Knowledgeable polite and informative service tech! Jimmy was great!
I really like this company. They are fair priced and have gone above and beyond on their service for me. Excellent customer service, friendly, honest and knowledgeable technicians. Been with them for five years and I expect many more.
David was upfront, honest , professional! He came in and repaired what was wrong. He didn’t make any repairs up!
Very professional. Gave me confidence about doing business with your company.
Jason was very thorough & professional
Very polite young man -knowledgeable which he shared with us. Thorough check-up of system.
All good and friendly and professional.
Performed diagnostic on 2002 Lennox system. Homeowner states system is not cooling, outdoor unit is not coming on. Cycled system for cooling. Indoor unit comes on, outdoor unit is unresponsive. Checked outdoor unit electrical and system components. Found that low voltage wire was chewed up where it comes out of the house, rodents most likely chewed up the wire. Advised homeowner wiring would have to be fixed. There is enough wiring left to where we can add a piece of wiring and run to the condenser, however outer jacket on wire is gone. Went over findings and recommendations with homeowner. Best option would be to re run new wire inside of a flex pipe to keep rodents away from it. Homeowner wants to go with the immediate repair for now, her husband will most likely be running wire and pipe when he comes home from deployment. Did wiring repair on unit. System kicked on and started cooling, producing proper temperature split. Signed homeowner up on yearly ESA maintenance program, perfo
Arrived on site to perform maintenance on 1989 system. On arrival, homeowner stated that she needed a diagnostic and a maintenance. Advised that we would start with the diagnostic first to see what was going on with the unit, and then once the unit was operational we would perform the maintenance. Cycled system for cooling. Indoor and outdoor unit are coming on like normal, but system is not cooling. Performed diagnostic and thorough evaluation of system, findings are as follows 1. System is low on refrigerant. Homeowner recalled that she added refrigerant to the system about 7 years ago, but it leaked out the following year and hasnâ€™t used it since 2. System uses old style R-22 refrigerant, which has been phased out. It is still available, but it is extremely expensive 3. Indoor blower wheel and motor is very dirty, and has been leaking a lot of oil 4. Ducting system is very old netting type of duct, and it is producing very poor air quality inside the home. 5. Homeowner develop
Quality control check
Performed AC maintenance/inspection on three system Rheem condensing units. During my maintenance I came across a few points of concerns They need to be evaluated and addressed. This will help maintain system Peak efficiency and increase longevity of systems Rheem 4 ton living area- 1. Found the compressor was pulling 20 A which is incredibly high when system is rated at 21.1 A 2. High voltage Relay responsible for starting system showing 12 ohms on low-voltage coil and pitting on contact points. 3. System pressures are adequate although indicating that there may be an air restriction causing coil to freeze up or be much lower in suction line temperature this cannot drop below 32 we are at 36 right now. 4. Single run capacitors taped together in weak on compressor side terminal in micro ferrets 5. Disconnect supported by fuses although not by surge protection 6. System contains our 22 refrigerant which was phased out January 1, 2020 Rheem 2 ton casita- 1. Found the contactor had abo
Performed maintenance and service for the cooling system. Replaced filter and measured indoor temperatures. Tested outdoor electrical equipment and rewired the compressor kit properly. Verified refrigerant charge. Tested starting loads and running amps for both motors, checked battery capacitance. Cleaned outdoor coil.
Performed AC maintenance on 4 ton Maytag condenser. During inspection found it for 10 a refrigerant pressures are low. System must have a leak search with leak dye/seal along with a charge up of refrigerant. Added 4 pounds of refrigerant along with sealant to system with return visit to confirm where leak is at.
Upon arrival performed diagnostic. Power distributor is not contacting fully to let power flow form one end to the other end of starter. It is pitted and burned. Secondary control is in range. Condenser fan motor is leaking oil. Older piece of equipment. Age 1997. Very minimum will get system up and running. Due to age and inefficiency recommend exploring options for replacement. System is non operational.
Upon arrival performed diagnostic on Goodman system. System had about 49 psi with a -12 sub cooling. Added 4 lbs of r410 refrigerant W/ leak dye & seal. System is now cooling at about 51 degrees out of every vent, 20 degree temp split. Will follow up with a return call to come out and look for leak. Customer paid In full. System was reset tested and fully functional.
Cooling service and inspection
Repair damaged line voltage wire that shorted.
Sanitize and clean blower wheel
Air scrubber Installation to prevent dust buildup and disinfect all surfaces in home. Air scrubber install
System fan motor not working
Inspected the homes airflow relative to the heat pump