Madison conducted himself in a professional manner. His knowledge and work ethics were with much pride. He truly did an amazing job! We are very happy customers! Thank You!
The technician Madison was great an very knowledgeable. He suggested that the drainage pipe can be rerouted, if we decided to go that way.
Madison worked very hard at cleaning my AC unit & it was a mess! He cleaned up after himself & left everything neat. Madison reviewed his findings and made different suggestions on how we could become more energy efficient. He will definitely be he one we call when we decide to replace the unit!
Great service, Jimmy took his time and explained everything. The staff when I’ve called have been amazing as well. Thank you!
Jimmy is very polite and customer friendly. He's very focus and handles himself very professional. He explain the maintenance service thoroughly. Im extemely satisfied with overall performance. Thank You !
Jimmy, was very knowledgeable in explaining the process of the maintenance service. He conducted himself in an excellent manner. Oh, an he offer us the promo on the Air Scrubber and we decided to go with the product. We're very please with the new system. The air quality feels cleaner and fresher. Thank you, Jimmy for your excellent service and patience seeing we were seniors. Very professional!
The salesman was very professional
Performed diagnostic. System was cooling on arrival. Checked system components indoor and outdoor units. Refrigerant pressures are good and system is cooling correctly. All electrical components are in range and no concerns are visible at this time.. possible user error on thermostat. Explained to son how to permanently hold temperature on thermostat. System is working correctly and there are no recommendations at this time.
Installed parts. Warranty valid for 90 days for non members. Also performed a leak dye search And only found evidence of leakage at Schrader core directly at suction line port. replaced core Schrader and applied nylog to threads to good seal. Upon departure system is hold charge and cooling 22 degree split.
Performed AC diagnostic on 2017 Rheem system. Upon my diagnostic client stated that there is no airflow inside the house. it is no longer Cooling They just moved in last December. I found multiple points concerns that were just with the homeowners 1. System Was Significantly low on R410a refrigerant charge. This is due to a leak somewhere within the refrigeration cycled of system 2. Duel secondary motor control has become weak on hermetic side terminals due to the compressor running with no refrigerant as long as it did 3. Compressor is beginning to pull High amps on start up. Recommend compressor saver kit is added to reduce wear and tear and amperage on start up 4. Indoor Blower motor has significant oil leakage coming off of bearing and can lead to a locking up or overheating 5. 1 inch filter needs to be swapped everyone to three months to maximize airflow in Home 6. Injecting leak dye/sealant into the system to help pinpoint and locate breach in system to prevent any further refrig
Scope of work: -cutting existing condensate line. -installing condensate pump, and wiring it to the unit. -connect low voltage safety switch to unit. -installing new condensate line into pump. -running hose from condensate pump into washer drain. -cleaning area. -testing condensate pump.
Tech arrived on site. No power to the thermostat. Found fuse had popped in attic. Inspection found condenser wires are damaged and need to be replaced. During the inspection found multiple other issues with electrical start components. Compressor is over amping. Indoor blower cap is low. Condenser fan motor is rusted and breaking apart. Do to age and condition of the unit, the client is exploring replacement options. Scheduled with field supervisor, Darren.
Performed diagnostic. Met with tenant. Spoke with Jerry over phone. Maria states that system will not keep up with temperature during the day and will not run until later in the day when itâ€™s cooled down outside. Found condenser was completely dirty and causing a restriction which could be causing unit to shut off on high pressure when itâ€™s hot outside. Pulled condenser fan motor off and thoroughly washed condenser coil. Cycled system on and refrigerant pressures had dropped significantly and now appears to be slightly low on refrigerant. Let homeowner know that system could either have developed a leak or could have not been properly charged up at the time of install. Added 1lb of r410A refrigerant. Refrigerant pressures are in Range and system is producing proper temperature split. Recommended maintenance program for routine maintenance. Jerry wants to hold off for now. Cycled system. System is operational upon departure.
Tech arrived on site. Found the secondary float had triggered. Float was wired to condenser wires. Causing it to turn on and off. Wired it to break R. Flushed out lines. Unit is cooling at this time. Both uv and air scrubber bulbs had failed on unit. Will replace during fall maintenance of equipment.
Performed AC maintenance on a Day and Night system. Systems cooling temperature split is 22 degrees. Condensate lines are clear but have no safety switch. Duct runs are sealed. Outdoor coils were caked in dog hair but chemically cleaned today. Primary start component is failed on the fan terminal causing the fan to leak oil prematurely. Suggesting replacement. Compressor amps are ok at this time. Refrigerant levels look ok. System was cycled before leaving.
Arrived on site to diagnose a no cooling 1995 unit. Client did as not home as he is on vaca And has daughter living at home. She stated unit stopped running and fan did not spin. She stated her dad is aware unit is old and fan could be bad. As unit is old. Found fan secondary motor control was bad and fan is on its way out and why secondary control failed. Primary start was replaced. Found secondary motor control for compressor is bad and weak which is out of range due to age and inefficiency over the past years. advised condenser coil was so heavily caked and dirty would be and extra charge to really get unit clean. Advised could not check pressure due to over condition of unit. Advised now is the time to consider full system replacement due to the age, condition , r-22 refrigerant, and cost of repairs and cleanings. Client is aware and would like to minimize repairs to keep home cool to the best it can and wants someone to come out for system replacement. Advised he would be back Mon
Upon arrival found compressor to not kick on, found common wire to be burnt off, wire was not fully holding onto contact points, replaced clip and ready to go. Compressor amperages in range.
Upon arrival found system to not be on, system was running without outdoor fan, compressor over heated. Replaced secondary motor control, cooled down the compressor, system now operational upon departure.
Performed AC maintenance on five-year-old Lennox condenser.
Tech arrived on site. Found 1 hvac system installed in 85. Did EXTENSIVE coil cleaning. Coil is in bad shape. Checked electrical start components. Caps are failing. Both fan motors are over amping. Compressor is being started by the hard start. Charge is okay. Temp split is 15. Customer declined to be quoted for recommended repairs and comfort club.
Tech arrived on site. Cleaned coils on a 3 ton hvac system. Checked electrical. Found LRA for compressor to be high. Everything else checked out. Ducts are older. Recommend replacing. Unit is charged good and cooling great.
Tech arrived on site. Found indoor blower not working. Cap was bad and the unit had 120v going to it. Replaced cap and it didnâ€™t work. Replaced motor and did a blower cleaning. Unit is operational. 1 year parts labor on blower and capacitor.