Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Went above and beyond by catching a mistake made by original installers (horizon) and fixed quickly and efficiently
Better than average service
Timely, good service. Too expensive!
Nice job by brian
Easy to get service when needed and technicians are top notch.
Fantastic service and professionalism.
Very pleasant and professional
Brian answered all my questions about my hvac system and advised me of possible future requirements.
Installed new inducer draft assembly and .65 pressure switch. Tested operation. Also performed precision heat tune up on Lennox gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Blew out condensate drain. Checked temperature rise. Cleaned flame sensor. Checked gas pressure. Performed combustion test. Gas furnace is working fine at time of service.
Service call that there was an Oil Leak. Arrived onsite and spoke with homeowner about issue. Found area around Oil Tank where oil was leaking. Homeowner turned Oil Supply off to furnace and shut system down. Inspected the Bottom of the Oil Tank. Tank has rust spots but no signs of oil leaking at this time. Did recommend to homeowner to begin planning to replace the oil tank. Turned oil supply on and saw oil leaking from the Oil Filter Cartridge. Checked cartridge and found a rust spot on the bottom that had rusted through the canister. Removed old Canister and installed a new RF-1 Oil Canister Assembly. Turned oil supply back on and monitored to ensure there were no leaks. Put furnace in operation and purge system of Air. Performed a Smoke Test and Combustion Test on Furnace. Smoke levels were 0 and combustion readings were within standards.
Found that after talking to homeowner, the two rooms are too hot in the winter, and too cold in the summer. Found fan speed is already set to low speed. No further adjustment can be made to lower the fan speed. One recommended adjustment that could be done is adding a separate wireless thermostat to one of the bedrooms that is being feed by the booster fan so that after temperature is achieved it will then kill the power to the booster fan to stop pushing air into the rooms.
Found that vent pipe was pushed un level. The roof was just redone and when the put the boot on the roof it made the vent un level. Straighten out vent by installing the vent strap in a different location and re leveling pipe through the roof. The roofing company is going to come back to reseal vent pipe on the roof. Performed precision heat tune up on both amana gas furnaces. Replaced 16x25x1 air filter in the attic. Replaced 20x25x5 filter for basement furnace ( customer supplied). Checked all electrical conections and components. Checked temperature rise. Cleaned flame sensor. Blew out condensate drains. Both systems are working fine at time of inspection.
Performed Precision Heating tune up on Amana Gas Furnace system. Inspected electrical components on system. Found Air Scrubber was not operating, and when tested, determined the Transformer for the Air Scrubber had failed. Replaced Transformer for the Air Scrubber under 2 Year Parts/Labor Warranty and tested Air Scrubber. Cleaned Furnace Drain Lines and Condensation Pump. Filled and tested pump operation. Performed Combustion Analysis on Furnace and adjusted Gas Pressure on system for High Stage. The High Efficiency 413 Air Filter is getting dirty and should be replaced soon. The Humidifier is dirty and the pad is deteriorating. Humidifier is shut off currently and not in operation. No one was home during time of Tune Up. Called Homeowners to receive approval to replace Air Filter and service Humidifier. Was unable to reach homeowners at this time. Included estimate for the replacement of the Air Filter and servicing the Humidifier.
Performed heating maintenance on heat pump, checked air filter itâ€™s new. Serviced humidifier, flipped the access around so the water panel can be removed. It was installed backwards... cleaned and replaced water panel. Checked voltage, amperage and electrical connections, measured capacitor values. Tested electric back up heaters. Started heat pump, measured btu output. Tested defrost cycle. Checked operation and temperature rise across coil.
Found Lennox gas furnace locked out on a code 3 pressure switch stuck open with inducer motor on. Checked venting for debris, checked pressure switch tubing for a clogg, no clogs were found. Excercised pressure switch and found inducer motor was very hot to the touch, got furnace to come on and heat came on. Recommend to replace inducer motor and pressure switch due to Lennox had issues with .65 pressure switches corroding internally. Will get price and availability tomorrow and get back to the customer with a quote.
Performed heating maintenance, checked air filter ok. Cleaned burners and flame sensor, inspected heat exchanger. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started gas furnace, tested limit and safety switches, measured fuel pressures and adjusted. Checked operation, found inducer motor running at full load . Checked inducer, found bearings are failing. Recommend replacing inducer assembly.
Checked no heat complaint, found house wrapped in plastic having mold remediation. Found furnace locking out on pressure switch. Checked plastic at termination, found vent blocked. Cut plastic away from vent pipe. By the time I got back to the basement the furnace was running. Checked air filter ok. Checked venting screens all clear. Recommend having furnace serviced $89.00
Performed heat pump tune up, replaced air filter, check blower cap and motor ok, coil is dirty, test back up heat ok, check temp rise ok, check rooftop unit refrigerant pressures capacitor and motor, motor cap ok compressor running just below amp rating 14 rated running at 12 amps, as stated on last year tune up, system is very inefficient and system goes off on high head sometimes due to to indoor coil being dirty, tried to clean coil last time, but did not had good success, as right now pressures are ok, also electric heat back is expected to run more often than normal from now on, system should be replaced
Performed precision oil tune up on thermo dynamics boiler. Replaced rf1 oil filter. Replaced.85x80a nozzle. Bleed and purged air from oil line. Brushed and vacuumed heat exchanger and smoke pipe. Checked pump screen. Cycled on thermostat and made sure loop was getting hot. Performed smoke and combustion test. Oil boiler is working fine at time of inspection.
Performed precision heat pump tune up on amana heat pump. Replaced Aprilaire 213 air filter. Checked all electrical conections and components. Blew out condensate drain. Checked operation of emergency heat. Checked temperature rise. Checked refrigerant pressures and temperatures at indoor and outdoor units. Heat pump is working fine at time of inspection.
Found some water on the floor near furnace. Found that after investigating the leak closely found that barb fitting that comes out of furnace was leaking at the threads. Took apart condensate drain at union on pipe and added pipe dope to the treads to make a water tight seal. Re conected drain and ran furnace for about 20 minutes to make sure drain was not leaking any more. No leaks. Dried up water that was on floor around furnace.
Heat tune up on Carrier propane furnace. Verified operation of thermostat and cycling of furnace. Temp rise 52F. Gas pressure ok. All electrical components are good. Combustion test proves proves integrity of heat exchanger. Furnace operating at 92% efficiency. Drain and pump are ok. Furnace is operating well at the time of this tune up/maintenance. Alicia is interested in exploring zoning/balancing and duct cleaning.
Heat tune up. Verified operation of thermostat and cycling of furnace. Checked gas pressure. Cleaned flame sensor, verified HSI ohms. 45F temp rise low fire. Combustion test proves integrity of heat exchanger. Furnace is operating at 93% efficiency. Trane electronic air cleaner is clean at this time . System is operating well at time of this tune up/maintenance.