Great service, Jimmy took his time and explained everything. The staff when I’ve called have been amazing as well. Thank you!
Jimmy is very polite and customer friendly. He's very focus and handles himself very professional. He explain the maintenance service thoroughly. Im extemely satisfied with overall performance. Thank You !
Jimmy, was very knowledgeable in explaining the process of the maintenance service. He conducted himself in an excellent manner. Oh, an he offer us the promo on the Air Scrubber and we decided to go with the product. We're very please with the new system. The air quality feels cleaner and fresher. Thank you, Jimmy for your excellent service and patience seeing we were seniors. Very professional!
The salesman was very professional
Service technician Michael was very professional and knowledgeable. We appreciated his patience with all our questions. VERY pleased with our service.
We had an emergency leak from our roof vent,call you guys that morning within 2 hour's your service tech LUKE was here to assess the problem and fixed it , it was raining and he still got up on the roof and fixed everything....thank you cool air solutions for the prompt response and sending a service tech that knew what he was doing......Happy customer....Pete Cruz
Arrived on site to perform fall tune up on a 2016 Lennox system. System located in hall closet client stated no issues. Cycled thermostat on and was good. Cleaned and wiped down system. Found flex ducting used. Filter was really dirty . Recommend replacing filter more often or as need. Blower assembly is accumulating slight dust. Motor is good. Amp draws are good. Inducer Motor is good and amps draws. Temperature rise is good and in heating range. Heat exchanger is good. Evaporator coil is good slight debris. Drain lines are clear but for slight dirt accumulating from dust and dirt entering system in past years. No protection on units recommended adding surge protectors on system to prevent system from getting damaged from electrical surges and power outages that can damage system or even components from electrical components. Cycled system to ensure system operating. Went over all findings and areas of concerns with client. Client is aware of condition of system and how itâ€™s running
Performed combo tune up on 4 year old Goodman system. Cycled system though heating and cooling modes. Checked indoor and outdoor unit electrical and system components. Tested all heating components. Wiped down blower assembly as well as heating compartment. Cleaned flame sensor. Blower wheel is clean, motor is healthy. Filter needs to be replaced, home will be ordering it and replacing themselves. Outdoor unit primary motor control is in good condition. Secondary motor control within range. Refrigerant levels are in range and system is producing proper temperature split. Thoroughly washed out condenser coil inside and out. Went over findings and recommendations with homeowner. Cycled system, system is operational upon departure.
Performed furnace maintenance on seven-year-old Lenox
Financed thru service finance
Upon arrival performed maintenance on furnace unit. Inspected blower motor. Blower wheel cleaning is dirty, causing weight on blower motor. Secondary motor control is out of range, rated for 10mfd actual is 3.2 mfd. heat exchanger has stress marks due to heat, did not identify any cracks. Evaporator coil is completely covered with inches of dirt, debree, hair etc. there is not one single part of evap coil shown, this is very critical to motors air flow issues, allergyâ€™s, dust inside of home. Dirty evap coil can cause harm to compressor, fan, secondary motor controls. Replaced 1inch filter. Circuit board and electrical connections are in fair conditon, circuit board has heat marks. System is operational, system needs extensive cleanings.
Upon arrival performed diagnostic. Thermostat is working at normal operations. Client said only the living room air changed AFTER we replaced thermostat from non WiFi to WiFi. Client said air flow was a lot better before thermostat replacement. Checked ducting, adjusted blower setting. Refrigerant levels are in the correct stand point. Temp split is good. System is operational and working as needed, refrigerant levels good, temp split good. Client may call office if not satisfied.
Performed AC/furnace maintenance on 17-year-old Goodman system. During the maintenance I came across a few points of concerns that were addressed. 5 ton Goodman- 1. Found that secondary motor control was Extremely weak and leaking oil. This is causing the compressor and fan to use more power 2. High voltage relay showing signs of pitting and burn marks on line voltage wiring due to high amperage pull. Contact points are also burned out 3. Fan motor is Over amping due to bearing wearing out. 4. System contained R22, a phased out refrigerant as of January 1, 2020 5. Condenser was completely plugged up with hair and debris 6. Power disconnect also broken Furnace- 1. Indoor blower cabinet covered in dust and debris due to washable filter not filtering out particles 2. Heat exchanger show no signs of cracks or heat stress marks Discussed options and repairs either Jaime. He would prefer system options and relocation of both systems rather than repairs due to age. Supervisor scheduled out
Customer was not home and sister could not reach him. She said she was not expecting us and didnâ€™t know what was going on. She said to try him later that he was working.
Installed m30 thermostat. Set thermostat up to WiFi. Set up homeowner account on phone and showed her how To use thermostat. System operational upon departure.
Performed diagnostic on 2018 trane system. Homeowner states system is not turning on at all. Tried cycling system for cooling, system is unresponsive. Went into attic and inspected indoor unit electrical and system components. Found a broken fuse at circuit board. Checked wiring and circuit board for any sign of a short, did not find anything concerning. Homeowner states he did remove thermostat from the wall to replace his batteries. This could have caused the fuse to break. Replaced fuse, system kicked on and started cooling. Filters are both dirty and should be replaced. Checked outdoor unit electrical and system components. All look to be in order, secondary motor control is in range. Outdoor condenser is very dirty with dust as well as pet hair. Strongly recommended having maintenance done on system. Refrigerant pressures are in range and system is producing proper temperature split. Went over findings and recommendations with homeowner. Only wants to take care of immediate fix fo
Substitute ml180 for sl280v
Customer canceled call as arriving.
WARRANTY. Found system operational upon arrival. Customer said he removed filter to see if it would work. It didnt. Customer also tried to wash unit outside. That didnâ€™t work either. Customer ended up leaving the unit off overnight. It has been cooling down the home all day today. Upon inspection found suction line freezing over and furnace with water all over it. Checked unit and found low pressures. As I began to add freon head pressure went up and suction did not rise. Refrigerant flow valve needs to be replaced along with filter drier. Customer is only responsible for $756 deductible to have this done. Ordering parts through lennox. Will contact customer when part is in. Unit not operational upon departure.
Performed cooling tune up on the system. Tested thermostat and. Measured indoor temperatures. Cleared condensate drain and replaced filter. Measured outdoor voltages and motor amp draws. Washed condenser unit inside and washed coils. Inspected fan motor. Checked electrical running and start components.
Replace existing system with below listed equipment. Enlarge existing r/a to a 30x20. $10,800 due upon completion. $500 and $250 rebate paid to customer. After rebates total $10,050