They were very knowledgeable, analyzed the issues, and came up with a resolution in a timely manner at a reasonable cost. You can’t ask for more.
Did what they said. They were on time, professional, patient, and explained what transpired answering all my curious questions.
Furnace door became lose and door switch opened. Readjusted door switch and system is fully operational and heating upon departure
Performed two system 2002 Bryant furnace maintenance. Client stated that they are very conservative do not use heat too often. When they do temperature set at about 75Â°. Began my maintenance and noticed multiple points of concerns. Furnaces 1. Found that both indoor blower motors are leaking oil and can cause the motor to over heat or lock up if left in this condition. 2. Both single secondary mother controls are out of range and week due to motor using more power than needed 3. Static pressure on system was at 0.75wc indicating to me that the airflow is not adequate enough and the proper specification should be at 0.5wc. This number is higher due to undersized returns vents. 4. Flame sensors are oxidized. This can cause failure with the sensor for it being able to detect that the burners are on. 5. Heat exchanger had extremely bad Heat spots. This is due to overheating and air flow restriction causing the temperature to operate at a much higher temperature than itâ€™s designed for.
Performed two system Goodman Heater Maintenance
Heating system maintenance. Serviced furnace, replaced filters.
Assessed home for condenser relocation estimate
Performed furnace maintenance on 2014 Lennox Heater
Arrived on site to perform fall tune up on a 2004 Bryant system. Furnace located in hall closet. Client stated no issues just wanted service. Cycled heating on and was operational. Found filter dirty and replaced filter. Blower assembly is accumulating dirt and debris and creating stress and wear on motor and work hard. Recommend a blower assembly cleaning to help reduce amp drawls and help motor run easier. Motor is good slight oil dried up from past 16 years of operation. Secondary motor control is not weak and border line bad from motor over working. Recommend replacing control before completely fails and system will then not produce airflow in heating or cooling. inducer motor is good and amp drawls are in range. Tried to pull and inspected heat exchanger and client did not want me to pull and inspected heat exchanger at this moment due to availability and would like for us to come back out some other time in the morning. Client is aware of safety inspection will not be performed a
Performed Furnace diagnostic on 2013 Goodman heater. Upon my diagnostic homeowner son had already open system up and found that igniter was broken. Upon starting diagnostic I read diagnosed system to find the problem is beginning at igniter so I added in a universal igniter and system sparked and is fully operational and heating up upon departure. Also signed up June for ESA plan To maintain heater and AC.
Tested equipment on the heating cycle. Measured temperature rise. Recorded voltages and motor amp draws. Tested blower motor battery cap. Measured ignitor in ohms. Cleaned flame sensor. Cleaned burner assembly.
Post job walk. We need to credit customer back for previous dx
Gas valve was shut off. Was most likely left off on when dampers were installed. Turned gas valve on. Cycled system for heat, system kicked on and started heating. Filters are clogged would recommend replacing filters So system does not short cycle and trip pressure switches. System is operational upon departure.
Install 4 dampers in the attic and also replace 3 registers in the master bedroom. damper sizes 10,9,8,8
Tested both heating and cooling systems. Measured indoor temperatures and system high and low supply voltages. Recorded motor amp draws. Tested outdoor starter run component. Replaced filter. Checked condenser fuses. Inspected fan motors. Verified refrigerant charge.
Arrived on site to diagnose a no cooling system. We were just put earlier in the day and did repairs and now system is not cooling. Upon arrival found condenser not operational. Furnace was operating. Inspected out door electrical compartment, wiring, and connection. Found no low voltage to out door unit and found low voltage wire happen to come lose and lose connection. Connected and secured wire and spade. Advised client of finding and she was aware. Client is now happy. Cycled system to ensure system operating. System is operational and cooling upon departure.
Upon arrival performed basic rejuvenation. Replaced all parts system is operational upon departure.