Mike was polite and a pleasant person. Even when he had to climb into the attic at 100° outside. He still had a good attitude. He was also knowledgeable about the system.
Jamie Garcia came today to do our regular maintenance check. He was very thorough and knowledgeable and answered all my questions. He took video of things in the attic that needed to be fixed. I liked how he wasn’t pushy about it and gave me several recommendations.
Prompt knowledgeable polite / professional
Upon arrival performed diagnostic. Found indoor motor to be completely covered and no breathing room. Evap coil is completely dirty with NO air flow. Customer denied to do work. Said she doesnâ€™t wanna do anything she is selling him. Customer replaced thermostat and thinks itâ€™s thermostat issue. Claimed she added 3 lbs of refrigerant. System is very old. Coil very dirty.
Arrived on site to diagnose a no cooling 2009 system. Condenser located in back yard. Furnace and evaporator coil located in attic. Client stated system was fine but a month ago system stopped cooling. Had another company come out and they replaced a secondary motor control and left but client was still facing issues as system was icing up and still kept doing soo after other company. Advised client I would evaluate full system both indoor and out door. The summary of finding are as followed. Condenser 1. 2009 system 2. System and condenser coil really dirty as people from client had never really maintained system. 3. Primary had some dark tone discoloration. 4. Secondary motor control is good as it was recently replaced. 5. Fan motor has been leaking lots of oil as motor has good layer of oil from. Wing over worked. Fan run amp drawls is pulling above max range and cause of it leaking oil. 6. Compressor start amp drawls are high from Self wear. Run amp drawls are pulling 10 amp sys
Upon arrival performed maintenance. Indoor motors looked very good. Dirty blower wheel. Outdoor coils were completely covered in debree. Secondary motor control low on range. Primary power distributor, pitted and burned. Compressor start amps are high. Run amps on compressor good. Condenser fan motor good. Shaft very good. Refrigerant levels very good.
Upon arrival performed maintenance on ac system. Found motor to be stopping mid operation and starts right up. Fan relay on circuit board starting to give out. Static pressures throughout full system is .92, system max is .5. Indoor blower wheel having so,e dust build up. Refrigerant levels Iâ€™m very good condition. Temp splits good. Secondary motor control good. Washed outdoor coils. System was reset tested and fully functional upon departure.
Performed AC diagnostic on three-year-old Goodman condensing unit. Upon my diagnostic and found that the secondary motor control who is blowing on the hermetic side and that the thermal expansion valve contained a restriction. Upon departure system is cooling although not operating properly and is not recommended to run in this condition. 3.5 ton Upstairs- 1. Found that secondary motor control was blown on hermetic side terminal due to compressor pulling high amperage or working too hard. 2. Measure refrigerant pressures and found that my sub cooling was 44Â° which is extremely high and out of range which indicates that the thermal expansion valve in the evaporator coil has a restriction and is starving the evaporator coil. This can cause the compressors head pressure to skyrocket and if left in this condition can result in more damage to the system. Recommendations- 1. Replace secondary motor control with new one to get compressor operational 2. Replace thermal expansion valve and c
Arrived on site to diagnose a no cooling system 1999 carrier system. Condenser located in back yard. Furnace located in garage. Spoke to client upon arrival. He stated system was working fine 2 days ago then Suddenly stopped. He went and saw out door unit was not operating and fan not spinning as no cool air was being produced. Had client cycled cooling mode. Indoor unit turned on but condenser was not operating. Advised client I would be inspecting indoor and out door unit. Checking electrical wiring, connections, circuit board, and components. Checking fan motor and blower motors and blower assembly. Inspected amp drawls of motors and compressor. Checking Refrigerant pressure and cooling temperature split.advised the summary of findings are as followed. Condenser 1. 1999 carrier condenser. Found donâ€™t operation upon arrival. 2. Condenser unit was really dirty and clogged up creating airflow restriction to out door unit Causing it to work harder to remove heat in home. 3.Prima
Getting a system up and running out here in Wildomar.
Replace existing system with listed equipment. Add Balancing dampeners to existing trunk lines. $16,934 Due Upon Completion. After Lennox Rebate $16,199
Performed AC diagnostic on one-year-old Lenix condensing unit. Upon my diagnostic I found the thermostat downstairs was completely blank. I then proceeded to the attic to check the incoming 120 V coming from the breaker and found that there was no power supply present. Upon further investigation found that the outdoor breaker was not in tripped position although not supplying power, flipped breaker and 120 V energized furnace and system is fully operational and cooling. Upon conclusion I believe that the breaker could be potentially weak or that other things may be tied into the circuit of the furnace and electrician should evaluate the breakers.
Post job walk. Customer said that the ac unit is very loud on start up. Inspected it and found it vibrating on the lineset cover. I put some plumbers tape on it and it helped dramatically. Compressor saver kit is causing a little start up noise. Customer wants to keep it on the unit.
Provided estimate for condenser relocate. (No electrical) 410A 4yrs 5 ton. 40ft lineset. Customer cutting access hole and doing his own electrical.
Tested the system for odors
Found system operational upon arrival. Replaced m1620255 Lennox hepa filter. Blower clean. Wheel clean. Board ok. Transformer ok. Evaporator coil clean. Washed condenser coil. Checked Freon pressures. Levels ok. Amp draw on motors within range. Motor controls working well and in range. Line voltage switch working well. Customer added 1 year ESM with 2 visits. Recommended extended warranty but customer declined. Understands Lennox only covers parts warranty and not labor, Freon, diagnostics, or warranty processing. Unit operational upon departure. 1. Recommend extended warranty from Lennox for full coverage. 2. Customer does not have air cleaner or purification to protect equipment.