On time & efficient
Luke was very professional and knowledgeable about the unit. Gave helpful advice on pre-maintenance and Energy efficient ways to save money.
Home Advisor recommended 3 names when I needed service on our a/c. I chose Cool Air Solutions after speaking w/Nick & we scheduled service for the following week between 11-1. However the day before my scheduled service, Nick called to remind me of our appointment the next day between '2-4' but I was planning on 11-1. I called him back to correct the time but although he apologized for the error, he said it could not be changed but that the serviceman would be out as soon as possible. The serviceman, Adam, did arrive at 2 & was very respectful, friendly & efficient. He didn't have one of the parts I needed, so had to return to the warehouse to get it. But he promised he would be back & get it fixed the same day. I was thankful he delivered & was good on his word. He completed the job by 5 & was a pleasure to work with & the A/C is working well! The job was very expensive & had I not been pressed for time, I would have called around to find a more reasonable price.
On time very efficient
Tech arrived on site. Began tune up of unit. Found filter extremely restricted. Replaced with customer supplied filter. Checked indoor motor and airflow. It was good. Ducts are old and dusty. No duck leakage seen at this time. Outdoor coil was hammered. Mostly with dog hair. Cleaned coils and electrical. Checked charge. It was low at this time. Did leak detection in evaporator coil. Could not find anything at this time. Got authorization from management to fill up unit with 1lbs of r410a. Management also said they will extend parts warranty of evap coil until our next visit. On our next visit, we will need to do an isolation test to confirm where the leak is.
Arrived on site to perform fall tune up on a 2016 Lennox system. Furnace and evaporator coil located in attic. Client stated no issues just wanted service. Cycled system in heating. Found filter really dirty due to the area house is surrounded by. Recommend replacing with a Merv16 filter Found new flex ducting and black flex ducting used. Blower assembly and wheel are good just slightly dusty. Motor is good and amp drawls are good and in range. Inducer motor is good and amp drawls. Evaporator coil good. Heat exchanger is good at this time. Blew drain lines out. Slight dirt accumulating in drain lines from dirt that has entered system. All safety switches are operational. Temperature rise is in range and heating. Found system receiving 122.3 voltage. No protection on either unit. Would recommend adding surge protectors on high efficient systems to protect from high voltage that can damage or short out components or damage systems. Cycled system to ensure system operating. Went over summ
Air conditioning maintenance on a Rheem system in Highland Palms, Homeland.
Heating maintenance in Homeland
Heating maintenance in Romoland
Performing routine maintenance in Highland Palms Park in Homeland for long time clients.
Performed routine fall maintenance on lennox heat pump.
Performed routine spring maintenance on lennox condensor in homeland
Repairing a broken air conditioner here in Homeland
Putting a ton of TLC in to a neglected air conditioner today
Repairing a broken AC
New system heat pump maintinence.