Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Great service and great people
Technician was very knowledgeable and helpful on diagnosing the situation and advising.
excellent service, very professional, on-time, reasonable price, with courtesy. Much appreciated. Thank you.
Great service! Always profesional
Chris came to service our new heat pump for the summer months. He gave the same professional care as the installers; answering questions and providing helpful tips. A pleasure to deal with DiBiase.
Mike and Paul did a great install of a heat pump while correcting errors from a previous job, while explaining it to me. They were polite, professional, prompt.
The DiBiase Team is very responsive, and continually provides excellent - professional services. I would continue to highly recommend their services to others, as I have done. Tony - Realtor/Residential property owner (multiple properties)
Performed heating maintenance on heat pump and mini split, washed air filters. Checked voltage, amperage and electrical connections. Measured capacitor values ok. Tested electric back up heaters. Started heat pumps, tested defrost cycle. Calculated btu output. Checked operation and temperature rise across coils.
Performed heating maintenance, checked media air filter ok. Checked v, amperage electrical connections, measured capacitor values ok. Tested electric back up heaters. Started heat pump, tested defrost cycle. Calculated btu output. Checked operation and temperature rise across coil.
Performed heat tune up on heat pump check electrical low and high ok replace filter test electric heat 15 kw ok outdoor unit r22 pressures ok test reversing valve ok capacitor ok noticed contactor little pitted would recommend replacing customer passed on repair quote for contactor cycle unit ok
Evaluated hot water system and looked at exhaust chimney system and intake system for water heaters,
Found 50 gallon electric water heater leaking. Called office and was able to coordinate to have it replaced today. ( will replace later this afternoon). Also performed precision heat tune up on trane heat pump system. Replaced dirty 16x20x1 air filter. Checked all electrical conections and components. Blew out condensate drain and tested pump with water. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at time of service. Installed new 50 gallon electric hot water heater and checked for leaks. Told. Homeowner water heater will take several hours to get hot from here but is working fine.
When I arrived found circulator pump running and boiler firing, could also hear air in the lines. Homeowner has 5 zones all on zone valves. When I disconnect t stat wire from boiler it would stop everything. Found 4 older t 87 thermostats,and one slightly newer electronic thermostat. Disconnected all thermostats from wall and still continued to run. Issue is somewhere over at the zone valves, they are not very accessible. Homeowner just wanted to purge air out for now and shut off breaker. Purged air out of lines and re filled boiler to 12 psi.
Performed precision heat tune up on rudd gas furnace. Replaced 16x24x1 air filter. Checked all electrical conections and components. Checked manifold gas pressure. Performed combustion test. Cleaned flame sensor, and blew out all condensate and pressure switch tubing. Rudd gas furnace is working fine at time of service. Also homeowner stated that after the water heater was replaced in 2017, we also replaced the pressure reducing valve in 2017, that the water pressure has changed especially on the hot side . Took water pressure from bottom of water heater and it was 43lbs with no fixtures running. After turning on kitchen sink , water pressure dropped down to 36 lbs possible sediment or just a failed pressure reducing valve. Told homeowner it could be a possibility that everyone is experiencing a lower water pressure. Homeowner is going to talk with neighbors first before making a decision.
Water leak coming from ac uni, found water on floor upon arrival, check pump and vinyl tubing, found pump not discharging correctly quoted for new pump and wired new pump safety on control board, customer ok repairs, after repairs check ac operation replace filter, and check split supply 54 return 71 also check pressures 260/67 discharge air on the condenser is 121 system is working very hard, highly recommended having system replacement due to condition
Performed precision heat tune up on Rudd heat pump. Replaced 16x20x1 air filter . Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. Blew out condensate drain. System is working fine at time of service.
Performed precision heat tune up on carrier heat pump. Replaced 20x22x1 air filter. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. Blew out condensate drain. System is working fine at time of service.
Removed flue pipe and cleaned out soot with vacuum. Brushed inside discharge pipe and vacuumed. Removed and replaced 75/80a nozzle. Cleaned and adjusted spark contacts. Checked and cleaned strainer screen. Replaced inline oil filter by tank. Purged air from system and preformed a smoke and combustion test. Results were good. Checked fan and found a worn out belt. Removed and replaced belt.
Performed precision heat tune up on Lennox heat pump. Replaced 16x20x1 air filter. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. Blew out condensate drain. Checked operation of emergency heat. Heat pump is working fine at time of service.
Installed new exhaust motor and test operation cycle heater and combustion test co 80 ppm cycle heater ok office to bill for payment
Performed heating maintenance on 2 heat pumps and a roof top unit, replaced air filters, tested electric back up heaters on heat pumps, checked voltage, amperage and electrical connections, measured capacitor values ok. Started heat pumps, caluated btu output. Tested defrost cycle. Checked operation and temperature rise across coils. Serviced rtu, checked voltage, amperage and electrical connections,. Checked incoming gas pressures. Started heat, inducer never started. Checked inducer, have 208 volts to inducer but no operation. Will need to replace inducer for heat. I Ordered inducer will also need 4L-38 belt
Performed 6 month inspection on mini split heat pump with two heads, clean both filters check electrical wiring ok test system on heat mode, both units putting out 110 degree air and 73 return outdoor unit ok system is running in perfect condition