The Tec was very knowledgeable and pleasant to deal with.
YOUR COMPANY, OFFICE PERSONAL AND FIELD PERSONAL ARE WESOME I THANK YOU ALL FOR YOUR COURTESY AND KINDNESS. JG.
Always professional and helpful
Luke was great. He wasn’t given the correct size filter for my hallway.
Replacement of condenser and coil with Lennox Equipment Re-insulate exposed ducting in garage.
Arrived on site to diagnose a non operating system. Clients had home warranty out and could not fix issues. Stated they had a shortage due to past owners dog chewed up condenser thermostat wires. Upon arrival system would. Or operate or have power coming in. Thermostat is bad and failing already recommend replacing thermostat. Found system with no filter as it was in the return plenum as it was not the right size and fall in. Found blower assembly hammered, and blower wheel dirty, motor is leaking oil and has layer of dirt and oil.Found someone has bypassed the Low voltage door switch as it it currently cut off. Advised that is a safety concern. They need that replaced or repaired immediately. Test for voltage was not getting none but was getting 120v at pig tail plug in. Replaced a transformer and now had power in furnace as I got blower motor working and operational. Went to out door unit found condenser thermostat wires were chewed up and exposed causing electrical shortages and why
Post job walk
Performed AC maintenance on 7 year old carrier system. Cycled system for cooling. This is a single stage system that is split off into 2 zones. Checked outdoor unit electrical and system components. Amp draws on compressor is in range. Amp draws on condenser fan motor are over amping. A lot of oil loss is present on condenser motor. Pulled condenser motor to thoroughly wash out condenser coil inside and out. Secondary motor control is in range. Primary motor control is in good condition. Refrigerant levels are in range and system is producing a good temperature split. Replaced 1 inch filters. Went over findings and recommendations with homeowner. Cycled system, system is operational upon departure.
We will be installing a used 3.5 ton Goodman ac and coil. Model GSX16. This also includes a filter rack under the existing furnace with a condenser pad and service disconnect. Also included will be a a filter dryer to filter contaminants switching from r22 to r410a. We will use rx11 flush kit to clean all the old Freon out so that we can use the new r410a Freon. Evaporator coil will have an emergency drain sensor to protect against flooding
Performed diagnostic on 2003 system. Homeowner states that system is leaking water in her bathroom and in her hallway. Bathroom ceiling has almost completely caved in and hallway is getting stained with water as well. Went into attic to inspect system. Performed thorough inspection of system, findings are as follows 1. Main drain pan is over flowing, leaking water over and into bathroom and hallway 2. System is not leveled correctly, which is causing all the water to towards the back of the drain pan and over 3. No water is making it to the drain lines for this reason as well 4. Evaporator coil is completely clogged up. 5. Seems like there was a rope tied around the drain pan to prop it up so that water would flow through the drain pan 6. Ducting is in horrible shape. It is not sealed correctly and ripped in numerous parts. Went over all findings and recommendations with homeowner. Gave her some repair options but mentioned that no warranty can be given on any work done based on
Upon arrival performed diagnostic. System does not cool properly. Found system icing up on refrigerant lines. Evap coil is dirty and causing air restrictions. Blower wheel is completely covered in dirt & debree. Indoor motor is leaking oil and has a lot of dirt covered in it. Outdoor fan motor leaking oil. Compressor is freezing up due to restrictions inside of system. Recommend replacing system due to age and inefficiency & cost of repairs.
Upon arrival performed diagnostic. System turns on. Pressures are completely flat. Refrigerant levels are really low for system. Darren coming out on Saturday to give replacement options.
Installed customer supplied thermostat. Rewired for common wire to be operational. Cycled system through heating and cooling modes. System is fully operational upon departure. Offered to do a thorough evaluation of system , homeowner did not want me to and said system has been running fine, only thing he needed was thermostat installed.
Quality control check
Performed Ac maint on 2008 Lennox system. Cycled system for cooling. Checked outdoor unit electrical and system components. Amp draws on compressor and condenser fan motor are fairly high, but within range. Secondary motor controls are in range, primary motor control is in good condition. Amp draws on compressor start up are high. Pulled condenser fan motor to thoroughly wash out condenser coil. Condenser coil is really deteriorated at a couple different spots and refrigerant lines are very exposed. Reassembled unit. Replaced 1 inch filter. Checked indoor unit electrical and system components. Blower wheel is starting to accumulate dust. Could not access attic due to full closet. Refrigerant levels are in range and system is producing a good temperature split.
Drop cloths on any traffic area- Shoe covers will be used- painters plastic around the attic access will also be used While performing work- Ducts have a limited lifetime warranty on parts and workmanship.
Upon arrival performed maintenance. Replaced2 blower motors and battery caps. Performed cleanings on system. Installed 2 air scrubber to maintain cleanliness throught system and help with odors, dust levels, pet dander, and have purified air inside of home. Surge protectors to keep system healthy. System was reset tested and fully functional upon departure.
Heating maintenance in Perris, Ca
Ac tune up in Perris, Ca.