Air conditioning maintenance
The service was thorough and the service technician explained everything found and everything done. Highly recommend this company.
Friendly competent. Cordial. Very knowledgeable. Answered all questions:)
Tech was very thorough and informative, walked me through the tune up step by step
Knowledgeable, well experienced tech. Thank you Luke!
Luke performed the annual heating inspection in his usual efficient manner. Its a rainy day today so Luke made sure he had dry shoes before coming into the house to adjust the thermostat. That's one of the most important items that my wife looks for. The discussion between Luke and myself was informative and made sure I understood how to look after the furnace operation.
Always wonderful customer service from Brian! So knowledgeable and helpful!
Explained process & was timely with results
Luke has been here before and give us the same thorough, outstanding service. Covering his shoes when entering the house showed he cared about our house more than just the air conditioner. He's a pleasant person to work with and always was patient to provide explanation of what he was doing.
We will be installing a new heating and cooling system. We will be changing 2 systems into 1. This includes returns in 4 bedrooms and replacing and enlarging master bedroom supply ducting. We will take purifier cell from one purifier thatâ€™s bad and install it into other purifier.
Replace both existing systems with below listed equipment. Seal all ducting and straighten for efficiency. Permits and HERS testing included. $23,534.00 10% Lowes Discount $-2,353 Total After $21,181.00
Upon arrival performed maintenance. Indoor motors are close to over amping. Blower wheels are starting to collect dust levels. Duct work is in good condition. Heat exchangers areok did not find any cracks. Minor hot spots. Inducer motor is good. Flame sensors were cleaned. Plenums and ducts sealed. Insulation good! Will follow up with owner to do cleanings.
Upon arrival performed maintenance, indoor motor and wheel are good. Filter was replaced. Air scrubber good. System is clean no dust, circuit board and electrical connections good. Amperages good. System was reset tested and fully functional upon departure.
Install new Lennox up flow 80% AFUE furnace, New gas flex, new electrical pigtail, Adapt to existing flue, and provide transition between furnace and evaporator coil. Ez-filter base included. $3225.00 Paid to Lowes and $500 clean air furnace rebate paid directly to customer.
Doing a single system AC and furnace tune up out here in Wildomar.
Doing a two system maintenance out here in Wildomar.
Furnace maintenance in Wildomar, Ca
Commercial maintenance in Wildomar, Ca.
2 system Ac maintenance in Wildomar, Ca.
Ac tune up in Wildomar, Ca.
Ac maintenance in Lake Elsinore, Ca.
No cool diag