Upon arrival performed maintenance on air conditioning system x2. Condenser fan motor on 5 ton system is over amping. Compressor Amperages are beginning to get close to max amps. Refrigerant levels are in range, filters are completely dirty, did not have any replacements . Tested primary and secondary motor controls are both in range . Washed outdoor coils and inside of condenser. Indoor blower wheels are beginning to collect dust levels. System does not have distribution boxes, return ducts are tapped into side of furnace. Dusted off all electrical connections. Systems do not have condensate saftey switches on coil to prevent any water damages. Ducting is sealed properly and strapped up correctly. Systems are working and cooling, running inefficient, systems at aged up pretty well. Standard filtration on systems. Client did not have time to go over systems has zoom meetings. Will call to go over systems.
Upon arrival performed diagnostic. Found I comfort thermostat to be bad. S 30 is on back order, comfort sync is next up. Client would love to speak to his wife about it. Thermostat needs to be replaced. Thermostat keeps going on and off. Outdoor system needs maintenance extremely bad coils are very dirty.
Removed panel to confirm timer on the system for the condenser
Performed routine fall maintenance on 2 payne furnaces in newport beach
Armstrong Air furnace and air conditioner maintenance
A.c. coil clean in Newport beach
Carrier complete system tune up.
Estimate add a/c