Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Great technician—Super knowledgeable and personable. It was a pleasure dealing with Kurt.
Performed precision peco heat pump tune up on Goodman heat pump system. 12x20x1 air filter is clean. Heat pump is 24,000 btuâ€™s. Checked all electrical conections and components. Recommend installing an ez trap for condensation drain protection. Checked refrigerant pressures and temperatures at indoor and outdoor units. Tested emergency heat. Gave customer an estimate to move the thermostat over to the knee wall and install an Ecobee. Also checked over the garage area to price out a ductless mini split install. Heat pump system is working fine at time of service.
Heat tune Up for 80K BTU Furnace with bypass humidifier. Replaced 16x25x1 filter. Cleaned flame sensor. Checked hot surface ignitor resistance. Checked temp rise. Checked all electric motors and components. Cycled HEAT at thermostat. Combustion test: GOOD. Checked gas pressure. Used foam tape to fix tear at suction line insulation near outdoor equipment. Re caulked hole. Humidifier serviced. Replaced pad cleaned housing and verified humidifier operation. Set damper to winter position. Completed Gas Furnace Inspection Form. System is operating safely at design conditions at the time of this maintenance.
No ac . found wet switch off and system down . when i checked high voltage / good . then i checked 24 / found 3 amp fuse blown for 24 volt transformer . checked wiring and found wires for wet switch shorted to ground . i fixed the wiring the replaced the fuse . aux pan had water in both front and back corners . i checked the coil pan to find systems cabinet had water in it from coil to blower . i checked coil pan for cracks / none . under the coil part of the system the pump up was in the middle of the coil were its only thin metal . the pump up was pushing the pan up right at the condensate outlet . the pump up had a rubber pad under it . i used band to hang coil part of system then moved pump ups that were at the coil side to the outside edge where there's thicker metal . i left straps on for extra support . i let the fan run for 20 mins to dry the water up in the unit. i then blew threw drain line to make sure nothing was clogged then tested out . system seemed to run fine and drain
Found open wet switch caused by humidity. Pan was dry. Replaced Wet Switch. System is operating well at the time of this service.
Found wet switch was tripped with no water in pan. Wet switch tripped possibly beacause of very high humidity in the attic. Reset wet switch and system came right on. Did however re pipe drain beacause the drain that the installers originally pipped into is a very long run. Pipped into a secondary drain that goes straight out to the gutter and tested with water. A/c system is working fine again, can not prevent a wet switch from tripping from humidity in the air. System will take into the night now to cool down,
Lifted air handler by strapping on both ends. Shifted pan to cover entire airhandler. Added piec of plywood to right (return) side if air handler to support feet. Added cork pads to feet to ensure proper pitch of air handler. Tested drain and ensured it did not leak at front return did corner.
Nomad attic unit, found wet switch tripped so,e condensation inside pan, check drain ok noticed some gaps between air handler and panel tape bottom of air handler to seal connection, tried to slope drain line, noticed air handler is not level correctly, system is working and draining correctly, return visit is required to tried to move auxiliary pan so it covers entire unit
Found after talking to customer that the system was more than likely low on charge. First checked that there was adequate water pressure in the geo water loop. Had 45 psi on the inlet side which is good. Found oil around air coil in water furnace geothermal. Checked 410a refrigerant pressures they were 193/66. System is low on charge. Started to call around to locate part. Will need to get back to customer after coil is located with a repair quote.
No cooling. Wet switch was tripped. Some water in pan. Dried pan. Verified drain visually at termination. Cycled system in cooling. System is operating well at the time of this maintenance.
AC Tune up 4 Ton Amana AC system. 17F temp split. Replaced filter. Both coils are in good condition. Drain/EZ trap ok. All electric motors and components ok. Compressor amps/indoor amps/outdoor voltage ok. Refrigerant pressures/subcooling ok. Tstat/cycling ok. All field and manufacturer wiring ok. System is operating well at the time of this tune up.
Performed cooling maintenance, replaced media air filters. Blew out condensate trap and drains. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioners, checked refrigerant charge and temperature drop across coil.
Performed cooling maintenance, checked air filter ok. Cl eztrap and drain. Checked voltage, amperage and electrical connections, measured capacitor values. Shut off humidifier for summer. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Performed precision heat tune up on a/c gas package roof top unit. (2) 16x24x2, and (2) 18x24x2 filters are clean. Checked all electrical conections and components. Tested all capacitors. Checked belt for blower motor is ok. Burners are rusted and corroded. Performed combustion test. Visually examined heat exchanger. Tested operation of thermostat. Roof top unit is getting older but is still functioning at time of service.
Found basement zone valve is put into the open position beacause valve does not work correctly and is tight when opening manually, recommended replacement of just the basement zone valve with Honeywell propress valve. Will need to drain and purge boiler. Also will replace both basement and 1 st floor thermostats with Honeywell t4 thermostats . Beacause zone valve is broken, this causes circulator pump to run consistently and pump hot water to the basement zone.
Checked no heat complaint, found heat pump locked out. Customer has no idea when or how long the lockout occurred. Accidentally cleared code. Lockouts reset and the heat pump started. Checked refrigerant charge ok. Checked voltage, amperage and electrical connections. Performed quality check. Not sue why mini split lockout out. If it lockouts again we need to get code.