Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Kurt was great...very professional
friendly and professional
My problem: Heat pump gradually stopped cooling over a period af about 1 month. Service diagnosis: Very slow refrigerant leak. What was done: Refrigerant was added to immediatly restore normal operation along with a fluorecent dye to enable inspection and location of the leak at a later time. Education: Learned that as the AC cools the air it dehumidifies. (I knew this) What I didn't know was that the dehumidification is the reverse of evaporation. Evaporation cools the air. Dehumidification heats the air the same amount as the air was cooled on evaporation. So this heating effect fights the AC trying to cool until the humidity is removed. Then the temperature starts to drop. This effect is most noticeable after the AC has been off for a long time and the house is hot and humid.
Texts were very friendly, helpful and professional.
Great work as always. Honest expert recommendations, respectful of our home, efficient service. We are very satisfied!
Very professional and qualified technicians!
These guys do a great job!
Performed heat check up, gas furnace check electrical low and high check filter, clean sensor, and check burners ok, gas pressure set to 3.5 wc combustion test ok check split ok also test pump cycle furnace ok inspect exchanger customer seen exchanger condition recommended having blower clean customer wants to wait at this moment... emailed quote
Replace high efficiency filter for air cleaner 413
Performed oil heat tune up, on boiler, clean exchanger and chimney base, replace nozzle 1x80B and Also replace electrodes, clean cad cell eye and check transformer ok,, check boiler operation pump strainer and oil filter ok performed smoke test ok combustion test ok check humidifier operation for first floor unit,,,set to 35% check hot water coils working ok, also check reversing valve operation,
Performed gas heat tune up check electrical low and high ok clean sensor and burners ok replce high efficiency filter 423....check gas pressures combustion test ok check split cycle furnace ok furnace is in good working order, supply temp 126 return 78
Performed precision heat tune up on Rudd gas furnace. Replaced 20x25x1 air filter. Also serviced Aprilaire humidifier replaced pad. Checked all electrical conections and components. Checked gas pressure and performed combustion test. Cleaned flame sensor and blew out all tubing. Tested operation of pump. Rudd gas furnace is working fine at time of service.
Performed precision heat tune up on oil furnace with Lennox heat pump. Checked model 2200 air filter is clean. Replaced.85x60b nozzle. Homeowner wants to replace garber oil filter next tune up. Performed combustion test. Checked operation of heat pump in heating mode. Checked operation of oil furnace in emergency heat mode. Checked temperature rise. System is working fine at time of service.
Performed Quality Assurance On Amana AC/Gas Furnace System. Replaced 20x20x4 Air Filter. Reviewed installation with homeowner. Completed Checklist Form in System.
Performed heating maintenance, checked media air filter. Cleaned flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections. Started gas furnace, measured fuel pressures. Performed combustion test. Checked operation and temperature rise
Performed heating maintenance, checked media filter, need to replace Rp 413. Cleaned flame sensor, inspected heat exchanger. Checked furnace setup. Checked voltage, amperage and electrical connections. Started gas furnace, measured fuel pressures. Performed combustion test. Checked operation and temperature rise. Need rp 413 did not have at time of maintenance
Performed gas heat check up, check electrical low and high clean sensor and burners ok check spark igniter ok, gas pressure and combustion test cycle heaternok filter ok quoted for humidifier installation special price unitâ€™ll next month
Performed heat pump check up/inspection check electrical low and and high ok filter ok test 10 kw back up elements ok, test humidifier will need new pad, check outdoor unit refrigerant pressures ok capacitor and contactor ok test reversing 16x25x4 filter found blower cap little weak on rating customer will wait in that repair
Installed intake drain system and caulked around gasket on top of furnace, this will help with condensation issue from pipe.
Performed precision tune up on 2 York gas furnaces. Both 16x20x1 air filters are clean. Checked all electrical conections and components. Checked gas pressures, and performed combustion test. Cleaned flame sensors and blew out condensate drains. Both gas furnaces are working fine.
Performed gas heat check up propane furnace, clean sensor and burners ok check gas pressure low and high combustion test ok check electrical low and high service humidifier and replace pad test and set up to 35% test pump ok air filter ok cycle heater
Found no surge protector on ecm blower motor. Installed surge protector. Also performed precision heat up on trane gas furnace. Aprilaire 413 air filter is clean. Checked all electrical conections and components. Adjusted gas pressures and performed combustion test. Blew out condensate drain and pressure switch tubing. Checked temperature rise. Trane gas furnace is working fine at time of service.