Jimmy was very educational and transparent in his diagnosis of our HVAC system. He answered all of our questions and took the time to explain the more technical concepts. Excellent experience!
Jorge Cervanes was my serviceperson today. He let me know he was coming with just the right advance notice and followed directions to easily find my house. He was careful not to let my animals in or out, and also careful with my floors. He explained things clearly and let me know my options. He then fixed my ailing air conditioner in short order. He represents Cool Air Solutions very very well.
Professional installation, both installers arrived in a timely manner and completed their work in a satisfactory manner. They were courteous, professional and did the job properly. They explained each step of the process, and any issues that they may have encountered during the installation. They showed me how to use the system and cleaned up after themselves. I have no issues with the service provided by these installers.
The service I received was outstanding. I was contacted, he arrived on time, was courteous and professional the entire time. He found and repaired the problem within a very short period. He broke down the invoice and showed me service plan options to maintain our system. I would definitely use your service again.
Performed Heating maintenance on a pair of Lennox furnaces. The living area furnace has a white icomfort thermostat, system turned on ok. Heating temperature split is within spec. Duct runs are sealed. Condensate lines are clear. Filter is clean. Gas valve was tested. Sensors and switches were cleaned and tested for correct operation. Blowe wheel and motor are in clean condition. Bedroom area furnace has a s30 icomfort. Customer reports the thermostat is not showing outdoor temperature. This was fixed before I left today. Heating temperature temperature split is within range. Sensors and switches were cleaned. Gas valve was tested. Both units are not electrically protected. Homeowner is aware of the risks regarding not having protection. Both systems were operational at end of appointment.
Tech arrived on site. Performed ac tune up. Cleaned condenser coils with spray foam. Cleaned indoor filters. Cleaned evaporator coil with chemicals. Tested system operations. Inspected current hvac split system. Advised client of options to add central air.
Set the gas valve to the on position. Tested the heat and recorded temperature. Cycled heat twice and allowed the sealant to burn and the odor to pass.
Arrived on site to perform fall tune up on a 2019 Bryant unit. Furnace located in attic. Condenser in back yard. Client stated no issues as home is new and less then 2 years old. Client cycled unit and was operational. Inspected attic. Found new flex ducting used and good. Filter were dirty and client stated he would replace himself. Blower assembly is good slight dust. Motor is good and in range. Inducer motor is good and in range. Igniter and flame sensor are good. Drain lines are good at This time but no safety over flow switches. Recommend adding surge protectors me to at least primary line to prevent any over flow in attic. No protection on unit. Recommend adding surge protectors to units to protect from electrical surge and power outages that can damage or even short out systems and components. Cycled unit and went over all findings with client and recommendations. Clips aware how unit is running and itâ€™s condition. Client did want to hold off for now since unit is new.
Install phenomenal Into supply plenum. with transformer
Upon arrival performed install on motors. System is operational upon departure.
Performed maintenance on furnace and air-conditioning maintenance. Maintenance checked out properly. Client did mention that they felt like system is not keeping up. Warranty has been out twice did all possible at this time. System is Cooling Efficiently at this time with a 20Â° temperature split. Electrical components and condenser coil are good outside. Compressor amps and fan or in range. Filter was recently swapped out. Heating maintenance check out properly. System is Heating With a 40 degree Temperature Rise. Flame sensor was cleaned up. Hot surface igniter is in proper range. Drain lines are clear at this time and show no signs of water in secondary pan. Discussed full condition of system homeowner And she does not want to continue with maintenance at this time. Client will reach out if you would like to continue. Heater and AC check out properly upon departure
Performed AC/furnace maintenance on a Lennox system. Heating temperature split is 30 degrees. All sensors, switches and burners were cleaned. Filter is ok and changed on a timely basis by the customer. Inducer motor is amping ok. Outdoor unit was very dirty but deep cleaned today. Starting components were checked. Compressor and fan amp draws are good. Refrigerant levels were adjusted 1 pound. Recommending hospital grade air purifier for the home to help with air health. System was running at end of appointment.
Performed AC diagnostic on 2001 Rheem condensing unit. Upon arrival Client trimmed bushes around condenser so that I may have access to unit. Client states that system is only blowing out hot air and the only repairs that have been done in the past was replacing a capacitor and rewiring due to the rats chewing it up. System has not been maintained the last four years. During my Troubleshooting I found multiple points of concern of concerns that addressed. 4 ton condenser- 1. Dual secondary motor control is defective on hermetic side terminal. This may have happened due high amp draw and even potentially power outages. 2. Starter has slight pitting and burn marks on contact points. 3. Compressor is pulling significantly high amps putting it at a higher risk of failing 4. Indoor blower motor Has oil leakage coming from bearing 5. System Contains R22 refrigerant which was phased out in 2020 Discussed full condition of system with homeowner And he is aware of the many problems that are
Upon arrival performed diagnostic. Found breaker tripped. Found secondary motor control out of range. Compressor has start amps of 113 amps. Added a booster kit and brought down to 3 amps. Client wants to replace both indoor & outdoor motors. Secondary motor control will be replaced inside. Coming back to do repairs.
System is not serviceable, client has a very big bush that is all around the entire system. Client needs to trip and keep away from system, this can really damage system. No charge
Client is selling home, said he will let next home owners take care of thermostat. Would have replaced if labor was covered. Decided not to do it
Summer AC Maintenance Performed Upon arrival system is working and operational. I began my maintenance at the outdoor condenser by breaking it down and cleaning with water and coil solution, removing dirt and debris. I inspected electrical components for wear and tight connections. I checked refrigerant pressures and charge. I tested system amperages. I then proceeded to the indoor furnace unit. I measured temperature splits. I checked condensates for proper drainage and safety. Filter was changed. Inspected electrical to ensure tight connections and monitor wear. Inspected blower compartment for dust and dirt as well as proper balance. Upon departure system is working and operational.
Upon arrival performed diagnostic. Found compressor to not be up and running. Tested secondary motor control, found that secondary motor control was low. Replaced with a heavy duty control, started system. Found compressor starting at 70 amperages on the kick. Added booster kit to system and dropped it down to 9.8 amps. Refrigerant levels are in range. Filter is clean. Every register is open. System is operational upon departure.