Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
On time, thorough service.
Checked no cooling and blower noise, found failed blower motor bearings. Replaced 1/2 hp blower motor and capacitor. Wired new motor, checked direction. Started and checked amp draw. Checked refrigerant charge and temperature drop across coil.
Checked no cooling complaint, checked air filter ok, set thermostat to cooling, found blower running but no outdoor, checked outdoor unit, found open dual run capacitor. Replaced run capacitor. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Performed Quality Assurance On recently Installed Amana System. Did not need to replace the Humidistat. Homeowner was concerned that it may have been part of the reason the system stopped working the night after the install. Spoke with Luis who said this was not the issue. Completed the Quality Assurance Checklist Form in System. Reviewed installation and system with Homeowner. Need to check the Wiring for the Humidistat when we return for the Six Month Inspection and make sure Humidistat is working properly.
Found unit off, blower off but compressor running, found condensate pump tripped, vinyl tuning blocking pump float switch, cut tubing to prevent blockage, also during visit found faulty humidistat, we will provide a manual humidistat at no cost during 6 month Or quality assurance call
Removed old equipment. Installed new brackets for new condenser. Installed new 90% percent gas furnace. Reconnected vent pipes, gas. Ran new line set and evacuated down to 230 microns. Leak checked all connections. Relocated humidifier. Installed new ez trap and condensate pump. Tested with water. Ran vinyl to sewage line. 19 delta t. System operating perfectly at time of install.
No ac, previously coil iced up, when arrived to location inspect coil, coil is clear, set stat to call for ac, both indoor and outdoor units running, cleaned outdoor coil to get better reading r22, discussed options with customer since unit is low in r22, customer want to add refrigerant for today and have home consultant to come out tomorrow for replacement options, added 2 lbs of r22 to get good pressures, 225/75 with suction line temp 48 runijg at 8 super heat target super heat is 9, and 17 sub cooling discharge temp 100,,,, split ok supply 51 return 75,,,amp draw om motor and compressor ok
Found boiler running properly at time of service, customer complained of having to turn thermostat all the way to 90 degrees for it to turn on. I did find unusual activity with it as well. The thermostat also did have a 6 degree offset to the actual set point, I replaced the thermostat proactively per Joe D, cycled thermostat 3 times to verify operation. I programmed the thermostat as well.
Upon arrival found unit low on charge. Added refrigerant and dye. Recommend maintenance plan
Upon arrival found leaking coil pan. Pan needs replaced . Venting 2" will need to be removed . Lineset cut and condensate cut in order to make repair . Along with pump down and evacuation. There may be additional charges when testing out the unit. When we make the ac repair home owner needs heater certification as well. Ac replacement of pan is no longer needed, customer states the issue has stopped and no leaking has occurred. Performed heat certification. Inspected duct work , electrical wiring and components, function and performance and heating system, combustion testing and tubing. Could not clean condensate pump due to it being hard piped in. Heating system is running to manufacture specifications.
Made all repairs but aquastat. Combustion testing results 8.7 o2, co 0, eff 83, co2 6.7. 5/18/18 update: Replaced aquastat and aquastat sensor well. Rewired and tested. System is operating and functioning at manufacture specifications.
Adjusting mixing valve and tested hot water. Hot water temp is 118F. No charge for this visit.
We will disconnect, and remove the ignition module. We will replace with a new Honeywell ignition module. We will test to ensure the boiler is operating properly. All work has been performed and tested.
Replaced air vent and thermostat. Set and tested . System is running to manufacture specifications.
Made air vent repairs and adjusted water pressure regulator. System is running to manufacture specifications at this time.
Found power to aquastat and power to intermittent pilot module but unit was not starting. Moved connection on intermittent pilot module for draft damper and unit started. Every time connection was moved unit would start and stop. Intermittent pilot module requires replacement. I was able to get unit running and up to temperature for now but part requires replacement. No charge call.