Jimmy, was very knowledgeable in explaining the process of the maintenance service. He conducted himself in an excellent manner. Oh, an he offer us the promo on the Air Scrubber and we decided to go with the product. We're very please with the new system. The air quality feels cleaner and fresher. Thank you, Jimmy for your excellent service and patience seeing we were seniors. Very professional!
The salesman was very professional
Service technician Michael was very professional and knowledgeable. We appreciated his patience with all our questions. VERY pleased with our service.
We had an emergency leak from our roof vent,call you guys that morning within 2 hour's your service tech LUKE was here to assess the problem and fixed it , it was raining and he still got up on the roof and fixed everything....thank you cool air solutions for the prompt response and sending a service tech that knew what he was doing......Happy customer....Pete Cruz
Performed diagnostic on 2018 trane system. Homeowner states system is not turning on at all. Tried cycling system for cooling, system is unresponsive. Went into attic and inspected indoor unit electrical and system components. Found a broken fuse at circuit board. Checked wiring and circuit board for any sign of a short, did not find anything concerning. Homeowner states he did remove thermostat from the wall to replace his batteries. This could have caused the fuse to break. Replaced fuse, system kicked on and started cooling. Filters are both dirty and should be replaced. Checked outdoor unit electrical and system components. All look to be in order, secondary motor control is in range. Outdoor condenser is very dirty with dust as well as pet hair. Strongly recommended having maintenance done on system. Refrigerant pressures are in range and system is producing proper temperature split. Went over findings and recommendations with homeowner. Only wants to take care of immediate fix fo
Substitute ml180 for sl280v
Customer canceled call as arriving.
WARRANTY. Found system operational upon arrival. Customer said he removed filter to see if it would work. It didnt. Customer also tried to wash unit outside. That didnâ€™t work either. Customer ended up leaving the unit off overnight. It has been cooling down the home all day today. Upon inspection found suction line freezing over and furnace with water all over it. Checked unit and found low pressures. As I began to add freon head pressure went up and suction did not rise. Refrigerant flow valve needs to be replaced along with filter drier. Customer is only responsible for $756 deductible to have this done. Ordering parts through lennox. Will contact customer when part is in. Unit not operational upon departure.
Performed cooling tune up on the system. Tested thermostat and. Measured indoor temperatures. Cleared condensate drain and replaced filter. Measured outdoor voltages and motor amp draws. Washed condenser unit inside and washed coils. Inspected fan motor. Checked electrical running and start components.
Replace existing system with below listed equipment. Enlarge existing r/a to a 30x20. $10,800 due upon completion. $500 and $250 rebate paid to customer. After rebates total $10,050
System assessment and check up
Ac system performance tune up and service
Indoor air upgrade Ac/furnace inspection
Ac and furnace maintenance in Moreno Valley
Ac tune up in Moreno Valley, Ca.
Doing an AC Maintenance out here in Moreno Valley
AC maintenance in Moreno Valley
Annual spring air conditioner maintenance on Lennox unit