They have Great planes of maintenance
GAVE LOTS OF DETAILS GREAT ATTITUDE LOVE THIS COMPANY VERRY HONEST.
I am satisfied with him, thank you
The Tec was very knowledgeable and pleasant to deal with.
YOUR COMPANY, OFFICE PERSONAL AND FIELD PERSONAL ARE WESOME I THANK YOU ALL FOR YOUR COURTESY AND KINDNESS. JG.
Always professional and helpful
Luke was great. He wasn’t given the correct size filter for my hallway.
Financed thru service finance
Arrived on site to perform diagnostic on 1994 York system. Homeowner states that system is not cooling as is used to before and struggles keeping temperature. Has had a couple service Calls in the past where they had to recharge the refrigerant and also relocate the condenser. Cycled system for Cooling. System came on normally. Checked outdoor unit electrical and system components. After troubleshooting, found system to be low on refrigerant. System uses r-22 refrigerant which has been phased out as of last year. It is still available but price has changed pretty significantly from the last time that they had to recharge it. System also has a obvious leak due to it having to be recharged in the past and now low again. Went over findings and recommendations with homeowner. Homeowner ultimately wants to replace system. She has a company coming out tomorrow from 1-3 to give quotes on replacement. She would like us to come out on Friday from 3-5. System is not operational upon departure.
Found refrigerant leak In a capillary tube connected to the outdoor heat pump coil. Confirmed leak with soap bubbles.
Performed diagnostic on system. Homeowner states that water is leaking through his ceiling. We performed a cut and clear about a month ago and he believes it needs it again. Went into attic to inspect drainage system. Primary line appears to not be getting any water. Opened up evap coil and found a completely clogged and restricted evaporator coil. Evaporator coil is causing such a big restriction that it is causing the water to shoot over the pan. Ductwork coming off plenum was completely soaked and full of water. Drain pan is extremely filthy as well. Went over findings and recommendations with homeowner. Went over different options. Homeowner wants to replace evap coil, but would also like to get some pricing on replacing the furnace as well for better pricing on the two. Turned call over to Darren for replacement options. System is not operational upon departure and highly advise homeowners not to run it due to potential ceiling Damage hazard.
Arrived on site to perform diagnostic on 14 year old unit. Homeowner states that upstairs system is not cooling. Has not worked for about a month. Cycled system for cooling. Thermostat is extremely finiky and they have to play with it for a while before they can get it to go into the cooling mode. System finally kicked on and indoor unit is blowing air, outdoor unit is not responsive. Checked outdoor unit electrical and system components. Found a bad secondary motor control for both compressor and condenser fan motor that was not allowing the system to turn on. Put in new secondary motor control and cycled system on. Refrigerant pressures are in range and system is producing proper temperature split. Amp draws for compressor and condenser fan motor are within range. Compressor start up amps are high. Unit is operating on r-22 refrigerant. Went over findings and recommendations with homeowner. Went over maintenance program. With approval replaced secondary motor control as well as repla
System was making loud noise due to vibration at the condenser. Installed rubber isolation strips on the metal plate behind the service ports, adjusted the position of the condenser slightly and replaced the plastic locking caps with metal caps to reduce vibration sound.
Arrived on site to diagnose a no cooling 2004 unit. Unit is original to home. Client stated they just moved in and had issues so home warranty referred us to him and he called us out. Upon arrival spoke over with client. He stated he recently noticed home getting warm. But system washer at 66 degrees and only hot air was coming out. He went outside and saw condenser was not spinning and shut it all off. Advised I would evaluate full system. Cycled system and unit did not turn on and made loud buzzing noise. Inspected electrical compartment and found secondary control completely bad and not turning on unit. Replaced to test and evaluate system. Found primary starter original and worn out on pittings. Fan motor is over amping pulling 1.5 amps as itâ€™s max rated at 1.4. Motor could fail In future due to age and condition. checked start up on Compressor and found it way above range as compressor is having a really hard time turning unit on. Run amps is pulling 24-25 amps advised max rate
Inspected the system and the unit is working on arrival, filter is very very dirty. Looking up at the system the coils are pretty dirty and the system probably just needs to be maintained itâ€™s been a year since the unit was installed. The unit is due for its first since install maintenance but the extension ladder needs to be very large as the one I have supplied is too short. Need to return with a taller ladder to perform maintenance.
Replaced failed icomfort thermostat with S30 display and smart hub.
Arrived on site to perform spring tune up on a 2010 trane unit. Condenser located in back yard furnace located in hall closet. Client stated he been on vacation for couple months and just got back. Doesn't use system a lot but just wanted serviced. Washed condenser coil inside and out. Unit was dirty. Primary control was worn out pitted on contact points. Secondary control was completely dead. Unit was only starting due to Compressor booster kit. Would need to be replaced to operate efficiently. Fan motor was operating in range. Found single run secondary control was below range for fan. Compressor start up amps are good and run amps are in range. Checked pressure and are good and cooling home at 23 degrees. Inspected indoor unit found secondary Control really low for blower motor. Recommend replacing before completely fails. Blower is good and filter was dirty and replaced. No protection on indoor unit either. Cycled unit to ensure system operating. Wen rover al findings and repairs
Performed diagnostic on 18 year old York unit. System is not cooling. Homeowner mentioned that we came out here last year and replaced some parts, and unit was working for a bit and then failed a month or so after but never called us back in. Advised that because he didnâ€™t call us out at that time unfortunately there is no longer any warranty on any work performed at the time, given if it is the same issue. Cycled thermostat for cooling, unit is completely unresponsive. Checked for power at indoor unit. Found a bad transformer not giving the unit any low voltage power. Also found a low secondary motor control for indoor motor. Evap coil and blower wheel are extremely dirty. Homeowner is selling the home, so he is only wanting to do what ever is absolutely necessary and is also not interested in replacing the unit. Replaced transformer and secondary motor control. System kicked on. Checked refrigerant pressures and found unit low on refrigerant. System uses r-22 refrigerant, and syste
Summer AC Maintenance Performed. Upon arrival system is working and operational. I began out the outdoor condenser by braking down the unit and cleaning with water and coil solution removing dirt and debris. Inspected all electrical components for wear, tested amp draws on system. Checked and measured refrigerant system pressures and charge. Recommended to member to add surge protection on outdoor unit to protect system, disconnect is fuseless. Proceeded to indoor furnace unit. Inspected electrical components to ensure tightness, inspected board for burns and marring. Inspected blower housing for dust and debris. Checked blow motor control. Inspected ducts for air leakage. Inspected main condensate. Recommend blower wheel cleaning, caked dust on wheel. Recommend cut and clean as main condensate was clear. Performed cut and clear for main condensate. Installed thermostat. Upon departure system is working and operational.
Upon arrival perorm diagnostic. Found issue to be a weak secondary motor. Filter has been replaced. Motor is leaking oil and over amping. High amp draws on start up. Client chose basic repair and membership. System is operational upon departure.
Technician arrived on site and found no power to the unit. Found the breaker had been tripped. Checked the motors to see if anything was grounded. Everything checked out. Coils were restricted from dirt. Lack of maintenance is not covered under warranty. Cleaned coils and inside of the condenser with chemicals and water. Unit is operational upon departure.