Jimmy was very helpful in getting our AC up and running again! He was very polite and patient with all of my questions. Educated me on the ins and outs of my ancient AC. He even talked to my dad on the phone about the situation 😂 Overall, great experience.
Great company! Never disappointed!
Left a google review. Work was done well and the process was transparent and honest. These guys had a smile on their face all the time and it was great.
Very helpful on explaining the system. Signed paperwork on a Wednesday installed on that Friday.
The technician was very friendly and professional.
Micheal is very knowledgeable, takes great care in explaining, and servicing unit...
He was on time earlier than I expected.
Performed AC maintenance on a 2 system house. Living area unit is a Duncane. System was cooling 20 degrees. Indoor amps are ok as well as the start component. Outdoor unit starter had burned out the load wires. Start component was completely dead and the fan motor was leaking oil. The customer decided to go with a full rejuvenation at this time in order to buy some time until replacement. Bedroom area system is a new Lennox. System is cooling 20 degrees, filter was very dirty due to construction in the house. Filter was changed today. Outdoor unit was chemically washed. Electrical components are good. Refrigerant levels are in range. Compressor and fan amps are healthy. Surge protection was added to this system. Both units were tested and running at end of appointment.
Performed AC maintenance on a Lennox system. Cooling temperature split is over 20 degrees. Blower motor is clean and amping ok. Filter was dirty and replaced today with a upgraded merv 16. Customer provided. Condensate line is clear. Outdoor unit was dirty and chemically washed. Compressor bay and service panel was cleaned. Refrigerant levels are ok. Compressor and fan amp draws are in range. Electrical components show minor signs of wear at thus time. Indoor and outdoor units are not protected, system was running at end of appointment.
Arrived on site to gather information on 5 units to give clients a proposal for a service plan on commercial units. Advised the fan coil would need access to get up and lift up to service indoor units. Clients are aware and office will call back once they get there proposal ready.
Left filter by the front door
Added insulation to the condenser service port plate to reduce vibration sound, shifted position of the condenser so the vibration goes into the pad and not into the lineset.
Arrived on site to diagnose no cooling 2002 unit. Spoke to client and she stated unit is just blowing cold air and out side dose not run. Cycled unit and inside was operational and outside unit Compressor was not turning on. Inspected electrical and found primary burnt up on contact points. Secondary control was bad and why compressor was not turning on. Had to use booster kit to help jump start unit and so replaced bad part and added booster kit to turn unit on to inspect system. System was operational and found start up high. Run amps were pulling 15 and max rated at 21 advised itâ€™s cold outside and on a really hot summer days system may be over amping which is draining life of secondary control. Fan motor is bad and bearings are seizing up and leaking so much oil. Motor is gunna fail in future and recommend replacing. Checked pressure and are good and cooling at 18 degrees. Unit uses r-22 and is no longer in production. Went over all findings and repairs and recommendations Who
Tested gobi condensate pump with water. Inspected outlet drain tube and adjusted position. Improved the slope of the condensate pump basin to allow water to flow easier into the pump. Tested multiple times, did notice a gurgling sound after pumping intermittently. Clients state that sometimes this happens constantly. Replacing the pump may relieve the gurgling noise, this could be cause by a faulty check valve.
Performed diagnostic on system. Condenser is from 1989. Furnace is from 2012. Upstairs is not cooling. Just moved into the home about a year ago. Upstairs also has very little aireflo. Cycled for cooling. Checked outdoor unit electrical and system components. Gauged up to unit and found unit completely flat on r-22 refrigerant. R-22 is no longer being produced and although it is available it is extremely expensive. Went into attic and ductwork is in very poor condition and torn in different areas, which can explain the poor airflow to upstairs. Went over findings and recommendations with homeowner. Ultimately decided that he does not want to repair it and would rather go over some replacement options. Turning call over for replacement options.
Installation of Variable Speed Air Conditioner, Lineset, Electrical, and drywall patchâ€™s necessary for the Lineset run.
Performed maintenance on 5 year old Lennox system. Cycled system for cooling. Checked outdoor unit electrical and system components. Amp draws are in range for compressor and condenser motor. Primary motor control is in ok condition, secondary motor control is within range. Refrigerant pressures are In range and system is producing proper temperature split. Removed condenser fan and thoroughly washed out condenser coil inside and out. Merv filter was dirty, and was also wet due to an extremely clogged drain line causing water to splash back in unit. Went over findings and recommendations. Replaced Merv filter and also cut and cleared drain line. Re-adjusted drain line and left primed. System is fully operational upon departure.
Upon arrival performed txv replacement and filter drier replacement. Vacuumed down system to 500 microns. Charged system up with proper refrigerant. 20 degree temp split. System is operational.
Upon arrival performed diagnostic. Found system to be really low on refrigerant. Evap coil is really dirty. Home is gonna be up for sale, client did not wanna do Refrigerant. Wants to look at long term solutions. System is operational but no cooling. Only 71 degrees coming out.
Upon arrival performed diagnostic on system. Found system to have a restriction in the refrigerant cycle. Replacing expansion valve & filter drier. Thursday will be out here. System was reset tested and operational but not at 100%. Client paid in full today.
Arrived on site to install a compressor booster kit on unit. Client is aware. Installed booster and and cycled unit to ensure system operating. System is operational and cooling upon departure.
Performed TXV repair and recharge. New TXV was installed along with System Was pressurized with dry nitro and pulled down to 500 micron. System was charged up to 10 sub cool along with a 17Â° differential split inside. Upon departure system is cooling.