The best service in town.
The service tech was knowledgeable, he kept me updated on everything he was doing, he was very thorough in the work he had to do to get our extremely dirty furnace and air conditioner clean. He was also friendly, polite and followed COVID rules.
He was prompt clean and knowledgeable. He review the system and gave all options on how to proceed.
Very pleased with service and professionalism.
My unit works better than it ever has!
Great and expeditions service!
Friendly, knowledgeable, efficient, polite
Jarvis was very polite and professional. I would recommend Cool Air Solutions
Arrived on site to perform fall tune up on a package unit that was not heating. Upon arrival spoke to home owner of what was happening and she stated 2 days ago they had a vivid thermostat installed by there company. They stated system was working fine and and after they had new thermostat installed system would not work or turn on. They called support line and they had the, trouble shoot over the phone and over the company told them itâ€™s there system and not thermostat and to call another company to diagnose issues. Upon arrival saw thermostat was really poor installed and was all lose as they didnâ€™t use Anchors to hold up thermostat so screws are lose and thermostat itself has a lot of movement and play and advised if thermostat falls off could risk and could create a short. Found thermostat was not getting voltage. Checked breaker for unit and was good and not tripped. Went on roof and inspected electrical compartment and connections and wires. Found system not operating. Jumped
Arrived on site to diagnose a 1994 Rheem system. Client has 3 system here but weâ€™re are only looking at 1 system for the bedrooms. Client stated he barely moved in 5 years ago and has yet to use system and once he did try to use system heater was not operational. He stated he was checking to make sure all wires were good and connected properly. But decide to call us out. Inspected electrical compartment and found condenser thermostat wires were not connected to board and hanging in compartment. Jumped system at control board and system did not operate. Found voltage coming to system. Found 24v at board. System is calling for heat but induce is not turning on. Found inducer motors is not getting power motor and found board itself spins not sending command to start heating operation. Advised client of findings and would have to replace control board first to continue my evaluation and ensure no other issues. Inspected system and found igniter white and a over range thatâ€™s itâ€™s rat
Upon arrival performed maintenance on package unit. Found system to be dirty in and out of cabinet. Evap coil was dirty, performed a clean and sanitization. Blower wheel was pulled apart and cleaned and sanitized. Adding a phenomenal air purification system. Indoor motor is in very good condtion. Heating cabinet was very dusty inside of burners and components, made sure to clean. Amperages throughout system good. Circuit board has a burnt spot near terminals, did not have surge protector to install. Advised client next visit we can bring one out at a discounted add on price. Filter was washed off. Systemmis in operational mode.\ - Dirty blower wheel / cleaned - dirty evaporator coil / cleaned - added whole home purification system. - dusted off all electrical components System was reset tested and fully functional upon departure.
Performed heating tune up on 2 1 year old heat pump units. Cycled for heat. Checked indoor and outdoor unit electrical and system components. Checked attic and ducting. Took temperature splits. Checked outdoor unit electrical and system components. Amp draws are all within range. Primary motor controls are in Good condition. Secondary motor controls are both within range. Pulled off condenser fans and thoroughly washed out condenser coils inside and out. Went over recommendations. Cycled system, system is operational upon departure.
Upon arrival performed maintence on older intertherm furnace. Pulled out motor and caging, cleaned and dusted inside of furnace cabinet off, there was extreme amounts of dust, vacuumed and got rid of. Motor is over amping over manufacture specs. Evap coil is really dirty and requires advanced cleaning. Restriction through dirty coil can cause motors to over run. Secondary motor controls have been replaced. Refrigerant levels are good, r22. Amperages are about 60% to max levels . Energy bills in summer are around 150 running full time. Recommmend replacing system due to age and efficiency. Motor leaking oil. Outdated refrigerant. Filter was replaced. 1. Dirty evap coil 2. Dirty blower wheel 3. Indoor motors leaking oil 4. R22 5. Heat exchanger has a lot of heat impingement System was reset tested and functional.
Arrived on site to perform FAU maintenance on 16 year old carrier system. System is original to home. Upon arrival homeowner mentioned that he has noticed lately that the system does not appear to be heating all that well and would also like that checked. Cycled system, system fire up and went through proper heating sequence. Flames kicked on and remained on for about 1 minute, but indoor motor never kicked on. Checked unit electrical and components. Circuit board is sending out proper voltage for fan motor to start up, but motor does not kick on. After troubleshooting, found that medium speed on fan motor is no longer operational. Hooked up motor low speed. Motor is now kicking on with heat, but system goes into high heat lock out. System is heating, but it shuts off after it goes into high heat due to high temperature in unit. Blower motor has leaked out quite a bit of oil and is pulling in high amperage draw. Motor should be replaced. Condensation Lines do not have any condensation
Inspected the system for problems
Replace existing system with listed equipment.
Performed AC/furnace maintenance on 37-year-old system
Upon arrival performed maintenance. Outdoor condenser was opened up and washed. chemically cleaned coils. Primary and secondary control good. Amperages on system good. Filter was good. Customer will replace filter himself. Voltages good. Electrical connections good. Fan motor good. Refrigerant levels good. System was reset tested and fully functional upon departure. No recommmdations at this time.
Getting a system up and running out here in Valley Center.
Ac and heating tuneup
Performed maintenance and installed Sensi Predict kit
Upon arrival performed furnace tune up. Inspected indoor unit. Noticed ducts are not properly sealed and there are breaches. Temperature rise good. Blower wheel and evaporator coil are dirty. Blower motor is leaking oil. Secondary motor control is low as well rated at 5uf and is at 4uf lowest we can be is at 4.75uf. Inducer motor amps are within range. Gas shut off valve works good. System is operational upon departure. Did change filters 20x20x1 and 18x18x1.