Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Luis Tenorio was extremely knowledgeable and extremely helpful in diagnosing and recommending solutions. Would highly recommend
Long time customer and always have experienced exceptional service & work!
Great service and great people
Technician was very knowledgeable and helpful on diagnosing the situation and advising.
excellent service, very professional, on-time, reasonable price, with courtesy. Much appreciated. Thank you.
Performed heating maintenance, replaced standard air filter. Cleaned burners and flame sensor, inspected heat exchanger. Blew out condensate trap and drain. Started gas furnace, tested limit and safety switches. Measured fuel pressures. Performed combustion test. Checked operation and temperature rise. Serviced humidifier, cleaned and replaced water panel. Started humidifier and checked operation. Set humidistat to 35% rh
Performed heating maintenance, replaced standard air filter. Checked voltage, amperage and electrical connections, measured capacitor values ok. Tested electric back up heaters. Started heat pump, tested defrost cycle. Measured btu output. Checked operation and temperature rise across coil.
Checked no heat complaint, found gas valves off in unit. Checked heat exchanger, found holes in heat exchanger. Opened gas valves, got 1 circuit to try to start but no ignition have 24 volts to ignition control but no spark. Pulled burners, see nothing preventing spark. Option 1: Recommend replacing heat exchanger and ignition control module. Will not be able to continue to troubleshoot until work is complete Option 2: Recommend replacing RTU.
Reclaimed and removed old equipment. Installed new Amana high efficiency gas furnace and coil. Installed new Amana 16 seer outdoor condenser. Ran new lineset and brazed in with nitrogen. Pressure tested to 300 psi and evacuated down to 180 microns. Reconnected electric and gas. Leak checked gas. No leaks found. Installed new condensate pump and ez trap, wired into unit. Reconnected thermostat wire. Installed Honeywell t4 thermostat. Installed April wire high efficiency filter. Sealed duct connections. Tested system and adjusted as needed. System running great at time of install.
Checked lights flickered when heat pump starts. Cycled heat pump and did not see lights flicker. Checked out unit and measured btu output. Did notice that an old dehumidifier did make the lights flicker. It is plugged into a extension cord with a chest freezer.
Turn power off to system and remove Zone Valve head for the Dining Room loop. Install new Zone Valve Actuator and complete all wiring connections. Turn system on and test Dining room zone from the Thermostat. Insure Valve Head is opening and baseboards are heating properly. 11/13/19. Installed zone head and checked operation of valve. Found thermostat near dining room already turned up above room temp , found baseboard heating up. Cycled thermostat down bellow room temp and made sure valve closed again. Then found zone that feeds the office area downstairs set to bypass, put back on auto, now zone it working properly.
Performed quality assurance check on Weil McLain 90% condensing boiler. Found that basement zone thermostat is inaccurate. ( homeowner at this time is just going to compensate for in accurate temp) . Added sentinel x100 inhibitor to the boiler. Checked all electrical conections. Performed combustion test on boiler and found it to be in specifications with the manufacture. Also added water alarm to side of boiler to alarm any water leakage.
Service call that the Boiler was not Heating the home. Had been onsite earlier to perform a Tune Up and found the Fill Valve was not working properly. Found system was not filled with water and not heating. Removed the current Fill Valve and Expansion Tank. Repiped the Main Water Feed and installed a new Watts Fill Valve. Piped Expansion Tank into loop and installed a new Automatic Air Vent onto the system. Once complete, we will refilled the boiler and put system in operation to test. Purged Baseboard Loops of Air and tested Zones to insure all areas are getting hot. While testing the zones, found the Dining room was not heating. Tested the Zone Valve head which is failing. Will provide an estimate and follow up with price for replacement of the Zone Valve Head.
Performed heating maintenance, cleaned burners and pilot burner. Checked voltage, amperage and electrical connections. Started boiler, hear air. Expansion tan was just installed. Purged air and boiler pressure went to 0 psi. Checked fill and supply water, found fill will not add water. Recommend replacing auto fill and vent on air scoop.
Checked no heat complaint, found 24 volts cut to the thermostat at the condensate pump. Pump is full and running. Cleaned pump, tested did not pump, blew out discharge itâ€™s clear. Replaced condensate pump. Wired and started heat.
Checked poor heat, found heat pump running and heating but no auxiliary heat, found thermostat display aux heat on but no call. Checked thermostat, found white wire on w2 not aux. retired thermostat, started heat pump, checked now heat pump is running with electric heat with call to aux.
Drained and removed old 80% gas boiler. Installed new Weil McLain 95% efficient modulation condensing evergreen series gas boiler. Installed new primary secondary piping and all necessary accessories. Installed new primary and secondary circulatory. Repiped gas line and ran new intake and exhaust venting. Installed new outdoor sensor. Removed bad zone valve. Checked for leaks and found none. Installed new condensate pump and vinyl to sump pump. Tested operation of boiler in low and high fire and performed combustion test. Boiler is operating at manufacture specifications.
Installed novo water softener and filter. With air gap separator . Set unit to correct levels and date and time. Unit is running to manufacture specs.
Performed heat pump check electrical low and high ok filters ok, check and test 10 kw back up ok check split, check outdoor unit 410 pressures ok capacitor and contactor ok, test defrost ok noticed evaporator coil is leaking there signs of dye on inside coil, quoted for repair on evaporator coil, unit was not register so only had 5 years warranty
Performed precision heat tune up on older York heat pump. Replaced 16x20x1 air filter. Blew out condensate drain. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is older and is corroded at outdoor and indoor coils. Should start considering replacement of system.