He was prompt clean and knowledgeable. He review the system and gave all options on how to proceed.
Very pleased with service and professionalism.
My unit works better than it ever has!
Great and expeditions service!
Friendly, knowledgeable, efficient, polite
Jarvis was very polite and professional. I would recommend Cool Air Solutions
Arrived on site to perform FAU maintenance on 16 year old carrier system. System is original to home. Upon arrival homeowner mentioned that he has noticed lately that the system does not appear to be heating all that well and would also like that checked. Cycled system, system fire up and went through proper heating sequence. Flames kicked on and remained on for about 1 minute, but indoor motor never kicked on. Checked unit electrical and components. Circuit board is sending out proper voltage for fan motor to start up, but motor does not kick on. After troubleshooting, found that medium speed on fan motor is no longer operational. Hooked up motor low speed. Motor is now kicking on with heat, but system goes into high heat lock out. System is heating, but it shuts off after it goes into high heat due to high temperature in unit. Blower motor has leaked out quite a bit of oil and is pulling in high amperage draw. Motor should be replaced. Condensation Lines do not have any condensation
Inspected the system for problems
Replace existing system with listed equipment.
Performed AC/furnace maintenance on 37-year-old system
Upon arrival performed maintenance. Outdoor condenser was opened up and washed. chemically cleaned coils. Primary and secondary control good. Amperages on system good. Filter was good. Customer will replace filter himself. Voltages good. Electrical connections good. Fan motor good. Refrigerant levels good. System was reset tested and fully functional upon departure. No recommmdations at this time.
Getting a system up and running out here in Valley Center.
Ac and heating tuneup
Performed maintenance and installed Sensi Predict kit
Upon arrival performed furnace tune up. Inspected indoor unit. Noticed ducts are not properly sealed and there are breaches. Temperature rise good. Blower wheel and evaporator coil are dirty. Blower motor is leaking oil. Secondary motor control is low as well rated at 5uf and is at 4uf lowest we can be is at 4.75uf. Inducer motor amps are within range. Gas shut off valve works good. System is operational upon departure. Did change filters 20x20x1 and 18x18x1.
Doing a single system air conditioner and furnace maintenance out here in Valley Center
Full system SDGE assessment in Valley Center
Installing a new Air Conditioning system in Valley Center.
Replacing an Air Conditioning System with a High Efficiency 25 SEER Air Conditioner.