Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
pleased with the whole company and how they do business
Kurt always does a great job and makes sure everything is right A++++++
Barry was very thorough and professional
Love the techs, Luis is one of the best
Great service, knowledgeable and nice workers. Would call again.
Kurt always does a great job. His knowledge and skills are outstanding.
Barry did a great job addressing several issues on a newly installed AC unit
Heat Tune Up under new maintenance plan for 100K BTU 2 stage propane furnace. Checked 20x24x1 filter. Verified thermostat operation. Checked all wiring. Cleaned flame sensor. Checked hot surface ignitor resistance and visually inspected for cracks during start up. Visually inspected heat exchanger and burners. Checked gas pressures. Measured temperature rise. Checked for gas leaks in gas piping using bubbles. Verified humidifier operation. Pad is ok at this time. Left bypass damper open. Set humidistat to 35%. Combustion test: passed. Completed Gas Furnace Inspection Form. Furnace is operating safely at design conditions at the time of this maintenance.
performed precision oil furnace tune up. 16x25x1 air filter is clean. Checked all electrical conections and components. Replaced rf1 oil filter. Replaced.85x80 b nozzle. Checked temperature rise was 65 degrees. Performed smoke and combustion test. Also blower wheel welds are breaking off of center of blower wheel grinding and making a lot of noise. Also found blower motor bearings are worn. Called distributer for price and availability on new motor with blower wheel. Also told homeowner the 2nd option would be to replace the oil furnace, homeowner wanted to due the repair at this point, ordered the parts from distributer. 10/22/21. Installed new blower wheel and blower motor. Ran system in fan on and checked operation of fan motor.
Performed precision heat tune up on carrier gas furnace. 16x25x1 air filter is clean. Checked all electrical conections and components. Cleaned flame sensor. Checked temperature rise. Found heat exchanger has some rust and corrosion, furnace is a 2001 recommended getting a price to replace system. Performed combustion test. Gas furnace is working at time of service.
Found thermostat calling but nothing running. Found ez trap foot switch popped up beacause of a clogged drain. Blew out condensate drain and flushed with hot water. Checked refrigerant pressures and temperatures at indoor and outdoor, a/c is working fine at time time of service. Recommend to homeowner to get on the maintenance plan to take a closer look at the system for both heating and cooling.
Found that the zone damper that was exsisting and was not part of the install for zone 2 had fallen apart. ( provided estimate to replace both existing zone dampers. For now System will operate off of first floor thermostat until dampers are replaced, second floor will not be accurate at this time. Also found second floor thermostat was programmed for heat pump not conventional. System is a communication heat pump and was making it run in cooling mode every time system would call for heating. Re- programmed to conventional and test ran system is now operating correctly. Will need to replace dampers for proper zoning operation. We will be coming back to replace the dampers under original contract.
Returned to replace defrost control board m removed failed board. Installed new defrost board. Started heat pump, tested defrost cycle. Checked operation ok. Ok to charge card on file..
Performed heat pump tune up, check electrical low and high voltage connections ok, test back up heat elements ok, replaced filter, check outdoor unit refrigerant pressures capacitor and contactor ok noticed outdoor unit not level 100 % added two pads to tried to level unit, unit seems to be level after adding pads, we will check outdoor unit next time we come out.
Checked no cooling complaint and noise coming from the furnace. Checked blower motor and inducer, ok. Cycled furnace, checked blower and inducer operation. Found no noise. Recommend maintenance plan $189 per year.
Performed gas heat tune up, check electrical low and high voltage connections ok cleaned flame sensor and burners, check manifold gas pressure performed combustion test check supply and rerun air temp, service humidifier and replaced pad, test pump pump is taking too long to discharge, recommend pump replacement quoted to replace pump customer approved replacement of pump and service on humidifier, test and set humidifier to winter 35%. Cycle furnace ok.
Performed heating maintenance, checked air filter ok. Blew out condensate trap and drain. Cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches, measured fuel pressures. Performed combustion test and checked temperature rise.
Found air handler on an e05 error code when I arrived. Found 2 3 amp fuses installed air handler, 1 was blown. Replaced fuse and it popped right away. Removed t-10 thermostat from the wall and found thermostat was black and had shorted out. System was installed November of 2019 so repair is warranty. Replaced t-10 and performed heat pump tune up on amana heat pump system. Replaced Aprilaire 313 air filter homeowner provided and Aprilaire humidifier pad is clean. Checked refrigerant pressures and temperatures at indoor and outdoor. Checked temperature rise, heat pump system is working fine at time of service.
Checked no cooling complaint, found display blank. Found boiler switch off. Turned on. Boiler booted and started. Ran boiler unil return ran warm. Boiler was not needed since repairs we may have left the switch off.
Performed six month quality m checked media filter ok. Checked furnace setup. Updated cool cloud. Started gas furnace, checked low and high fire. Cycled air conditioner. Checked operation and temperature rise.
Performed heating maintenance, replaced air filter. Blew out condensate trap and drain. Cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections, measured capacitor values. Started gas furnace, tested limit and safety switches. Measured fuel pressures and performed combustion test.
Performed precision heat tune up on amana gas furnace. Replaced Aprilaire 413 air filter. Checked all electrical conections and components. Blew out condensate drain. Cleaned flame sensor. Found burners not lighting across. Removed burners and thoroughly cleaned off rust and corrosion. ( furnace is propane which is normal wear and tear) serviced Aprilaire humidifier with #35 humidifier pad. Performed combustion test, no further recommendations at this time. Furnace is working fine at time of inspection.