Arrived on site to perform diagnostic on 3 year old Goodman system. Homeowner states that unit is blowing, but the air is not cold coming out the vents. Cycled system for cooling. Indoor unit kicks on, outdoor condenser fan motor kicks on, but compressor is not turning over. Checked refrigerant levels and unit is not on low pressure lock out. Found a dead secondary motor control for compressor, which is not allowing compressor to kick on. Also found primary motor control extremely burnt and pitted at contact points. Went over findings and recommendations with homeowner. With approval replaced primary and secondary motor control. Signed homeowner up on monthly maintenance program, performed AC maintenance today due to condenser being extremely dirty. Thoroughly washed outdoor condenser coil inside and out. Cycled system, system is fully operational and cooling upon departure.