Thank you, Jorge for servicing our air conditioner and giving us a price quote.
Our technician, Jimmie, was prompt, polite, and thorough. Explained the problems in our AC system and gave various alternatives on each one. I am inclined to call Cool Air Solutions in the future, as needed.
Daniel the technician was extremely thorough and professional. The service was beyond what I expected. I feel my ac/heating system is in great hands. Thanks to Elaine for referral.
Amazing job by everyone involved and great experience.
Installation of a new HVAC system went very smoothly and efficiently. New system appears to be working well.
Removal of old HVAC system and installation of new one went very well. New system performing very well. No attempts at annoying "upselling" by sales staff.
Provided me with great information.
Exceeded my expectations
Tech arrived on site. Found no power to the thermostat. Fuse on control board was popped. Replaced fuse and tested fan and heating. It was good. Tried cooling and it popped. Removed low voltage wires to the contractor outside. Tested cooling again and it didnâ€™t pop. Ohmed out low voltage terminals and found the contractor to be bad. Replaced contractor and the unit began to cool.
Upon arrival performed diagnositc on Package unit on roof. Client had replaced breaker thinking breaker was bad. Replaced and still kept tripping system. Found compressor to be grounded on the start terminal. System, is not operational. Darren to come out tomorrow morning to give replacement options.
Tech arrived on and found 1 hvac system operational. Homeowner said unit wasnâ€™t cooling yesterday. Found the capacitor to be low. Wiring was a mess. Cleaned up the wiring, and installed a new capacitor. Cleaned out the electrical. Tested unit and itâ€™s operational. Helped customer install the nest app and hook up WiFi. 1 year parts labor warranty on the capacitor. Membership is for 1 year at $14.95. After a year it can be canceled.
Arrived on site to perform spring tune up on a 2009 Goodman unit. Client stated no issues as they have yet to use system. Condenser located in back yard. Furnace and Evaporator coil located in attic. Washed condenser coil inside and out. Primary is burnt up on contact points from self wear. Secondary motor controls is good. Fan motor is working at max rate. Could fail in future from self wear. Checked compressor amps. Start ups was really high and over max from self wear and age. Run amps are good and in range. System pressure are good and cooling home at 20 degrees. System uses R-22 refrigerant and no longer in production. Inspected indoor unit. Filter was slightly dusty but good. Blower assembly and motor are good. Evaporator coil has slight dust and debris from past dirty that has entered system. No protection on out door unit. Cycled system. Went over all findings and recommendations with client. Client is aware of how system is and itâ€™s condition. Client did declined recommended
Performed AC maintenance on 2019 AC Pro condenser.
Performed system diagnostic on 2012 Goodman. Upon my diagnostic homeowner stated that water is been leaking from under the system since Sunday. Advise me that a plumber that came out and said there was no issue with the water heater in that it Has to be related to the HVAC system. Further into my diagnostic I inspected the system and found that water was filling up in the return platform. Tested the primary condensate line is draining out properly and primed it with four bottles of water, No issue with draining or signs of flooding. There is also a secondary float switch in the case of the flood ever does occur this would actually trip the system and turn it off before water ever has a possibility of leaking out. Did further investigation and this may be due to a possible slab leak from the plumbing, Found out the water meter out front is continuously moving even though thereâ€™s no running water in the home. Notified homeowner and he is having a plumber come out. Upon departure system
Quality control check
Performed cooling maintenance on 10 year old Lennox system. Installed by us. Cycled system for cooling. Checked outdoor unit electrical and system components. Refrigerant pressures are in range and system is producing proper temperature split. Primary motor control is starting to hum on low voltage coil. Secondary motor control is out of range for condenser fan motor side. Compressor amp draws are in range, but on start up it is loud and hard. Pulled off condenser fan motor as well as all condenser Panels and thoroughly washed condenser coil inside and out. Checked indoor unit electrical and system components. Filter is ok, homeowner replaces himself every 3 months. Went over findings and recommendations with homeowner. He wants to take care of repairs but is not ready at the moment, but wants to do it before summer. He will call in when he wants us to come out and take care of it. Cycled system. System is fully operational upon departure.
Arrived on site to perform AC maintenance on package unit. Home has 2 systems, we are only working on the unit on the roof as that is the older of the two. Homeowners just recently moved into home. They had inspection done that said everything was ok, but they want to get it checked. Cycled system for cooling. Checked package unit components and electrical. Compressor amp draws are close to over amping. Amp draws on indoor fan motor and condenser fan motor are going over allowed range, and indoor blower motor has started to leak oil. Temperature split is in range and refrigerant pressures good. Indoor blower wheel is dirty. Primary motor control has some pitting and burning marks at contact points. Rinsed off outdoor condenser coil. Performed attic duct inspection. Ducts are old and outer liner is starting to fall off. System is still operating, but it is older and super inefficient and parts are going to start failing. Went over findings and recommendations with homeowners. They want
Performed AC diagnostic on 2007 carrier condenser. Prior to diagnostic Mac had stated that home warranty had done a diagnosis on the system and recommended that he replaced everything due to it not working. I begin my diagnostic at the outdoor unit and found that it was not energized with 240 V. Capacitor was also replaced and left accidentally buy home warranty company. Found that outdoor breaker coming from panel were miss labeled And breaker for AC was off. Flipped the breaker back in the on position And system fired up properly. Compressor was pulling 9 Amps considering at the highest is 14. System also contained R22 refrigerant which was completely phased out January 1, 2020. Contactor was pitted. Indoor unit was from 1989 and had original evaporator coil that was covered in duct tape. Also found signs of water leakage coming from primary pan of the evap coil due to it rusting out over the years. Ultimately system worked but Mac would like to replace the system once he moves into
Arrived on site to return to install phenomenal air on a 2017 lennox system. Furnace and evaporator coil located in garage. Discharged unit and made whole bigger installed and secured unit and has good airflow. Cycled system. Unit is operational as client leaves fan mode on. Client is aware of how system works and registered client up for her warranty. System is operational upon departure. Collected remaining balance. Client is happy with repairs and work done. System operational upon departure.
Performed diagnostic on system. Homeowner states that his nest thermostat says it has no power. Happened yesterday morning. Checked for power at thermostat and not recieving 24 volts. Went into attic and found a broken fuse. Used pigtail fuse to see if unit had a short, system tripped fuse as soon as power was restored. Troubleshoot the short down to a bad outdoor defrost board. Defrost board needs to be replaced. System is in poor condition as well as ducting has rips and tears throughout the tubes. Went over findings and recommendations with homeowner. Homeowner thought price was too much, said he has a friend in San Diego that could do it but he couldnâ€™t get him out here today. Said He will be ordering parts and doing the repairs himself. No work performed other than the diagnostic.
Arrived on site to perform combo tune up on a 2017 lennox unit. Client renewed over phone. Condenser located on side of home client stated no issues just wanted service. Washed condenser coil inside and out. All electrical and components are good and in range. Compressor amp draws are good. Fan motor is good and in range. System pressure is good and cooling home at 20 degrees. Inspected indoor unit. Filter was dirty and needing replacement. Blower assembly and wheel is good. Motor is good. Inducer motor is good. Drain lines are good and in range. Found air scrubber purifying system bulb burnt and bad. Recommend adding a phenomenal air to prevent maintenance and yearly replacement parts and would better air quality. Evaporator coil is good. System is heating and cooling good. Client dose want to go forward with adding phenomenal air to system to not be having to do maintenance. Unable due to time and would have to come back out and install. Collected amount of $100 for deposits. System
Performed Ac maintenance on 2020 system. Cycled system for cooling. Checked indoor unit electrical and system components. Merv filter is dirty and should be replaced, homeowner wants to order it from amazon and replace himself. Temperature split is in range and system is cooling efficiently. Checked outdoor unit electrical and system components. Amp draws are in range. Primary motor control is in good condition. Secondary motor control and compressor booster kit is within range. Pulled condenser fan motor off as well as condenser cage and thoroughly washed out condenser coil inside and out. Cycled system, system is fully operational upon departure.
Performed furnace maintenance on a Aire flo furnace. Homeowner had condensate overflow problems in the past. Condensate lines are free and clear of any debris. Combustion blower is over amping. Temperature split is in range. Blower motor and scroll wheel are clean and dry of any oil. Duct runs look good. Performed A/C maintenance on a air flow condensing unit. System was coil cleaned and reinstalled. Start and run Amps are in range. Fan motor is spinning good and clean of any oil. Starter is showing signs of failure. System was cycled and running smoothly