Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Luis looked at our system extensively and found no problems (air supply at lower flow rate than others). Thoroughly inspected duct work and air handler. Professional and pleasant!
Dave arrived Friday morning and it was HOT outside. He said it would be a two day install but would stay until at least he had the AC running for us. He was true to his word and stayed late on Friday to make sure we had AC for the weekend until they came back to finish the entire job the following week. Thank you!
WERE NOT TOLD THE LEAK COULD BE LOCATED
Kurt was a really nice guy and total professional. Great personality and customer service!
Response from DiBiase Heating and Cooling Company:
Thank you, David!
Response from DiBiase Heating and Cooling Company:
Thank you for the review, Mary!
The service tech was friendly and professional
Performed cooling maintenance, checked air filter ok. Cleaned condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Performed precision a/c tune up on 2 mini split heat pump systems. Both have 3 indoor heads. Cleaned all wasable filters. Checked all electrical conections and components. Blew out drains. Checked temperature split at each indoor head. Checked amp draw at outdoor units. Inspected coils. Both mini split heat pump systems are working fine at time of inspection.
AC Tune Up 3 Ton Amana AC system. 29F temp split. Both coils in good condition. Replaced both blower capacitor and Outdoor capacitor. Field and manufacturer wiring ok. Superheat/refrigerant pressures ok. Compressor amps/indoor amps/ outdoor voltage ok. System is operating well at the time of this tune up.
Installed 3/4 gas line made of galvanized pipe outside and tract pipe inside. Put 3/4â€ shut off on gas line. Soap checked, found no leaks. Siliconed penitrations. Secured gas line with 2 hole metal straps. Gas line is secured.
Found system low on charge. 410 a refrigerant pressures were 227/73 at 68 degrees. Added 2 lbs of 410a now pressures are 274/119. Also added leak dye to the system and will need to return in 30 days to look for dye. Also performed precision a/c tune up on Lennox a/c system. Replaced 16x25x1 air filter. Checked temperature split at indoor unit. A/c system is working fine at time of service.
Performed ac tune up, system is set up for zoning two zones not sure if itâ€™s first and second floor, zoning panel has two thermostat inputs and two zoning damper outputs zone 1 and zone 3. On zone 1 two dampers 10x24 are tide in in zone 1 contacts, tried to look zone 3 damper could not see based on customer information second floor thermostat controls zone 3 did not find zone 3 damper, or of the 10x24 dampers is not opening 100% would recommended replacement of that damper right side of unit by humidifier, check operation of system replaced filter flushed drain test pump check airflow ok good temp split inside temp is 65 no load inside the house, check outdoor unit refrigerant pressures 200/60 suction line temp is very cold due to to low temp inside the house, pressures look ok based on indoor and outdoor temp, capacitor ok contactor should get replaced emailed proposal for recommendations on new contactor and zone damper
Performed cooling maintenance, checked air filter. Cleaned condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner checked refrigerant charge and temperature drop across coil.
Performed ac tune up check electrical low and high voltage ok check air filter, slushed drain add tabs to pan, check supply and return, check outdoor unit refrigerant pressures capacitor and contactor ok, contactor is just within standard next year might have to get replaced 70/5....system has no filtration system and would recommended adding whole house humidifier to maintain humidity during winter season
AC tune up 4 Ton Carrier AC system 19.5F temp split. Changed Filter. Drain ok. All electric motors and components ok. Both could in good condition. Field/manufacturer wiring ok. Refrigerant pressures/subcooling ok. Compressor amps/indoor amps ok. System is operating well at the time of this tune up. Mr. DiLuigi renewed his plan membership.
No ac found system to be low on refrigerant system is from 2007 provided options to customer adding refrigerant vs system replacement, customer decided to add refrigerant for now, added four lbs of puron 410A check sub cooling and super heat values ok
Reclaimed and removed old ac unit and removed coil off if furnace. Installed a new amana ac unit on a new level plastic pad. New copper lines from indoor coil to outdoor, brazed and leak checked with nitro and soapy bubbles. Installed new amana coil on top of existing furnace. Modified supply metal as needed and taped all joints. Installed a new ez trap wired into unit. Drained and removed old hot water heater and installed a new Bradford white hot water heater in a drain pan. Modified all piping as needed and put in a new shutoff. Checked for leaks and tested hot water heater. Tempature is set to the hot setting. 125*
Performed precision a/c tune up on 2 carrier a/c systems. Homeowner recently replaced both 16x25x1 air filters. Checked all electrical conections and components. There was a recent issue where there was water on the floor around the second floor furnace. Recommend installing a wet switch at both systems to shut the systems down in the case of water on the floor. Checked both temperature splits. Checked refrigerant pressures and temperatures at indoor and outdoor units. Both a/c systems are working fine at time of service.
AC Tune up for 3 Ton R22 Goodman AC system. Cleaned outdoor coil, replace filter, cleaned and tested drain. Both coils in good condition. All electric motors and components ok. Refrigerant pressures/superheat ok. 18F temp split; ok. Compressor Amos/indoir Amos/outdoor voltage ok. All field and manufacturer wiring ok. System is operating well at the time of this tune up. Provided an estimate for replacing thermostats and elements for existing hot water heater and for installation of new 75 gallon Bradford White Electric hot water heater. Mr. Krcelich renewed plan membership
Performed cooling maintenance, checked air media air filter ok. Blew out condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Performed Quality Assurance on Amana Heat Pump system. Reviewed installation with homeowner and addressed any concerns/questions. Completed checklist form in system. It was a nice looking installation, did not pass because of sealing around Lineset, Schrader cap missing on true suction port, and vinyl tubing being kinked. Corrected any issues that were found.