Arrived on site to diagnose no cooling 2017 carrier unit client stated unit is working just not cooling and blowing warm air. Upon arrival client cycled unit and found compressor not on. Inspected electrical compartment and found secon Was completely bad for compressor. Needed replacement. Replaced to replace napery unit. Primary stater is good. Fan motor has oil to be leaking. Amp draws is pulling 1.8 and max rated at 1.4 advised is over amping but would like to get system maintenance and cleaned out before dying motor should be replaced just advised in case dose fail from over amping. Compressor start up are I. Range but recommended a compressor booster kit to help prolong life of compressor. Run amps are pulling 11 and max rated at 15. Advised working hard cause unit is dirty. Checked pressure and are stable and good and unit is cooling home. Found to what looked like oil under condenser and in the condenser coil showed client and advised pressure are okay now and to not let dog
Arrived on site to perform diagnostic on 3 year old Goodman system. Homeowner states that unit is blowing, but the air is not cold coming out the vents. Cycled system for cooling. Indoor unit kicks on, outdoor condenser fan motor kicks on, but compressor is not turning over. Checked refrigerant levels and unit is not on low pressure lock out. Found a dead secondary motor control for compressor, which is not allowing compressor to kick on. Also found primary motor control extremely burnt and pitted at contact points. Went over findings and recommendations with homeowner. With approval replaced primary and secondary motor control. Signed homeowner up on monthly maintenance program, performed AC maintenance today due to condenser being extremely dirty. Thoroughly washed outdoor condenser coil inside and out. Cycled system, system is fully operational and cooling upon departure.