Knowledgeable, friendly, polite
Great service, very professional
Courteous, knowledgeable and thorough
Professional, friendly, very skilled.
Evan is very friendly and knowledgeable. He answered all my questions with professionalism and was very courteous. He’s an asset to the company.
Super nice guy, professional and effective.
Tony was thorough, looked at everything, and communicated his findings.
Excellent experience all around.
Arrived on site to diagnose a noise complaint on a 1 year old lennox unit. Client stated unit si brand new and didnâ€™t make this noise in past or when installed and just the past couple days started. They just wanted to ensure nothing is going on with unit. Cycled on and heater turned on and once blower motor started is sounded like a whistle noise advised looked into return vent and didn't see anything. Inspected attic and return plenum And filter rack. Found the tape on the outside sealing up connections from plenum and rack the stale had came lose and cause the noise as itâ€™s sucked air. Pressed back ona no noise stopped. Sealed up return and filter rack with more tape to seal up the lose tape and noise had completely stopped. Showed client the noise and what caused it. Unit is operational and heating home and noise is gone. Cycled unit and unit is operational upon departure.
Performed furnace maintenance on 4 year old Lennox unit. Cleaned return grate. Inspected filter and found it to be in good condition. Flushed condensate drain with water. Temperature rise is within limits. Inspected flame sensor. Tested resistance of hot surface igniter. Measured external static pressure and found it to be high. Inspected ductwork and found it to be an inefficient design that utilizes a remote plenum which is increasing the static pressure. Inspected blower compartment and found the blower wheel to be clean and balanced. Electrical amperage draws are all within limits. Upon departure system is operational.
Arrived on site to perform heat tune up on 2016 Goodman unit. Client stated no issues and he be using it. Cycled heater and is operational. Found filter clogged and they replaced filter and advised filter needs to be replaced more often cause this is causing a restriction and unit will over heat due to that. Blower assembly and whee are dirty from dirt going into unit. Found repairs made last time good. Motor is in range. Inducer motor is in range. All safety switches are operational. Temperature rise is in range and good drain lines are good. Over flow switch was added last time. Phenomenal air is good and operating. Found no protection on unit and recommended added to protection to protect from electrical surges and power outages. Cycled unit and went over all findings. Client is aware of how unit is running and conditions. Client did hold off on recommendations but did renew maintenance plan. Cycled unit and u it is operational.
Performed heating maintenance on 5 year old Lennox air handler and heat pump. Cleaned return grates. Inspected and replaced filter with owner-supplied MERV 11 filter. Checked electrical draw of system and found it to be within limits. Inspected blower compartment and found blower wheel to be clean and balanced. Checked all electrical connections. Flushed condensate drain with water. Temperature rise is normal. Cleaned heat pump coil fins and exterior unit. Upon departure system is operational.
Returned to install Phenomenal Aire cold plasma generator. Installed Phenomenal Aire in evaporator coil and ensure coil was properly sealed. Installed 24v transformer in blower compartment. Thermostat fan setting set to circulate mode. Installed MERV 16 20X26X5 filter. Upon departure system is operational.
Performed a heating maintenance on a 2020 Lennox system. Cleaned and Adjust Burners. Check Combustion Air for Proper Venting. Examine the Heat Exchanger for Damage / Corrosion. Test Furnace Safety Controls. Inspect Gas Piping. Tighten Electrical Connections. Measure the Voltage and Amperage. Flush the Condensate Drains. Measure Tempurature Difference between Supply and Return Air. Vacuum Furnace Return Grille. Adjust Gas Pressure & Pilot. Clean in-place Blower Compartment. Inspect Blower Wheel for Proper Balance. Check the System's Static Pressures to Ensure Proper Airflow. Inspect Duct Connections for Air Leaks / Sizing / Insulation. Check all System Safety and Limit Switches. Clean Flame Sensor. Inspect Carbon Monoxide Detector. Check Thermostat for Proper Operation / Calibration. Filters where not changed this visit. System was fully operational on time of departure.
During my twenty point heating inspection, I started with the thermostat. Giving a call for heating, and going to furnace to start maintenance. Temp rise of 40-70 needed, I got a temp rise of 42. House heats up to designated temperature. I checked out blower motor of any dirt or debris and itâ€™s clean. Replaced air filter for new air filter. Owner had extra one, so just used his. Hot surface igniter not cracked or having white spots. Flame sensor still working good, no need to be cleaned. Ducting done correctly, and all runs intact. Inducer motor is working at high amps. Moved onto the upstairs unit, I shut off downstairs after I was done with my inspection. Put system in a call for heating mode. Soon as the house warmed up after thirty minutes. I got a temp rise of 46 which is perfect in my temperature rise range. House heats up to designated temperature. I checked out blower motor and motor is failing. Wasnâ€™t able to service motor today due to labor to get it out. Existing air f
Arrived on site to perform maintenance on Lennox system. Cycled system for heating. Initially, heater did not start up due to a clog in hose from inducer to pressure switch. Cleaned out and cycled for heat. Unit kicked on normally and started heating. Verified proper heating sequence of operations. Temperature rise across heat exchanger within range. Ran system through inspection checklist. System is operational upon departure.
Preformed furnace maintenance on 2014 aireflo
Performed furnace maintenance on 2 year old Lennox unit. Cleaned return grate. Flushed condensate drain with water. Inspected filtration kit and PCO is due for a maintenance kit. This was brought up with Jamie and he may want to proceed with a Phenomenal Aire rather than maintain the PCO. Inspected blower compartment, blower wheel is clean and balanced. Inspected all electrical connections. Tested resistance of hot surface igniter. Inspected flame sensor. Temperature rise is within limits. Tested all safety switches. Upon departure system is operational.
During my twenty point heating inspection, I started with the thermostat. Giving a call for heating, and going to furnace to start maintenance. Temp rise of 40-70 needed, I got a temp rise of 44. House heats up to designated temperature. I checked out blower motor of any dirt or debris and its clean. Blower motor wheel I has debris on fins. Hot surface igniter not cracked or having white spots. Flame sensor still working good, no need to be cleaned. Ducting done correctly, and all runs intact. Inducer motor is working efficiently. House heats good and ready for winter.
Arrived at customers house to preform a heating tuneup. We first cycled system on and everything turned on and was operational. Next we checked the total bower amps and inducer amp draw, both were within limits and testing good. Next we checked static pressure and took a temp rise, both static pressure and temp rise were both good and within their desired range. Next we checked all safety and high limit switches, the switches were testing good and were function and operational when tested. Drain lines are clear. Cleaned flame sensor and igniter is good. We changed filter 20x25x5 as the filter was lookin dirty and needed to be replaced. Over all the while we were there the system was testing good and was operational. Surge protection is good and active. Phenomenal air is good and cleaning. Cycled system to ensure system operating. System is operational upon departure.
Arrived on site to perform maintenance on 2 ComfortMaker units. Cycled systems for heating. Replaced both filters. Verified proper heating sequence of operations. Ran systems through 20 points inspections. Mirror inspected heat exchanger. Went over findings and recommendations with homeowner. Want to hold off on any recommendations today as we just performed a major repair not too long ago. Systems are operational upon departure.
Returned to install new iComfort S30 thermostat under warranty and perform heating maintenance on 7 year old Lennox air handler and heat pump. Installed new iComfort S30 thermostat. Indoor Unit: Cleaned return grate. Flushed condensate drain with water. Measured total amp draw and found it to be within limits. Inspected blower compartment and found blower wheel to be clean and balanced. Inspected electrical connections. Tested in both cooling and heating, temperature rise is normal. Outdoor Unit: Removed heat pump covers and cleaned coil fins as well as around exterior unit. Replaced covers. Upon departure the system is operational but turned off at the thermostat because there is not filter installed.
Arrived on site to pet tune up 2 5 year old lennox units. Client stated he was as having issues upstairs and wanted to diagnose upstairs as well. Cycled both heaters on and both turned on. Inspected upstairs unit after a couple minutes unit shut off due to no flame sensed. Unit tripped safety switch. Pulled and found flame sensor really oxidized and corroded from burning up in the past years. Cleaned sensor and unit was operational and. Did trip at this time. advised client flame sensor is running at this time but recommend replacing. Performed tune up. Filter are dirty and client has a purification kit on both units. He has yet to replace maintenance kit on both and has just been doing filter. Recommend replacing maintenance as they are not operating as they should. U.V light is very dim. Both blower assembly and wheels are good. Inducer motor are both good and in range. Both igniters are in range. Both flame sensors are oxidized and not good. Recommend replacing. Drain lines good at