Michael was very quick to find the solution to our leaky AC unit. Very satisfied!
Cool Air Solutions installed our HVAC system several years ago. Their followup service has been excellent.
Did a thorough inspection
My tech Jimmy was extremely knowledgeable, examined my furnace thoroughly, explained his findings clearly to me, and was very pleasant and courteous. I am so happy to have found Cool Air Solutions.
Mike was great. Explained everything easily to us.
Luis was very professional and was very knowledgeable.
Luis did a fantastic job and was very professional and courteous
Jorge and Mateo were great....they truly offer great service and I would highly recommend. They both stayed late on a Friday night.
Preformed 2 system maintenance on Lennox condenser.
System was low on refrigerant on arrival. Added 2 lbs to bubble test flare fittings and welds. Found small leak on the suction line flare connection. Tightened the connection and confirmed with soap bubbles. Found no leaks on the welded joints. Charged system by weight up to manufacturing specifications. Tested dealt a T and retested the flare joint.
Installation of a 2.5 ton 16 SEER air conditioning condenser with single stage cooling and high efficiency coil. House is currently plumbed for new AC with line set, electrical, condensate line. Sensi WiFi thermostat is included. $6,885 - Total Investment (cash or check)
Performed diagnostic on 4 year old unit. Homeowner states downstairs unit is not cooling, has not been cooling since Saturday. Cycled system for cooling. Indoor unit kicks on, outdoor unit is unresponsive. Outdoor unit is not recieving low voltage command. Found low voltage wire to condenser had came off the indoor circuit board. Re-stripped wire and re-connected to board. Cycled system, condenser kicks on normally. System is cooling upon departure. Recommended adding surge protectors to units to protect from any electrical failures or possible problems. Needs to talk it over with husband. Renewed ESA maintenance program, wants to keep it on yearly basis.
Tech arrived on site. Installed phenomenal aire and new gas valve. Did a gas leak detection on connections. Made sure phenomenal aire was operational. Registered product. Addressed some airflow issues due to zoning. ***paying with financing***
Performed 3 system AC maintenance on Weather king condensers. During my maintenance I noticed a few things that were addressed with Mrs. Mashburn Guest house condenser- 1. System Contained R22 refrigerant which was completely phased out January 1, 2020 2. Outdoor condensing fan motor had significant oil leak is coming from bearing. If left in this condition fan motor can potentially lock up 3. Amperage on fan was exceeding manufacture specification due to oil loss Central living area condenser- 1. System also contained R22 refrigerant 2. Condenser coil was very dirty and was cleaned off 3. Condenser fan motor amps were coming very close to exceeding proper range Front of home condenser- 1. Condenser fan motor had major oil loss occurring from bearing. 2. Fan motor was exceeding 0.80 A due to this which path put this at a higher risk of failing during the summer 3. System Contained R22 refrigerant. Discuss full conditioner system with Mrs Mashburn and sheâ€™s completely aware of ho
Tech arrived on site and started maintenance on 1 hvac 3 ton split system. Cleaned coils and checked electrical. All was good in condenser. Refrigerant charge appeared low. However the outdoor and indoor temperature was low as well. Went inside and found the bulb for the air scrubber was out. Recommended installed a phenomenal air. Also found the gas valve for the furnace to be faulty. Same with the thermostat. Will cover under parts warranty.
Performed A/C maintenance on a carrier unit. Upstairs unit was cooling 28 degree split. Systems fan and compressor run amps are ok. Refrigerant levels are good. Condensate lines are clear of any debris. Duct work is sealed tight. Outdoor fan motor is leaking oil heavily. Performed maintenance on a carrier unit, upstairs system. Systems temperature split is low at 13 degrees. Refrigerant levels are off, could be low on Freon. Compressor start amps are ok. Fan motor is in range. Both units were chemically cleaned and cycled before appointment is over.
Upon arrival performed air conditioning tune up. Did a thorough evaluation on system. Opened up electrical components and dusted all connections off. Primary and secondary motor control in range. Refrigerant levels good. Temp split is great. Filter was replaced that client provided. Dusted off all heating components, was very dusty took care of that for client. Static pressures are in range. Installed surge protector to keep system protected. Signed client up with membership. 2 visits. Opened up condenser and chemically cleaned outdoor coils. System was reset tested and fully functional upon departure.
Performed furnace/AC maintenance on 2019 Goodman system. Installed search protection on both outdoor and indoor unit in the case of a power outage that may cause damage to the system. Both search protectors have a one year warranty. Upon departure systems are functioning properly. System was reset and tested and is fully operational in heating and cooling.
Replace existing systems with listed equipment. Mount slim line condensers to exterior wall. Extend lines and power to new ac locations. Permits and HERS included. Financing available= 24 Months 0% interest Several Options that are included in the bid can be removed for a cheaper price.
Technicians arrived on site and performed maintenance on two 3 ton furnaces. Checked all safety components and main mechanical components. Checked the following: - temp rise - flame sensors -motor amp draw -hot surface igniter ohms -static pressure -motor start components -checked filters Cleaned the inside of electrical compartment. Wiped down outside of units. Units were operating good at this time and on departure. Units were not equipped with surge protectors.
Performed furnace maintenance on 2007 Payne heater. During the maintenance I noticed a few points and concerns that were brought up with the homeowner although he did decline that the heat exchanger is not pulled and tested. Furnace- 1. Measured a 80Â° Temperature rise Within the system when the rated specification temperature rise is 30-60 degrees. This is an indication of serious overheating and will trigger the high limit to trip once it reaches top temperatures. Due to the temperature is being so high it is recommended that the heat exchanger is verified to be in good condition and is safe for operation. With such a high temperature rise there is a highly likely chance the heat spot formed And had caused the metal to expand and contract. 2. indoor blower motor was heavily covered in dust and debris due to 1 inch filter is not being swapped out enough. Also found slight oil leak is coming from bearing which can lead to the motor locking up our overheating. Motor control is not only
Performed diagnostic on 12 year old system. This is a furnace only no AC. Homeowner states that her system is working fine and is heating fine. The only issue is that the temperature on the thermostat does not what to what she set it through and will change throughout the day. Thermostat in the home is a programmable thermostat and it was resorting back to the schedule throughout the day. Showed homeowner how to set a temperature and hold it so that it will not change throughout the day. Had homeowner do it on her own and she fully understands how to work thermostat. System is operational upon departure.
Performed routine fall maintenance on 3 Weather king furnaces in Carlsbad, replaced all air filters and tested and verified correct operation of systems. All systems are running correctly at this time. Recommend replacing both flame sensors on downstairs units, igniter on the living room/family room unit, a transformer on the bedrooms unit and all 3 systems donâ€™t have a sediment trap