I am satisfied with him, thank you
The Tec was very knowledgeable and pleasant to deal with.
YOUR COMPANY, OFFICE PERSONAL AND FIELD PERSONAL ARE WESOME I THANK YOU ALL FOR YOUR COURTESY AND KINDNESS. JG.
Always professional and helpful
Luke was great. He wasn’t given the correct size filter for my hallway.
Performed AC maintenance on 11 year old unit. Cycled system for cooling. Checked indoor unit electrical and system components. Refrigerant levels are in range and system is producing proper temperature split and cooling correctly. Checked outdoor unit electrical and system components. Pulled condenser motor and thoroughly washed out condenser coil inside and out. Ran system through point inspection. Concerns are as follows: 1. Indoor condensation lines do not have condensation switches to prevent water over flowing. Homeowner mentioned that her secondary line had been dripping but a couple days ago they cleared the lines from the master bedroom, which is where the drain lines are routed. I always performed a basic drain line clear up in attic, but problem could be a little more severe and would need a drain line cut and clear. 2. Furnace is sitting on wooden 2x4â€™s. 3. Outdoor unit primary motor control is starting to burn and pit up at the contact point. 4. Secondary motor control f
Performed AC maintenance on 4 year old Goodman system. Cycled system for cooling. Checked indoor unit electrical and system components. Blower wheel is clean. Secondary motor control in Range. Filter is slightly dirty, homeowner has extra filters she ordered for when it needs to be replaced. Temperature split is in range and system is producing proper temperature split. Checked outdoor unit electrical and system components. Amp draws in range for compressor and condenser fan motor. Primary motor control is in good condition, secondary motor control is within range. Pulled off condenser fan motor and thoroughly washed out condenser coil inside and out. Homeowner had mentioned that she has had some heater issues in the past as far as it making a weird nose, cycled the furnace a couple times to see if anything was out of the ordinary but everything fires up normally. Cycled system, system is operational upon departure.
Arrived on site to diagnose and maintenance a 2004 airflow system. Condenser located in back yard. Furnace located in attic. Found unit not turning on as low voltage is not coming to condenser. As low found low voltage thermostat wires all chewed up maybe from the dog and has exposed wires. Advised we should replace exposed thermostat wires to prevent shortage. Inspected and did a level 1 repair to rewire the low voltage wires back on board and got system operational. Client wanted to sign up on esa and perform first Ac visit today. Washed condenser coil inside and out. Coil is in very bad condition. A dog from previous owners was peeing on condenser and coil is now missing a big section of coil and is now deteriorating. Primary is really pitted and burnt up from self wear. Secondary is border line bad in range from fan and compressor working hard. Fan motor is pulling max amps and could fail from age and over working. Compressor is over amping on start up as its over rated max. Compr
Arrived on site to perform spring tune up on a 2017 Goodman unit. Condenser located in back yard, furnace is in garage. Client stated no issues and systems is good. Washed condenser coil inside and out. Checked electrical compartment and components. Primary and secondary motor controls are both good. Fan motor is good and Amp draws are good. Compressor start up amps are pulling 55 and Max rated at 112. Would recommend adding a Compressor booster kit to help keep high start up down and prolong life of compressor. Run amps are good. System pressure are good and cooling hole at 21 degrees. Filter was good. Blower assembly and wheel slight dust. Evaporator coil is good and drain lines are clear. All safety switches are operational. No protection on unit. Advised to to protect unit with adding surge protectors to prevent any electrical surges that can damage system or components. Went over all findings and recommendations with client. Client did declined recommended work at this time. Clien
Arrived on site to perform spring tune up on a 2013 lennox system. Condenser in pack yard furnace and Evaporator coil located in garage. Client stated no issues as they donâ€™t use system a lot and has yet to use it. Washed condenser inside and out. Unit was in very bad condition from previous owners dogs peeing on unit is missing coil areas and deteriorating over time. Checked electrical compartment and components. Primary pitting were burnt. Secondary was good for compressor. Fan was good and secondary motor controls for fan was weak as it just went out of range. Start up aamps are good. Run amps is pulling 13. Fan is go and in range of amps. Refrigerant were okay and cooling home over conditions of condenser is bad. System is cooling home at 20 degrees. R-22 unit. No protection on unit. Inspected indoor unit. Filter was good. Blower assembly was dirty previous tech advised client of it. Evaporator coil dirty from dirty that has entered system. Drain lines have debris but clear at t
Arrived on site to perform furnace maintenance on 20+ year old furnace maintenance. Unknown age. Prior to starting Homeowner stated that they have not used the furnace in a very long time and have no need for it. Does not remember when the last time they turned it on was. I cycled system for heat. Upon inspecting heating sequence, the gas valve never engaged and furnace did not kick on all the way. System kept going through cycle but never kicked on. Checked all wiring and made sure everything was connected correctly, still did not kick on. Checked for voltage at the gas valve and it is recieving proper voltage but not engaging. Tried hitting gas valve to see maybe if it was stuck due to it not being used in so long, but had no luck. Informed homeowner of findings and informed could not fully complete a maintenance on the system without it being operational. Discussed the price of the repair, but homeowner ultimately just wants to leave it for now as he does not use it and does not wan
Performed furnace maintenance on 2014 carrier heater. 1. Found that flame sensor was corroded and oxidized. Clean sensor 2. Gas line did not have dripleg.
Performed Furnace diagnostic on one-year-old Goodman heater. Upon my diagnostic found no evidence of any type of metal or plastic within indoor blower wheel. I then started the system in heating mode and found that the inducer motor had some type of dust or sand like material within the inducer once it begin spinning creating a rattling noise. This only lasted a few seconds would completely go away. Confirmed systems for heating sequence in operation was correct and upon departure rattling noise has depleted And is heating.
Upon arrival performed diagnostic on furnace. Found pressure switch to be defective. Also blower motor does not kick on when calling for heat, have proper voltage coming from circuit board just no response from motor. System is non operational.
Upon arrival performed maintenance on Lennox system. Replaced filter 18x24. Recommmend to be consistent with replacing filters. Filters should be replaced every 2 months. Indoor motor is in good condtion. Blower wheel beginning to build dust levels. Circuit board and electrical connections in good condition. Inducer draft motor good. Pressure switch in working order. Dusted off all electrical components and furnace burners. Cycled heating multiple times, heating order of operations in perfect condition. Temp rise splits good. Gas valve in working order. Voltages throughout system good. System was reset tested and fully functional upon departure.
AC/HEAT MAINTENANCE. Found system operational upon arrival. Replaced standard 20251 filter. The filter that was in there before the maintenance was past due and restrictive. Blower clean. Evaporator clean. Burners and burner cabinet clean. Gas pressure ok. Inducer ok. Limits and switches operational at this time. Board ok. Flame sensor ok. Igniter ok. Temp rise ok. Static ok. Washed condenser coil. Freon pressures ok. Temp split ok. Motor and compressor amps ok. Motor bearings ok. Motor control is within range at this time. High voltage line relay in good condition. Unit operational upon departure.
Jimmy installing secondsryncomtrol
Upon arrival found system low on refrigerant. Advised customer we can charge system up with refrigerant, declined gonna think about replacing system will give us a call back.
Customer canceled due to thinking we were his home warranty company. Meant to cancel us but canceled his home warranties.
NO COOL. Found system non operational. Customer stated unit doesnâ€™t run after changing the batteries. Checked thermostat and saw battery compartment is separate and very accessible without removing thermostat. Checked for power and found no low voltage coming out of low voltage controller. Would have to check if manufacture still has this part due to the age of the system. Due to age and condition of the system we highly recommend replacement options. Customer will talk it over with the dad and sister to find out if they want to move forward with replacement options. Customer will call us when he knows. Unit not operational upon departure.