During my twenty point heating inspection, I started with the thermostat. Giving a call for heating, and going to furnace to start maintenance. Temp rise of 40-70 needed, I got a temp rise of 44. House heats up to designated temperature. I checked out blower motor of any dirt or debris and itâ€™s clean. Hot surface igniter not cracked or having white spots. Flame sensor still working good, no need to be cleaned. Ducting done correctly, and all runs intact. Inducer motor is working high amps. House heats good and ready for winter.
Technician arrived to perform furnace tune up -Igniter and sensor cleaned off -Amperage and resistance are good -Filter will be replaced next visit -Electrical connections tightened -Heating elements are all working properly and efficiently -Ducting is intact and not leaking air -Phenomenal air was installed to combat seasonal allergies -Client renewed comfort club membership
Arrived on site to perform AC diagnostic on 1997 York condensing unit. Upon arrival Richard stated that system was fix five years ago and he believed that the compressor was replaced. Now he states that it just blows warm air in the house. Began diagnostic and immediately found the compressor was not on. Duel secondary motor control checked out properly and starter looked OK. Found that compressor start wire was completely melted off of terminal connecting to compressor. Due to the severity of the Burnt terminal I was unable to reconnect with a new female fitting due to the pin connector being deformed from high amps. System has severe oxidization due to it being close to Ocean. Ultimately pin connector are damaged on compressor, this would have to be swapped out. R22 is no longer manufactured as of 2020 and will result in this becoming a very expensive repair for 1997 system. At this time Richard will be going on a trip to Europe for three weeks and will not be using the system so rec
Arrived on site to perform commercial AC diagnostic on heat pump condensing unit from 1997. Upon arrival client stated that system is operational today but there are times when he does not turn on at all or pump any cold air into the building which results in it becoming 80+ Degrees inside the show room. Proceeded to roof and found unit was operational. r22 condenser coil was replaced in 2019. Inspected evaporator coil and found that it was heavily covered in dust and debris due to no filtration inside of the unit and lack of maintenance. Measured amperage for compressor and found that it was extremely high indicating that the compressor is overworking and is at higher risk of going off on thermal overload on really hot days as well. Measured refrigerant pressures and found that they were in range although R22 was completely phased out January 1, 2020. Ultimately during the visit system was operational and cooling, system is past design life and any component at this point is at high r
Check System Static Pressures Check all Safety and Limit Switches Clean Condenser Coil Duct Leakage Inspection Remove Debris from the Condenser Check Refrigeration Pressures Perform Visual Inspection and Clean Service Panel Measure Starting Amperage of the Compressor Tighten Electrical Connections Measure System Amperage and Voltage Flush Condensate Drain Lines Measure Temperature Difference Vacuum Furnace Return Air Grille Clean in Place Blower Compartment Inspect Blower Wheel for Proper Balance Monitor Air Purification System Apply UV Protective Coating on Condenser Perform Energy Usage Calculation Test Condenser Pressure Switches Check Thermostat for Proper Operation / Calibration
Performed heating and cooling maintenance on a 2019 ACPro Gas furnace and Bryant AC. Heating sensors and switches were cleaned and tested. Filter was changed today. Heating temperature rise is I. Range. Heating components and controls are in range. Outdoor unit was deep cleaned. Components and controls were measured and recorded. A corrosion inhibitor was installed today. System is operational at end of appointment.
Arrived on site to perform diagnostic on 5 year old Day N Night unit. Homeowner had the system replaced 5 years ago but can no longer get a hold of the company that installed it. He replaced his older system and also the lineset running underground because he would always have to recharge the old system until they located the leak in the lineset. Now his new system started to have trouble cooling down the home a couple weeks ago. Cycled System for cooling. Unit kicked on normally and started operating. Gauged up to system to check refrigerant pressures. Let system run for a while to get heat load. System does have a refrigerant charge, but it is definitely low on refrigerant which is causing the unit to not cool the home down. System has developed a refrigerant leak in either the indoor or outdoor coil, or the lineset. Went over findings and recommendations with homeowner, as well as possible future repairs associated with a leak once it is located. Homeowner wants to hold off on any r
Upon arrival performed maintenance on air conditioning system x2. Condenser fan motor on 5 ton system is over amping. Compressor Amperages are beginning to get close to max amps. Refrigerant levels are in range, filters are completely dirty, did not have any replacements . Tested primary and secondary motor controls are both in range . Washed outdoor coils and inside of condenser. Indoor blower wheels are beginning to collect dust levels. System does not have distribution boxes, return ducts are tapped into side of furnace. Dusted off all electrical connections. Systems do not have condensate saftey switches on coil to prevent any water damages. Ducting is sealed properly and strapped up correctly. Systems are working and cooling, running inefficient, systems at aged up pretty well. Standard filtration on systems. Client did not have time to go over systems has zoom meetings. Will call to go over systems.
Upon arrival performed diagnostic. Found I comfort thermostat to be bad. S 30 is on back order, comfort sync is next up. Client would love to speak to his wife about it. Thermostat needs to be replaced. Thermostat keeps going on and off. Outdoor system needs maintenance extremely bad coils are very dirty.
Removed panel to confirm timer on the system for the condenser
Performed routine fall maintenance on 2 payne furnaces in newport beach
Armstrong Air furnace and air conditioner maintenance
A.c. coil clean in Newport beach
Carrier complete system tune up.
Estimate add a/c