Our tech was great in communicating every step of the process and what he found and how it affects our HVAC system.
Thank you for being clean and doing a great job. 10/10!
Great professional and informative service from Madison!
Jimmy was awesome with the service and Cool-Air Solutions with the pricing. Thank you.
Lenox makes a good product. Mateo did a great job. He gave us many options. My wife and I still think we paid to much for the units.
Was very knowledgeable and explained everything well.
Will be performing condenser relocate 3 feet from original spot. Advised Danny that system is from 2003 and that there are potential complications That can happen due to moving a very old system. Heâ€™s completely aware and would still like to move forward with the relocate. Office will be reaching out to him for scheduling. Need extra line set for three feet.
Performed furnace maintenance on 1996 Comfort maker heater. Upon my maintenance client stated that secondary drain has been leaking since she has moved in and is getting the house repainted and would like this fixed. Upon the maintenance I came across multiple points of concerns that were just with the homeowner. Comfortmaker heater- 1. Found that inducer draft motor has oil leaking from bearings this has the potential to cause the motor to lock up over heat if more oil loss occurs. 2. Indoor blower compartment is heavily covered in dust and debris due to 1 inch filter is not being swapped out enough in the past. Recommend that 5 inch thick filters are used For best efficiency in indoor air quality filtration 3. Indoor blower is also covered in dust and debris 4. Systems temperature rise was 50Â° 5. Static pressure was 0.71WC exceeding the 1.5 WC manufactures recommendation this indicates to me that the airflow in the system is restricted 6. Found that evaporator coil drain lines were
Performed AC maintenance on 16 year old Aireflo unit. Homeowners have lived in home 16 years, have had maintenance done here and there but never routine maintenance. Cycled system for cooling. Ran system through thorough inspection. Washed out outdoor condenser coil. Performed basic drain line clear. Temperature split is in range and refrigerant levels are good. Concerns with unit are as follows: 1. Unit is condensating through secondary drain line outside of home meaning primary could be clogged. Did basic condensation clear, homeowner will monitor to see if a more advanced clearing is necessary. 2. No condensation safety switch on drain lines. 3. Insulation is attic is very poor and not nearly enough to keep heat out of home. 4. Compressor is pulling significant amount of power and is inefficient and loud. 5. Condenser fan motor is leaking oil and is over amping. 6. Primary motor control is burnt and pitted, secondary motor control is out of Range. 7. System is operating on r-22 ref
Tech arrived on site. Found the first unit (reception) to be completely down. Capacitor on fan motor is out. Fan motor is looking really bad. Leaking oil and is rusty. Blower wheel is completely caked with dirt. Made estimates to fix everything.
Switched gas valve to the on position, his was accidentally left off on previous visit
Performed tune up on Ac system. Tested temperature splits. Inspected ducting. Monitored voltages and motor draws. Measured refrigerant pressures. Washed condenser coil and used spray bubbles to inspect corrosion areas. Cleaned inside condenser.
Install phenomenal air with three-year warranty and performed complementary drain line cleaning and evaporator coil cleaning. All work was performed. Upon departure also replaced filter removed all seals on supply vents and system is operational. Recommend that fan is running to get full efficiency of purifier.
Performed maintenance on a 2006 Goodman furnace. Systems temperature split is good at 32. Combustion motor amping close to max specification but still in range at this time. System does not have a condensate switch or a service port. Ignitor is in range. Flame sensor was cleaned. Blower compartment has significant dust build up, I cleaned the walls of the compartment. The blower housing and fan blades are very dirty. Blower motor looks is free from any oil leak and is amping ok. Homeowner is using washable filters and is on a good cleaning regiment.
Performed maintenance on 3 year old Lennox system. Cycled system for cooling. Checked outdoor unit electrical and system components. Primary motor control is in good condition. Secondary motor control is in range for both compressor and condenser fan motor. Compressor and condenser fan motor amp draws are within range. Pulled condenser fan motor and thoroughly washed out condenser coil inside and out. Refrigerant levels are in Range and system is producing proper temperature split. Checked indoor unit electrical and components. Replaced filter with filter provided by customer. Flushed out condensation line. Cycled system, system is operational upon departure.
Performed system diagnostic on carrier evaporator coil. Upon my diagnostic client stated that entire upstairs system smells like a dead rat is inside the duct work creating a odor that is overwhelming preventing them from sleeping upstairs. I first started by checking the filter and found that it was completely plugged up and dirty, Also every single supply vent was sealed up preventing airflow from coming out. I made my way to the evaporator coil in the attic and open the case. Found no evidence of a dead rat but the drain lines are completely clogged up and show signs of dirt buildup and debris within the coil that can cause a smell to linger throughout the house once moisture builds up in cooling mode. Recommended To prevent any smell or mold/bacteria buildup inside the evaporator coil that a phenomenal air is installed into the supply Plenum of the coil. Provided information on the process of how this works and recommended that a maintenance plan is also done to keep the system at
Reformed system tuneup on both cooling units. Washed condenser coils and inside condenser. Tested voltages and motor amp draws. Inspected Ted controls and fan motors. Tested capacitors. Measured refrigerant pressures.
10k down $17,546 financed thru service finance 36 Months 0% interest
Performed AC maintenance on 2010 carrier condenser. Tenet stated that system was not keep up With the desired temperature call on the thermostat. Also electric bills have increased due to this. Found multiple points of concerns that were addressed with Steve. 3.5 ton carrier- 1. Found the system was extremely low on refrigerant charge. This was caused by a refrigerant leak within the cycle. Refrigerant leaks will only get worse due to the leak not being sealed 2. System also has a potential restriction within the TXV due to this leak 3. Hermetic side duel secondary motor control has become week due to the compressor using more power over time 4. Contactor showed signs of pitting on contact points this component acts like the brakes for the system 5. Recommended that leak dye injected into the system 6. Outdoor condensing fan motor had a oil leak is coming from bearing this could potentially lead to the motor locking up or overheating Discussed full condition with Steve and heâ€™s comp
Installation of a Single Stage 16 SEER Lennox ML14XC1 Air Conditioner with High Performance/Efficiency Coil, Including 80% Single Stage Furnace, Promotional UV Purification Device, and Permits.