Frank was awesome in explaining what was wrong and documented everything with pictures. He was not trying to sell me on everything little thing that could be done, But was helpful in explaining what really was broken and needed to be fixed soon or today. He was honest, respectful, kind and went out of his way to make the experience fantastic. I highly recommend him and his company. I was also extremely pleased and excited that the day I called I got someone out to fix the problem that day. That was impressive.
Am so appreciative of the quality of time and expertise that went into the installation. Beginning with my initial call that was answered on a Saturday night followed by a Sunday consultation and Wednesday installation, Everyone with Adon provided exceptional customer service. The owner is fully involved and truly wants to do a great job for the customer. Am also pleased to support a local business vs a behemoth company where only sales matter. Many thanks to everyone at Adon for their kindness, assistance, professionalism and quality of service.
Would recommend him to anyone needing service.
Quick response, friendly and professional. Didn't feel rushed or pressured. I would use this company again and will recommend them to everyone I know.
Very thorough, professional and clearly explained. Highly recommended.
Adon was a wonderful company to work with. They were quick, helped to explain things, took their time to figure out the problem, and gave their honest opinions on what options we had to fix the problem. I would recommend them to anyone.
Frank was fantastic! He made sure we understood everything and answered all questions throughout the entire visit. He went above and beyond to ensure our units were serviced and that everything looked great.
A blessing to know a company that hires honest and dependable employees
Had a great experience today and received valuable information.
I couldn’t be happier with the service provided by Alex. They were willing to price match a quote from another company and Alex went above and way beyond to take care of our system and even trouble shooting an issue that wasn’t his problem. He wanted to make sure everything was perfect before he left. Additionally, it’s rare to find someone so professional in both their appearance and customer interaction and someone who communicates so well. He really explained everything clearly and you could tell he takes pride in his job and work ethic. I can’t say enough nice things about him. He even honored the agreed upon price even though I know he could have charged us way more for the time he spent. It was so refreshing to meet someone so honest and friendly. Thanks Alex and thanks Adon!!!
Professional air conditioning installation. Remove a 20 years old AC and installed a brand new TRane system, AC installation in Howe, Texas
AC REpair in old air conditioning system. Upon arrival system was not running. I discovered that some wires going to the board were loose. After reconnecting the wires the unit would come on and run. During my inspection I found that the capacitors for the heat pump had failed and so had the hard start kit. I replaced them per the customers approval. The system is cooling at this time.
AC Repair in Denison, Texas. Upon arrival system wasn’t coming on. Thermostat had no power going to it. The issue was a corroded wire going from the breaker to the contactor inside of the air handler. I cut the corrosion off the wire and re installed it into the contactor. System is cooling at this time.
AC Repair. Unit had a fire in the disconnect box on the weathermaker unit. It this time I cannot make any repairs until an electrician can come out and verify that the high voltage wires are ok and sake to use. R22 old unit went bad, time to be replaced.
Air Duct Cleaning. Before and After pictures of duct cleaning performed in Mckinney, Removed allergens and bad smells
Ductwork repair. Tied into existing Return Plenum, cut in a new Return Duct using R6 Flex 14” Duct, boot, and Grill. Add VIP Annual Preventive Maintenance (includes 2 preventive Seasonal Maintenance and 10% off future parts/repairs, and priority service with discounted service dispatch charges) Washed Coil inside out on outdoor Heat Pump Everything is functioning properly at this time
AC repair in Denison, Texas. Found the unit frozen.After this time the fan has been turned on to help with the thawing. Freon pressures were low. The unit was installed in February and was most likely never charged correctly. At this time I added a pound of Freon to the system to acquire a good temp split and move the equipment out of the freezing zone. The unit is now cooling properly.
Customs home air conditioning installation in Celina, Texas. Beautiful day and expert new construction installation
AC Maintenance, tune up. Performed cooling maintenance on a 2015 Lennox heat pump and air handler. During my inspection I found that the capacitor on the outdoor unit was getting weak. I informed the customer of it and he wants to wait to replace it at this time. Everything else is functioning properly at this time.
AC Expert in Mckinney, Texas. Adon Complete Air Conditioning replaced ductwork and old air conditioning and heating unit. Customer now cooling with right air flow and efficient system.
AC Expert Installation in Anna, Texas. Adon Complete Air Conditioning replaced an old Lennox system for a brand new Trane heat pump system. Cooling efficiently for years to come.
Ductwork repair. Birds destroyed the dryer vent . Adon Complete Air Conditioning opened ceilings, repaired dryer vent. Cleaning air duct equal health house
AC Repair in Melissa. Found blower motor seized. The unit is sending the proper signals to turn on but it is stuck. I could not get pricing for the motor replacement at this time but once we get through to the supplier we will provide a cost to the customer. The unit is out of warranty. It was installed in 2010
There is a piece of insulation inside the boot duct on the grill. Systems were ran without filter in one of them. And the other filter on the other unit was completely plugged drywall dust and dirt .Recommend both systems be thoroughly cleaned. Cleaning evaporator coil in place, pulling and cleaning blower assembly and duct work. Scaffolding will have to be brought in to be able to reach living room vents. Removed filter in the one unit and put downstairs up against the stairs. The other one is still in the attic where someone left it. One is a 20 x 25 x 4 and the other one is a 20 x 25 x 1
Best AC repair in Richardson. Compressor was not coming on. Found a bad buss fuse causing the system to not get the proper voltage supply. This is a 3 phase system so i could not replace the disconnect. Replaced and now system is cooling at its best.