fast and Certious service
David provided excellent service, detailed explanations of areas of concern along with pictures of the attic and under-performing parts for us to discuss. In addition, he provided a full report, along with the readings from his tests. Well worth your investment. He then provided costs for various options, and after researching them on our own, we decided to replace our system.
Installed nest E thermostat for the bedrooms system. Opened the master bedroom damper to lower the amount of airflow to the back two bedrooms. Set up a sensor in the office. Connected the thermostat to clients WiFi and assisted in setup process. Instructed how to use both thermostat and nest app.
Two system heating maintenance
Cash Discount applied.
Upon arrival performed maintenance. Indoor motor is in very good condtion. Circuit board and electrical connections in good shape. Temp rise good. Duct work is in very good condtion. Filter is new. Gas valve in working order. Heating order of operations good. Cycled heat on and off. Pressure switch good. Inducer draft motor good. Wiring intact. Dusted off all electrical, cleaned inside of furnace cabinet. Attic has very little insulation. Overall system is in good conditon, has new circuit board and blower motor. System was reset tested and fully functional upon departure.
Upon arrival nothing wrong with thermostat, clients concern was fans would turn on. Client had circulation of fan for 30%. Turned feature off. System is operational.
Replace both existing systems complete with listed equipment. Duct corrections. Tie supply duct feeding pool room into the main house system. Tie both existing cut-in supplies feeding office and daughters bedroom into return air of bedroom systems and balance air to force 30% more air into those 2 rooms. 3% cash discount applied
Tested both systems for cooling and measured indoor temperatures. Replaced filters. Inspected outdoor condensers and cleared debris from pad. Cleared dirt and webs from electrical panels and measured system incoming voltages. Measured compressor motor and outdoor fan amp draws. Tested primary run component capacitance and checked starters for pitting. Cleaned outdoor condenser coils.
Tune up and service for both condenser and fau
Furnace trap repair
Upon arrival performed maintenance. Indoor motor and wheel are good. Circuit board and electrical connections good. 20x30x1 filter was replaced. Circuit board and electrical connections good. Temp split good. Gas valve in working condition. System was reset tested and fully functional upon departure.
Performed heating maintenance and performance tune up on both furnaces. Checked all electrical controls. Monitored burners and ignition. Wiped down blower cabinet. Measured amp draws and temperature rise.
Replaced system blower motor under Amanda warranty and replaced clients thermostat with nest. Tested equipment and performed fall maintenance
Two system maintenance and repair in Norco, Ca.
Ac and furnace maintenance in Norco, Ca.
Two system heating maintenance in Norco