My service technician, Daniel did a great job performing my A/C maintenance today. He really explained everything that he did. Outstanding job! Thank you!!
I love cooler solutions. And I am a super fan of Jorge. I’ve had the best experience from getting a new system installed from the sales person that came out and now to the person who is helping maintain the quality of the work. I 1000% recommend cooler solutions and I have.
Great Customer Service, Very knowledgeable, and Very caring, explained everything in detail all that we needed to know, upgraded our fan motor which was a little pricey but quality was much better then the one i had in there, but it also included the maintenance program, so all in all it was a good deal.
Asked Madison if everything put back together, he said yes. I checked evaporater and lid was not screwed on and one side was bent up and not fixed. I found the tray under the evaporator very clean with no oil.? The picture he showed me was not my evaporator. So what a waste of money and trying to get to the bottom of my problem. Madison was polite but I’m not convinced he got to the bottom of my problem
They were very knowledgeable, analyzed the issues, and came up with a resolution in a timely manner at a reasonable cost. You can’t ask for more.
Performed a leak dye search on 2013 Aireflo condenser. Upon my search client stated that system has been cooling fine and hasnâ€™t noticed any change yet. Started search at outdoor unit and found that the condenser coil had significant coil rot on the aluminum part of it. This was caused by the dogs urinating on it overtime Alice potentially make this a red flags on for a leak. On the outdoor unit found no leaks present and verified the refrigerant pressures were holding up as of this second. Proceeded to evaporator coil an attic to find that it had multiple leaks. Found that the 5 year warranty is no longer available for the evap coil. Coil will need to be replace to prevent any further leakage and refrigerant loss. Also performed AC maintenance as of now this is one of two visits. Supervisor will be contacting Xavier regarding his options. Upon departure leak was found and maintenance was done
Performed AC maintenance on a American standard system. Units cooling temperature split is over 20 degrees. Condensate line is clear and equipped with a safety switch. Primary blower is amping in range. Blower fins are dirty. Primary start component for the blower is out of range. Filter was washed today. Outdoor unit was chemically cleaned. UV protection was applied today. Compressor start amps are high for this unit. Fan is amping in range and free of any oil leakage. System was running at the end of the appointment
Performed AC diagnostic on year 2000 and Lennox condenser. Upon my diagnostic homeowner son was only one present and he stated that the system just stopped working a couple days ago and is no longer cooling. Upon my diagnostic I found a major terminal fault in their system. 1. Found a Condenser high-voltage wires connected to starter were completely burnt up and Crisp due to the high amperage pull of the heart of the system. 2. The compressor is only design for 26 A and is using a total of 27 to 30 A run time and even exceeding this due to the amount of wires that are burnt up. Homeowner even stated that the breaker that tripped previously prior to calling me due to the compressor using too much power 3. Starter had significant burning on contact points and on compressor wire lugs 4. R22 refrigerant levels were low as well due to a leak somewhere within the refrigeration cycle Discussed the full condition of the system with homeowner over the phone. Homeowner was suspicious of me tryi
Performed AC maintenance on a Bryant system. Systems cooling split is 23 degrees. Duct runs are sealed. Indoor blower is clean. Indoor motor is not leaking oil at this time. Primary start component is failed and out of range. Condensate lines are clear but has no safety switch. Outdoor unit was cleaned. Compressor bay and service panel were cleaned. Electrical components are in range. Compressor and fan amps are ok. Refrigerant levels are ok. System was cycled before leaving.
Performed Ac maintenance on (2) 1 year old Lennox systems. Replaced Merv 11 filters provided by homeowner. Temperature splits are in range for both systems, refrigerant pressures are good. Checked outdoor unit electrical and system components. Primary motor controls are in good condition. Secondary motor control for right side unit had a bad fan reading, replaced under warranty. Pulled condenser fan motors off and thoroughly washed out condenser coils inside and out. Went over findings and recommendations. Homeowner liked the idea of adding whole home air purification to systems. Needs to talk it over before making a decision. Cycled systems, systems are operational upon departure.
Arrived on site to perform spring tune on a 2013 Goodman unit. Condenser located in back. Furnace and Evaporator coil located in outdoor closet. Cycled unit. Washed condenser coil inside and out. Checked electrical compartment. Primary starter was a bit worn out due to age and normal operation. Secondary motor control was good in range. Fan motor was good and amp were in range. Checked pressure and are good and cooling hole at 22 degrees. Inspected indoor unit. Furnace really dusty due to being in a Outdoor closet and where home is surrounded by. Found 2 flyer used and advised that is not good and should only have one filter to prevent airflow restriction. Left one filter in furnace and was replaced. Blower assembly is dirty. Motor is good and secondary control as well. Drain line has no safety overflow switches. System is cooling at 22 degrees. Cycled system to ensure system operating. Went over all findings with client. Client is aware of how system is running and itâ€™s condition. C
Arrived on site to replace oem blower motor and secondary motor control. Replaced and cycled units. Both indoor and out door units are operational and cooling. System is operational and cooling upon departure. Parts will only have warranty for 90 days. Recommend adding surge protectors on units to protect from electrical surge protectors and power outages.
Arrived on site to diagnose a no cooling unit. Found unit to be From 2013. Furnace is original to home. Upon arrival client cycled system and was operational. Found that condenser was replaced but evaporator coil was not by a family friend. Client stated unit will run and then stop cooling. Inspected out door unit found secondary dead and why spun it was not cooling. Primary starter was burnt up. Start up amp weâ€™re at max. Recommend replacing starter and adding a compressor booster kit to help lower startups. Fan motor is over amping and could fail at any time. Recommend replacing as bad motor can cause secondary motor to fail again. Pressure were in range and cooling home at 20 degrees.inspected indoor unit and is original to home. Found evaporator coil was never replaced and could be really dirty due to no filter rack to hold filter down. Drain lines are dirty and only one is in use. Found also drywall base of furnace furnace had big black spot of what look to be biological
Quality control check
Arrived on site to diagnose a no cooling unit from 2007 trane unit. Client stated she just had it serviced and and unit is not working. Cycled unit. Indoor unit was no producing airflow and out door unit didnâ€™t sound like compressor was running. Inspected indoor unit. Jumped from board and thermostat. Found power coming in and going out with 24v and 120v. Found motor was not turning on and 120 voltage was getting to motor overall found a bad motor. Advised since unit is not working unable to inspect out door unit with out it working inside. Would have to replace motor to ensure no other issues are present. Due to weekend unable to get price of motor so would have to cal back Monday and get price first. Client is aware office is gunna reach out and give her the price. System is in operational upon departure due to bad aria bow speed blower motor. Hollie would cover cost of todayâ€™s visit. System is not operational upon departure.
Performed AC maintenance on a Trane condenser. Systems temperature cooling split is 26 degrees. Condensate lines do not have a safety switch but is clear at this time. Indoor blower is amping in range. System is equipped with a AIr scrubber device which is in need of a new catalyst. Filter is dirty but replaced today. Outdoor unit was chemically cleaned and a UV resistant wax was applied. Battery cap is out of range. Starter is ok. Compressor and fan amps are in range at this time. Refrigerant levels are ok. System was
Need to return and install two sediment traps on Both heaters
Performed AC maintenance on an Arcoaire Condenser. Systems cooling temperature split is 21 degrees. Upon arrival the condensate was clogged right at the P trap and was able to be easily cleared. Filter was changed. Outdoor coils were chemically cleaned. Fan motor is heavily leaking oil, it is also over amping. The starter has burn marks on the high voltage side and is heavily pitted. The battery cap is out of range on the compressor terminals which is decreasing the life of the compressor. Refrigerant levels look ok. System was cycled before leaving.
Performed AC diagnostic on 2014 Aireflo Condenser. Upon my diagnostic client stated that system has been charged approximately three times in the past by a home warranty company. I began my diagnostic at the outdoor condensing unit and found that the system is operational although extremely low on refrigerant charge due to a leak within the refrigeration cycle. 4 ton condenser- 1. System was low approximately 5 pounds of R410a refrigerant 2. Leaked Dye/sealant was injected into the system To help locate and pinpoint location of leak and potentially seal with this kit. 3. Need to return in approximately one month to do leak dye search Charged system up and got a 10Â° sub cool with a 18Â° split inside. Client is aware of how system is running at the moment and will be waiting for us to return for a leak dye search. Once the leak is found repair options will be represented and client will decide whether or not he would like to replace or repair at this time of the appointment. Upon depa
Need to return and install sediment traps