Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed quality assurance inspection on daikin mini split. Added screws to end caps on snow legs to keep the end caps from popping off. Went over all wiring including at the electrical panel. All wiring is correct and secure. Ran mini split system in cooling mode and obersved condensation draining outside. Checked temperature split at indoor head was 22 degrees. System is working fine at time of quality assurance check.
50% deposit required to order equipment and materials. Installed a new Daikin mini split unit on a new plastic pad with crushed rock underneath. Installed a new disconnect box with a surge protector and electrical wiring to unit. Ran new copper lines and new line hide down the outside wall. Caulked hole and around linehide head. Hung mini head centered on wall. Couldnâ€™t do start up due to electrician running the wrong sized wire. Balanced not collected.
Performed QA on Daikin Ductless System with 1 Outdoor and 3 Indoor Units. Ran all three units together and poured water into each drain pan to ensure they were draining. Measured 20 Degree Temp Split on each unit. Completed checklist form in system. Reviewed installation with homeowner. Homeowner is going to email his PECO Information over for us to submit the rebate. This Install Passed the QA Inspection.
Installed a new Daikin 3 head mini split system. Ran linehide to indoor heads. Mounted heads and drilled hole to exterior. Flared and connected linesets, drain lines, and electrical. Pressure tested system and then evacuated system. Ran new high volt wire to panel and wired into 25a breaker. Sealed all penetrations. Tested system. Working great at time of install. Will need to return to finish linehide.
Checked noise from blower, found blower wheel grinding at the hub. Need to replace blower wheel or unit. Please schedule a sales appointment.
Performed precision a/c tune up on American standard a/c system. Replaced 16x25x1 air filter. Checked all electrical conections and components. Blew out condensate drain and tested pump with water. Checked temperature split at indoor coil. Recommend installing a reme uv air scrubber for better air quality. Checked refrigerant pressures and temperatures at indoor and outdoor units. A/c system is working fine at time of service. 5/26/21. Installed reme halo air scrubber and Honeywell t6 WiFi thermostat. Tested and connected to WiFi
Performed 6 month inspection on amana a/c system. Replaced dirty Aprilaire 413 air filter. Checked all electrical conections and components. Blew out condensate drain and tested condensation pump. Checked temperature split at indoor unit. Checked refrigerant pressures and temperatures at indoor and outdoor units. A/c system is working fine at at time of inspection . Also notice expansion tank bladder is blown out and is stressing on shark bite coupler recommended replacement. Provided estimate for repair.
Service call that there was water leaking from the Furnace. Upon arrival found water collecting around the Furnace and in the bottom of the Blower Cabinet there was some water. Found one of the Drain Tubes had become loose and water was leaking from the tubing. Reconnected tubing and tested to ensure it was a tight fit. Blew through drain lines to ensure they were clear. Dried water and inspected furnace components . Put system in operation and tested.
Tuesday 10/27: Returned to site and installed new Control Board. Completed all wiring connections. Installed new ECM Motor Surge Protector and completed wiring. Started system and Control Board was displaying B1 Error Code. Removed Blower Motor and inspected Module. Found Blower Motor had also been damaged in Power Surge and will need to be replaced. Will order new Blower Motor and schedule return visit to replace. Monday 10/26: Service call that the Heat was not working. Was informed that they experienced a power surge and the system stopped working after that. Found thermostat display on. Set thermostat to heating to test. Found no display on the Air Handler Control Board. The outdoor unit was running but the indoor unit was not operation. Also found ECM Motor surge protector had blown. Removed surge protector and directly plugged the Motor back in. The motor was receiving the correct High Voltage but the Control Board was not sending out any low voltage to the motor. The Control
Performed precision heat tune up on American standard gas furnace. Replace 16x25x1 filter. Cleaned collector box drain tube. Cleaned flame sensor observed some pitting but not enough to justify replacing. 46 degree temp rise. Performed combustion analysis. Furnace is working fine at time of inspection.
Turned water supply off to the home and drained down old water heater. Disconnected piping and venting for water heater and removed. Installed a new 50 Gallon Propane Powervented Bradford White water heater in an Auxiliary Drain Pan elevated on bricks with a Water Alarm in the Drain Pan. Adapted piping and installed a new Expansion Tank and new Shut Off Valves for the Hot and Cold Lines. Reconnected Venting and adapted Gas Piping. Tested gas piping to ensure there were no leaks. Filled water heater and purged lines of air. Put in operation and measured Water Pressure and temperature once water heater had fully heated. When removing old water heater found water lines heavily clogged with sediment and buildup. After installing new Water Heater tested water for hardness. Water was testing at 12 Grains Hardness. Would recommend installing a Water Treatment/Softener system. Also noted that water pressure was high on the water heater. Adjusted the regulator down but could not lower water p
Performed Quality Assurance on recently installed Amana Gas Furnace/AC system. Reviewed installation with homeowner. Completed checklist form in system. Recorded PECO Account number so we can process the rebates. Informed homeowners that they need to sign the E-Doc Signature. Need to bring 2-3 bags of stone when we return for Six-Month AC Inspection to fill in ground by the wall of the home where we dug up.
Reclaimed and removed old ac , coil and heater. Installed a new Amana gas heater with a new coil with a txv. Installed a new amana ac unit with rocks under a new plastic pad. Ran new copper lines from ac to coil and brazed and leak checked with soapy bubbles and 300 psi of nitrogen. Reconnected gas piping and adapted all duct work as needed. Ran a new return drop duct with a He filter installed. Ran a new fresh air flue pipe. Sealed all penetrations into the house. Ran a new electrical box with a switch and outlet . Installed a new condensate drain with a ez trap wired in and a new pump with new vinyl tubing ran over to discharge sink. Cut in a new return for the dining room and cut in to return duct. Used existing thermostat. Ac unit was installed with a new disconnect box and whip wired into unit. Installed a new Aprilaire humidifier and piped it in to supply. Ran water line to hit water heater piping. Tested unit in cool and in heat and unit is running at manufacture specifications.
Service call that the Heat was not working. Upon arrival, found system was operating and was informed that the system was working intermittently. System was not out on a Hard Lockout Code. Turned system up to test operation. Found unit very dirty and filter was very dirty. Recommended a Tune Up on the Gas Furnace. Performed Tune Up and tested combustion levels of Furnace. Inspected Electrical Components and cleaned Flame Sensor and Spark Ignitor Assembly. While testing system, found Heat Exchanger was very rusted in each burner chamber. Did not see any rust through, but due to the large amount of rust, would recommend replacement of the system before any further damage occurs. Also found when system lights off the last burner hesitates to fully ignite. When doing tune up, cleaned burners, but if the unit fails to light due to the burners, would recommend replacement of the whole burner assembly. Would need to contact Rheem to get pricing for the replacement of the Burners. System is op
Performed Precision Heating Tune Up on Propane Fired Furnace. Replaced 16x25x1 Air Filter. Inspected Electrical Components on Furnace. Cleaned Furnace Drain Lines and Condensation Pump. Inspected Burners and Flame Sensor. Flame Sensor has minor pitting beginning to form. Cleaned Sensor and it is still in good condition. Due to the moisture and corrosiveness of the Propane, the Flame Sensor will likely need to be replaced every 2-3 Years to ensure no issues with the Heating. Performed a Combustion Analysis on the system. Furnace is operating to standards at this time.