Great service all around. Keep system top notch.
Excellent, Quality service provided. Jorge was very professional and highly skilled!
Micheal explained everything well and diagnosed the issues with the cooling and heating. He was on time did what was needed and cleaned up everything afterwards.
The best service in town.
The service tech was knowledgeable, he kept me updated on everything he was doing, he was very thorough in the work he had to do to get our extremely dirty furnace and air conditioner clean. He was also friendly, polite and followed COVID rules.
He was prompt clean and knowledgeable. He review the system and gave all options on how to proceed.
Very pleased with service and professionalism.
My unit works better than it ever has!
Great and expeditions service!
Friendly, knowledgeable, efficient, polite
Jarvis was very polite and professional. I would recommend Cool Air Solutions
Technician performed spring tune up for both systems. Condenser was throughly washed and cleaned. All amperage draws were within range. All refrigerant levels were within range. Both AC systems are dialed in and ready for summer. All filters were changed as well.
Arrived on site to perform AC diagnostic on 2008 train condensing unit. Upon arrival Greg stated that the system was installed in 2015 by his buddy which is no longer available for service. He stated that his buddy that was working on the unit found a leak inside the evaporator coil but never got back to him for pricing on it. Began diagnostic at condenser and found that it was significantly low on R410a charge. At this time electrical checked out OK. Temperature split was only 2Â° differential indicating that the system was indeed. Advised Greg that recharging the unit will only result in it being low again in a unknown period of time due to us not knowing how big the leak is or where it is exactly located. Greg did decline a leak dye injection into the system and would only like to charge it up for this one time only. Charged approximately 5 pounds of refrigerant into the system and found that there was a pre-filter and a 5 inch filter which is not recommended for the systems airflow
Preformed ac maintenance on 2018 kenmoore.
Collected 1000 by credit card. The balance due of 6345 will be paid by financing
Performed Furnace diagnostic on 1985 RUUD heater. Upon arrival homeowner stated that the system was just maintained about a year ago and was told everything was OK. Now it appears at the system is working intermittently but they only really use it in the morning but the last two days it was nonfunctional. Began my troubleshooting and conducted a safety inspection on the furnace and found many points of concerns. 1. Furnace had shut down after about five minutes and found that filter inside of indoor blower cabinet was really blocked up with With Dust and debris due to it being a washable filter it needs to be cleaned out every month 2. Spark ignition box appears to not be sending power to spark igniter. Although does at certain times. 3. Indoor blower motor has oil leakage coming from its bearing and will lead to it locking up or overheating. 4. Airflow was measured on Furnace and found that it was 0.88 WC total which is heavily restricted for a furnace 5. Gas line also was directly r
Heating Maintenances Performed Upon arrival systems are working and operational. I began my maintenance in the attic by performing a duct leakage inspection. I then proceeded to the air handler units, split attic access. I checked and tightened electrical connections. I inspected the heating components for proper operation and wear. Condensates lines were inspected for proper drainage. Static pressures and temperature splits were taken. Filters have been changed at this time. Blower housing and wheel was inspected for balance and dust build up. Air supply was measured. Inspected safety switches as well as inspected home for fire and carbon monoxide detectors. I then proceeded to the outdoor units, I broke them down and cleaned them by flushing the coil of debris and dirt. I checked refrigerant pressures and measured amp draws. I checked for wear and tight connections on the units. Upon inspection of the indoor air handler units I found there to be no form of electrical protection on
Upon arrival performed maintenance on heating system. System is a heat pump. Client decided to do heating, signed client up with membership, now we come out before summer time for ac. Filter is really restricted, maybe hasnâ€™t been changed in 4 years. Declined replacement of filter, will purchase own. Compressor has start up amps of 112/118, hardstart kit will help with high start amps. Opened up condenser and washed out coils. Dusted off all electrical components. Secondary motor control in range. Refrigerant levels good. Ducting is good strapped and sealed. System is operational upon departure . Home owner left home, sent recommendations over.
Upon arrival performed hvac system. Indoor blower wheel is beginning to get dirty. Pulled blower wheel out and cleaned inside of furnace dusted everything out circuitboard and electrical connections. Flame sensor has a lot of oxidation buildup, client said he will replace flame sensor when it starts giving them problems. Filter was extremely dirty replaced the client provided. Client will use his own surge protector. System static pressure in range. System is operational upon departure.
Summer AC Maintenance Performed Upon arrival system is working and operational. I began my maintenance at the outdoor condenser by breaking it down and cleaning with water and coil solution, removing dirt and debris. I inspected electrical components for wear and tight connections. I checked refrigerant pressures and charge. I tested system amperages. I then proceeded to the indoor furnace unit. I measured temperature splits. I checked condensates for proper drainage and safety. Filter was changed. Inspected electrical to ensure tight connections and monitor wear. Inspected blower compartment for dust and dirt as well as proper balance. Upon inspection of both units I found there to be no form of electrical protection, recommend having surge protection added to both units to protect electrical components. Upon departure system is working and operational.
Tech arrived on site. Unit was installed in 1996. No power to stat. FAU had been bypassed.. found the condensate pump to be full and not operational. Homeowner will order one on amazon. Evap coil and filter are clogged. Belt on motor Should be replaced. Unit is on the old refrigerant. Homeowner is interested in a new unit.
Performed AC maintenance on a 2017 Maytag system. Cooling temperature split is 22 degrees. Indoor blower is clean and amping in range. Outdoor coils were chemically cleaned. Fan motor is amping in range. Primary start control is failed. Starter is in ok shape at this time. Refrigerant levels are ok at this time. System was cycled before departure.
Upon arrival performed maintenance on two air-conditioning systems. Opened up condensers and completely washed out coils. Verified refrigerant levels are in range. Primary and secondary motor controls are in range. Tested amperage is on compressor and fan motors both in range. Tested fuses. Replaced three standard filters. Recommended adding booster kit to bigger system. Ducting is fully strapped and sealed correctly. Thermostats are in working order. Systems were reset tested and fully functional and departure.
Arrived on site to perform combo tune up on 3 year old Lennox equipment. Cycled system for heating and cooling. Checked indoor and outdoor unit electrical and system components. Cleaned indoor unit heating compartment and blower assembly. Indoor blower motor is clean. Checked heating safety components all working accordingly. Cleaned flame sensor. Merv filter should be replaced soon homeowner will be ordering on amazon and replacing. Cycled system for cooling. Checked outdoor unit electrical and system components. Primary motor control is in good condition. Secondary motor control is within range. Amp draws for compressor and condenser fan motor are within range. Pulled condenser fan motor and thoroughly washed out condenser coil inside and out. Cycled system, system is fully operational upon departure.
Performance tune up and service for the cooling system. Measured temp splits and checked filter. Verified refrigerant charge. Adjusted damper for kitchen. Set thermostat for 1stage heating to reduce gas bill. Cleaned outdoor condenser coil. Inspected air scrubber. Tested outdoor electrical loads and controls. Inspected condenser fan motor.
Surge protector installation