Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Explains any challenge well, is courteous and careful.
If I was staying in the area, I would definitely continue to use DiBiase Heating and Cooling. Recommended by my neighbor. Great service. Luis was very professional.
Thanks Brian. We discussed new a/c unit pros and cons.
Dean, the DiBaise employee, was able to correct all installation discrepancies that I had. They seemed minor to him but were major for me. 110% satisfied with this company.
Prompt service and courteous employees all around; from the original service call to the follow up appointment after installation of new system.
Luis was excellent! Very professional
Kurt did a fine job in explaining that our units were basically shot. He said he’s never seen any so old (30 years)! He setup an appointment for an estimate the same day.
Given that our a/c system cut out on a Saturday night during a heat wave, we were very pleased to have it fixed first thing on Sunday. Thanks very much!
Reclaimed and removed old equipment. Installed new leveled pad, disconnect, whip, and Trane condenser. Flushed lineset and brazed in with nitrogen. Installed new Trane 96 percent efficiency gas furnace. Installed new coil and brazed in with nitrogen. Pressure tested to 300 psi and evacuated down to 213 microns. Installed new condensate line, ez trap, pump, switch, and receptacle. Wired safteys to break r. Installed wire saver to work with new t6 thermostat. Reconnected gas and leak checked. Reconnected flus. Installed new filter rack and 16x25x1 filter. Tested system in cooling and heating and made necessary adjustments and performed combustion test. System working well at time of install.
Performed two gas furnaces tune up check electrical low and high ok replaced filters, cleaned sensor and check burners, combustion test ok both units ok, second floor unit running ok this time, first floor unit does not work, igniters does not glow completely and burners are covered by rust, would recommend replacing burners and igniter is required for the furnace to work emailed proposal for recommendations on first floor also joe to come out tomorrow for proposal on new system
Performed ac and heat tune up on heat pump with electric heat back up, check electrical low and high ok filter ok test 15 kw back up ok 20 amps each element 3 elements, flushed drain, test pump ok cleaned pump, and added union for better drain access, check temp split ok, indoor coil and blower wheel is dirty would recommend cleaning both items. ok outdoor unit refrigerant pressures are low needs some refrigerant, also check capacitor ok, contactor is pitted burnt contacts, start cap has lot of corrosion would recommend replacing, emailed proposal for the recommendations would recommend having an estimate for system replacement
Performed Quality Assurance inspection on a newly installed gas furnace and air conditioning system. Checked over entire system. Checked all piping and ductwork. Everything looks good. No gas leaks. No air leaks. Condensate properly pitched. Customer very happy. Working great at time of QA.
Noise from outdoor unit when system Shuts off cycle couple times and did not see any issues, unit is ruining within manufacture specifications did not see any problems
Zip locked a piece of copper of the existing copper that was abandoned in wall. Ran electrical wiring in the electrical panel. Installed old disconnect and electrical wiring to unit. Leveled pad for amana ac unit. Brazed all other copper joints as needed and leak checked with nitro and soapy bubbles. Tested out unit in cooling mode and made sure unit worked.
Performed precision heat tune up. Homeowner just replaced Aprilaire 413 air filter. Checked all electrical conections and components. Checked gas pressure. Performed combustion test. Cleaned flame sensor. Checked temperature rise. Checked a/c out on start up. A/c compressor is running fine compressor noise is normal. System is working fine at time of inspection.
Performed two propane furnaces check ups, check electrical low and high ok replaced both filters, clean sensor and check manifold pressures ok burners ok performed combustion test cycle both furnaces ok, check temps rise ok
Performed gas heat tune up, check electrical low and high ok replaced standard filter 16x25x1 test pump ok clean sensor and check burners ok gas pressure ok performed combustion test cycle furnace ok informed customer that inducer is leaking water bottom portion small leak,
Performed gas heat tune up check electrical low and high ok check electrical low and high ok check filter ok 413. Check humidifier operation ok test ok, cleaned flame sensor gas pressure low and high ok performed combustion test cycle furnace test pump ok
installed 50 gallon propane powervented water heater. Re adapted to gas and water piping. Installed new expansion tank. Installed 2 new shut off valves. Leak check gas and water side. Adapted to 3â€ pvc exahaust pipe. Set on 4 brinks with drain pan and water alarm. Water heater is working fine at time of install.
Turn power off to system and disconnect and remove current ECM Fan Motor for the Outdoor Unit. Install new OEM Motor and Defrost Control Board for the Motor. Complete all Wiring connections and reassemble the Outdoor Unit. Restore power to system and put into operation. Test unit in Cooling and Heating Modes to ensure proper operation of system.
Performed AC Tune Up on system. Inspected 14x25x1 Air Filter. Filter was just changed and in good condition. Inspected indoor coil and found trash and debris on top of Coil. Inside of Coil has large amounts of hair and fur. Also found growth formations throughout the coil and the interior of the cabinet. Removed trash and reassembled coil. Also found areas of coil where the trash had damaged the fins and rust was forming. Cleaned drain line and filled pump to test operation. Vinyl tubing is very dirty but pump is discharging right now. Would recommend replacement of the vinyl tubing. Also noted Blower Fan Motor operating properly, but motor was very hot which could indicate that it may have been over amping which could result in failure. Checked refrigerant charge and outdoor components. Recommend replacement of the Outdoor Capacitor and Contactor due to excessive rust and Contactor being pitted. Outdoor Coil fins are smashed in multiple areas and completely gone in one small area. Ref
Performed heating maintenance, checked media ok. Cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches. Performed combustion test. Checked operation and temperature rise.
Reclaimed. Old heatpump and installed a new amana heat pump on a new plastic pad. Ran new copper lines and brazed and leak checked with nitro and soapy bubbles. Installed a new disconnect box and electrical wiring to unit. Tested unit in all modes.