Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
I have nothing but praise for all of your employees. Shawn was efficient, knowledgeable and courteous. He makes a challenging situation bearable. Thanks
Installed two thermostats had to use one of the extra thermostats, serial 415535142060, added transformer and wired into thermostat wire to give power to the thermostats and control the heat only.
Performed Quality Assurance on Amana AC/Air Handler Cut In install. Reviewed installation with homeowner. Checked all duct work to make sure it was sealed completely. All dampers are open and all registers are open. Ran system and tested EZ Trap Safety and Wet Switch safety. Filled and tested condensation pump. Added a union to condensation Drain to allow access to remove pump. Secured vinyl tubing to condenser pad outside. Installed 1â€ Drain Plug for the Auxiliary Drain Pan. Completed checklist form in system. This install passed the QA inspection. Installers did a great job! Homeowner would like information sent to her for the Maintenance Plan. She has a Gas Boiler/AC & Air Handler systems.
Cleared condensation drain line customer has a high velocity ac system, spacepak air handler match to Lennox outdoor, customer explained last time they used the ac, they started to noticed water coming from ceiling above where the unit is located, ac hasnâ€™t been in use since then, upon arrival turn ac on and check filter, refrigerant pressures ok, check drain started to noticed slow drain, provided an estimate to cleared drain customer approved drain cleaning, drain line is clear and draining correctly now. Ran unit and check temp split ok, noticed lot of air leaking on supply plenum right at the location where customer thinks water was dripping, canâ€™t get to actual unit due to location. An access has to be crated for us to sealed exposed air. Provided an estimate to install ez trap and wet switch. System is from 2006 other option is to replace system. Office will get back to customer to schedule tune up on the ac.
Installed new air handler in attic above dining room. Installed new pan and decking for unit. Installed new trunk ductwork and sealed and insulated. Installed new feeds in each room according to proposal. Attached all flex duct to trunk and sealed. Installed new 20x20 filter grill with 16in flex and 20x20 filter. Installed new lineset and line hide. Installed new disconnect and surge protector. Pressure tested and evacuated below 500 microns. Installed new outdoor on leveled stone and pad. Installed new 1 1/4 conduit from panel into attic area. Ran new wire for indoor air handler, installed new disconnect, made all necessary high voltage connections. Installed new 110v light and outlet for condensate pump. Installed new slim condensate pump and vinyl tubing. Installed new ez trap and wet switch to break R. Installed customer supplied nest thermostat. Checked all supply registers, all supplyâ€™s getting good air flow. Tested condensate pump. Tested system in cooling, system running prop
Performed heating maintenance, replaced air filter. Tested electric back up heaters. Checked voltage, amperage and electrical connections, measured capacitor values.Started heat pump, calculated btu output. Tested defrost cycle. Checked operation and temperature rise across coil
Performed six month quality on 3 head mini split, cleaned air filters. Checked voltage, amperage and electrical connections. Started heat pump, checked operation and temperature rise across coils. Checked refrigerant charge.
Replaced blower motor and surge protector, reprogrammed for new motor, tested operation. System is working correctly at this time.
System is out on b1 error, blower surge protector not tripped, tried with removing surge blower still not coming on, checked the blower control module and it is bad, also smoked the motor with the surge.
performed precision heat tune up American standard gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Found flame sensor pitted , recommended replacing flame sensor. Replaced flame sensor. Also added an ecm surge protector for blower motor. Checked temperature rise. Performed combustion test, gas furnace is working fine at time of inspection.
Performed quality assurance inspection on daikin mini split. Added screws to end caps on snow legs to keep the end caps from popping off. Went over all wiring including at the electrical panel. All wiring is correct and secure. Ran mini split system in cooling mode and obersved condensation draining outside. Checked temperature split at indoor head was 22 degrees. System is working fine at time of quality assurance check.
50% deposit required to order equipment and materials. Installed a new Daikin mini split unit on a new plastic pad with crushed rock underneath. Installed a new disconnect box with a surge protector and electrical wiring to unit. Ran new copper lines and new line hide down the outside wall. Caulked hole and around linehide head. Hung mini head centered on wall. Couldnâ€™t do start up due to electrician running the wrong sized wire. Balanced not collected.
Performed QA on Daikin Ductless System with 1 Outdoor and 3 Indoor Units. Ran all three units together and poured water into each drain pan to ensure they were draining. Measured 20 Degree Temp Split on each unit. Completed checklist form in system. Reviewed installation with homeowner. Homeowner is going to email his PECO Information over for us to submit the rebate. This Install Passed the QA Inspection.
Installed a new Daikin 3 head mini split system. Ran linehide to indoor heads. Mounted heads and drilled hole to exterior. Flared and connected linesets, drain lines, and electrical. Pressure tested system and then evacuated system. Ran new high volt wire to panel and wired into 25a breaker. Sealed all penetrations. Tested system. Working great at time of install. Will need to return to finish linehide.
Checked noise from blower, found blower wheel grinding at the hub. Need to replace blower wheel or unit. Please schedule a sales appointment.
Performed precision a/c tune up on American standard a/c system. Replaced 16x25x1 air filter. Checked all electrical conections and components. Blew out condensate drain and tested pump with water. Checked temperature split at indoor coil. Recommend installing a reme uv air scrubber for better air quality. Checked refrigerant pressures and temperatures at indoor and outdoor units. A/c system is working fine at time of service. 5/26/21. Installed reme halo air scrubber and Honeywell t6 WiFi thermostat. Tested and connected to WiFi