Cool Air Solutions installed our HVAC system several years ago. They also have done 6 month service calls on our equipment. The service has been above my expectations.
Outstanding service was provided, completed the job on schedule and your Technician, George was very professional.
We had our one year check-up with shane. He did an outstanding job letting us know what he was doing and then going over everything he did. Very neat and very courteous. A real asset to the Cool Air Solutions team!
Jimmy was prompt and efficient. Very pleasant personality. Very satisfied
Michael was very quick to find the solution to our leaky AC unit. Very satisfied!
Cool Air Solutions installed our HVAC system several years ago. Their followup service has been excellent.
Did a thorough inspection
My tech Jimmy was extremely knowledgeable, examined my furnace thoroughly, explained his findings clearly to me, and was very pleasant and courteous. I am so happy to have found Cool Air Solutions.
Inspected heat pump for vibration issues. Found compressor motor bolts over tightened and stripped. Removed stripped bolt and tightened remaining bolts.
Tech arrived on site. Performed heating tune up of Maytag furnace. Tested all electrical components. Hot surface igniter is reading low on ohm value. Still operational. Motors are good. Heating operation is good. Changed filter with customer supplied filter. Installed new CO detector in hallway with thermostat with customer supplied detector. Installed new thermostat. Tested operation. Unit is operational upon departure.
Arrived on site to return for for repairs client went forward with. Client approved of installing a new merv 16 filter rack, phenomenal air, 2 premium surge protectors, secondary overflow switches, primary starter, compressor booster kit, and clean blower assembly and wheel with blower compartment, and cleaned and sanitize evaporator coil in attic. Cycled full system after all repairs were installed and cycled to ensure system operating. Client is aware of all repairs made. Removed old filter in vents as they are no longer needed. Client is happy with repairs man and todayâ€™s visit. System is operational upon departure.
Upon arrival performed maintenance on hvac units, both systems were washed, washed coils off, refrigerant levels are in range. Air flow is good. Filters are clean. Recommended adding surge protection on systems. Indoor motors are good. Thermostats in working order. Circuit board and electrical connections good. Systems are efficient and very quiet. Cycled systems on and off. Systems were reset tested and fully functional upon departure. Signed client up with membership to come out and service systems yearly. Ducting seals are in very good shape.
Upon arrival performed filter change out, client ordered wrong filter so I provided filter , signed client up for maintenance plan.
Upon arrival performed maintenance on heating and ac systems. Systems are Goodman make. Found secondary motor controls for indoor & outdoor systems both low and out of range. Filters are all clean client replaced very often. Cleaned flame sensors on both systems. Circuit board and electrical connections in range. Waxed both furnace units. Dusted off all electrical components, amperages are in range. Condenser fan motors on upstairs unit is over amping. Working harder then needed, found secondary control low. High start up amperages. Downstairs unit is very low on charge. And has a temperature difference of 6 degrees. Client would wanna do leak dye and repairs in January, will not be using air conditioning this year. Signed client up for maintenance plan. Washed condenser coils. Disconnects in working order. Primary controls good. Systems were reset and tested. Downstairs not working at standards for cooling.
Arrived on site to perform spring tune up on a 2015 lennox unit. Client stated no issues. She said we service her rental home and wanted up to come and service her home. Cycled unit in cooling. Condenser coil in back yard. Furnace and Evaporator coil located in attic. Washed out condenser coil inside and out. Client stated she hasnâ€™t did maintenance since system was installed. Checked electrical compartment and components. Primary starter is worn out from normal operation and use. Contact points are bit burnt up due to operation. Secondary motor control is good and in range. Fan motor is good at this time. Start ups on compressor are high and recommended adding a compressor booster kit to help prevent hard start up and prolong unit. Checked pressure and are good and cooling. No protection outside. Inspected indoor unit. Replaced filter. Blower assembly is accumulating dust due to lack of filter change out and maintenance. Motor is good and amps are good. Drain lines is clear. Found
Performed Furnace maintenance on a 2018 Trane furnace. Limit switches and flame sensor was cleaned and tested for correct operation. Filter is clean at thus time. Heating temperature split is over 30 degrees. Gas valve was tested. Ignitor readings were recorded. Component amp draws were recorded. Inducer motor is amping high. Blower wheel needs to be cleaned soon. Installed a nest pro for user ease. Customer was given a tutorial and was satisfied with the thermostat. System was tested in all modes. Running in cooling mode at end of appointment.
Preformed furnace maintenance on 2020 Lennox heater.
Performed AC maintenance on a Goodman condenser. Filter is clean. Systems cooling temperature split is 18 degrees. Indoor amp draws are ok. Condensate lines are clear. Outdoor unit was chemically cleaned. A corrosion inhibitor was installed due to the location of the home to prevent any damage to this newer system. Refrigerant levels are ok. Starting components were checked. Compressor bay and service panel was cleaned. Compressor and fan are amping good at thus time. System was cycled before leaving.
Performed combo tuneup on a ACPro condenser and furnace. Heating safety switches were verified working condition. Filter is clean at thus time. Hot surface ignitor was measured and recorded. Flame sensor was cleaned. Gas valve was tested. Heating temperature split is in range. Cooling temperature split is 18 degrees. Outdoor unit was dirty and chemically washed today. Starting components were checked. Compressor and fan amperages are in range. Refrigerant levels were verified ok today. Recommending outdoor protection. System was running at end of appointment
Tech arrived on site. Indoor blower motor wasnâ€™t operational. Water had entered the electrical cabinet from the condensate leak. Board has corrosion from water. Need to order board and install in order to test the system. Client said the unit had been recharged before. Standing pressure of system appeared low at this time. Will confirm when parts are installed. Client is interested in replacement options.
Summer AC Maintenance Performed Upon arrival system is working and operational. I began my maintenance at the outdoor condenser by breaking it down and cleaning with water and coil solution, removing dirt and debris. I inspected electrical components for wear and tight connections. I checked refrigerant pressures and charge. I tested system amperages. I then proceeded to the indoor furnace unit. I measured temperature splits. I checked condensates for proper drainage and safety. Filter was checked, should replace during winter maintenance. Inspected electrical to ensure tight connections and monitor wear. Inspected blower compartment for dust and dirt as well as proper balance. Adjusted dampers upon home owner request to limit air to master and increase to other rooms. Upon inspection of both units I found there to be no form of electrical protection, recommend adding surge protection onto both units. Upon departure system is working and operational.
Replaced circuit board and transformer. Added surge protection at indoor electrical box. Secured all wires and connections. Cycled system through modes. Checked outdoor unit electrical and system components. System is fully operational upon departure.
Arrived on site to perform spring tune up on a 2004 unit. Condenser located in back yard. Client stated no issues just wanted service and filter replaced. Cycled unit. Washed condenser coil inside and out. Checked electrical compartment and components. Found primary starter worn out and looks to be original. Recommend replacing due to burnt up pittings on contact points. Secondary is good and Lola to have been replaced. Unit added a compressor booster kit. Fan motor was replaced in past and is good. Start up amps are good and in place. Run amps are in range and pulling 11 amps max rated for 19. Checked pressure and are good and cooling home. Replaced filter and inspected indoor unit and ducting. Dusting is good and new as it was just replaced recently. Slight dust just need to stay on top of filter more. No protection on either unit. Recommend adding surge protectors on unit to protect from electrical and power outage and more cause of the condenser dose not have any disconnect and hi