Luis from Cold Air Solutions did a fantastic job of serving our air conditioning units!
So polite,professional and knows his stuff!
Luis was great! Explained everything. Very satisfied.
Thank you for helping us to extend the life of our older heater/air conditioner system
My technician Jimmy was great. He was very professional and explained everything to me.
Shane is very friendly and professional, excellent in the knowledge of Heating and Air, very courteous and works quickly !! He is ready for the next step up the ladder at his job.....
Luis was great I highly recommend
My technician Daniel was a pleasure. He was social and we had good conversation. He explained everything he performed on my unit and suggested some safety upgrades for consideration. I hope he continues to come back.
It's really pleasant to have Michael out to check our system before the winter use of heater.. He is very professional, great at explaining how the heat pump works. Michael also was very helpful in explaining the service contract we chose to renew.
Jimmy was stellar. He preformed all the services and explained everything with great knowledge.
It’s nice to have the same technician come to our home for service. Great customer service and will continue to use this company!
The guys that came out to replace our AC/Furnace were great. Very professional, kind and did a wonderful job! Now our house is cool!!
20 Point Inspection: Check System Static Pressures Check all Safety and Limit Switches Clean Condenser Coil Duct Leakage Inspection Remove Debris from the Condenser Check Refrigeration Pressures Perform Visual Inspection and Clean Service Panel Measure Starting Amperage of the Compressor Tighten Electrical Connections Measure System Amperage and Voltage Flush Condensate Drain Lines Measure Temperature Difference Vacuum Furnace Return Air Grille Clean in Place Blower Compartment Inspect Blower Wheel for Proper Balance Monitor Air Purification System Apply UV Protective Coating on Condenser Perform Energy Usage Calculation Test Condenser Pressure Switches Check Thermostat for Proper Operation / Calibration
Performed AC maintenance on six year old system. Inspected indoor unit system has protection. Did recommend customers change filter. Inspected indoor unit blower housing for cleanliness and proper balance. And components. Cleaned outdoor condenser coil. Tested capacitor it is. Outdoor unit also has service protection. Unit is cooling and operational upon departure.
Upon arrival client stated system does not kick on. Found outside disconnect to be reversed in the off position. Client said they have never touched that. I asked if any one is in there back yard gardener etc. was just working last week. System is operational checked refrigerant levels, primary & secondary controls. Condenser fan motor is leaking oil. Will speak to husband. System is operational.
Performed a Summer tune up for both systems. Downstairs AC was working great, refrigerant levels were good, capacitor was good, and all amperages draws were within range. The startup amperage draw was a bit high so a hard start kit was recommended to ease the rough startup. Upstairs ac was working good however the refrigerant levels were a bit low. It was recommended that we add refrigerant to get the system to peak performance. We also recommended a hard start kit for this unit as well because of the high amp draw upon start up. The blower motor for both units were dirty and a cleaning was recommended to make the quality of air cleaner in the house.
Arrived on site and performed AC maintenance on Lenox heat pump. Maintenance checked out properly. Measured refrigerant pressures and amperage and found that they were in range. Electrical components are in good condition. System was not equipped with surge protection. Perform deep cleaning on outdoor coil. Replaced filter supplied by client. Temperature split is in range. Discussed full maintenance with Al at this time due to unfortunate situation of his brother passing away he will not be able to renew today but would like to renew in November Once heâ€™s in a better financial position. Client is aware that all benefits will be discontinued and no membership is active at this time and upon departure system is operational and cooling.
Inspected system for operation and discovered dead electrical leg on the outdoor unit. Inspected the breaker panel and the current breaker is not sufficient for the equipment installed. Replaced the bsing,e pole breakers with a dual throw 20 amp and replaced the fuses with 20 amp from 25. System was tested and is working properly at this time.
Performed Ac maintenance on Lennox system. Cycled system for cooling. Checked indoor unit electrical and system components. Temperature split is within range. Replaced filter with filter provided by homeowner. Checked outdoor unit electrical and system components. Pulled panels and thoroughly washed out condenser coil inside and out. Went over findings and recommendations. Installed indoor and outdoor surge protection for full system protection. Cycled system, system is operational upon departure.
Upon arrival performed diagnostic on AC system. Client just needed wire to be replaced. Replaced wire and system started working without compressor? Found compressor to not be kicking on due to secondary motor control was completely out of range. Replaced and got system going. Checked refrigerant levels and system is in range. Amperageâ€™s are good. System is very old with no model and serial numbers. Client signed up to Memebrship, he is moving to New York, and will be a rental property. System is operational.
Performed maintenance on a 2019 Lennox system. Customer reports light use of the system through the year. Outdoor unit was chemically washed. Refrigerant levels were verified. Electrical components were measured and tested. Compressor bay and service panel was cleaned. Filter is good. Indoor amp draws are good. System is operational.
Upon arrival client said system wouldnâ€™t cool on hot days. Previous visit out the tech found issues with high static pressure. System is not getting enough return airflow. Made recommendations on how to do a new return cut in.
Upon arrival performed diagnostic. System is throwing out a e312 code. Client says between times of 11-3 system doesnâ€™t work. System has been running & cooling. Found return is very undersized for 5 ton system. Only have about 1200 cfms on a 5 ton system. Ducting is original. Freddy to come out and asses ducting. System is operational as Iâ€™m here and as I leave.
Performed combo tuneup on a ACPro heating air system. Filter was ok. Indoor and outdoor unit were washed. Electrical components were measured and are healthy at this time. System is operational at end of appointment.
Upon arrival client stated they heard a loud vibrating noise on outdoor system. Advised system was in defrost mode. Thermostat temperature; matching with temp probe.
Arrived on site to perform spring tune up on a 2020 Lennox unit. Condenser located in back and furnace in closet. Cycled cooling and good. Filter are good as tenant buys her own. Washed condenser coil inside and out. Primary starter is good. Secondary secondary control is good. Fan motor is good and amp draws are in range. Start up amps on compressor are in range and run amps are good as well. Checked pressure as unit is on R-410a. Unit is holding pressure good and cooling at 19 degrees in home. Found no protection on units from electrical surges and power outage that can damage unit or even short out systems and components. Cycled unit and went rover all findings with misty as she stated she would like a report of it all emailed over to her with estimates.
Performed ac maintenance on 5 year old unit. Checked electrical components. Washed outdoor coils with coil cleaner. Measured temperature split. Strapped condensate line. Detailed service panel, waxed condenser unit. Checked refrigerant levels. Serviced indoor unit. Customer provided and changed filter and renewed membership. Unit operational upon departure.