Excellent job. Very informative. Thank you.
Cool Air Solutions installed our HVAC systems a few years back and has maintained it ever since. The system drastically changed the comfort level of our home and our lives for the better. The company has a top-notch quality culture. Justin knows his stuff. We recommend both Cool Air Solutions to anyone in the Menifee area looking to upgrade or repair their air conditioning system.
Prompt service, good prices, flexible payment options.
Mike came out to give me an estimate on AC service. He was very thorough and accommodating. What sets him apart from most of my experiences is how friendly and easygoing he is. I’m looking forward to working with this company.
Michael did a yearly service of our system. He was very professional and courteous while in our home. He fully explained what the service entailed and explained the actual costs. He also explained the service contract.
My experience was awesome. Great customer service . Kinberly was very helpful and George Cervantes exceptional !
Tyler arrived on time and was very professional, knowledgeable on his products. Completed the cooling system tuneup in minimal time which allowed him to ask me if I had any questions or concerns regarding my system. I will definitely recommend to my neighbors and friends.
Great service! Very friendly and saved us a lot compared to other company we called first!
Arrived to perform an ac tune up. Customer said heâ€™s been living in the home fro six years, never had a maintenance done on it. Wants to see condition, cools them down, donâ€™t use it much because they have a swamp cooler. Cycled system on. Checked readings on the motor and are high, checked airflow pressures and like blood pressures on your body if they are high you will have health issues, same thing with the heating and ac system. Pressures are high going into mild suffocation. Pulled blower assembly out, motor is leaking oil, wheel is extremely dirty, lowering indoor air quality, but also making the motor work harder because itâ€™s heavier to spin it, less airflow high energy costs. Heat exchanger completely discolored. Evap coil is dirty. Debris in th coils. No condensate safety switch installed. The circuit board has a burned mark on it. Has a washable filter installed and was completely clogged up. Causing that suffocation, system restriction, and high energy costs. Supply ple
Arrived on site to perform spring tune up on a 2001 system. Condenser located in back yard. Furnace and evaporator coil located in attic. Client or Tenant stated no issues. had tenant cycled cooling mode to ensure system operating. Inspected out door unit. Washed condenser coil inside and out. Checked electrical compartment and components. Checked amp drawls o. Compressor and fan motor. Checked refrigerant pressure. Did indoor unit inspection. Replaced filter. Checked electrical wiring, connections, circuit board, and components. Checked blower assembly and evaporator coil. Checked secondary drain pan, drain lines, and temperature split. The summary of findings are as followed. Cycled system to ensure systems is operational. Condenser 1. Condenser is starting to corroded at bottom of the condenser coil. 2. Thermostat wires are exported on line set that run into home and electrical compartment as the whipper is not coving thermostat wires completely. 3. Line set has no isolation
Performed AC maintenance on American Standard unit in Menifee, replaced 20 x 30 x 1 merv 8 air Filter. Tested system and verified correct operation.
Performed AC diagnostic on 2003 Aire flo system. Homeowner states system is blowing warm air. Cycled system for cooling. Outdoor condenser fan motor kicked on, but compressor is not turning on. Checked unit electrical and components. Found a bad secondary motor control. Put a temporary secondary motor control in to perform thorough evaluation of system. System kicked on. Refrigerant levels are in good range. Compressor amp draws are high and is close to over amping. Condenser fan motor is over amping and is leaking oil. Primary motor control is burnt an pitted. Condenser coil is extremely dirty. Went over findings and recommendations with homeowner. Talked about system replacement and answered some questions homeowner had about replacing. Homeowner is aware that system is older and inefficient, and that it will need to be replaced soon. Wants to take care of the immediate repair today and sign up for ESA membership. Put secondary motor control in permanently, and also performed Spring
Checked system indoor temperatures. Checked air filter (this was good). Checked condensate drain line. Verified refrigerant pressures. Monitored the motor amp draws and measured incoming high voltage and low voltage. Removed leaves from condenser bottom. Cleaned condenser bottom and coils with water. Checked battery capacitance.
Arrived on site to diagnose a no cooling system. Upon arrival spoke over client client on what was going on. Client stated just a few days ago her neighbors came by and stated there unit is making loud noises. Sheâ€™s stated prior to he neighbor. Okâ€™ing and advising her she said her unit did cool. She also stated husband went and replaced the secondary control to the condenser unit . Unit still did not operate. Upon arrival had client wife shows me the equipment. Found out door unit not operational and making loud buzzing noise. Fan was not operational. Inspected electrical compartment.found primary pittings burnt up. Secondary control husband replaced is good. Found motor completely bad as bearing are seized up and dose not spin at all.called client out side so she can see the issues her self. I stated to wife since unit is not operating properly I can. To determine if unit cools properly. We would have to do repairs and get system operating properly and then ensure itâ€™s cooling a
Performed maintenance on 2 13 year old systems. Homeowners were not available, met with homeowners brother. Cycled systems for cooling. Checked outdoor unit electrical and system components. Pulled condenser fan motors on both units and thoroughly washed wash out and vacuumed condenser coil inside and out. Condensers were super dirty. Performed thorough evaluation of systems, concerns are as follows 1. Compressors on both units are starting up hard 2. Condenser fan motors on both systems are over amping 3. Condenser fan motors on both systems have leaked out a significant amount of oil 4. Condenser coils are starting to corrode 5. Indoor blower wheels are dirty 6. Indoor blower motors are leaking oil as well There was no homeowner available to go over recommendations. Writing up invoice and emailing it over. Cycled systems, systems are fully operational upon departure.
10 year parts, 2 year labor, 10 year compressor warranty included
Performed Ac maintenance on 1991 system. Met with husband, wife is out of town. Homeowner states system has been working perfectly. Cycled system for cooling. Checked indoor and outdoor unit electrical and system components. Thoroughly washed out condenser coil. Replaced 1 inch filter. Thoroughly evaluated complete system, findings are as follows: 1. Indoor ducting system is in poor condition. Outer insulation is ripping off In a few portions of ducting system 2. Furnace is a Premier brand furnace. This particular make and model of furnace is recalled due To it being extremely unsafe to operate and known for catching fire 3. Outdoor compressor is over amping on start up 4. Compressor is close to over amping on running 5. Condenser fan motor is starting to leak oil 6. System is very old and inefficient. It is working very hard and indoor furnace is unsafe to operate Went over all findings and recommendations with homeowner. Homeowner is fully informed and is fully aware of the cond
This includes a 2 stage heating and cooling system that can be zoned. This will have 2 zones with a thermostat upstairs and downstairs. Both thermostats will be WiFi and can be used with a phone of iPad. We will dispose of the old equipment to the dump and in the trash. This will be installed on the 2nd and if we need to return on the 3rd to finish we will.
Customer called me that water was leaking underneath the sink. I performed a cut and clear yesterday. Came back to see what was going on. Found a tear in the rubber house that connects the drain line to the sink, which is where the water is leaking. Cut off this portion of the house and reconnected to sink. No more leaking, system is operational upon departure. Call back on myself, no charge to customer.
Performed AC maintenance on 2 2006 York systems. Homeowner purchased the home about a year ago and has never had it checked. Checked outdoor unit electrical and system components. Pulled condenser fan motors to thoroughly wash out condenser coils inside and out on both units. Cleaned electrical compartment. Left replacement filters with homeowner. Performed thorough evaluation of systems. Conditions are as follows Upstairs System: 1. Compressor is over amping on start up 2. Condenser fan motor amps in range 3. Primary motor control is in good condition 4. Secondary motor control is out of range 5. Lineset rubitex is completely chewed through Downstairs System 1. Compressor is over amping on start up 2. Condenser fan motor is over amping 3. Condenser fan motor is starting to leak oil and becoming hard to spin 4. Primary motor control in good condition 5. Secondary motor control is on the verge of falling out of range Both systems have proper refrigerant pressures and are produci
Performed diagnostic on 2013 system. We met with homeowners mother onsite, both homeowners were not present. Homeowner states that system is working and cooling the way it should, but there is a noise coming from the outside. After evaluating the problem, found that the noise is actually water coming from the secondary drain line from above the upstairs window and hitting the porch laminate. Went over findings with Homeowner, she mentioned that they recently were having issues with the sink Being clogged. Main drain line has to get cleared out. Upon authorization, cleared out main drain line. Replaced 1 inch filters. Homeowner signed up on monthly ESA maintenance program, first visit will be in the fall for furnace. Cycled system, system is fully operational upon departure.
Upon arrival performed diagnostic. There is no air flow on the 2 back rooms. Customer stated it can get as hot as 120 degrees in these 2 rooms. System is original to the home. Bill and Darren are following up with each other to get proper airflow to home. Design of havoc system is very old and inefficient. Recommend replacing.
Performed Diagnostic on 2005 system. Homeowners dog chewed up the condenser low voltage wires as well as the rubitex around the lineset. Quoted homeowner on replacing wire and rubitex as that is where we would have to start in order to test unit operations. Removed all checked up wire and rubitex, ran new wire inside of new rubitex in hopes that dog does not chew it through. Cycled system for cooling and system came right on. Condensers are extremely dirty and clogged with pet hair. Recommended performing maintenance on condensers, as well as recommended our maintenance program for both systems. Homeowner wants to sign up on yearly maintenance program for both systems. Went ahead and performed maintenance on both units. Checked electrical and system components. Pulled condenser fan motors on both units and thoroughly washed out the condenser coils inside and out. Replaced both 1 inch filters. Added new compressor booster kits to both units per homeowner Approval. Cycled systems for coo