Jimmy was patient at explaining service details
Jorge did an excellent job giving me the good, the bad, and the ugly. I’d highly recommend him to other people in need of your services.
Team showed up exactly as scheduled, performed and completed ac install as quickly possible. Very professional and attentive to our questions and concerns.
Professional, courteous and knowledgeable.
Great costumer service and knowledgeable service
Cool air solutions are the best! New AC went in perfectly. Very professional installers and explained everything to us. Inspectors gave an A+ rating to the installation.
We are more than happy with the service we receive.
Performed furnace maintenance on a 2004 Bryant furnace. Upon arrival the Heater was not turning on, I restarted the furnace and it cycled back on. Systems static pressure is high at .9. Heating temperature split is 50. Inducer motor is amping high but still in range. Blower wheel is very dirty, flame sensor was cleaned. Ignitor was measured and recorded. Blower motor is heavily leaking oil and needs to be replaced. Battery cap is ok. Burn marks on a diode on the control board. The heat exchanger is cracked on 3 of the chambers. The gas valve was turned off at end of appointment. Homeowner went over pricing with Darren today.
Performed AC Diagnostic on 2011 Bryant condensing unit. Upon arrival homeowner called in stating that his Property in California is no longer cooling at which his daughter is a tenant at. Valerie did mention that she noticed last month it was no longer Cooling in the previous month before that it was showing signs of loss of efficiency and extended time still temperature starts to drop. 1. Found that system was completely almost empty of its R410a refrigerant charge. This is due to a leak somewhere within the refrigeration cycle 2. Proceeded to attic and found that evaporator coil is the main location of where the refrigerant leak is occurring. Unfortunately the coils made out of an aluminum and cannot be soldered and must be completely replaced. Informed and discussed for conditioning system with Conrad and at the moment he has no urgency to do anything and would like to wait about a week or two so That he can get the funds arranged. Once he determines that he will give us a call. At
Performed heat pump txv replacement. Fully recovered all the refrigerant. Removed and replaced the txv. Pressurized and cleared lines on system with nitrogen. Held pressure for 15 minutes. Vacuumed system down to 580 microns. Recharged em by weight and adjusted charge in cooling. Tested heating for 15 minutes and monitored operation. System is working properly at this time.
Performed furnace maintenance on Goodman heating unit. Upon arrival client stated that system is only been turned on a couple times and she keeps the temperature normally set at 75Â° 1. Found that the system is static pressure was extremely high indicating that there is a significant a restriction in the system also can be heard Throughout all the register vents. 2. Indoor blower Cabinet is dirty from years of dust buildup and can be cleaned out with proper filtration 3. Draft motor is in range 4. Filter needs to be swapped everyone to three months Discussed full condition of system with homeowner and she is aware of the condition and dust buildup within the indoor blower cabinet. System was reset and tested and is fully operational upon departure.
Arrived on site to perform estimate. Homeowner is getting a pool put in and would like to relocate the condenser from the back of the home to the side of the home. Evaluated now spot for unit. System would have more than enough room to pass code. Could not get into home, let homeowner know estimate would be rough until we know the exact location of furnace and if side of home is accessible through attic for new lineset. Gave homeowner rough pricing if all work was to be done by us, and also If he were to have someone else do the electrical. Has to talk everything over with wife, will give us a call if they decide to move forward.
Cash discount applied
Preformed Ac maintenance on 2017 carrier unit.
Performed furnace maintenance on 2019 Lennox furnace. System is checking out properly. Temp rise and static are in range. Inducer amps are good. Flame sensor and igniter are in good condition. Filter okay at the moment. Installed surge protection on indoor and out door for maximum protection from power outages, surges, thunderstorms etc. parts have 1 year warranty. System was reset and tested upon departure.
Arrived on site. Homeowner was having trouble getting her heat to kick on. Thermostat was set to off position. Cycled thermostat to heat and set at 75 degrees. Furnace kicked on normally and started heating. Showed homeowner how to navigate through thermostat and how to set heating and cooling. System is fully operational and heating upon departure.
Put down 250 for heat exchanger and OEM motor. Need to return for install.
Verified cracked heat Exchanger in 3 chambers
Preformed Ac/Furnace maintenances. Upon arrival play say that system has been working properly no questions at this time and also plans on moving out very soon So he will not be renewing the maintenance plan even though it is transferable to the new property. During the maintenance there were a few pcoints that I noticed that were addressed 1. Both indoor and outdoor unit had no surg wax e protection in the case of a power outage 2. Starter is pitted and burnt slightly on contact points 3. Recommend booster kit to increase longevity of compressor 4. Indoor blower scroll wheel has significant dust buildup and can lead to the wheel losing its balance overtime 5. Blower cabinet is also dirty 6. Return duct is not sealed 7. Static pressure on furnace was way over the recommended static pressure. This is an indication of restricted airflow due to the undersize return And kinked return duct Informed Donald of the condition of his system at the moment he would like to decline any repairs and
Performed combo tune up on 1 year old Lennox system. Cycled and checked components for both heating and cooling. Pulled outdoor condenser fan motor and thoroughly washed out condenser coil inside and out. Refrigerant levels are within range and system is cooling correctly. Filter is dirty and needs to be replaced. Homeowner states he will order from Amazon and replace when it comes in. Cycled system, System is fully operational upon departure.
Performed AC Diagnostic on 2017 Lennox condensing unit. Client stated that house is in escrow right now inspector noticed that temperature split was not in the proper range. 1. System Was slightly low on R410a refrigerant charge 2. Charged approximately 3 pounds of refrigerant into the system and Home is now cooling with a 20Â° temperature split. 3. Recommend filters are swapped every one to three months 4. Recommend that system is maintenance at least twice a year during the winter and summer season. System was fully charged up and is cooling with 21 degree temp split upon departure.
Found heating high pressure switch installed on the suction line, moved this to the liquid line service port. Located small refrigerant leak on the high pressure switch with soap bubbles, tightened the one too and confirmed with soap bubbles again the connection is sealed. Added a little r410a to the system.