Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Great job as always as your work crew is efficient
My first experience with DiBiase, is good
Kurt was on time and on the issue right away. He explained what the problems were and how much it would cost to fix each. He had me up and running quickly.
He was amazing, polite and professional, the quality of service provided by Luis was exceptional. I will be using Dibiase hvac again because of Luis and Angie in the office who was also super to deal with. Thank you, Dave Rucker
Very cordial, helpful, and most cooperative -Will return to replace frame for outside outlet
Paul, Luke and Zack were most efficient and were respectful of the fact that we are in a pandemic and wore masks when around us which we appreciated. DiBiase is most fortunate to have such capable employees, including Angie at the office.
Excellent job. Friendly and clean. Thanks
Performed heater certification on 80% Gibson gas furnace. 24x24x1 filter is dirty (tenet to replace). Checked all electrical conections and components. Checked gas pressure and performed combustion test. Cleaned flame sensor. Blower housing does rattle a little bit but is not a mechanical problem. Gas furnace is working fine at time of inspection.
Performed precision heat tune up on Weil McLain oil boiler. Vacuumed out heat exchanger and in smoke pipe. Replaced rf1 oil filter and nozzle. Performed smoke and combustion test. Ran boiler and made sure supply and return piping were getting hot. Oil boiler is working fine at time of inspection.
Performed 6month inspection on American standard heat pump. Aprilaire 413 air filter is ready to be changed ( homeowner will replace) checked all electrical components and connections. Blew out condensate drain. Checked temperature rise at indoor unit. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at time of inspection.
Performed gas heat tune up check electrical low and high ok cleaned flame sensor and inspect burners gas pressures low and high ok, replace air filter and also service humidifier new #35 performed combustion test cycle furnace ok
Performed ac tune check electrical low and high ok filter ok flushed drain check temp split outdoor unit refrigerant pressures ok capacitor and contactor ok cycle unit ok
Performed gas heat tune up check electrical low and high ok check filter, ok cleaned flame sensor and check burners, manifold propane pressure ok performed combustion test ok cycle furnace, noticed heater is a one pipe system recommend adding grill to mechanical room, currently does not have enough to supply combustion needs more air and by adding grill on mechanical room wall this will make up combustion air
Performed Quality Assurance inspection on a newly installed gas furnace and air conditioning system. Also tested heating side now that propane tank installed and connected. Checked all fittings for gas leaks. No gas leaks. Checked over entire system. Everything looks great! Guys did a great job and system working great at time of QA. Did not have a combustion analyzer to check combustion. Inside temp split of 48/68 Gas pressure inlet - 10.5 Gas pressure outlet - 9.6
Performed heating maintenance, replaced air filter. Pulled and cleaned burners, inspected heat exchanger.Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches, measured fuel pressures. Performed combustion test. Checked operation and temperature rise.
Checked condensate leak, found condensate drain clogged, cleared drain, condensate pan drained. Started air conditioner, checked refrigerant charge and temperature drop across coil
Reclaimed and removed old equipment. Installed new leveled pad, disconnect, whip, And lineset. Brazed in with nitrogen. Placed new Amana high efficiency gas furnace on furnace feet and sealed coil on top. Brazed in with nitrogen and pressure tested to 300 then evacuated down to 221 microns. Ran new intake and exhaust vents across basement to outside wall. Ran new gas line to exterior. Was not able to test heating due to gas line not being connected. Installed new ez trap and condensate pump and wired safteys to break r. Installed new return and supply ductwork and relocated to left side of unit. Tested system in cool and adjusted charge. System working well at time of install.
Checked new coil iced up, started heat pump, checked refrigerant charge, found low on charge, added refrigerant, after a pound the sub cooling started to climb. Stopped adding refrigerant, checked metering device, found a factory installed piston. Piston is either restricted or too small. Recommend replacing piston with correct size or a txv, 8-31-20 Luis re,over old piston and installed new piston pressure test system no leaks found, triple evacuation added 1/2 lb of refrigerant ran unit for 30 mins check dampers operation ok 300/128 with 20 sub cooling and 14 super heat cycle unit ok no charge
Performed Quality Assurance inspection on a newly installed air conditioning system. Checked over entire system. No air leaks present. All penetrations sealed and wiring secure and proper. Did quickly check gas line and didnâ€™t find any leaks. System working great at time of QA
Performed cooling maintenance, checked air filter ok. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started heat pump, checked refrigerant charge and temperature drop across coil.
Performed cooling maintenance, checked air filter ok. Blew out condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Installed 50 gallon electric Bradford white water heater. Cut of piping to domestic coil on boiler and to boiler feed valve. Oil boiler is in very bad condition and should not be operating. Rand about 90 feet of 10-2 power wire and installed 30 amp breaker in panel . Filled and tested water heater.