Appreciate your company coming back to fix the vent.
Had a few quotes from several HVAC service companies, and the technician at Cool Air seemed the most knowledgeable and even more was in tune with our needs and didn't try to upsell.
Marvin came through with your normal thorough and professional service.
Had a post install checkup and found a couple things that needed adjustment.
Tech was cordial and knowledgeable
Easy fast affordable
I loved that Michael took the time to explain what he did. He also explained what to expect next. He was very personable and made it easy to talk to. I also really liked that he knew our service history and I didn't have to tell him.
Michael Pierson was very professional, courteous and respectful. Punctual, efficient and very knowledgeable about their available products and services.
Routine maintenance. As always polite, competent, and efficient.
Arrived on site to perform spring tune ups on a 2017 Goodman unit. Condenser located in back yard. Furnace located in garage. Client stated no issues. Cycled unit and was cooling. Washed condenser coil inside and out. Primary board was good. Secondary motor controls is good and in range. Compressor start and run amps both good. Fan motor was good and in range in amps. Checked refrigerant pressure and are good and cooling home at 22 degrees. No protection on high efficient communicating systems. Inspected unit before unit. And found filter dirty and replaced. Blower assembly is good and motor is good. Evaporator coil good drain lines are draining. No protection on unit. Recommend adding surge protectors on unit to protect units from electrical surges and power outages that can damage or even shot out systems or components. Went over all findings and recommendations With client. Client is aware and did declined recommended work. Cycled system to ensure system operating. System is ope
AC Maintenance, upon arrival system working and operational. I began at the outdoor condenser, took system panels off and cleaned condenser coil, system was heavily impacted with dirt and debris. Inspected fan motor for leakage or play, cleaned electrical compartment, checked and tightened connections. Tested system amperage and refrigeration level, all functioning properly. Tightened indoor furnaces electrical components and connections. Swapped filter customer had on hand, inspected safety switch and condensate lines. Checked blower compartment for dirt and debris, checked blower motor for oil leakage. Recommended outdoor surge protection on unit. Upon departure system is functioning and operational
Adjusted the return grille fines to reduce the vibration of airflow passing over the metal.
Full system replacement
Tested cooling system and performed tune up. Replaced filter. Recorded temperatures and measured voltages and motor loads. Tested controls and verified charge. Cleaned inside condenser and washed coils.
Upon arrival performed maintenance. Indoor motor is in good condition. Circuit board and electrical connections very good. Outdoor system was washed out. Syste, refrigerant charge subcooling and superheat in very good standing. Merv 16 filter was replaced. Amperages throughout system very good. Condenser fan motor good. Electrical fuses good. Primary motor control good. Secodarynmotor control in range. System was reset tested and fully functional upon departure.
Heating and cooling maintenance and cleaning
Ac diagnostic on a Lennox furnace in Laguna Hills, Ca.
Doing a single system air conditioner maintenance house in Lake Forest
Furnace repair with system enhancement here in Lake Forest
Annual spring air conditioner maintenance on Lennox unit
Heating Diagnostic on American Standard Furnace
Performed routine spring maintenance in lake forest. Installed surge protection and ss2 switch
Heating maintenance on Carrier Furnace
Diagnostic in Lake forest