Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Chris was very informative with my questions
Workers were polite and friendly, conscientious about viruses and keeping me safe
Awesome crew!!!! Handled the problem effectively and quickly and had heat back in within a half hour Great company
Very quick to respond and provided great service! Will definitely make our new go to HVAC company!
The technicians were courteous and professional but there were several issues with the quality of work performed that I observed after work was complete. 1. Dust and woodchip debris from a board sawed by the technician was left in a pile where it fell in our basement. 2. An elbow duct joining a main duct had a large gap that was neither screwed nor taped and one could feel air being lost through this large gap. 3. Other joints/connections in ductwork where one would expect there to be tape there was none and one could feel air being lost. 4. A new electric line that had to be run from the thermostat to the new furnace was not stapled to the ceiling joist in the basement but was left hanging. 5. Two large holes had to be drilled through our block walls in the basement to accommodate PVC pipes to the outside- The gaps left around the PVC pipes were only partially caulked on the top of the PVC from the outside but were not caulked at all on the bottom of the PVC. On the inside from the basement you could clearly see daylight through both holes and the void from the inside around both holes was not filled in at all. 6. The pump attached to the humidifier was placed directly on the concrete floor of the basement rather than on something that would raise the pump off the floor to avoid contact with any moisture. The salesman, who was also very courteous and professional, assured me the quality of work performed by his crew would surpass that of previous contractors. This is no different than other contractors especially given the price I paid, which was high. What concerns me the most is that if details like this were overlooked, what else was overlooked that I can't see directly? Given the price I paid, which was on the high end, I expected flawless service. It is attention to detail that produces an exceptional quality product in the end. I suppose only time will tell.
Installed drain kit on intake pipe, used vinyl tubing to run drain line, also cleaned gas piping inside furnace close to furnace gas valve no charge for todayâ€™s visit
Performed cooling maintenance, checked media air filter ok. Cleaned eztrap and drain. Shut off humidifier for summer. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil.
No Cooling. Outdoor 45-05 capacitor reading 0 between HERM and common and 1.2 between FAN and common. Mrs Menta approved repair. Replaced capacitor. Ran system in cooling. 17F temp split. System is operating well at the time of this service.
Customer is hearing a noise coming from ductwork, check geothermal unit found dirty filter, replaced customer supplied filter, also added water to geo loop system 40 psi, noticed compressor capacitor reading below standards informed customer about findings, customer ok repairs after repairs inspect unit check 45 supply and 68 return air temp ok, turned system off and did hear noise from ductwork, could not exactly pin point location but is between return and supply ducts, after replacing filter noise level came down to minimum, also added some drive on return box to minimize vibration
Reclaimed and removed old coil and ac unit. Installed a new amana coil on top of existing furnace. Modified supply metal as needed and taped all joints. Ran new copper lines from indoor coil to outdoor unit. Installed a new amana ac unit on a new leveled pad with rocks underneath. New disconnect box and electrical to unit. Ran a new new condensate drain with an ez trap wired in and a new pump wired in. Ran new vinyl tubing over to discharge pipe tested unit in cooling mode.
No ac, found system off upon arrival, set thermostat to call for ac, liquid line getting super hot, condenser fan motor not working also contactor pitted, quoted for repairs, new motor blade and contactor also provided price to replace indoor coil and condenser unit, customer paid 50% for the repairs, office will follow up with customer Friday morning to schedule repairs visit or system replacement visit. Repairs were not performed, customer moved forward with the installation and the 50% deposit was applied to the install.
Found that expansion tank was full of water and relief vale was leaking with about14 psi on the boiler. Found that relief valve had gone off reliving the pressure but did not seat back again. Checked pressure with a water gauge and found fill valve filling boiler right around 13 psi, which is ok. Drained down expansion tank and installed ne relief valve. Boiler as back up and working fine again at time of service. Boiler gauge on boiler is in accurate by about 8-10 psi.
Found no surge protection on ecm blower motor. Installed ecm surge protector. Also performed precision a/c tune up on amana a/c system. Replaced 16x25x1 air filter. Checked all electrical conections and components. Blew out condensate drain. Tested condensation pump. Checked temperature split at indoor coil. Checked refrigerant pressures and temperatures at indoor and outdoor units. Amana a/c system is working fine at time of inspection.
Not hot water found water heater working on just one element, found thermostats not working properly, check resistance on both elements and both reading 12.5 k ohms Quoted for repairs and also pricing on new water heater
Performed precision heat tune up on amana gas furnace. 16x25x1 air filter is clean. Checked all electrical conections and components. Blew out all condensation lines and pressure switch tubing. Checked temperature rise. Checked gas pressure. Performed combustion test. Found on start up the second time we fired furnace gas valve started to pulsate gas pressure across the burners. Also found some corrosion on burners, recommended replacement of 2stage lp gas valve and burners. Furnace is working at time of service Will install new burners and gas valve, leak check and set up to factory peramiters.2/24/21. Installed new 2 stage lp gas valve. Converted and changed orifices and burners. Performed combustion test. Also checked gas pressure. Gas furnace is working fine at time of service. Low pressure was 6â€ w.c. Could only get high pressure to 8.25 w.c. Suggested to homeowner to have propane company adjust regulator. Gas furnace is working fine at time of inspection.
Performed Quality Assurance inspection on a newly installed gas furnace. Checked over system. No gas leaks. All wiring proper and secure. Missing rubber grommet where line voltage wires go into furnace from switch and outlet box. Transition between furnace and indoor coil could have been cleaner with less tape. System working good at time of QA
Found error code E3 on Amana propane furnace; (open limit). Excessively dirty filter and loose insulation in blower compartment that was sucked against blower caused limit on blower to open. Replaced filter, removed insulation and reset limit. Cycled furnace; performed combustion analysis. Combustion analysis results ok. Customer approved of recommended surge protection. NOTE: propane tank level below 20%. Unstable flame on start up system could shut off if propane is not filled. Mr. Dallas . assured us that he ordered propane earlier this week and it should be arriving tomorrow.
Installed 80% Amana gas furnace. Adapted to exsisting a/c coil with small metal plenum between furnace and coil. Adapted to exsisting high and low voltage wiring. Adapted to exsisting gas piping. Checked for leaks. Installed 1â€ 16x25x1 filter rack inside furnace blower compartment. Replaced 8 feet of 4â€ metal exahaust piping with 2 four inch elbows. Checked gas pressure and performed combustion test. Thermostat is older and not mounted very well. Cycled on exsisting a/c but a/c canâ€™t be tested in the winter time. Furnace is working well at time of install.
Performed heat pump check up check electrical low and high voltage ok, replaced filter, 20x20x1, test back up heat ok blower cap ok, found blower wheel very dirty and indoor coil super dirty, showed customer about details, check outdoor unit refrigerant r22 pressures amp draw ok check supply and return temps ok, would recommended cleaning indoor coil, blower wheel and adding supply and return up light
No heat, customer lost heat sometime during night, found system on limit code tried to reset limit but could not get to close, check filter, filter was dirty, also blower cap reading low, blower wheel is super dirty, quoted to replaced limit and blower cap customer ok repairs after repairs were made check furnace operation and performed combustion test ok, inducer assembly makes noise from bearings, also noticed igniter does not glows 100%, informed customer about furnace condition would recommend replacing system, home comfort specialist to come out on Tuesday at 10 am