want to keep Jimmy in your company for sure ,he will bring in good business and give you a good reputation. I’d give him a raise!!
The motor I had to buy was pricy for me but if I had to buy it for it to work.
Install Heatpump condenser on garage side of the home. Route refrigerant lines and electrical under the house to the indoor locations ( no exterior lines) Install Coleman downflow furnace in place of gas furnace. Modify cabinet for proper fitment. Relocate supply register in back TV room and abandon/seal supply under the couch. Financing available
Replace existing furnace with listed unit. Adapt to existing AC and ECOBee thermostat. Financing available 18 months 0% or several other options
Arrived on site to diagnose a 1987 Payne system located in laundry room closet. Client stated she shuts off system and unit does not turn off and fan keeps spinning. By passed thermostat and unwired thermostat wires off of board to see if system would shut off and still kept running. Jumped the heater directly and heater would turn on but fan would still turn on. Over all determined control board is bad and would need to be replaced to continue system Evaluation to ensure no other issues. Advised I would evaluate system in current condition and for safety. Found blower wheel is hammered of dirt. Filter was clogged and hammered. Motor is cover of oil and dirt from dirt entering system in past years. Found primary starter component was burnt up as well and some wires were burnt up from over heating from electrical. And heat exchanger was examined and found dimples to have a huge separation between them and itâ€™s indefinite wear shows sign of high wear in past year and heat exchanger can
Performed AC/furnace tuneup on 2009 on amana system. Upon my maintenance there were multiple points of concerns that were addressed with the homeowner. AC- 1. Found that high-voltage relay low-voltage coilâ€™s going out due to load vibration noise Coming off of coil. If this fails this can lead to the system not starting 2. Compressor was pulling high amperage on start up in recommend that compressor hard start kit is installed to the increase the life and reduce amperage on start up. 3. Condenser coil was extremely caked in covered in dust, Clean coil 4. System was not equipped with surge protection. Furnace- 1. Found inducer motor was over amping Due to bearing going bad and iscausing a loud noise during operation. 2. Furnace was also not equipped with surge protection 3. Flame sensor was slightly oxidize
Preformed furnace maintenance on 3 year old 96% Lennox heater. Upon my maintenance I noticed a few point of concerns that were addressed with the homeowner. Furnace- 1. System had no surge protection on both furnace and condenser 2. Furnace had no trap 3. 1 inch not filtering out enough dust and debris particles. This is causing build up within the system. Conducted leak search and found no signs of leak refrigerant leaks. Although did tighten core done on service port of suction side. Recommended that pressure are checked just before the summer to ensure no issues.
Cash discount applied
Performed routine fall maintenance on Coleman furnace in Vista.
Performed routine fall maintenance on Weatherking furnace in vista. Tested and verified correct operation of system and tested all safeties. Replaced air filter and made sure unit had good airflow. Recommend the following to keep system going long as possible 1. Adding sediment trap to system 2. Replacing hot surface igniter on system 3. Replacing transformer on system (Completed) 4. Adding SS2 switch for Drainline (Completed) 5. Replacing flame sensor 6. Upgrading thermostat
Upon arrival found system thermostat disconnected from wall. Reconnected thermostat and tested and verified correct operation of system. Checked the system and everything checked out good. Return is very restrictive and filter was really dirty before it was replaced yesterday. Flame sensor was also extremely dirty and needed to be cleaned. Recommended signing up for ESA to make sure system can last as long as possible. Also recommend upgrading filter and opening up return
Could not complete diagnostic due to heavy rain and furnace is outside of mobile home with nothing covering it. Need to reschedule.
Tested the system and found defective thermostat in the main lobby. System calibration is bad and cannot read the temperature in the room, thermostat was replaced. Programmed the new thermostat and tested both modes. Measured outlet temperature for both heating and cooling, disabled WiFi and scheduling.
Inspected furnace for faults. Found defective circuit board. Circuit board was replaced and system was tested. The high limit opened when the system runs on a single zone. Adjusted the gas pressure with both zones open and system is operating properly, would not advise running system on heat with one zone at a time.
Performed Heating tune up on front and back house 14 year old furnaces. Ran systems through inspection checklist. Went over findings and recommendations with homeowner. Stated they will be moving soon and wanted to see what condition they were in. Cycled systems, system is operational upon departure. Payment was collected through Loweâ€™s app.
Cash discount applied
Performed furnace diagnostic on 2006 Payne heater. Upon my diagnostic I found that circuitboard was a Display error code 13 which indicates that high limit or flame rollout has occurred. Upon further inspection I found that the indoor blower motor has failed along with the capacitor has become out of range. Also inspected heat exchanger and found multiple heat spots due to overheating over the years. Discussed the condition of furnace with homeowner And is aware that motor Needs to be installed So I can do a full inspection with system operational. Installed new blower motor and system was able to ignite and begin heating the home. Took static pressure readings and Found a total of 1.05 wc Considering that the specifications on the data chart is only rated for 0.5wc, Also found a 63Â° temperature rise which exceeded the max temperature of 60 on the data plate as well. Due to air restrictions and high static pressure this will result in a higher temperature within the heat exchanger hav