I am satisfied with him, thank you
The Tec was very knowledgeable and pleasant to deal with.
YOUR COMPANY, OFFICE PERSONAL AND FIELD PERSONAL ARE WESOME I THANK YOU ALL FOR YOUR COURTESY AND KINDNESS. JG.
Always professional and helpful
Luke was great. He wasn’t given the correct size filter for my hallway.
Jimmy installing secondsryncomtrol
Upon arrival found system low on refrigerant. Advised customer we can charge system up with refrigerant, declined gonna think about replacing system will give us a call back.
Customer canceled due to thinking we were his home warranty company. Meant to cancel us but canceled his home warranties.
NO COOL. Found system non operational. Customer stated unit doesnâ€™t run after changing the batteries. Checked thermostat and saw battery compartment is separate and very accessible without removing thermostat. Checked for power and found no low voltage coming out of low voltage controller. Would have to check if manufacture still has this part due to the age of the system. Due to age and condition of the system we highly recommend replacement options. Customer will talk it over with the dad and sister to find out if they want to move forward with replacement options. Customer will call us when he knows. Unit not operational upon departure.
CALLBACK/WARRANTY. Customer stated unit is still leaking water. Says tech was out here yesterday and said he didnâ€™t have all the parts to fix it so he only put glue on the leak. Checked line and it was overflowing at t connection to p trap. Cut line open to pressurize. Blew out rocks and gunk out of the line. Also used nearby hose to clean inner lining. Removed damaged connection and went home supply store to get new one/s. Flushed line with over 2 gallons to test. Line is cleared upon departure.
Replaced the thermostat, repaired the primary condensate line and cleared the line. Added a trap and safety switch to the condensate drain.
Performed AC diagnostic on 1995 comfort maker condensing unit. Upon my diagnostic I found that the system was on although would shut off after about 15 minutes. This has been caused due to the compressor going off on thermal overload and the pressure relief valve releasing pressure due to high amounts building up. 3.5 ton Comfortmaker- 1. Compressor going off on thermal overload and opening pressure release valve. Windings within compressor are overheating due to insulation thinning out. Compressor is on borrowed time and occurs at the end of compressor life. 2. System contains R22 refrigerant Which has been completely phased out as of January 1, 2020. 3. High voltage relay showing signs of pitting/burn makes on contact points about 95%. 4. Compressor pulling incredibly high amperage at 21 A with max rated amps on data plate are only 19.2. This is also the reason why the compressor is failing due to high energy consumption in overworking. Recommendations- 1. Replacement of R22 3.5 ton
Replacement of condenser and coil with Lennox Equipment Re-insulate exposed ducting in garage.
Arrived on site to diagnose a non operating system. Clients had home warranty out and could not fix issues. Stated they had a shortage due to past owners dog chewed up condenser thermostat wires. Upon arrival system would. Or operate or have power coming in. Thermostat is bad and failing already recommend replacing thermostat. Found system with no filter as it was in the return plenum as it was not the right size and fall in. Found blower assembly hammered, and blower wheel dirty, motor is leaking oil and has layer of dirt and oil.Found someone has bypassed the Low voltage door switch as it it currently cut off. Advised that is a safety concern. They need that replaced or repaired immediately. Test for voltage was not getting none but was getting 120v at pig tail plug in. Replaced a transformer and now had power in furnace as I got blower motor working and operational. Went to out door unit found condenser thermostat wires were chewed up and exposed causing electrical shortages and why
Post job walk
Performed AC maintenance on 7 year old carrier system. Cycled system for cooling. This is a single stage system that is split off into 2 zones. Checked outdoor unit electrical and system components. Amp draws on compressor is in range. Amp draws on condenser fan motor are over amping. A lot of oil loss is present on condenser motor. Pulled condenser motor to thoroughly wash out condenser coil inside and out. Secondary motor control is in range. Primary motor control is in good condition. Refrigerant levels are in range and system is producing a good temperature split. Replaced 1 inch filters. Went over findings and recommendations with homeowner. Cycled system, system is operational upon departure.
We will be installing a used 3.5 ton Goodman ac and coil. Model GSX16. This also includes a filter rack under the existing furnace with a condenser pad and service disconnect. Also included will be a a filter dryer to filter contaminants switching from r22 to r410a. We will use rx11 flush kit to clean all the old Freon out so that we can use the new r410a Freon. Evaporator coil will have an emergency drain sensor to protect against flooding
Performed diagnostic on 2003 system. Homeowner states that system is leaking water in her bathroom and in her hallway. Bathroom ceiling has almost completely caved in and hallway is getting stained with water as well. Went into attic to inspect system. Performed thorough inspection of system, findings are as follows 1. Main drain pan is over flowing, leaking water over and into bathroom and hallway 2. System is not leveled correctly, which is causing all the water to towards the back of the drain pan and over 3. No water is making it to the drain lines for this reason as well 4. Evaporator coil is completely clogged up. 5. Seems like there was a rope tied around the drain pan to prop it up so that water would flow through the drain pan 6. Ducting is in horrible shape. It is not sealed correctly and ripped in numerous parts. Went over all findings and recommendations with homeowner. Gave her some repair options but mentioned that no warranty can be given on any work done based on
Upon arrival performed diagnostic. System does not cool properly. Found system icing up on refrigerant lines. Evap coil is dirty and causing air restrictions. Blower wheel is completely covered in dirt & debree. Indoor motor is leaking oil and has a lot of dirt covered in it. Outdoor fan motor leaking oil. Compressor is freezing up due to restrictions inside of system. Recommend replacing system due to age and inefficiency & cost of repairs.
Upon arrival performed diagnostic. System turns on. Pressures are completely flat. Refrigerant levels are really low for system. Darren coming out on Saturday to give replacement options.