Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Service is always prompt and painless. Thanks DiBiase
He was fantastic!
Quick response and follow up
Very professional and easy to work with. They did a great job. Addressed all our issues. Placed gas line extension for our new range and outdoor grill.
DiBiase and their service people run a conscientious, competent operation, and are most knowledgeable. They do what they commit and promise, with no nonsense. They are highly recommended.
Found thermostat not bringing on auxiliary heat, bad relay in thermostat. Replaced thermostat with Honeywell t-6 programable thermostat and went over operation with tennet. Also performed precision heat tune up on amana heat pump system. 16x20x1 air filter is clean. Checked all electrical conections and components. Checked temperature rise in heating mode. Also checked refrigerant pressures and temperatures at indoor and outdoor units. Heat pump is working fine at time of service.
Reclaimed and removed old heatpump and coil. Removed old airhandler and return drop. Installed a new amana airhandler onto a new return box with a new HE filter. Modified taped and sealed all duct work. Ran new copper lines from indoor coil to new heatpump. Installed a new amana heatpump in existing location. New disconnect box and electrical wiring to unit. Installed a new humidifier and ran bypass over to supply. Tested unit in all modes and unit is working great. Ran a new condensate drain with a ez trap wired in. Ran new Vinyl tubing over to discharge pipe for washer. Installed a new condensate pump. Installed an eco bee thermostat.
Heat tune up for carrier 100k BTU single stage natural gas furnace. Checked filter; ok. Cleaned flame sensor. Verified HSI resistance and condition (56.6 Ohms ok). Cleaned secondary drain and collector box using drain gun. Combustion test ok. Gas pressure ok. 56F temp rise ok. Electric motors are mechanically sound; components tested ok. Verified operation of both thermostats. Furnace is operating well at the time of this maintenance. Mr. Pasupulati mentioned that a clicking or dripping sound is noticeable in the duct system and can be heard in various room when the furnace is running. This is a balancing issue.
Performed heat pump tune up, check electrical low and high ok, check electronic filter ok check back up heat , blower motor and cap, noticed lot of build up on wheel, would recommended removing blower housing and cleaning it, check supply and return air ok outdoor unit refrigerant pressure ok capacitor ok contactor is wearing out would recommended replacing, emailed proposal for recommendations
No hot water, found water on the floor upon arrival, check for leaks and found tank leaking, new water heater is required, quoted for new water heater and land lord accepted the repairs, we will be installing a new water heater, drained old water heater. Installed new natural gas atmospheric water heater. Adapted to exsisting water lines with 3/4â€ copper piping. Adapted to exsisting gas line and soap checked for leaks. Set new water heater in drain pan with tank alarm. Checked for water leaks. Set gas valve to hot position. Water heater is working fine at time of install.
Water leak, customer has gas boiler with indirect hot water storage tank, upon arrival customer explained what was going on, water was coming off boiler relief valve, check water pressure at boiler reading 30 psi, expansion tank was full of water, quoted to drain expansion tank customer ok, when draining tank found that water was still coming off relaid valve and pressure kept going up, isolate house pressure and boiler side, found storage tank leaking water bill into heating circuit (boiler loop) isolate boiler from domestic water, this way customer will have heat, and quoted for new storage how water tank, customer ok repairs /replacement, current condition, customer has heat but no hot water we will come back tomorrow to install new storage tank, customer paid 50% down, We abandoned the buderus tank and all the pipes going to it. Redirected the pipes off the boiler to new indirect tank. Replaced all pex piping that was for the domestic side of the water heater, added shut off valv
Second floor thermostat losing power after minutes the furnace runs, check furnace operation and system goes into high limit code and cuts power between R and C at the board contacts, check all safeties ok, increase airflow to the way it was before medium high, unit stays on for more than 15 minutes and thermostat satisfied cycle unit ok
Performed 6 month quality check, checked furnace setup. Tested water safetyâ€™s. Tested humidifier. Cycled furnace, checked fuel pressures on low and high fire. Performed combustion test. Checked operation and temperature rise.
Service call that the Heat was not working for the 1st Floor System. Upon arrival found system turned off. Turned power on to unit to test. Found System going through startup but the Gas Valve would not open. Tested Gas Valve and was intermittently receiving voltage for only a split second before cutting out and then unit would try to start again. Tested Coil on Gas Valve and removed leads to test voltage. When leads are removed the Gas Valve maintains the 24 Volts. The Gas Valve has failed internally and due to the control board only sending an Intermittent signal to the Valve, the Control Board is failing also. Would have to replace Gas Valve and Control Board. Due to age of system, homeowner is going to look into replacement of the system rather than repair.
Went over concerns with homeowner for de humidificaton and also humidification for dry skin in the winter time. Found that there was not enough room in the basement to fit a dehumidifier set up, but for a humidifier recommended installing a powered humidifier. Gave homeowner a quote to install.
Adjusted reme cells from fully open to about an 1/8 â€œ of the way open for 1200 cfmâ€™s, this should help some with the smell of the reme some. Also moved heat terminal from medium high to medium blower speed tapping for second floor furnace. This changed amp draw from 1.8 to 1.3 . Recommend to keep thermostats ethier on fan on or circulate. Told homeowner to see how these adjustments work for him. Also put dehumidifier low voltage controls to basement thermostat.
Gave homeowner options for humidifier installation. Homeowner liked the powered humidifier the best. Gave homeowner the best option with a heating and cooling membership included. Homeowner will get back to us about install.
Found when we arrived furnace not glowing hsi. Found second floor gas furnace with inducer motor running but not proving pressure switch. Used a digital manometer and found inducer motor pulling 1.8 w.c. But not proving 1.20 w.c. Pressure switch. Checked all ports condensation and vacuum tubing, all clear. Checked outside at 2â€ exahaust pipe, did not see any debris. Pressure switch itself went bad. Replaced with universal pressure switch and set up to 1.0â€ w.c. Furnace fired right up and is working properly. Explained to homeowner how pressure switch functions.
Performed heating maintenance, replaced standard air. Cleaned burners and flame, inspected heat exchangers. Blew out condensate trap and drain. Started gas furnace, performed combustion test. Tested limit and safety. Checked operation and temperature rise.
Performed precision heat tune up on 2 climate master geothermal systems. 1 system is a split system for second floor, other system is a package geothermal for first floor. Homeowner to replace 20x25x1 air filter for second floor and Aprilaire 413 for first floor. Checked temperature rise at both systems. Checked temperature split at geo well loop on first and second floor geothermal. Both were 5 degrees on well loop very good. Checked all electrical conections and components. Found mold in second floor air handler. Recommend installing a reme halo indoor air quality system. First found geo look ok as far as no visible mold growth. Checked operation of well circulator pumps. Inspected coils for rust and corrosion. Tested operation of emergency heat on both systems. Geoâ€™s are working fine at time of service.