Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed Precision Heating Tune Up on Gas Fired Boiler with Single Zone. Removed and cleaned Burners/Pilot Assembly. Inspected Heat Exchanger. Tested Expansion Tank to insure it had Air Pressure. Put system in operation and completed Combustion Analysis. Measured Supply and Return Water Temperatures while system was running. System had not reached temperature upon completion of tests. Manually checked the Water Temperature Cut-Off to insure it was shutting the boiler off. Burners are starting to rust but all channels are clear. System is operating to standards at this time.