Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed Precision Tune Up on Gas Fired Boiler. Removed and cleaned Burner assembly. With burners removed, inspected Heat exchanger. Cleaned Flame Sensor and Spark Ignitor. Inspected Electrical Controls on unit. Tested expansion tank for air pressure. Reassembled burners and put system into operation. Performed Combustion Analysis on Boiler and measured Supply and Return Water Temperatures, while monitoring Water Pressure. Measured Amp Draw on the Circulator pump. This was a cold start on the boiler as it has not been used for the season yet. Lowered the High Limit Cutoff temperature to test and ensure it was shutting the boiler down. Cycled the boiler several times to ensure it was firing off properly. While boiler is operating, due to age and overall efficiency would recommend begin planning for replacement of the system before any major component or heat exchanger failure occurs.
Checked no cooling complaint, filter just replaced. Started air conditioner, checked refrigerant charge, found low on charge. Topped off refrigerant and balanced by superheat.
Performed Precision Heating Tune Up on Gas Fired Boiler with Single Zone. Removed and cleaned Burners/Pilot Assembly. Inspected Heat Exchanger. Tested Expansion Tank to insure it had Air Pressure. Put system in operation and completed Combustion Analysis. Measured Supply and Return Water Temperatures while system was running. System had not reached temperature upon completion of tests. Manually checked the Water Temperature Cut-Off to insure it was shutting the boiler off. Burners are starting to rust but all channels are clear. System is operating to standards at this time.