Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
After our heater checked out okay, Chris discovered that our humidifier wasn’t working. He rewired it correctly and fixed the problem.
Luis is always pleasant, reliable and thorough. He is an asset to Di Biase!
Efficient and friendly
Luis was prompt fixed problem very quickly
My system went on the fritz. Called just after lunchtime, a couple hours later Barry was at my door. He found my issue quickly and fixed me right up. I really appreciated the level of professionalism and courtesy that Barry demonstrated. He explained what my issue was with language I could understand. Great job!
Found main fan not running and locked out on freezestat. Reset freezestat and fan started. Found fan shut down on wednesday morning at around 630 am. Put fan in on position to test.
Performed gas heat tune up check electrical low and high voltage connections, replaced filter 413 cleaned flame sensor check low and high stage, performed combustion test cycle furnace chec temperature rise, static pressure ok recommended adding whole house humidifier emailed proposal for installation of humidifier
Customer keeps smelling odor from furnace, check operation of oil furnace, check smoke and performed combustion test ok check all airflow and temps readings, check static pressure ok replaced filter, cycle furnace did not see or find any issues with furnace also did not smell odor, furnace is working to standards.
Removed existing low boy furnace. Installed new high boy furnace. Installed new return drop and boot. Installed new supply plenum. Sealed all duct work connections. Installed new oil line to filter and installed new filter. Installed new bx wire to furnace and installed new switch and outlet. Installed new 5 in smoke pipe and damper. Sealed hole in chimney with cement. Made all necessary high and low voltage connections. Could not test system because of no oil in tank. Will need to return to test system out. Everything is completed just need to test system. Will need to turn disconnect on near steps for main power, will need to turn oil back on also.
Completed Heating System Tune Up / Inspection. Cleaned flame sensor, inspected hot surface igniter and blew out burners. Pulled amp draw on all major components, all in correct specs. Replaced air filter, tested condition of blower motor and performed combustion and static pressure tests. Also tested all safeties and made sure drains were clear. System has a few rust spots an is showing signs of aging.
Bad gas valve. Gas valve is Ordered at Johnstone Supply under DiBiase/Straub. Informed homeowner that we will return to replace valve between 3-5PM today. If sooner spot becomes available we will contact homeowner. BRING 8â€™ Ladder
No heat, found air bound on hydronic system, bleed air from recently installed (customer installation) spiral vent, ran system as single loop to get rid of all air completely, after 35 mins of running time switched system to primary/secondary loop, ran unit for over 20 minutes unit did not stopped during all testing period. System is heating correctly
Performed oil boiler cleaning tune up, cleaned heat exchanger and flue pipe, replaced nozzle pump strainer and oil filter, cleaned and adjust electrodes, check oil pressure, test aqua stat and performed combustion/smoke test ok cycle boiler ok water pressure 15 psi and temp ok
Performed heating maintenance, checked air filter ok. Cleaned burners and flame sensor, inspected heat exchanger. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches. Performed combustion test and checked temperature rise.
Removed furnace. Installed a new Goodman furnace in existing Location on furnace feet underneath. Modified gas line as needed checked for leaks w bubbles. Modified a piece of metal between coil and furnace. Modified electric w a new electrical box and switch / outlet. 16/25/1 filter was good so reinstalled. Tested unit in heating and cooling and unit is working as it should.
Weil McLain wall hung boiler not working, found boiler in locked mode, low water cutoff, check water pressure and reading 15 psi, reset boiler and check operation, water pressure remained at 15 did hear water noise coming from boiler, boiler would run for 1 minute but eventually low water cutoff will open, unit air air bound, tried to purge water, the current set up is very difficult to purge, make up water is in the return and air vent 1 in is installed the supply tried to isolate boiler to tried to bleed air from primaryâ€™s loop, purge air from primary and secondary loops, boiler remained running during testing period, spiral vent is not working, had to manually open up to bleed air. If boiler still have issues with low water cutoff would recommend, piping modification, and also replacement of spiral vent head 1 in.
No heat for 80K BTU natural gas furnace. Found severely worn hot surface ignitor reading high ohms. As I took top combustion plate off hot surface ignitor broke. Replaced hot surface ignitor. Found open pressure switch error code. Set pressure switch to close at -.75â€. Trial for ignition was stopping after gas valve opened because Glowfly universal hot surface ignitor does not properly align. Installed Goodman OEM hot surface ignitior. Trial for ignition did complete but cut out at various lengths of time after trial for ignition was comolete. Determined that pressure switch is randomly opening. Jumped pressure switch to be able to run furnace for combustion test. 71 ppm CO. Checked flues and draft. Draft is good as is pressure at pressure switch (-1,45â€ WC)
Found after investigating situation that the Oil furnace with heat pump located in closet area had several issues. 1st issue coil is only 3 inches from the plastic pan to the heat exchanger. Also found that inside supply plenum to feed main trunk is only a 6â€ or 7â€ hole cut into trunk. Entire supply plenum would need re-done. Also found sensing bulb to txv just hanging in the cabinet. Also found what looks like refrigerant oil dripping from mechanical fitting for equalizer line of txv. Told homeowner that I would discuss the details with the office and go from there.
Heater tune up . Renewal on gas and a/c tune ups. Check all safetyâ€™s and check filter still ok at this time. Check static in high fire ; and check temp rise ,system is running correctly at this time. 413 filter still good , should be replaced on spring tune up. Check humidifier, customer installed new humidifier pad .
Oil boiler, customer experience some noise from boiler, found boiler off upon arrival asked customer to increase temperature on thermostat, boiler started, noticed both returns not getting hot, check water pressure and found 0 psi, also expansion tank was valve off, quoted to add water and purge hydronic loop customer Approved repairs, added water and purge system, noticed fill valve not working, had to manually open after opening manually valve worked and filling boiler, after pruning and filling system check both returns and getting hot, would recommended replacement of fill valve, replacing expansion tank to bladder type, new air scoop, and pressure relief valve emailed proposal for recommendations