Michael really polite and friendly. The issue has fixed perfect and his performance detail.
Ensured gas line was tightened and bubble tested. Replaced return flat register. Added foam tape to refrigerant entry in return platform.
Arrived on site to perform fall tune up on a 1999 American standard system. Furnace located in garage. Client stated he did not want attic and ducting inspected advised itâ€™s part of tune up and ask itâ€™s fine not to checked duct work. Filter was dirty and replaced client supplied his own. Blower assembly and wheel dirty creating stress on motor. Recommend cleaning assembly to reduce stress and high amp on motor. Motor is leaking oil from over working And pulling 8 amps when max rated at 12. Indicating Motor has Indefinite wear and could fail in future. Recommend replacing blower motor to extend life of system. Heat exchanger has heat impingement at this time no cracks found. Found igniter really low on rang and could fail in future. Safety flames sensor is Oxidized and has burnt spots from self wear over past years of operation. Could fail due to condition itâ€™s currently in. Recommend replacing flame sensor and igniter to prevent heat not operating properly. Evaporator coil good
Include bubble wrap closet walls and sheet metal platform skin.
Upon arrival performed maintenance. Outdoor system was opened up and washed out. Amperages on compressor are good. Refrigerant levels and temp splits are very good. Subcool and superheat in range. Indoor moto lesking oil.customer has home warranties. System is 2 years old. Dusted off and blew out all dust from electrical components. Circuit board good. Secondary motor control good. Primary motor control good. Customer replaced capacitor. 20x25x1 filter was replaced. System was reset tested and fully functional upon departure.
Estimate for system replacement in Aliso Viejo
Airconditioning service in Aliso Viejo
Total system furnace tune up and maintenance in Laguna Woods.