Really nice, professional, and outstanding service!
Brian made u very happy to go with cool air I am happy to go with cool air 👍👍
Brian was also nice & answer all my questions I also give him a 10 👍😀
I give u guy a 10. Very good job !!😊😊
Performed AC maintenance on a 2016 Goodman condenser. Filter is clean. Cooling temperature split is 19 degrees. Blower wheel is clean and spinning well. Duct runs are sealed. Condensate lines are clear, condensate pump is in good condition. Outdoor unit was deep cleaned. Starting components were measured and recorded. Outdoor amp draws are good at this time. Refrigerant levels are in range. Outdoor unit is not electrically protected. Customer requested a heating check, verified heating temperature split at 30 degrees. System was cycled and off at end of appointment.
Upon arrival performed maintenance on heating system. We installed about 4 years ago. Ducting is in very good condtion. Condensation pump in working order. Filter is beginning to get dirty. Dusted off all electrical components. Circuit board and electrical components good. Offered to replace surge protector that client has up in attic, client has power strip connected to furnace. Offered to have surge protector that comes with system warranty. Client denied. Went over checklist with client. System is operating at normal operations, passed inspection. System was reset tested and fully functional.
ESA AC MAINTENANCE. Found system operational upon arrival. Customer approved replacing m1616255 Hepa filter. Coil is clean. Blower is clean. Duct ok. Pump ok. Washed condenser coil. Amp draw ok. Motor control ok. High voltage line switch ok. Freon is ok. Bearings ok. Unit operational upon departure.
Fall Maintenance 12/20/2018
Fan Maintenance 12/2/2018
Fall Maintenance 12/3/2018
Heater maintenance in Garden Grove.
Doing paperwork for install
Working in the city of Garden Grove this morning evaluating a 30 year old furnace.
Referral customer on furnace estimate!
Estimate on system for home