Thorough, attention to detail, listens, explains for the homeowner to understand. Installed our HVAC and still servicing it over 10 years. Responsive. Easy to work with. Sets reasonable expectations and meets them. Keeps you in the loop to know when arrive and what is happening.
Michael Pierson was great in all areas, i.e., service, professionalism, knowledge, etc.. Can't say enough of good workmanship. Thank you.
My Tech. Luis M. Was amazing. He went above and beyond to answer and questions I had. He took his time to make sure that I understood everything. He was courteous of my house and animals. I really appreciate the professionals at Cool Air Solutions. I have never had a bad experience.
Job well done though a tad late from arrival. But understandable.
As always, great professional, friendly service.
Luis does an excellent job representing Cool Air Solutions
Daniel was friendly and professional and arrived on time as advised. Daniel took the time to go over the service performed and the recommended services.
Replaced thermostat and smart hub under warranty. Tested system on both modes.
Upon arrival performed diagnostic. Client had replaced his capacitor and got system up and running. Wanted us to give it a check. Checked ampergess in compressor, it is running very close to max amperages. This can cause capacitors to give out due to high demand. Filters are dirty and need replacements. Coil is dirty. Indoor blower wheel is rusted up. Dusted off all electrical components. Transformer does have a lot of rust build up. System is operational upon departure. Client gets maintenance every 3 months.
Upon arrival found hose to inducer motor had rubbed. Replaced hose. Tested operation. Unit is good.
Serviced both heating systems. Measured temperatures. Recorded electrical values. Tested safeties and controls. Cleaned furnace cabinet. Repaired small gas leak on flex connection. Inspected ducting and airflow.
Programmed the thermostat for single stage heat / cool. The system had no common wire at the furnace board either, this was added. System was tested on both modes and is working properly. Also routed the high voltage whip behind the cabinet In the garage.
Performed 20 point inspection and service for two Lennox heating systems.
Heating Maintenance Performed Upon arrival system is working and operational. I began my maintenance in the attic by performing a duct leakage inspection. I then proceeded to the furnace unit, I checked and tightened electrical connections. I inspected the heating components for proper operation and wear. Burners were inspected for proper operation. Flame sensor was cleaned. Condensates lines were inspected for proper drainage. Static pressures and temperature splits were taken. Filter has been changed at this time, home owner supplied. Blower housing and wheel was inspected for balance and dust build up. Air supply was measured. Inspected safety switches as well as inspected home for fire and carbon monoxide detectors. Upon departure system is working and operational.
Installed phenomenal aire and set fan circulate mode up to run 15 mins out the hour. Registered the product. Unit is operational upon departure.
Performed heating and cooling maintenance on a follow up from install. Heating sensors and switches were cleaned and tested. Heating temperature split is in range. Gas valve was tested. Heating components were tested and recorded. Outdoor unit was dirty but cleaned today. Primary condenser components were cleaned tested and recorded. Refrigerant levels are good. Outdoor and indoor units are not protected. System is operational. Homeowner signed up for scheduled maintenance.
Upon arrival performed plenum air scrubber and meet rack installation. Waiting for uV light to come in then coming to install .
Performed hearing maintenance on a 2015 Lennox gas furnace. Systems heating temperature split is in range. Gas valve was tested. Sensors were cleaned and tested. Filters are ok today. Primary blower and combustion blower are reading in range. System is equipped with an Air Scrubber home purifier which is ok today. Duct runs are sealed. Condensate lines are clear but have no safety switch. This was installed today to ensure ceiling protection in the event of a clog. Furnace is protected. System is operational at end of appointment.
Tech arrived on site. Found the unit not heating. Jumped unit out on control module and only the inducer motor came on. Inducer motor sounded rough but amps indicated it was still okay. Pressure switches would close but hot surface wouldnâ€™t come on. After adjusting wires the hot surface would come on. No gas and no ignition. After checking for voltage on gas valve it energized and we had ignition. Determined it was a faulty control module. Temporarily the unit is operational. It still can shut down. Ordered new module from supply house. Office will call and schedule return visit.
Tech arrived on site. Performed fall tune up. Cleaned furnace burners and started unit. Measured temp rise and motor amps. Unit is operating properly. Ducts are older but still in tact. Client went forward with air cleaner. Unit is operational upon departure.
Upon arrival performed diagnostic. System has very poor filtration. Filter that is currently in system is doing 20/30%. System doesnâ€™t have the greatest filtration, having cats, cat litter and all the dust accumulates and goes through filters back into our air streams. Coming out to install ultra defense package on 2 systems. Friday.
Return grille downstairs had a humming sound with the removal of the old filter. The return grille fins were individually adjusted to alleviate the sound.