They have helped us a few times when we've had problems at the office and are very proficient. They have always found the problem quickly and fix it at a very reasonable price!
Replaced thermostat under a part only warranty. Performed fall inspection on two systems. First unit downstairs gas furnace Trane. Check the electrical components amps on furnace. Found return short on return air. Also found one flex return duct by fireplace insulation coming off and ducts going to wall returns leaking at ceiling were duct connects. Recommend cleaning on system but not before returns are corrected so it doesnâ€™t pull dirt from attic into system. Upstairs unit heat pump checked electrical components and Freon levels. Washed out condensing coil. Capacitor for compressor and condenser fan motor duel run still within six percent range. Disconnect for air handler was not installed with unit when it was installed.
Ran water down evaporator drain is clear at this time. Sink drain backing up. Customers calling a plumber. Sealed boot for vent above kitchen refrigerator. Will need to check airflow during heating maintenance of system. Unit is on and running at this time
Cleaned out dryer vent. Included before picture and after video leading outside(no clogs)(no restrictions). 7-16-2020 Informed mrs. Tuttle of restricted laundry room exhaust duct noticed from attic. Lessened restriction, but not like new as metal was severely bent (before picture included).
Vickie W equipment
Mike May part find
Tammie pad, air handler, etc pickup
Tammie condenser pickup
Trane parts pickup
Found Restriction In txv on evaporator coil. Will email estimate for replacement evaporator coil and TXV. Will also email estimate for replacement of entire air handler
Found fuse blown for control board, checked control wiring and found no issues. Replaced fuse, tested equipment. System ran 35-40 minutes until thermostat was satisfied. No further issues.
Principal Pain and Spine Consultants. Coil/ txv install