Came when requested. Very informative.
Scheduling and staff were awesome, our technician Jorge was a sweetheart, very honest and very knowledgeable, all in all we ate a very happy customer.
Mr. Cervantes was very professional and polite. I especially appreciate that he was knowledgeable and competent concerning the task at hand and explained why and what he was doing. Sincerely.
Upon arrival performed heating tune up. Checked heat exchangers, did not find any that were damaged or cracked. Circuit board and electrical connections in range. Indoor blower motors are leaking oil and need some replacement soon. Client stated they donâ€™t use heater that much due to propane costs. Advised moving to a dual fuel system to utilize solar on home and use propane as back up cause be a good outcome. Indoor blower wheels are dirty. Dusted off electrical connections. Did not have any filters for client. System checked, system operational. Client wanted to email husband with all pictures.
Performed heating and cooling maintenance on a 2020 Lennox heat pump. All electrical components were measured tested and recorded. Refrigerant levels are in range. Filter is ok today. Indoor unit was chemically washed. Outdoor unit was very dirty and chemically washed today. Condition of system was discussed with the homeowner. A maintenance schedule was Setup. System is fully operational.
Adjusted circuit board setting to stage to second stage after 7 minutes of heating. Tested supply temperatures and monitored. Removed piece of gas nipple in the attic space and removed length of return ducting. Programmed the Sensi app and connected the WiFi network. Added a summer and a winter schedule for the thermostat.
Installation of a Lennox Variable Speed Furnace. Cash Discount is only applicable if payment is completed with either Cash or Check, failure to do so with result in cash discount being revoked.
Upon arrival found system not heating. Blower motor would stay on for 30 mins plus after call for heating ended. Upon inspection found the control module yellow and had failed. Further inspection revealed the ignition components are old and worn down. Blower motor is leaking oil. Tried to replace with universal board on van but it wasnâ€™t the correct one. Order control module. Client is interested for replacement of furnace since part is a couple days out.
Tech arrived on site. Performed fall tune up. Inspected ignition components. Unit is 21 years old. Flame sensor is oxidized, and hot surface igniter has high readings. Both still operational. Inducer motor is okay. Blower motor is over amping and will fail. Pulled blower motor to inspect heat exchanger. Temp rise and static are okay. Heat exchanger is not cracked at this time. Hot spots on heat exchanger. No secondary drain pan on condensate line. Talked about replacement options as well as repair options. Unit is operational upon departure.
Combo Maintenance Performed Upon arrival system is working and operational. I began my maintenance in the attic by performing a duct leakage inspection. I then proceeded to the furnace unit, I checked and tightened electrical connections. I inspected the heating components for proper operation and wear. Burners were inspected for proper operation. Flame sensor was cleaned. Condensates lines were inspected for proper drainage. Static pressures and temperature splits were taken. Filter has been checked, does not need to be changed at this time. Blower housing and wheel was inspected for balance and dust build up. Air supply was measured. Inspected safety switches as well as inspected home for fire and carbon monoxide detectors. I then proceeded to the outdoor unit. I checked electrical components as well as measured amp draws. Inspected components for wear. Checked refrigerant pressures. Recommended a phenomenal aire to customer for allergies and dust concern. Upon departure system is w
Customer was confused on todayâ€™s scheduling, he thought todayâ€™s visit was being rescheduled. He is leaving in 35 minutes. No time for a combo tuneup and is happy to reschedule. Customer is nice, states if there is any bill for the mixup to go ahead and email it.
Upon arrival performed diagnostic. Client saidnsystem just keeps running and running after doing its cycle. Client had some registers closed, dirty filter. Advised we have to keep filters clean every 2 months. System is operating at normal standard, reaches out of temperature, cycle to cool heat exchanger down then shuts off. System is operational. Client will speak to husband about membership.
Found defective condensate float switches keeping the system from operating properly.
Tech arrived on site. Started AC tune up on a Rheem split system. Unit is operational. Cleaned condenser coils with chemicals. Cleaned and tested components in the electrical cabinet. All start components are good and had been replaced recently. Condenser fan motor is leaking oil and rusty. It is recommended that it be replaced before it fails. Refrigerant charge and temperature split are good. Went into attic and started checking Airflow. Static pressure is low. Duct connections are not sealed. Blower wheel is dirty, and there is no emergency drain pan installed. Flushed out condensate line. It is strongly recommended that we install an emergency drain pan to prevent ceiling damage in the event that both lines clog up. Compressor amps are 18/21. Compressor is struggling. Service disconnect is not secure on the wall. Went over replacement options with client. Customer is aware of all issues and recommendations. Client declined them at this time. Unit is operational upon d
Inspected duct system and performed assessment of the entire homes temperature splits and layout.
Tested system for operation. Measured temperatures. Added refrigerant charge. Inspected air filter. Tested welds for leaks with soap bubbles. Inspected fan motor and evaporator. Inspected attic space and ducting. Tested temperature splits at the return grille, and at the system.
Installation of a Lennox 16 SEER Single Stage A/C with High Performance Coil Add on inducing lineset, electrical 220/208V was ran by homeowner in the previous years. Pricing shown will be check pricing including every applicable discount
Arrived on site to perform AC maintenance on 17 year old Goodman systems. As homeowner was showing me around, she mentioned that they recently were in the market to replace the system and had gotten a couple different quotes. After realizing how much an expense like that would be, they are no longer looking to replace the systems as they are most likely going to be selling the home and moving. They are hoping that a maintenance will hopefully make systems run smoother and squeeze some life out of them. Advised I will be doing thorough maintenance and inspection and will let them know how them systems are doing. Cycled systems for cooling. Checked outdoor units electrical and system components. Primary motor controls for main unit has burn and pit marks. Secondary motor controls are in range. Amp draws for compressor and condenser fan motor are within range. Condenser fan motors are both leaking oil. Compressors are starting up hard, and they are noisy. Refrigerant levels are within ran