Great service! Quick response!! Mike was so nice and very helpful! Had the job done so quickly!! He made sure we didn’t have any questions and explained everything to us!
This was easy a thorough. A good price for the service.
Knowledgeable polite and informative service tech! Jimmy was great!
I really like this company. They are fair priced and have gone above and beyond on their service for me. Excellent customer service, friendly, honest and knowledgeable technicians. Been with them for five years and I expect many more.
David was upfront, honest , professional! He came in and repaired what was wrong. He didn’t make any repairs up!
Very professional. Gave me confidence about doing business with your company.
Performance maintenance on both comfortmaker furnaces. Tested heating cycle on both units and measured temperature rise. Measured amp draws on blower and combustion fan motors. Tested secondary run components. Measured ignitors in ohms. Cleaned flame sensors. Checked Honeywell electronic air cleaners. Cleaned burner assembly. Inspected burner inlets with mirror for cracks. -
Performance maintenance on both comfortmaker furnaces. Tested heating cycle on both units and measured temperature rise. Measured amp draws on blower and combustion fan motors. Tested secondary run components. Measured ignitors in ohms. Cleaned flame sensors. Checked Honeywell electronic air cleaners. Cleaned burner assembly. Inspected burner inlets with mirror for cracks.
Upon arrival performed maintenance. Wiped the entire inside of furnace cabinet, system was extremely dirty. Client moved forward with extensive cleanings. Blower wheel was extremely dirty and performed cleanings. Cycled heat on. Heat exchanger looks good. Inducer good. Amperages good. Filter was washed. System was reset tested and fully functional upon departure.
Performed maintenance on 15 year old package unit. Cycled system for cooling. Checked system electrical and components. Primary motor control is in good condition. Secondary motor control is in range as well but it is starting to leak some oil. Compressor amp draws are within range. Condenser fan motor amp draws are within range. Indoor blower motor was recently replaced and is in good condition. Pulled off condenser fan motor and thoroughly washed out condenser coil. Left homeowner replacement filter. Went over findings and recommendations with homeowner. Cycled system. System is operational upon departure.
12k BTU for main floor and 12k BTU for upstairs
Installation of a 5 ton Single Stage Bronze Package with ducting
Performed AC and Furnace tune up on 2 2 year old systems. Cycled systems for heating and cooling. Checked indoor and outdoor units electrical and system components. Temperature rise in heat mode is within range for both units. Heating components are all in good condition. Pressure switches and gas shut offs are working accordingly. Homeowner has his own Merv 11 filter replacements, both Filters were clean and did not need to be replaced on todayâ€™s visit. Checked outdoor units electrical and system components. Refrigerant levels are within range and systems are producing proper temperature splits. Primary motor controls are in good shape. Secondary motor controls are both in range. Amp draws for compressors and condenser fan motors are within range. Pulled off panels and thoroughly washed out condenser coils on both units. S30 thermostat is not displaying outdoor temperature. This thermostat was not installed by us. I tried resetting it and can not get the thermostat to display outdoo
RETURN FOR LEAK SEARCH. Checked for leak in evaporative coil. Checked for leak in exposed line set. Checked for leak in condenser coil. Found no leaks visible at this time. Informed customer that leak may come back or other leaks may form even though nothing was visible today. Previous customer had the same coil and there were 3 leaks in that coil. Customer understands. Customer is also on maintenance program. Unit operational upon departure.
Performed leak dye check on Maytag condensing unit. Upon my search I found no signs of leak de penetration anywhere within the outdoor condensing unit and evaporator coil. Leak that contains a sealant that may have plugged up leak location. System is holding pressure and is fully charged correctly. Applied and I log to service valve caps and King valve. System is fully operational and cooling upon departure
Upon arrival found motor not to be running when calling for cooling. Found motor wire to not be complete in tact. System was reset wired in correctly. System is operational.
Installation of a 2 ton silver
Inspected system for faults and replaced faulty component. Tested system for functionality. Measured indoor temp splits and checked filter.
Installation of 4 surge protectors. Installed surge protectors on both heat pump units outside. As well installed surge protectors on both Air handlers in attic. Ensures LED lights are on and have protection. Cycled both systems in cooling. Both systems are operational and cooling after install. Both systems are operational upon departure.
Performed AC diagnostic on 2 1990s York condensing. Upon my diagnostic I found that the left side condenser of home was not working and right side was. Upon Further investigation many points and concerns were addressed. 4 ton left side of home- 1. Secondary motor control was blown on hermetic And fan side terminals 2. High voltage really burnt on contact points 3. Compressor pulling incredibly high amps 4. Condenser fan motor completely rusted and over amping 5. Compressor saver kit added to reduce start up amps of compressor 6. System contained R22 which is a completely phased out refrigerant as of January 1, 2020 4 ton right side- 1. Compressor pulling high amps on runtime. 2. Secondary float switch is being tripped due to primary clog 3. Compressor failing on start up amps adding compressor saver kit 4. System contains R22 refrigerant as well 5. Fan motor also not in good condition due to rust
Arrived on site to diagnose a no cooling 2002 rheem system. Condenser located in back yard. Furnace and evaporator coil located in attic. Spoke to client upon arrival she stated sheâ€™s tried to have home warranty come out but has had a hard time getting them out here. System has been down supine August 18. So had us come out. Upon arrival had client tune systems on. Indoor unit was operating. Found out door unit on to operational. Inspected both systems. Checked electrical compartment and components. Checked amp drawls and recorded reading for compressor, fan motor and Blower motor. Advised the summary of finds are as followed. Condenser 1. 2002 rheem system. 2. Found disconnect was set to off. Replace and system turned on but compressor shut off right away. 3. Primary control is completely burnt and pitted on contact points and is bad. 4. Secondary motor control is not weak and below range from compressor and fan motor working hard to turn on in past years. 5. Compressor will no