Great service! Quick response!! Mike was so nice and very helpful! Had the job done so quickly!! He made sure we didn’t have any questions and explained everything to us!
This was easy a thorough. A good price for the service.
Knowledgeable polite and informative service tech! Jimmy was great!
I really like this company. They are fair priced and have gone above and beyond on their service for me. Excellent customer service, friendly, honest and knowledgeable technicians. Been with them for five years and I expect many more.
David was upfront, honest , professional! He came in and repaired what was wrong. He didn’t make any repairs up!
Returned to perform repair. Installed new high limit switch. Cycled system for heat. Verified proper operation. System is operational upon departure.
Upon arrival performed heating maintenance. Dusted off all electrical and indoor furnace cabinet components, sanitized outdoor cabinet. Blower motor and inducer motor are in good condition. Found secondary motor control to be out of range, client approved to replace. Replaced filter that customer provided. Gas valve in working order. System does not have a sediment trap on gas lines. Temp splits in range. Circuit board and electrical connections good. - blower wheel starting to accumulate dust. - secondary motor control low ( replaced ) - electrical connectiongs good. - indoor motor good System was reset tested and fully functional upon departure.
Tested furnace on both zones and recorded temperature rise. Set date and time for both thermostats. Measured voltages, amp draws on motors. Tightened electrical fittings. Tested ignitor in ohms. Cleaned flame sensor. Wiped down furnace internal cabinet. Inspected blower cabinet and motor. Inspected ducting.
Technicians arrived on site to swap out heat exchanger and service the evaporator coil. Removed old heat exchanger and cleaned off ignition components. Cleaned off coil with coil cleaner amp rinsed off with water. Installed new heat exchanger along with the burner assembly and inducer motor. Tested system and checked temp split. Unit is operating good now.
Performed maintenance on 11 year old Rheem heat pump system. Cycled for heat. Checked indoor and outdoor unit electrical and system components. Evap coil and blower wheel are clean. Germicidal light is still operational. Replaced filter with filter provided by customer. Checked outdoor unit electrical and system components. Primary motor control are within range. Compressor hard start kit also within range. Pulled off condenser fan motor And thoroughly washed out condenser coil inside and out. Washed unit exterior. Cycled system, system is fully operational upon departure. No recommendations at this time.
Installed PCO MAINTENANCE kit
Performed furnace maintenance on a Lennox signature series heat pump. Tested electrical furnace components. Recorded temperatures and inspected air filters. Performed furnace maintenance on a Lennox signature series heat pump. Tested electrical furnace components. Recorded temperatures and inspected air filters.
Preformed furnace maintenance on Lennox duel fuel system
Two system air handler tune up and service. Tested indoor blowers and recorded capacitor values. Inspected ducting and indoor cabinets. Tightened electrical connections. Cleared condensate traps. Replaced both filters. Verified refrigerant charge. Recorded temperatures. Inspected breaker and tested thermostats.
Diagnosed. Furnace tripped main limit switch. Switch is defective and is no longer allowing to be reset. Need to return with new limit switch. Will order tomorrow and return when part is in.
Installed x2 indoor blower motors, x2 flame sensors, performed 2 blower house sanitize/cleanings. Need to return for heat exchanger install an evaporator coil cleaning once part is shipped to shop.
Tested heating equipment. Measured temp rise and recorded electrical loads. Cleaned flame sensor and tested ignitor. Inspected blower motor. Replaced filters. The system is running too hot due to lack of airflow, the returns are too small but the returns are custom. The flue vent is bolted into the blower cabinet so the heat exchanger was not checked, the most likely areas to fail on this heat exchanger would be all the way on the bottom near the coil. Recommending some high level Co detectors for the home just as a precaution.
Returned to replace indoor motor. Removed old motor. Cleaned out and washed blower wheel. Installed new motor. Secured motor. Re-installed motor. Lit pilot for homeowner. Cycled system. System is operational upon departure.
Performed AC/furnace maintenance on 2001 Rheem 3 system. Upon my maintenance there were multiple points and concerns that were addressed with the homeowners. Central furnace- 1. Found that heat exchanger was cracked on multiple tubes. This was caused due to overheating and the metal expanding and contracting Due to high temperature rise and Restricted airflow 2. Static pressure on system was 1.29 due to clog filters never been swapped out along with dirty evaporator coil. This is a major air restrictions due to the dirt buildup and has resulted in overheating conditions 3. Single secondary motor controls has become out of range Due to Motor using more power than needing from oil leakage 4. Indoor blower motor Lubricant seal has popped from high usage and AC mode most likely. If left in this condition can cause motor to overheat or lock up due to lack of lubrication. 5. Flame sensor has oxidized and can cause failure on ignition if left like this 6. Evaporator coil covered in dust and d
Performed Fau maintenance on 7 year old Maytag furnace. Cycled system for heat. Verified proper heating sequence of operations. Temperature rise across heat exchanger is within allowable range. Cleaned furnace, blower assembly and compartment, and heating compartment. Ran system through 20 point inspection checklist. Filter was dirty, replaced filter with homeowner approval. Cycled System. System is fully operational upon departure.