He was on time earlier than I expected.
This is NOT company you want inside or around your home. The sales people are professionals. But the installers are way below par. They don’t show up at their scheduled time. They lack any respect or professionalism on site. Taking personal calls, talking slang and cursing aloud while they listen to music. Just to let you know during COVID while most are working from home and taking meetings, you can not have your installers answering calls saying “what’s up Bimbo?!”. Furthermore, they do not wear booties or face masks when they are inside your home. I expected for the price they’d be more respectful. I would NEVER recommend them to anyone EVER!
The guys were knowledgeable, friendly and clean work. They also took the time to answer any questions I had.
Madison was very professional and thorough
Jimmy was amazing and he was very honest up front and showed us everything he was doing and explained it. This guy was awesome and I look forward to working with him in the future!
Michael was so nice and friendly, he felt like a long-time friend by the time he left. He took the time to explain everything to me and didn’t make me feel like an inconvenience for asking questions. I hope he can come back for future service calls.
Darren asked me questions about my system and its operation, then provided options for me based on my needs and wants. I don’t see customer service like that at all anymore; it was a pleasant surprise!
Michael did an excellent job describing our systems and the work needed for improvement. Plan to sell house in next year so only reason we didn’t move forward.
Performed maintenance on 2 Rheem units, one is 2017 other is 2013. Originally met with homeowners, but they had an appointment to get to so adult son was on site. Cycled systems for cooling. Checked indoor and outdoor units electrical and system components. Temperature split for both units is within range, and systems are cooling properly. Merv filters are both clean, homeowner does carry his own replacement filters. Checked outdoor units electrical and system components. Amp draws are within range. Primary and secondary motor controls are in good condition and within range. Pulled condenser fan motors and thoroughly washed out condenser coils inside and out.
Inspected system for operation.
Performed AC tuneup on 2007 carrier heatpump. Upon my maintenance there were a few points of concerns that were addressed with The homeowner. Carrier condenser- 1. Found that single secondary motor control the powers fan has become weak reading at 4MFD when our reading should be at 5 MFD. The weaker the battery gets the more strain and damage it causes to the component that it powers. 2. Dual secondary motor control that powers compressor was also at 36MFD when itâ€™s actual reading should read at 40. 3. High voltage relay had a bit of pitting/burnt on contact points. 4. Condenser fan motor showed no signs of oil leakage in spinner freely. 5. Refrigerant pressures for R410a weâ€™re in range 6. Amperages were in range at this moment 7. Condenser coil was cleaned off and ready for summer 8. Air handler on side of home had no return plenum on tops. Also filter needs to be swapped every one to three months For best filtration 9. Drain lines were cleared and weâ€™re properly draining Discu
Arrived on site to diagnose not working and no airflow on 2 2000 units. Client stated systems have been down for a while and have used system and heaters did not operate. Now upstairs dose not turn on and downstairs turns on but has no air flow at all. Clients stated they know system are old and have issues. Went and cycled units downstairs had no airflow at all and upstairs was not operational and loud buzzing noise created in attic. Went over big major issues and possible issues they could face in future due to condition and age of unit. Went over findings and advised now is the time to consider full system replacement due to the age over all condition and cost of repairs and recommendations needed. Compared to full system replacement. Client is aware units really old and not worth putting money into old systems. As they would someone to come out to go over pricing with client. Shaun was previously out and got Shaun back out to go over system replacement options client is aware and c
18 Months 0% Finance
Repaired low voltage short in the wiring connecting the outdoor system and the indoor circuit board.
Replaced defective M30 thermostat and outdoor contractor. Have to order circuit board on Monday, advising replacing board with Sensi WiFi stat as well.
Installation Of A Comfort Pro 20 SEER Variable Speed 105 Stage Air Conditioner With High Performance/Efficiency All Aluminum Coil To Assist In Higher SEER Rating, Remove Moisture From Air, and Decline Chances of Bacterial Growth. Including Promotional Germicidal UV Purification Device, Including A80U2SVL Variable Speed Furnace with 2 Stage Gas Valve, MERV 16 5â€ Hospital HEPA Filter with 95% Capture Rate And Carbon Coating. Check Pricing Is Shown, Full payment Is Expected Upon Completion.
Arrived on site to perform spring tune up on a 2018 Ac pro system. Unit located in back yard. Furnace and Evaporator coil located in attic. Filters replaced by client. Washed out condenser coil inside and out. Primary and secondary motor controls are both good. Fan motor is good and amp draws are in range. Compressor start ups are high crating stress and wear. Recommend adding a booster kit to prevent it from hard start ups. Run amps are good. System is cooling home good at 20 degrees. Blower assembly good has dust accumulating. Motor is good. Evaporator coil is good slight dust. Drain lines are good. No protection on unit. Cycled system. Went over all findings and areas of concerns with client. Client is aware of how system is running and itâ€™s condition. Client did declined recommended work at this time as they have things going and will call us when they are able to go forward with recommendations. System is operational and cooling upon departure.
Arrived on site to perform spring tune up. Client stated no issues. Condenser in back yard. Furnace and Evaporator coil located in closet. Washed condenser inside and out. Checked all electrical compartment and components. Primary starter is showing wear as its slight Burt up on putting. Secondary motor control is good in range. Fan motor is good and in range of amps. Start up on compressor is in range but really high as itâ€™s pulling 62 and Max rated at 67. Recommend adding a compromise booster kit to reduce high and hard start up to prolong life of compressor and help it start up easier. Run amps are good and in range. System is cooling home at 19 degrees. No protection on unit. Recommend adding a surge protector on unit to protect it from getting damaged from electrical surges and power outages that can damage or even short out systems and components. Filter was supplied by client and replaced and was really dirty. Blower assembly is dirty from the amount of the dirt that has ent
Enlarge main Trunkline from garage to attic and re-design + replace all attic ducts. 5k down. $7,578 Financed 24 months 0% interest
18 Months 0% interest
Tech arrived on site, started ac tune up. -cleaned coils - cleaned electrical - tested system Found: -cap is out of range and needs to be replaced. -fan motor amping at max - condenser coils disintegrating - charge okay -compressor okay
Arrived on site to perform spring tune up on 2 Ac units. A 2019 lennox unit and a 2006 air strong unit condenser located on side of home. Furnace and Evaporator coils are located in attic. Client stated he wants service and cleaning. Washed both condenser coils inside and out. Older unit was hammered of leaves. Primary were both good. Secondary motor control ok older unit is bad and out of range recommended replacing. Before completely fails. Amp draws on compressor and fan motor were good on new unit. Older unit start up amps were above range from self wear. Run amps are in range. Recommend adding a compressor booster kit to help reduce high amps. Fan amps are at Max and motor has been leaking oil from over working in past years motor is not spinning as freely as it should and could fail. Older unit is in R-22 and is no longer around. Inspec Both indoor units. Both filter were dirty and client supplies his own filters going forward. Blower assembly were both dirty and need cleaning
Preformed Ac maintenance 2018 Lennox system.