Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Luis was awesome!
My Tenants were there and let your person into the Townhouse to do his work. They texted me after the visit and told me “all went great”... Usually, I am there and talk with the workers and would be able to give you more information...I personally have never had a problem with the workers...Knowledgeable, pleasant, focused on the job, cleaned up areas, arrived on time....overall great!
This was a follow-up check on a potential refrigerant leak. A very slow leak was discovered. Kurt showed me where the fluorescent dye was showing on an indoor coil. He then measured the system pressures and found that almost no refrigerant was lost during the 1 month elapsed period. Kurt discussed all the repair or replace options and answered my questions. I decided on a "wait and see" strategy for now. Very satisfied with how this service problem was handled. Five stars.
I had an annual checkup for my gas furnaces. The guys were very polite and professional. Luis explained everything they did and answered all my questions. Very happy with the service.
Kurt was great...very professional
friendly and professional
My problem: Heat pump gradually stopped cooling over a period af about 1 month. Service diagnosis: Very slow refrigerant leak. What was done: Refrigerant was added to immediatly restore normal operation along with a fluorecent dye to enable inspection and location of the leak at a later time. Education: Learned that as the AC cools the air it dehumidifies. (I knew this) What I didn't know was that the dehumidification is the reverse of evaporation. Evaporation cools the air. Dehumidification heats the air the same amount as the air was cooled on evaporation. So this heating effect fights the AC trying to cool until the humidity is removed. Then the temperature starts to drop. This effect is most noticeable after the AC has been off for a long time and the house is hot and humid.
Installed a new Amana gas furnace. Converted from gas to propane. Raised coil on top of a transition to get height required. Adapted and sealed all duct work. Adapted gas piping as needed and leaked checked with soapy bubbles. Ran new condensate piping for heating. Installed a new pump and new vinyl tubing over to discharge pipe. Put a horizontal flue drain kit in and adapt condensate line. Installed a new t4. Thermostat. Installed a new filter 20â€/25â€/1â€ filter. Tested in heating and cooling and walked threw with customer. Unit is running at manufacture specifications.
Found collector box leaking and rusting away at furnace. Sealed up collector box with high temp silcone and performed precision heat tune up on Goodman gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Blew out condensate drain. Adjusted gas pressures. Cleaned flame sensor, and performed combustion test. Gas furnace is working fine at time of service but has quite a bit of rust and corrosion from collector box leaking.
Installed a new Amana gas furnace. Adapted duct work as needed. Raised ac coil on to a transition to get the height required. Installed a new condensate pump with new vinyl tubing ran over to sump pump. Left hard pipe over vinyl tubing so cat wonâ€™t bite it . Put a new filter in 16â€/20â€/1â€ . Adapted and leak checked all gas piping. Installed a new t6 thermostat and walked threw with customer, unit is running at manufacture specifications. Tested in heating and cooling.
Performed heating maintenance, checked air filters ok. Cleaned burners and flame sensor, inspected heat exchangers. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started gas furnace, tested limit and safety switches, measured fuel pressures and performed combustion test. Checked operation and temperature rise When testing basement condensate, found that pump was slow to pump, the check valve has failed on the condensate pump and the discharge is pinched. Recommend replacing condensate pump and discharge.
Performed heating maintenance, replaced standard air filter. Cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started gas furnace, tested limit and safety switches. Measured fuel pressures and performed combustion test. Checked operation and temperature rise.
Found 24 volts going to contacter, but did not have 240volts passing thru. Found contacter burned up. Replaced with 40 amp single pole contactor and then went on to check refrigerant pressures. Pressures were 329/106 at 48 degrees out door air temp. Also had 22 degrees of subcooling. System is not low on charge at this point. Found washable filter inside needs washed ( homeowner to take care of it). Found a 27 degree temperature rise with not aux heat assisting it. Talked to homeowner about using a leak stop agent, at this time he wants to leave the system the way it is.
Replace air scrubber, removed failed air scrubber, installed new air scrubber. Powered air scrubber and checked operation ok.
Performed heating maintenance, checked media air filters. Serviced humidifiers, cleaned and replaced water panels. Started and checked operation. Cleaned burners and flame sensors, inspected heat exchangers. Checked voltage, amperage and electrical connections, measured capacitor values ok. Blew out condensate traps. Cleaned condensate pumps. Condensate discharge Lines are getting clogged and will not blow out clear, recommend replacing vinyl discharge lines, also wire first floor condensate pump safety. Measured fuel pressures adjusted to 3.5â€. Started gas furnaces, performed combustion test. Checked operation and temperature rise. Need to drop off filters when they come in.
Performed heating maintenance, replaced standard air. Checked v, amperage and electrical connections, measured capacitor values. Tested electric back up heaters. Started heat pump, checked btu output. Tested defrost cycle. Checked operation and temperature rise across coil.
Performed 6 month check, replaced electronic air cleaner cells with 16x25x1, can also use 16x25x4 filters. Checked voltage, amperage and electrical connections, checked fuel pressures and temperature rise. Performed combustion test. Checked humidifier, found no water going to humidifier, found failed saddle valve. Recommend installing new saddle valve on hot water side.
Performed heating maintenance, checked air filter ok. Cleaned burners and flame sensor. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started gas furnace, measured fuel pressures. Performed combustion test and checked temperature rise.
Removed old heater and replaced with Amana high efficiency condensing furnace. Converted to propane. Reconnected supply and return ductwork. Added new filter rack. Reconnected electric and gas. Leak checked gas. no leaks found. Reconnected venting. Tested system and adjusted gas pressures and airflow to specifications. Installed new condensate pump. System running great at time of install.
No heat customer has three gas furnaces, left side first floor is the one not working, upon arrival found system off, start furnace and was lock out on pressure switch problem, check venting and was restricted, also needs new flame sensor, quoted for repair customer ok, cleared intake and exhaust and also replace flame sensor, after repairs test furnace and performed combustion test cycle heater ok
Performed gas heat check up, check electrical low and high ok clean sensor and check burners ok replace air filter, performed combustion test ok check split, flushed furnace trap and test pump ok also check air scrubber we need to return to replace air scrubber membrane underway warranty
Performed heating maintenance, replaced standard air filter, cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started gas furnace, measured fuel pressures. Tested limit and safety switches. Performed combustion test. Checked operation and temperature rise.