Jimmy was ver polite and spend time explaining what the issue was and options to fix it.
We pay for maintenance of our HVAC system twice a year. Each time the service person has been friendly and thorough in the service provided.
Jorge is an excellent technician and I would recommend highly to anyone
He did a great job. Very professional.
Really liked how he explained things and very personable.
Cool Air Solutions installed our HVAC system several years ago. They also have done 6 month service calls on our equipment. The service has been above my expectations.
Outstanding service was provided, completed the job on schedule and your Technician, George was very professional.
We had our one year check-up with shane. He did an outstanding job letting us know what he was doing and then going over everything he did. Very neat and very courteous. A real asset to the Cool Air Solutions team!
Jimmy was prompt and efficient. Very pleasant personality. Very satisfied
Michael was very quick to find the solution to our leaky AC unit. Very satisfied!
Cool Air Solutions installed our HVAC system several years ago. Their followup service has been excellent.
Did a thorough inspection
My tech Jimmy was extremely knowledgeable, examined my furnace thoroughly, explained his findings clearly to me, and was very pleasant and courteous. I am so happy to have found Cool Air Solutions.
Upon arrival performed diagnostic. Connected to system and found system to have no refrigerant inside of system at all. Let client know. They will use there brother in law. Does not want me to perform any work. System is non operational for cooling.
Performed service on a thermal king/Goodman mix match system. Customer reports no response to any thermostat function. I found the low-voltage fuse to be popped. Indoor transformer was measured and tested. Transformer appears to be a bit weak but is not the primary issue. The outdoor Contactor was popping the fuse on the low-voltage part of the circuit. This was replaced today. The customer signed up for future maintenance is and is aware that with a system is old Electrical components can become weak. System is operational at end of appointment.
Performed maintenance on a 202p Lennox condenser. Outdoor unit was chemically cleaned. Electrical amp readings shows components to be in healthy working condition. Starting components were measured and tested. Refrigerant levels are ok. Filter was recently changed and is clean. Condensate lines are clear. Duct runs are sealed. System is operational
Arrived on site to diagnose unit have a issues with draining and not cooling good. Spoke to client and she stated she had remodeled whole home units had been removed and but back in attic once hole was done. Client stated sheâ€™s had nothing but issues with condensation and had water damage in past and other company come out to fix but they had to her she needs to replace. Inspected indoor unit doing unit to have no drain lines primary or secondary. After the over flow she had a secondary pan put in but now both condensation lines go right into secondary pan and drain out which is not good at all. They had to run a line from secondary pan. Found pan to have a decent crack and advised evaporator coil would have to be replaced. Found so since there is not enough room she would have to get both units removed out to get the coil out. Went out side to look at out door unit and found condenser about flat. Advised client this is not good as this mean there is a leak present but unknow where i
Upon arrival started ac tune up. Cleaned condenser coils. Checked electrical. Refrigerant charge appeared low at this time. Outdoor temp is low. Temp split is 16/20. Indoor temp was 66. Want to explore issues more next visit with warmer weather. Unit is operational upon departure.
Performed maintenance tuneup on two cooling systems. Inspected indoor unit and tested thermostats in cooling, checked ducting and inspected filters. Recorded temperature splits and checked drain lines. Monitored operation and recorded all electrical loads. Washed outdoor condensers and coils.
Performed AC maintenance on one and a half year old system. Checked and tightened electrical components. I inspected safety mechanisms on unit. System has flood protection and was venting properly. Blower wheel is balanced and free of dust. Inspected capacitor it is within range. Cleaned outdoor condenser coils and remove debris from bottom of unit. System is cooling at a 20Â° split. Filter was dirty and was changed at todayâ€™s visit customer supplies filter. Inspected condensate line condensate line is clear and free of debris. I system is cooling and operational upon departure.
The proposal includes two systems with a total of 10 indoor units. Payment Schedule: 20% ($15,184.20) deposit due for special order equipment 35% ($26,572.35) due upon HVAC rough-in 25% ($18,980.25) due upon outdoor condenser sets 10% ($7,592.10) due upon completion of trims and controls 10% ($7,592.10) due upon completion of system commissioning
Arrived on site to perform combo tune up on a 3 2007 weather king units. Client stated she just moved back into home and the whole house is getting remodeled. All 3 unit. Found 1 inch filter in return vents and pulled all of them out since they have a 5 in filter in attic. All 3 blower assembly are dirty from past years of dirt entering unit. Past owners did not do maintenance. All 3 secondary controls have been replaced. Motor are amping high and can fail in future as they get used heating and cooling. One motor is leaking a lot of oil from stress and age of unit. Igniter for found 2 igniter readying really high over 100. Advised these should be from 50-100. These can fail in future. Flame sensors have been replaced in past as well. Gas lines are good. Tempe rise is good on all 3 units. No protection on units and recommended adding protection to protect from electrical surge and power outages due to age and conditions. Cycled heaters. Washed all 3 condenser inside and out. Checked e
Upon arrival performed heating maintenance. Indoor motor is running pretty high in amperageâ€™s. Indoor blower wheel beginning to accumulate a lot of dust, client has really bad allergies. Is really interested in the purification kits, but has to do some research, Said itâ€™s normal for her to do this. Advised there is no rush, to take her time. System is older and getting to its late stages of running. Isnâ€™t to sure weather it makes sense to do it or not, advised most sense would be replace systems, but if she is not ready she can always have purification moved over to new systems when in future replaces. Liked the fact that she can do that. Left checklist with customer & renewed Memebrship.
Arrived on site to install high limit switch. Removed the original defective high limit and new part worked. Advised graciela that system is still over heating with a 78 degree temperature rise. This furnace only recommends 35-75 temperature rise. She plans on only using for short periods of time but understand system is old with airflow issues. They will give us a call if they have any questions. System was operational upon departure
Upon arrival performed heating maintenance. Indoor motor and wheel are in good condition. Circuit board & electrical connections in range. Surge protectors good. FlMe sensor was cleaned. Filter was replaced. Burners weee cleaned. Ducting & insulation good. System is operational upon completion.
Performed Furnace maintenance on 1 year old Lennox system. Ran system through 20 point inspection checklist. Replaced 4 downstairs supply registers with bar type registers. Sealed registers. Cycled system, system is operational upon completion.
Arrived on site to perform combo tune up. Furnace located in garage and condenser in back yard. Cycled both and good. Filter was replaced. Both motor in furnace are good and in range. Gas line good. Temperature rise is good. All safety switches are operational. Drain lines are good and clear. Clean blue flame. New flex ducting used. No protection on unit. Washed condenser coil inside and out. Primary and secondary motor controls are both good. Fan motor was good and oil free. As well good in range. Conor start up and run amps are good as well. Checked pressure and are good. Cooling home at 20 degrees. No protection on unit. Recommended adding a whole home purifying system that will clean and purify the whole home and clean the air for better quality of air in home as client dose have high allergies. Cycled unit and went over all findings. Client os aware of condition and how unit is running as well as the recommendations. Client did hold off for now as she has other things she has to t
Wrong part came in and ordering correct one at This time.