Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
We have an older solidly built Kutz home with three custom-sized in-wall air conditioners that needed replaced (2 on the top floor and 1 on the second). Definitely not an easy job!! Joe was kind enough to come out on a Sunday in the rain to measure and then researched to give us the best product at a fair price. Nathan and Chris showed up on right as scheduled to remove the old units and install the new. They encountered challenge after challenge and still managed to get those units in and functioning in one day. Nathan then came back promptly (thank you Angie!) and put the final touches in place and answered all our questions. Nothing but good to say about the DiBiase team. Highly recommended. We will definitely be calling them again next year for the other three.
Friendly service. Bryan came in and quickly went to work doing a full inspection of my ac system. Any questions I had, he was quick to provide answers if he had them, or point in the right direction for whatever else I needed.
Performed precision ac tune up on Rheem ac. Replaced 16x25x1 air filter. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. Blew out condensate drain. After talking to homeowner about comfort issue, the 2nd floor in general is where the problem area is. Homeowner would like a quote on possibly adding a second system in the attic. Called and set up appointment with the office.
Installed a new amana 80% natural gas furnace.. re connected using flex connector for the plenum new line sets and thermostat wiring for outdoor unit installed new vinyl and ez trap with condensate pump installed new whip disconnect was reused because of siding cut out still in good shape tested both the air and heat both worked great set pressures for gas and checked for leaks.. installed new comfort net thermostat . And set up for communicating systems, redlink wirless gateway installed as well. When coming back we need to bring a humidifier pad for April air 600 series. And wire in the humidifier.
Performed ac tune up, check electrical low and high ok test u,p ok new filter, recommend adding an ez trap and wet switch, check split ok outdoor unit temp is 47 check r22 pressures are 200/70 system is working as if was 85 to 90 outside, due to performance would highly recommend replacing unit,
AC Tune Up . Went to the door and rang the door bell 3 times with no answer. Homeowner did not answer phone calls from the office as well. the call will have to be rescheduled.
We will remove the existing through the wall air conditioners and dispose of them. We will install new Amana brand PTAC though the wall air conditioner units Model PBC122G00CC with cooling capacity of 11,800 btu/hr. We will install a new sleeve if needed. We will seal the unit at the outside All work is completed as specifications indicated above.
Performed precision heat tune up. System is running to manufacture specifications but does need repairs. New air vent 1 1/2 inch in size, new water feeder, and 4 floor needs to be bled of air but can not until new water feeder is installed. So gasket around domestic hot water seal is leaking and needs replaced.
Performed precision heat tune up on oil boiler. Adjusted aquastat Low side was adjusted to 140 with differential set to 25. High side kept at 180. Was set at 160 low with 10 diff. Noticed that the shut off valve for the cold water intake for the domestic hot water is leaking. We also noticed there were no mixing valve to the domestic hot water. We recommend installing to help control hot water supply and temperature. Adding the mixing valve will resolve the water leak at the shut off valve as well. Noticed leaking on one of the existing zone valves. We recommend replacing. Estimate will be attached with options. System is running at manufacture specifications.
Found vinyl tubing clogged . Replaced 13ft feet of vinyl tubing and tested operation.
Installed new oil fired boiler for family in Pottstown