Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Kurt is Always polite and competent
I've had several uses for DiBiase over the years, and ALL of them have been timely and professional. I would recommend to anyone asking.
Kurt was very thorough and he helped us out tremendously thank you very much for your prompt attention to our problem today take care
Courteous knowledgeable personnel
Great job as always as your work crew is efficient
My first experience with DiBiase, is good
Performed gas heat tune up, check electrical low and high ok replaced filter, Cleaned flame sensor and check burners, gas pressure ok check temp rise ok combustion test ok cycle furnace check humidifier operation and recommend replacing all interior parts emailed proposal for repair and also for new humidifier
Performed precision heat tune up on 3 system. One oil boiler tune up and 2 Goodman split heat pump systems. Checked all electrical conections and components. Blew out condensate drains. Checked refrigerant pressures and temperature rise at both air handlers. Checked operation of condensation pump in basement. Replaced rf1 oil filter on boiler and 1.25x80 a nozzle. Brushed and vacuumed smoke pipe and heat exchanger. Tested circulator pump and made sure loop was getting hot. Performed smoke and combustion test. Checked operation of thermostats to engage emergency heat if thermostat was separated by 2 degrees, all systems are working fine at time of inspection.
Performed oil furnace tune up cleaning, check electrical low and high ok replaced filter, check blower cap ok cleaned heat exchanger and flue pipe, chimney base ok, replace oil filter nozzle and pump strainer, very hard to removed pump strainer two screws at the bottom of pump are also round on the heads, not sure if next time would be able to removed screws, performed Smoke and combustion test ok cycle furnace
Performed precision heat tune up on Lennox heat pump system. Replaced 15x20x1 air filter. Checked all electrical conections and components. Blew out condensate drain. Checked temperature rise. Checked operation of emergency heat. Checked refrigerant pressures and temperatures at outdoor units. Heat pump system is getting older , but is working fine at time of inspection.
Performed Quality Assurance inspection on a newly installed gas furnace and air conditioning system. Checked over entire system. Wiring proper and secure. Duct connections sealed. Venting proper. No gas leaks. System running great at time of QA
Customer stated there is no domestic hot water from boiler, found system off upon arrival, boiler is firing, check hot water side and noticed no mixing valve is present, found a manual valve was slightly open mixing with the hot water this was costing lower temp on the outlet, closed valve would recommended adding a mixing valve to regulate water temp to prevent any asking damage, also during inspection could not check boiler pressure, both valves canâ€™t be open, massive corrosion is around valves and canâ€™t not be open, explained to customer water pressure on boiler canâ€™t be checked, also expansion tank is full of water and canâ€™t be drained, due to malfunctioning of drain valve, boiler is in bad shape needs cleaning, emailed proposal, for recommendations would recommend replacing boiler
Service call the Gas Furnace was not working, and we were onsite the previous day for a Maintenance. Upon arrival found unit locked out on a 3 Flash/Pressure Switch Code. Cycled power and measured Pressure across the Pressure Switch. Found unit was not running at a highest pressure and the Inducer Motor was filling with water. Found Drain Line was clogged after the Main Furnace Trap. Cleared Drain Line and found a rubber cap was lodged into the drain. Removed and reassembled drain line. Put system in operation to test.
Installed a amana heater in existing location. Installed coil on top of heater and adapted all ductwork as needed. Taped and sealed all duct, flushed copper lines and brazed and leak checked with nitro and soapy bubbles. Installed a new amana ac unit on a new plastic pad. New disconnect box and electrical wiring and surge protector to unit . Adapted. Gaspinoing and flue piping . Installed a t10 stat. Went over with customer.
Performed gas heat tune up check electrical low and high ok filter ok, cleaned flame sensor and burners, check manifold gas pressure ok 3.5wc performed combustion test check blower cap, flushed furnace trap check temp rise ok cycle furnace
Performed oil boiler tune up check electrical low low and high ok, cleaned heat exchanger and flue pipe, cleaned chimney base, replace oil filter, pump strainer and burner nozzle, check oil pressure ok, performed smoke and combustion test check draft ok water pressure and temp ok cycle boiler ok test limit, also moved thermostat location from living room to hallway cycle unit ok
Service call that the Oil Furnace was not working. Upon arrival found system turned off. Homeowner informed me that he recently replaced the Oil Filter and Oil Pump and coupling. Put system in operation to test. Furnace was coming on and attempting to light, but would shut down after not igniting. Inspected components and found Oil Nozzle completely clogged and Electrodes very worn. Replaced Electrodes and set positioning. Installed new Oil Nozzle and cleaned assembly. Put system in operation to test. Performed Combustion Test, Draft Test, and Smoke test. Replaced 16x24x1 Air Filter provided by the homeowner. Temperature rise of Heater is very high. Measured a 110 Degree temperature rise. Supply duct work is undersized which would cause the higher splits. Cycled system to ensure it was firing properly. Would recommend a full maintenance being performed on the system. Furnace is about 25 Years old. Due to age, would recommend replacement of the Furnace.
Customer installed its own oil furnace, and canâ€™t get to start, check furnace operation and found valve at the tank not open fully, open up valve and purge line, also performed smoke and combustion test, burners is within manufacture numbers, customer will reconnect return dropped back into place,
Service call that the Heat was not working. Upon arrival found home at 61 Degrees with system turned off. Turned heat on to 70 to test. Gas Furnace was not coming on and Indicator Light on Control Board was blank. Checked Voltages and found 120Volts incoming. Found Door Switch was broken which was keeping the system off. Bypassed door switch and put system in operation. Checked 16x25x1 Air Filter. Performed a combustion test and measured Air Temperatures. System has not had any maintenance performed since 2018. Would recommend replacing the Door Switch as this is a safety feature. If the blower door is opened the system will continue to run without the door switch. If opening door to change filter need to shut power off to furnace at the switch on the unit. Included an estimate for a new Door Switch and performing a Heating Tune Up on system.
Performed Quality Assurance inspection on a newly installed 5 headed ductless system. Checked over entire system. Everything sealed properly. Everything straight and level. Wiring proper and secure. System running great at time of QA. Issues customer was having was just issues with operating system. Went over system with customer and answered questions about the financing.
Performed precision heat tune up on 2.5 ton Trane HP with a 10KW strip heater. System is operating fine at this time. All electrical and mechanical components are in good condition.TD is 22 F with a 46 F outdoor. Customer is considering converting to a propane furnace/HP when the time for system replacement occurs. He has three 120s already for the purpose of a generator.