Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Luis was great, clean,meticulous and helpful. My system was shot but he did his best. Appreciative of the effort.
Very nice and helpful
Kirt was professional and friendly. Thanks
Very professional and real informative
Very positive. Thanks
Excellent. Everyone at your company with whom I have had contact is professional, helpful and friendly
Super professional and easy to work with
Kurt Manges and his partner appear to have solved my issue. I am very pleased with the experience and with all the support I have received from Sarah and the Dibiase Company
Checked no cooling complaint, set thermostat to cooling, blower runs, checked outdoor unit, getting a 24 volt call but contactor is not getting power, checked pressure switches, found open low pressure switch, checked unit for pressure, unit has pressure. Bypassed low pressure switch, ran air conditioner, checked refrigerant charge. Kyle to replace switch. Did not email
Reclaimed and removed old equipment. Installed new leveled pad, disconnect, whip, and flushed lineset. Placed new American standard condenser on pad and brazed in lineset with nitrogen. Wired in high and low volt connections. Installed new American standard high efficiency gas furnace and evaporator coil. Secured and sealed return and adapted supply ductwork and sealed. Ran new vents to exterior of home and tied into furnace. Brazed in coil with nitrogen and pressure tested to 300 psi then evacuated down to 129 microns. Installed new ez trap and condensate pump. Ran vinyl tubing to discharge line. Installed new humidifier and routed drain to pump. Wired safetyâ€™s to break r. Reconnected gas and leak checked. Installed new switch and receptacle. Wired all high and low volt connections. Installed horizontal drain kit on intake vent. Tested operation in heating and cooling. Adjusted refrigerant charge and adjusted gas pressures. Performed combustion test. System working great at time of
Installed new blower motor. Re conected all blower motor connections. Turned on and blower motor is working correctly. Found 24 volts going to outdoor heat pump, but heat pump not coming on. Brandon is going to see if he left the disconnect out on the roof and he will check it out and call us if he needs further assistance on this system.
Installed new blower motor, old blower motor shaft was rusted very bad, had to use a drill to drill out old motor shaft. After replacing motor made all electrical conections and re- installed air filter. Also checked temperature split at air handler. Temperature split was 18 degrees and system is back up and running in cooling mode.
Performed oil boiler tune up, clean heat exchanger, flue pipe and chimney base, Check electrical low and high voltage ok, replaced oil filter and new nozzle, check electrodes and realigned them, check transformer found to be below rating, emailed proposal for part replacement, check for oil and water leaks no leaks found, cycle boiler, test temp limit, ok triple aqua stat set to 160 high and 140 low, performed smoker and combustion test cycle unit ok check draft ok
Performed precision a/c tune up on Lennox a/c system. Replaced 16x25x1 air filter. Checked all electrical conections and components. Blew out condensate drain and tested condensation pump. Checked refrigerant pressures and temperatures at indoor and outdoor units system is working fine at time of inspection.
Checked no cooling complaint, found wet switch tripped. Found condensate trap clogged. Installed union and blew out condensate trap. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Checked no cooling complaint, fuse is blowing when air conditioner starts. Checked for shorts and grounds, found shorted compressor contactor. Replaced compressor contactor. Started air conditioner, checked operation and temperature drop across coil. Did not email
Checked condensate leak, found trap clogged. Blew out clogged trap. Flushed with water. Started air conditioner, checked operation and temperature drop across coil. Did not email.
Performed ac tune up, check electrical low and high ok, replaced air filter, test pump ok check temp split, noticed blower wheel is super dirty lot of dirt accumulation, check outdoor unit refrigerant pressures capacitor and contactor ok washed outdoor coil, cycle unit ok would frocked adding air cleaner and blower cleaning emailed proposal emailed proposal to customer
After installing motor in apartment air handler, motor started to run and the began to smoke shut off will need to order another motor to replace. 7/31/20. Removed old motor for warranty. Installed replacement motor. Turned system to cooling. Checked temperature split . Had an 18 degree temperature split, system back up and cooling again.
Performed Quality Assurance inspection on a newly installed gas furnace and air conditioning system. No air leaks, penetrations sealed. No gas leaks found. Customer very happy with everything! Inside temp split of 49/70 at time of QA. System running great at time of QA. Spoke to customer about 6 month inspection and answered questions he had. Need to schedule 6 month inspection to test out gas furnace and humidifier.
Install new vent pipe from boiler to power venter. Install new pipe from venter through window opening to the outside and cement opening. Run new wire to power venter location and connect wiring to venter. Install new control interlock kit for boiler and complete all wiring connections. Test operation of system at completion. Installed 360 degree manual resetable thermal switch and performed combustion test.
Installation of Customer Supplied TXV for the Indoor Air Handler. Pump down Refrigerant and remove Indoor TXV. Install new TXV and pressure test system and leak check connections. Evacuate system to below 500 Microns and release refrigerant. Test refrigerant charge and add additional refrigerant as needed. Informed customer that there is no guarantee if the supplied TXV does not work. Office will bill out. Installed new indoor txv, pressure test system at 300 psi for 30 mins ok no leaks, triple evacuation added 4 lbs to bring sub cooling to normal readings, 370/140 with 13 super heat and 9 sub cooling cycle unit ok
Checked no cooling complaint, found air conditioner running but not maintaining temperature, checked air filter, noticed coil is not getting wet while cooling. Checked refrigerant charge, found high superheat but normal sub cooling, found a fail indoor txv. Need to replace txv they have a valve here for the repair please schedule. Did not email