Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Great technician—Super knowledgeable and personable. It was a pleasure dealing with Kurt.
Heat Tune up on Trane Air handler. Homeowner has abandoned Space Guard high efficiency filter and is instead using a 20x22x1 filer which is serving to protect blower and coil. 37F temp rise with OAT of 64. No strip heater is installed. Buderus boiler serves as secondary heat source. Indoor coil and blower in good condition. Outdoor capacitors fine at this time. 230 volts at contactor in good shape without pitting. Suction and liquid pressures at design numbers for 64 OAT. Ffhf
Performed heating maintenance, checked air filter ok. Serviced humidifier, cleaned and replaced water panel. Started and checked operation, set humidistat to auto. Cleaned burners and flame sensor, inspected heat exchanger. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches. Performed combustion test. Checked operation and temperature rise.
Performed heating maintenance, cleaned burners and flame sensor, inspected heat exchanger. Checked boiler pressure and temperature, adjusted boiler pressure to 20 psi. Inspected venting. Started boiler, measured fuel pressures. Tested limit and safety switches. Performed combustion test.
Performed heating maintenance, checked media air filters. Cleaned burners and flame sensors, inspected heat exchangers. Checked voltage, amperage and electrical connections. Started gas furnaces, tested limit and safety switches. Performed combustion test. Checked operation and temperature rise.
Found that tenet said when oil boiler kicks on sometimes she can smell exahaust. Found some soot in the boiler. Boiler could be cleaned. She said she did not see any smoke in the house just could smell it when it first kicks on. Called landlord let him know we will need to come back to perform the maintenance. Sent him over pricing in an email. Boiler needs cleaned but is not extremely sooted up.
Performed precision a/c tune up on trane heat pump system. Replaced 20x22x1 air filter. Checked all electrical conections and components. Blew out condensate drain drain. Checked temperature split at indoor unit. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at time of inspection.
Checked no cooling complaint, found wet switch tripped but no water is in the pan. Reset wet switch, started air conditioner and checked refrigerant charge and temperature drop across coil.
Performed 6 month inspection on mini split system for the basement, and performed 2 precision a/c tune ups on 2 amana a/c systems. Cleaned washable filters on mini split system, replaced 2 Aprilaire 413 air filters on 1st and 2nd floor a/c systems. Blew out all condensation drains. Checked temperature split on all a/c systems. Checked refrigerant pressures and temperatures at indoor and outdoor units. Systems are working fine at time of inspection.
Performed Quality Assurance on Daikin Mini Split system. Reviewed installation with homeowner. Tested unit in both heating and cooling modes. Completed checklist form in system.
Installed new txv at air handler. Also put down 3/4 plywood in the attic for walkway. After installing new valve, pressure tested and leak checked at 200 psi nitrogen. Put system on vacuum pump and pump system down to 400 microns. Released charge pulled back in condenser and performed quality assurance inspection. Temperature inside was a little cool during testing process only 62 degrees. Checked all electrical conections and components. Checked refrigerant pressures at outdoor unit. They were 206/ 104 with a subcooling of 26 and a super heat of 15. Covered outdoor fan and pressures were changing with fan being covered. System is working fine at time of service. 24x24x1 air filter is clean.
Reclaimed and removed old equipment. Leveled new condensate pad and installed new Amana condenser with new disconnect and whip. Flushed lineset and brazed in with nitrogen. Installed new Amana air handler and brazed in with nitrogen. Pressure tested to 300 and evacuated to 132 microns. Reconnected electric with new disconnect and tied in low volt wires with ez trap and wet switch safteys. Reconnected supply and return ducts and sealed. Reconnected condensate lines. Installed new Honeywell t6 thermostat. Went to test system and found bad txv from factory. Will return to replace and test again.
Reclaimed and removed old equipment. Installed new daikin heat pump on new leveled pad and ductless head. Installed new whip, disconnect, and surge protector. Installed new lineset and flared into both units with flare tite seals. Pressure tested to 400 psi and checked with bubbles. Evacuated down to 65 microns. Replaced all linehide and installed new pump for condensate. Tested system operation. System running perfectly at time of install.
Performed ac tune up check electrical low and high ok replace air filter check blower and coil flushed drain ok check outdoor unit refrigerant pressures capacitor and contactor ok noticed condenser fan motor pulling 1.5 amps and rated at 1.5 informed customer and recommended having system replace bill to come out on Wednesday at 10 am for new system replacement attic
Daiken mini split unit not working, upon arrival found unit off, after talking to customer, they said unit was not coming for cooling or heating, set unit for heating and 86, unit came on check supply and rerun temp supply 120 return 70, explained to customer that mini split ac mode does not operate when outdoor temperature is below 50 but also by having dirty filters and blower housing unit runs below freezing and prevents the unit from coming, blower housing/wheel and coil needs to be cleaned, and also unit need to come off the wall to insulate both lines behind unit, if new piping is required we will informed customer additional cost will be required if new piping is needed, emailed proposal for repairs removed indoor unit from wall insulate lines and clean blower wheel, also we will be sending proposal for new system replacement
Performed ac tune up check electrical low and high ok replace air filter, flushed drain test pump check blower cap ok check split, check outdoor unit refrigerant pressures capacitor and contactor ok, recommend adding hard start kit to unit quoted but customer would do it next year, also performed water test water has 10 grains of calcium and magnesium chlorine levels are in the middle emailed customer proposal for water treatment systems