Tyler was on time and kept me informed as to his tasks and if I had any questions. I did have a few questions and Tyler provided the answer in a way that made sense to me. He was courteous and thoughtful. Great job!
Luke came by in the winter for our winter service and did a great job. So, here we are due for our summer service and we lucky enough to draw Luke again. And like before, Luke was on time and very timely on his visit. He explained the work and made sure I knew what he did. Even before leaving he helped bring in some groceries from the garage....has that for service. Thank you again Luke.
Luke arrived on time and explained what he planned to do. He was courteous and, having had some rain that morning, was good at wearing his booties. He provided an estimate on how long he should be and finished as he expected.
Arrived on site to perform spring maintenance on 2015 Lennox system. Condenser located in back yard. Furnace and evaporator coil located in attic. Client stated no issues just wanted to ensure this is no issues with drain lines. Hey had system running and cooling upon arrival. Condenser was really clogged with dog hair and hair. Checked fan blades, bearings, and motor. Checked electrical compartment circuit board and components. All good. Primary control is good. Amp drawls on compressor and fan motor are both in range. Refrigerant pressure are good. Found no protection on units. Cycled system to ensure system operating. Did attic and indoor inspection. Found new flex ducting used. Filter was dirty and old. Recommend replacing filter and doing so as needed to reduce amount of dirt entering system. Blower wheel has light dust. Motor is good. Evaporator coil is good at this time. Drain lines are good. Blew drain lines out. Inspected drain line and found connections from drain line and T-
Upon arrival performed furnace maintenance on 2015 unit. Inspected indoor unit. Temperature rise was good. Filter was still clean no need to change it out perhaps on next visit. Burner assembly was good. Blower wheel and motor also good. Amps on blower motor and inducer good. Duct work is ok. Customer did say vent in one room wasnâ€™t getting enough air. Checked duct work going to room everything was fine damper fully open. Checked vent in room and was blowing a fair amount of air. Customer renewed membership. Cycled system on and off. System is operational upon departure.
Doing a single system Lennox system out here in Yorba Linda
Fall Maintenance 11/27/2018
Performed routine air conditioning maintenance on lennox unit in yorba Linda. Also installed surge protection on unit
Preventive AC Maintenance
Performed routine air conditioning maintenance on lennox unit in yorba Linda
Working on a complete Lennox system in Yorba Linda for a first time client making sure everything is working properly for summer
Performed Routine Fall Maintenance on Lennox Furnace. Replaced 16x25x5 Merv 16 Air Filter. Checked all heating components.