Jimmy Garcia did a through job. He was very informative.
Tech guy was very knowledgeable, understanding and helpful
The service and the technician were excellent. Enjoyed
Driving, giving a call back later.
Replacing plenum made of insulation , Replaced return plenum as before didnt have one. Cleaned blower wheel and added merv rack. Coming back Monday for replacement options. Or Wednesday to do an advanced coil cleaning. System is very dirty and needs advanced cleanings .
Upon arrival performed maintenance. System is extremely dirty inside. Blower wheel needs advanced cleanings. Gonna add a 5 inch filtration kit. This will give the system 90-95% of filtration. Gonna replace both plenums. Add sheet metal plenums and not insulation plenums. Surge protectors in working order .system is operational just extremely dirty.
Upon arrival unit was operational. Checked amps they were in range, condensation line was free and clear of debris and temperature rise was in range. Checked safety switches to make sure they were operating properly. Blower wheel was free of oil and debris. Filter wasnâ€™t dirty, upon departure unit was operational and heating.
Arrived on site to perform spring tune up on a 2010 carrier units. Client stated no issues and runs. Cycled both unit and are operational. Washed both units inside and out. Units were both really clogged up from dirt and dog hair. Found both fan motor leaking oil and over amping in range. Advised they can fail from over working. Checked primary Staters and both are pitted from age and operation.checked both Second motor Control and found one for upstairs unit is bad and should be replaced to keep unit running. Downstairs one was good. Checked start up and run amps and found both start up are in range just high and we want to reduce it to preserve compressor from hard start up. Run amps are high but in range. Checked pressure on both units and found down unit to have a big refrigerant restriction as pressure were out of range. Upstairs unit was cooling but was low on charge. Advise due to the age it have and how pressure are they could possibly have a leak present but unit is still coo
Client stated noisy condenser -Upon arrival , condenser was operating normally and sounded good -Amperage draw on compressor and fan motor were at prop levels -Refrigerant levels are within range -Condenser coil was rinsed off -Filter was changed -Tried multiple times to kill power and restart unit but it never made a loud noise -If it is the compressor the client is hearing then that is just normal operation -System is working properly
Performed diagnostic on unit. Has basically already diagnosed unit on last visit and homeowner knew what the problem was as well. Was waiting on home warranty to fix the issue as that is what he pays for, but at this point he is fed up with them and wants it fixed. Unit is low on refrigerant, which is why itâ€™s not cooling. Homeowner wants to only recharge it for now and see if unit can make it through summer, and will deal with it in the winter time. Recharged unit with 4lbs of r410A refrigerant to bring unit back to proper operating pressures. Unit producing perfect 20 degree split. Homeowner knows there is no warranties with refrigerant. Cycled system, system is operational upon departure.
Arrived on site to diagnose a no cooling unit. Client stated he moved in 5 years ago and heâ€™s been having the unit shut off every other year so thought it was a fuse. Tried to cycled down stairs nothing. Client has a home alarm system that he has his thermostat connected to and thatâ€™s how he controls it all from his phone. Found nothing was operational at the home alarms system. He did have a separate thermostat. Found batteries low. Advised he needs them replaced. Jumped in attic inspected electrical compartment. Found power was there and just just in normal Stand by. Inspected thermostat on wall. Found low voltage fuse as going to thermostat. Found thermostat on wall was not operating properly. Jump Ac on from the thermostat wires at the wall and unit was operational. Tried to turn on from alarm systems and still did not work. Advised him his issues is there thermostat on wall is not working. So home alarm system is not controlling the thermostat on was since itâ€™s bad. Showed c
Client stated no cooling -Condenser fan motor is seizing up and very rusted and needs to be replaced -Contactor is not providing constant voltage, cutting in and out, chattering, needs to be replaced -Capacitor is a little out of range and replacement was recommended but not needed -Fan motor and start were replaced -Amperages draws taken after repairs are at proper levels -Refrigerant is also at the proper levels -AC is currently cooling
Arrived on site to perform spring tune up on. 2 year old unit. Client stated no issues. Cycled unit on and operational. Washed condenser coil inside and out. Unit was really dirty. Checked electrical compartment. Primary starter is good. Secondary motor control is good as well. Fan motor is good and in range of amps. Compressor start up is good and in range. Run amps are good as well. Checked pressure and unit is holding a good charge and cooling hole good. Found no protection on either unit. Recommended protection as well to protect from electrical surges and power outages that can damage or even short out systems and components. Unit is cooling at 19 degrees. Cycled unit and went over how unit is running and conditions and recommendations. Clips aware and did hold off for now. Cycled unit and is operational upon departure. Client did renew maintenance plan yearly. Client Happy we came out today.
Arrived on site to perform diagnostic on a 2004 airflow unit. Client stated unit is old and has been in home for 3 years and has maintenance it. Unit was running and recently unit started making loud noises and then would stop at times and then run okay other times. Advised client wounding inspect how unit is running and condition. Inspected electrical. Found secondary motor control is completely bad. Unit was only operational due to a old compressor booster that was barley turning it on but wouldnâ€™t run right out new one in to turn unit on. . Stater was burnt Up from age and operation in past years. Booster kit was old but was some what still operational. Fan motor has dried up oil spots from it leaking. Motor is pulling max amps and is going to start to over amps from working at its max. Could fail in future. Run amps on compressor are pulling 16.5 and max rated at 20. Advised due to age and condition unit can get to max when it get really out outside and advised compressor is on b
Arrived on site to perform diagnostic. Upon arrival, homeowner was under the impression that we were doing maintenance an wants both unit to be serviced. Advised that call was scheduled as a diagnostic as it seemed like upstairs unit was not working. Stated that his filter was extremely dirty and he replaced it and it feels like itâ€™s been working better and would like both units maintained. Went over maintenance costs and maintenance program. Homeowner like the idea of the maintenance program and signed up on yearly maintenance program. Office to call and schedule maintenance. No appointment date or time was given or promised.
Arrived on site to diagnose 2 no cooling 2017 unit. Client stated units are new as home. He has not gotten them serviced since. He stated downstairs is not cooling and upstairs unit make a loud squeaking noise at time. Had him cycled both and upstairs ran. Downstairs compressor was not on. Inspected electrical compartment and components. Found secondary motor control on both unit to be bad. Downstairs was bad on compressor. Upstairs was bad on fan side and fan would not turn on at time. Compressor was not running at all and did not produce cold air. Put in new one to test found both operational and cooling now. Both Staters are good. Fan motor are good unable to tell if they were leaking as client put wd40 on. But are in range just working hard due to unit being dirty and not maintenance in the past 5 years. Found pressure okay but look like both units are running hard. Could be airflow restriction or just unit just working hard as pressure seem okay just bit off. Units are both now c
Arrived on site to perform AC diagnostic on 2006 carrier condensing unit. Upon arrival Juan stated that they moved into the home in 2017 and They have never done service or maintenance. just recently they noticed a buzzing at the outdoor condensing unit. Begin diagnostic and found that due secondary motor control was defective on fan side and compressor side terminal. These component Typically fails for an underlying reason. Installed new component and compressors was on thermal lock out due to overheating. Condenser fan motor was over amping using a total of 1.6 A. Starter was burnt and pitted on contact points. Lastly system was slightly low on R22 refrigerant charge possibly it may have always been low from installation or has a small microleakage within the system. Presented full diagnostic report with Juan and he is aware of all current and possible failure points within the 2006 unit. At this time they do not plan on living in the house too much longer and would like to just do a
Upon arrival performed diagnostic on lennox unit. Found system to kick on for AC, but condenser fan motor was stuck in place. Shut power off to unit & proceeded to check electrical components, found secondary motor control compellty flat. Replaced with a tester & system kicked on at normal operational. Indoor secondary motor control is out of range, indoor blower motor leaking oil. Client decided to do the very minimum repair to get system up & going. System is operational upon completion.