Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
I'm new customer. Found a problem my previous provider overlooked. Repair cost was reasonable. Technician was professional, competent and courteous.
Luis did a thorough job checking over my system as well as educating me on how it works.
Chris was remarkably thorough and communicative with lots of information about options open to us. Instead of pressure to take the expensive way, he provided ideas on how to simplify and save. The service itself was excellent.
We have used many HVAC companies and found a true gem in DiBiasi! Professional, knowledgeable, courteous and prompt. We have used them for maintenance for nearly 4 years and just recently replaced our 12 year old system with wonderful success. Thank you DiBiasi!
Cut 3 in pvc exhaust stack higher and also re attached bathroom exhaust flex use pipe strap to hung flex, all connections were taped and zip tied,
removed suction valve recto seal gas Guard, and install new regular brass cap, and also install internet red link gate way to make thermostat WiFi, set up thermostat and gate way, went over settings and how to manage app from the phone customer ok
Checked condensate, read home inspector report, he stated that the inducer has water in it. Tested inducer, found no water in it started inducer, found that the bearings are failing. Need to replace inducer for first floor air furnace Need inducer for Trane model TUX100C948D2
Performed peco heat-pump check up, electric heat as back up, customer has thermostat that has no emergency heat option, replace filter 20x25x1 flushed drain test pump ok check outdoor unit 410 pressures ok capacitor, contactor needs replace, cycle unit, quoted for repairs and also new T6 WiFi thermostat
Need to work up estimates, customer has unusual set up. Mini split do 3 rooms on first floor and attic system does second floor and one room on first floor.
Installed new amana heat pump system. Installed new 16x20x1 air filter. Ran new lineset. Adapted to existing metal plenum. Installed 115 v condensate pump and vinyl hose. Pressures and leak checked system. Tested out system, system is running to manufacture specifications.
Checked bathroom exhaust, found flex is very long and trapped and the stack is at attic floor level. Need to cut stack and replace exhaust venting. Checked mini split, found poor cooling, checked refrigerant charge, found indoor eev not opening enough causing high head pressure and low suction pressure 29 subcooing and 0 superheat. Need to return with 20â€ 5â€ exhaust flex and hanging strap. Need to remove old exhaust and cut the stack higher and pitch new exhaust Need someone to look at first floor lay out and see if attic air conditioner can cool 3 rooms 2 have min splits nothing in the kitchen
Performed cooling maintenance, checked air filter, inspected cooling coil. Cleaned condensate drain and trap. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Drop off filters
Found blockage at the exhaust pipe termination outside house, quoted for repairs to clear pipe customer ok with price, cleared blockage, removed bird nest both pipes are clean now,
Performed cooling maintenance, replaced 2 standard air filters, 16x20x1, checked media filter rp413. Cleaned condensate drain and, blew out condensate traps. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioners and heat pump, checked refrigerant charge and temperature drop across coils.
Checked no cooling complaint on second floor air conditioner, checked air filter ok. Started air conditioner, checked refrigerant charge, found low on charge. Topped off refrigerant charge, balanced by superheat. Checked operation and temperature drop across coil.
New Heat Pump Installation
Performed Precision Air Conditioning Tune Up on First Floor and Second Floor Systems. Replaced all Air Filters for both Systems. Closed Damper on Humidifier and turned off at the Humidistat Control. Cleaned Drain Lines and the Condensation Pump that is with the First Floor System. The Vinyl Tubing appears to be dirty and getting debris in it. While cleaning the Pump removed Vinyl Tubing and blew through to ensure it was clear. Filled Pump and tested operation to ensure it was primping out. Checked Electrical Components on both Systems. Measured Refrigerant Charge on both Units. Both systems are running, but are doing so inefficiently. Amp Draw on each Compressor is within rating, but is slightly higher than normal. This could be attributed to the age of the Systems. The Compressors are working harder to run than usual. Do to age of the Systems, would recommend begin planning for replacement of the First Floor and Second Floor Systems. Thank you for renewing your Service Membership fo
Checked no cooling complaint, found breaker tripped, found bad dual run capacitor, also a shorted compressor on 14 year old heat pump canâ€™t read outdoor label but the unit next door is a 2 ton heat pump. Recommend replacing system due to age.