Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Quick response and follow up
Very professional and easy to work with. They did a great job. Addressed all our issues. Placed gas line extension for our new range and outdoor grill.
DiBiase and their service people run a conscientious, competent operation, and are most knowledgeable. They do what they commit and promise, with no nonsense. They are highly recommended.
He was great
He was absolutely great
Performed heating maintenance, serviced humidifier, cleaned and replaced water panel. Checked media filter ok. Cleaned burners and flame sensor, inspected heat exchanger. Blew out condensate trap and drain. Started gas furnace, tested limit and safety switches. Checked operation and temperature rise across coil.
Found Heat Pump on a hard lockout. Code 4. Gauges showed a standing pressure of 49 psi. Using leak detection bubbles, found leak at 3/4 elbow on suction side. Turned thermostat off for the night. Kurt will return to repair leak. 10/27/20. Replaced 3 ft section of 3/4â€ copper pipe. Brazed and leak checked fittings at 300 psi nitrogen and bubble checked. Vacuumed down system to 500 microns and turned off pump to made sure vaccum would hold. Added 9lbs 7ozs of 410a . Tested heat pump in heating and cooling mode. In heating mode pressures were 299/121 at 70 degrees. Heat pump is working fine at time of service.
Performed precision heating tune up on Amana Gas Furnace system. Replaced High efficiency 413 Air Filter. Cleaned and serviced Humidifier. Tested operation of Humidifier and set control to 35% and opened dampers. Cleaned all furnace drain lines and condensation pump. Pump tubing is starting to become very dirty and could potentially become clogged. Filled pump and test operation. Added Cleaning tablets to basin of pump to help clean tubing. Vinyl tubing to Sump pump may need to be replaced in the future. Removed and cleaned Burners which are beginning to rust due to the propane. While inspecting system, found a small leak on the gas fitting at the Gas Valve. Disconnected the gas piping and resealed and retightened. Tested Fittings for leaks. Performed Combustion Analysis Test on Furnace. Would recommend begin planning for replacement of the Hot Water Heater. Unit is currently 10 years old. Average life is between 10-12 Years on residential water heaters.
Performed precision heat tune up on Rheem gas furnace. Checked all electrical conections and components. Replaced 16x25x1 air filter. Checked temperature rise. Blew out condensate drain. Tested condensation pump. Performed combustion test. Gas furnace is working fine at time of inspection. Also performed a water test and found water to be 12 grains hard, explained to homeowner the benefit of a water softener with brine tank. Recommend installing a water softener system.
Responded to gas Odor from piping we just installed last week, upon arrival Check for all gas connections, found gas flange to be small leak, replaced gas flange and soap bubble all connections all connections checked out ok no leaks found, no charge warranty labor
Performed heating maintenance, replaced standard air filter. Cleaned burners and flame sensor, inspected heat exchangers. Checked voltage, amperage and electrical connections, measured capacitor values. Started gas furnace, tested limit and safety switches, measured fuel pressures. Performed combustion test. Checked operation and temperature rise.
gave Quote to install 2 gas lines. 1 for stove and 1 for gas grill.installed 2 gas lines 1 for the stove and one for the outside grill.
Performed Quality Assurance inspection on a newly installed gas furnace and ac system. Checked over entire system. All connections sealed and penetrations sealed. All wiring proper and secure. No leaks at gas line or condensate drain. Outdoor unit and disconnect are level. Did find a little bit of trash inside furnace cabinet. Removed. Everything looks great.
Performed precision gas furnace tune up on amana gas furnace. Replaced Aprilaire 413 air filter. Checked all electrical conections and components. Blew out condensate drain. Cleaned flame sensor. Checked temperature rise. Performed combustion test. Gas furnace is working fine at time of inspection.
Drained and removed old water heater. Installed new navien tankless water heater. Mounted on wall and converted to propane. Ran new copper piping and installed new valves. Installed condensate pump and ran vinyl to discharge line. Installed new receptacle. Reconnected vent. Connected gas line and sprayed all fittings in room and found no leaks. Tested water heater operation and adjusted gas flow to spec. Performed heat tune up on furnace. Checked all electrical connections and components. Tested unit in heat and performed a combustion test and checked gas pressures. Tested temp rise. Cycled thermostat. Cleaned flame sensor. Noticed burners on furnace were very rusty and corroded and should be replaced. Will contact customer with quote. Everything else on furnace looked good.
Performed Six Month Inspection on Amana Gas Furnace system. Replaced 14x24x1 Air Filter. Inspected electrical components. Checked setting programming on system. Put system in Heating Mode and performed Combustion Analysis and measured Gas Pressures. Tested system in Low Stage Heat and High Stage Heat. Tested Humidifier and humidifier was not turning on. Checked Wiring and tested for 24 Volts. The Humidistat Control does not seem to be operating properly. Would recommend removal of the existing Humidistat and installing a new Manual Humidifier Control and rewiring into system. Included an estimate for the Humidifier Control Replacement. The office will call to schedule repair.
Replacement of Two Outdoor Unit Tops. Removed condenser fan motor and reinstalled it with new outdoor top also installed new disconnect cover and silicone around both outdoor disconnects
Reclaimed and removed old ac unit and coil. Removed old heater from attic and replaced the existing drain pan. Installed a new American standard heater with an American standard coil on top. Adapted all supply ducting as needed and taped and sealed all duct. Adapted return ductwork to fit with HE filter. Installed a new condensate pump in basement for both units. Installed an ez trap and wired it into heater. Wired in a wet switch. Flushed copper lines and brazed and leak checked with nitro and soapy bubbles. Put ac back on wall brackets. With a new plastic pad and a disconnect box and electrical wiring to unit. Tested unit in all modes and performed all test out procedures.
Performed 6 month inspection on recently installed gas furnace check high efficiency air cleaner ok, check both low and high stage of heat check airflow ok combustion test on furnace cycle furnace ok check both intake and exhaust pipes ok, emailed estimates for current promotions and water system treatment water is 12 grain of hardness
Performed heating maintenance, replaced standard air. Cleaned burners and flame sensor, inspected heat exchangers ok. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches. Performed combustion test. Checked operation and temperature rise.