Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
This company is very easy to use. They update you when their technician is near. They stick to the appointment time. Their technicians are competent and don’t try to upsell you.
On time and very courteous!
Performed Quality Assurance, went over system Peco account 41929-01804 system settings ok installation looks good
Performed ac check up, check electrical low and high ok flushed drain test pump check split ok outdoor unit 410 pressures capacitor and contactor ok informed customer about age of water heater would recommend repla
Performed ac check up check electrical low and high ok filter ok check split, flushed drain ok replace blower capacitor, check outdoor unit 410 pressures capacitor and contactor ok installed hard start kit app8 cycle unit ok
Performed Inspection of Burnham Oil Boiler. Removed Burner Assembly and replaced Oil Nozzle. Cleaned and reset Electrodes. Changed Oil Filter and Cleaned Assembly. Removed Flue Pipe to Clean Chimney Base and to Clean Heat Exchanger on Boiler. Reassembled and used Furnace Cement to seal around Chimney Base. Put Boiler in operation to test. Bled Oil Line of Air. Performed a Combustion Test, Draft Test, and Smoke Test on Boiler. Smoke Test was measured a Trace at 1. Combustion and Draft Tests all measured within standards. Monitored system to ensure it was Heating properly. Water pressure in System was low at about 5 PSI. Added water to system to increase pressure to around 10 PSI. System is operating to standards at this time.
Performed Quality Assurance On AC System. Taped Insulation around bottom of Return Flex. Reviewed with customer any questions/comments she had about the system and installation.
Performed 8 ac outdoor units and 7 air handlers tuneups, two systems are twin, check electrical low and high ok flushed drain test pump check split ok replace all filters, check outdoor unit pressures r22 ok capacitors and control cycle units ok for unit number #2 found condenser fan motor seized and open run capacitor quoted for repairs customer ok installed new fan motor and new run capacitor test and cycle unit ok all splits units currently are in working condition, We will return some time next week to perform all rooftop systems check ups, Replace condenser fan motor for unit number #2
Reclaimed and removed old equipment. Installed whip and disconnect, new leveled pad, new line set and 24v wire. Installed new 2 stage gas furnace and evaporator coil. Reconnected to existing supply and return ducting. Taped all seams. Installed txv and brazed joints. Pressure tested and evacuated down to 287 microns. Installed new ez trap and condensate pump. Ran vinyl into septic line. Installed new receptacle and switch. Installed length of gas pipe and leak tested. Reconnected venting. Wired low volt safety's to aux terminal on Amana board. Delta t 22. Temp rise 46. Tested combustion and adjusted gas pressures. Everything operating to specification at time of service.
Performed ac check up, check electrical low and high ok clear trap and flushed as much as possible, replace filter, 16x25x1 check split supply 51 return 72 check outdoor unit r22 pressures contactor ok found 70/7.5 reading 65/7.5 also found disconnect not operating correctly canâ€™t pull it out to shut power off to unit, there are couple recommendations, cycle unit ok
Performed Precision AC Tune Up on the Main Air Handler and the Meeting Room Air Handler which are supplied by the Chiller System. Replaced the 8 - 20x25x2 Air Filters for the Main Air Handler and the 2 - 16x25x2 Air Filters for the Meeting Room Air Handler. Checked Condition of Blower Belts and adjusted the Tension on the Main Air Handler Blower Belt. Put Systems in operation and checked Cold Water Supply and Return Temperatures on both Systems. Checked Pneumatic Control Panel and Gauge Pressures. Inspected the Air Compressor. The Air Compressor may need to be filled with Lubrication Oil and the Air Filter needs to be cleaned/replaced. Will review manufacturer specifications and follow up if needed. System is operating to standards at this time.
Installed new heat pump and outdoor unit inside we installed a new heat pump with with a new ez trap and condensate pump. We ran a new lineset and thermostat wire to the outdoor unit. Vinyl was ran to the discharge line out side we installed a heat pump on furnace feet and a new whip and disconnect as well. Form for installation must be completed by service tech finished up installation settings, start up, let unit run in ac mode for 30 mins super heat and sub cooling ok 10 super heat and 9 sub cooling supply temp 49 return air 70 check and test 10 kw electric heat, went over all settings ok both heat pump and electric heat ok, final charge for heat pump was factory charge test pump ok
Performed ac check up, check electrical low and high ok replace filter, flushed drain ok check split, outdoor unit r22 pressures ok capacitor and contactor ok found blower wheel dirty, and condensation trap was partially blocked, cleared drain line quoted for repairs new ez trap and clean blower wheel
Performed ac check up, check electrical low and high ok replace filter, check split ok supply 53 return 75, could not flush drain there no excess to flush drain recommend ez trap installation, check outdoor unit r22 pressures contactor ok found capacitor reading 52 rated at 55 quoted for repairs, also informed customer about age of water heater would recommend replacing water heater and some water protection
Performed propane boiler check up, condensing boiler, wall hung, clean trap and flushed with water test pump, clean flame sensor/igniter check Inputs and outputs ok warm weather shutdown, test boiler only one zone is active combustion test ok water pressure and temp ok cycle boiler ok summer shutdown is set to 69
Performed cooling maintenance, replaced standard air filter. Inspected cooling coil. Blew out condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil
Performed cooling maintenance, replaced rp213 media filter. Checked voltage, amperage and electrical connections, measured capacitor values ok. Inspected cooling coil, cleaned condensate drain and pump. Started air conditioner, checked refrigerant charge and temperature drop across coil.