Installation of a new HVAC system went very smoothly and efficiently. New system appears to be working well.
Removal of old HVAC system and installation of new one went very well. New system performing very well. No attempts at annoying "upselling" by sales staff.
Provided me with great information.
Exceeded my expectations
Excellent knowledgeable service technician
The crew was thorough and professional. Every aspect of the job was explained in detail with no surprises. A company you can trust.
Great Service! Technician (Jamie) arrived as scheduled and completed all work as promised. Kepted us informed as to what he was doing thru the entire process. System works great!
Installed outdoor fan motor and duel secondary motor warranty for 1 year on components
Installed outdoor fan motor and duel battery cap 1 year warranty on parts
Performed AC/furnace tuneup on 2003 Aireflo System. Upon my maintenance there were multiple points of concerns that were addressed with the homeowner. AC- 1. Found the condenser fan motor Leaking oil from bearing due Lubricant seal rupturing. This can cause the motor to pull hire Amperage along with it locking up or overheating From lack of lubrication. If this component fails this can cause compressor to overheat and create much more damage than what has already has occurred. 2. Duel secondary motor control has become weak on the hermetic and fans side terminals. 3. High-voltage relay contained putting on contact points. This completed access the brakes for the system and can cause failure on start up and shut down if pitting worsens. 4. Measured compressor amperage and found a total of 15 A being pulled which is fairly high considering that there is no heat load in the house and the ambient temperature is very low today. 5. Condenser fan motor Amperage was also exceeding manufactur
Performed AC/furnace maintenance A 1994 comfort maker system. This is the rental property of John Peterson. During the maintenance we also came across a few points of concerns that were addressed with John. AC- 1. Found the condenser fan motor had a oil leakage Coming from Lubricant seal of bearing. This can ultimately lead to the motor locking up or overheating due to lack of lubrication around bearing. 2. Duel secondary motor control has become weak and compressor side terminal. 3. Compressor pulling 10 A coming very close to the manufacture specification of 13 A 4. High voltage relay also contained high amount of pitting on contact points due to compressor using high amperage overtime this was eventually completely eat away at the brakes of the system. 5. System also contains R22 refrigerant which was completely phased out January 1, 2020 Furnace- 1. Inspected the heat exchanger and found no signs of cracks on eyelids. 2. Found an indoor blower motor was completely covered in du
Will be returning to sync new Lennox remote with mini split due to previous one being lost. Also confirmed that Heater is running properly and is our install from 2020. System had a 53Â° temperature rise with 125Â° coming out. Due to heat rising, downstairs will feel a bit colder versus upstairs having much more heat build up. Recommended that filter swapped out as well. Signed client up ESA maintenance And will be returning with new remote once part is in. Upon departure system is fully operational and Heating home at this time.
Upon arrival performed maintenance, indoor motor is in good condition. Indoor blower wheel is very dusty and has dust on fins. This causes off balance on blower wheel and weight on motor. Circuit board and electrical connections good. Gas piping does not has 3 inch sediment trap. Client would like to cancel membership, due to filter having to be charged for. Client was Just upset. Client said she never seen the benefit of membership if we arenâ€™t including filters. Flame sensor has a lot of oxide build. Gas valve in working order. System was reset tested and fully functional
Arrived on site to perform fall tun up on a 2014 carrier system. Client stated no issues. Cycled both thermostat and are good. Found all filter dirty and over due replacement. Recommend replacing more often are as needed to prevent air flow restrictions and dirt entering system. Blower assembly and wheel are getting dirty and accumulating dirt and debris. Recommend cleaning blower assembly to reducer wear on motor. System has 2 zones on a single stage system. Advised would want variable speed system to help improve airflow all around home and less stress on motor. Secondary motor control is good. Flames sensor slight wear. Igniter is good and in range. Found inducer motor with a lot of play on wheel and is pulling almost max amps. Wheel of inducer is getting unbalanced and can cause inducer motor to fail sooner then expected to wear its self caused. Heat exchanger is good. Drain lines are dirt and accumulating debris in system. Advised secondary line is dripping straight into emergenc
Installation of a Lennox Single Stage 16 SEER A/C with High Performance Coil and Single Stage Ultra Low NOx Furnace, including UV Light and upgraded Filtration
Collected 1050. Balance due of 19873 paid by service finance
Upon arrival performed maintenance on 2005 comfort maker. Cleaned and dusted indoor cabinet and outdoor of furnace. Gas valve and shut off in working order. Disassembled burners and cleaned all dust inside. Circuit board and electrical connections good. Evap coil is dirty, recommend cleanings and swapping filters out more frequently. Inducer draft motor running close to high amperages. Examined heat exchanger, lots of hot spots and corrosion. Checked for any damaged parts of heat exchanger, did not verify any cracks. Temp rise splits in range. - dirty blower wheel - dirty evaporator coil - dusted all electrical components - cleaned and sanitized indoor caging Disassembled burners and dusted off System was reset tested and fully functional upon departure.
Arrived on site to diagnose a no heating system on a 2006 aireflow. Client stated system has been down for a couple years. Advised client i would inspect system of issues and see whatâ€™s going on. Inspected all electrical compartment and found system giving error code of bad polarity and found pig outlet bad as it wasnâ€™t send proper voltage to system to operate properly. Also found something stuck and broken in side the outlet as well. Advised we got system operational and ran system for a bit and shortly after had all smoke detectors and carbon monoxide detectors all go off in home and we shut system down. Advised client of finds and we would do a safety evaluation of the system to ensure system would be safe to run. Pulled heat exchanger out and found system was leaking and heat exchanger is now compromised and no longer safe to run and we would have to shut gas off to system for safety reason as compromised heat exchanger is not safe for anyone in home and could risk allowing com
Arrived on site to perform fall tune up on a 2003 carrier unit. Furnace located in attic. Client stated no issues just wanted system serviced. Cycled thermostat on and was good. Found filter to be washable and good. Found black flex ducting used and old condition. Found blower assembly really dirty due to the amount of dirt that has entered system is past years and creating stress on motor.recommend cleaning blower assembly to help reduce wear and stress on motor. Motor is now leaking oil as there is oil down shaft of motor and in blower wheel it self. Motor is pulling high amp draws and almost at max and could be failing at any time. Recommend replacing motor before completely fails. Inducer motor is over amping as itâ€™s pulling 1.7 amps and max rated at 1.4 amps. Indicating inducer motor could fail at any time due to age and how hard itâ€™s working. Secondary motor control is weak and bad from blower motor working hard draining life of unit. Inspected and pulled heat exchanger and
Performed furnace maintenance on 7 year old trane system. Cycled system for heating. Verified proper heating sequence of operations. Temperature rise across heat exchanger is within range. Replaced 1 inch filters. Ran system through 20 point inspection checklist. Went over findings and recommendations with homeowner. Homeowner mentioned that she has a couple rooms with airflow problems that she would like to get fixed. Spoke about doing some minor tweaks to the existing ducting, or replacing all the ducting altogether. Homeowner ultimately wants to replace the ductwork. Gave her a approx estimate to get ducting replaced. Would need to get a specialist out to properly size ducting. Homeowner has to get her schedule coordinated as she does not live on the property year round. She will give us a call when ready. Cycled system, system is operational upon departure.
Upon arrival performed routine maintenance. Indoor motors are both in good condition. Blower wheels are both starting to collect some dust on fins. Flame sensors on both systems have a lot of corrosion build up, this can cause systems to intermittently stop working. There is no distribution boxes on returns, returns are connected to side of furnace. Gas valve and shut offs in working order. Cleaned inside of furnace took out all insulation and dust from heating cabinet. Gas pressures good. - corroded flame sensors - standard filtration - dirty blower wheels - circuit board good - cleaned off furnaces Gonna follow up with client, gonna speak to wife about membership and upgraded filtration.