Excellent, Quality service provided. Jorge was very professional and highly skilled!
Micheal explained everything well and diagnosed the issues with the cooling and heating. He was on time did what was needed and cleaned up everything afterwards.
The best service in town.
The service tech was knowledgeable, he kept me updated on everything he was doing, he was very thorough in the work he had to do to get our extremely dirty furnace and air conditioner clean. He was also friendly, polite and followed COVID rules.
He was prompt clean and knowledgeable. He review the system and gave all options on how to proceed.
Very pleased with service and professionalism.
My unit works better than it ever has!
Great and expeditions service!
Tech arrived on site. Unit was installed in 1996. No power to stat. FAU had been bypassed.. found the condensate pump to be full and not operational. Homeowner will order one on amazon. Evap coil and filter are clogged. Belt on motor Should be replaced. Unit is on the old refrigerant. Homeowner is interested in a new unit.
Performed AC maintenance on a 2017 Maytag system. Cooling temperature split is 22 degrees. Indoor blower is clean and amping in range. Outdoor coils were chemically cleaned. Fan motor is amping in range. Primary start control is failed. Starter is in ok shape at this time. Refrigerant levels are ok at this time. System was cycled before departure.
Upon arrival performed maintenance on two air-conditioning systems. Opened up condensers and completely washed out coils. Verified refrigerant levels are in range. Primary and secondary motor controls are in range. Tested amperage is on compressor and fan motors both in range. Tested fuses. Replaced three standard filters. Recommended adding booster kit to bigger system. Ducting is fully strapped and sealed correctly. Thermostats are in working order. Systems were reset tested and fully functional and departure.
Arrived on site to perform combo tune up on 3 year old Lennox equipment. Cycled system for heating and cooling. Checked indoor and outdoor unit electrical and system components. Cleaned indoor unit heating compartment and blower assembly. Indoor blower motor is clean. Checked heating safety components all working accordingly. Cleaned flame sensor. Merv filter should be replaced soon homeowner will be ordering on amazon and replacing. Cycled system for cooling. Checked outdoor unit electrical and system components. Primary motor control is in good condition. Secondary motor control is within range. Amp draws for compressor and condenser fan motor are within range. Pulled condenser fan motor and thoroughly washed out condenser coil inside and out. Cycled system, system is fully operational upon departure.
Performance tune up and service for the cooling system. Measured temp splits and checked filter. Verified refrigerant charge. Adjusted damper for kitchen. Set thermostat for 1stage heating to reduce gas bill. Cleaned outdoor condenser coil. Inspected air scrubber. Tested outdoor electrical loads and controls. Inspected condenser fan motor.
Surge protector installation
Arrived on site to perform fall tune up on a package unit that was not heating. Upon arrival spoke to home owner of what was happening and she stated 2 days ago they had a vivid thermostat installed by there company. They stated system was working fine and and after they had new thermostat installed system would not work or turn on. They called support line and they had the, trouble shoot over the phone and over the company told them itâ€™s there system and not thermostat and to call another company to diagnose issues. Upon arrival saw thermostat was really poor installed and was all lose as they didnâ€™t use Anchors to hold up thermostat so screws are lose and thermostat itself has a lot of movement and play and advised if thermostat falls off could risk and could create a short. Found thermostat was not getting voltage. Checked breaker for unit and was good and not tripped. Went on roof and inspected electrical compartment and connections and wires. Found system not operating. Jumped
Arrived on site to diagnose a 1994 Rheem system. Client has 3 system here but weâ€™re are only looking at 1 system for the bedrooms. Client stated he barely moved in 5 years ago and has yet to use system and once he did try to use system heater was not operational. He stated he was checking to make sure all wires were good and connected properly. But decide to call us out. Inspected electrical compartment and found condenser thermostat wires were not connected to board and hanging in compartment. Jumped system at control board and system did not operate. Found voltage coming to system. Found 24v at board. System is calling for heat but induce is not turning on. Found inducer motors is not getting power motor and found board itself spins not sending command to start heating operation. Advised client of findings and would have to replace control board first to continue my evaluation and ensure no other issues. Inspected system and found igniter white and a over range thatâ€™s itâ€™s rat
Upon arrival performed maintenance on package unit. Found system to be dirty in and out of cabinet. Evap coil was dirty, performed a clean and sanitization. Blower wheel was pulled apart and cleaned and sanitized. Adding a phenomenal air purification system. Indoor motor is in very good condtion. Heating cabinet was very dusty inside of burners and components, made sure to clean. Amperages throughout system good. Circuit board has a burnt spot near terminals, did not have surge protector to install. Advised client next visit we can bring one out at a discounted add on price. Filter was washed off. Systemmis in operational mode.\ - Dirty blower wheel / cleaned - dirty evaporator coil / cleaned - added whole home purification system. - dusted off all electrical components System was reset tested and fully functional upon departure.
Performed heating tune up on 2 1 year old heat pump units. Cycled for heat. Checked indoor and outdoor unit electrical and system components. Checked attic and ducting. Took temperature splits. Checked outdoor unit electrical and system components. Amp draws are all within range. Primary motor controls are in Good condition. Secondary motor controls are both within range. Pulled off condenser fans and thoroughly washed out condenser coils inside and out. Went over recommendations. Cycled system, system is operational upon departure.
Upon arrival performed maintence on older intertherm furnace. Pulled out motor and caging, cleaned and dusted inside of furnace cabinet off, there was extreme amounts of dust, vacuumed and got rid of. Motor is over amping over manufacture specs. Evap coil is really dirty and requires advanced cleaning. Restriction through dirty coil can cause motors to over run. Secondary motor controls have been replaced. Refrigerant levels are good, r22. Amperages are about 60% to max levels . Energy bills in summer are around 150 running full time. Recommmend replacing system due to age and efficiency. Motor leaking oil. Outdated refrigerant. Filter was replaced. 1. Dirty evap coil 2. Dirty blower wheel 3. Indoor motors leaking oil 4. R22 5. Heat exchanger has a lot of heat impingement System was reset tested and functional.
Arrived on site to perform FAU maintenance on 16 year old carrier system. System is original to home. Upon arrival homeowner mentioned that he has noticed lately that the system does not appear to be heating all that well and would also like that checked. Cycled system, system fire up and went through proper heating sequence. Flames kicked on and remained on for about 1 minute, but indoor motor never kicked on. Checked unit electrical and components. Circuit board is sending out proper voltage for fan motor to start up, but motor does not kick on. After troubleshooting, found that medium speed on fan motor is no longer operational. Hooked up motor low speed. Motor is now kicking on with heat, but system goes into high heat lock out. System is heating, but it shuts off after it goes into high heat due to high temperature in unit. Blower motor has leaked out quite a bit of oil and is pulling in high amperage draw. Motor should be replaced. Condensation Lines do not have any condensation
Inspected the system for problems
Replace existing system with listed equipment.
Performed AC/furnace maintenance on 37-year-old system