Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
On Time, even early. Went right to work and got everything up and running.
Luis was great, clean,meticulous and helpful. My system was shot but he did his best. Appreciative of the effort.
Very nice and helpful
Kirt was professional and friendly. Thanks
Very professional and real informative
Very positive. Thanks
Excellent. Everyone at your company with whom I have had contact is professional, helpful and friendly
Super professional and easy to work with
Performed Precision Heating Tune Up on Propane Gas Furnace. Replaced the 413 and 14x14x1 Air Filter. Cleaned Furnace Drain Lines and Condensation Pump. Filled Pump and tested operation. Cleaned all tubing and furnace hoses. Tested electrical components on system. Inspected Burners which are clean and free of rust. Put system into operation and performed Combustion Analysis on Furnace.
Performed precision heat tune up on thermopride oil furnace. Replaced garbar oil filter. Replaced nozzle. Performed smoke and combustion test. Checked temperature rise. Tested draft. Vacuumed out smoke pipe and heat exchanger. Serviced Aprilaire humidifier with #35 humidifier pad. Oil furnace is working fine at time of service.
Performed precision heat tune up on trane gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Blew out condensate drain. Turned on humidifier for the season. Cleaned flame sensor. Checked temperature rise. Performed combustion test. Gas furnace is working fine at time of inspection.
Performed Precision Heating Tune Up on Carrier Gas Furnace system. Replaced 16x25x1 Air Filter. Inspected and tested electrical components on Furnace. While testing system noted the Inducer Motor is operating but is drawing higher Amps than its rating. Also noted bearings are making a rubbing/whining sound. This could be an indication that the Draft Inducer Motor bearings are starting to wear or become weak. Cleaned all Furnace Drain Lines and tubing. Cleaned condensation Pump and filled to test. Had previously recommended wiring pump safety into system and adding additional water protection to the system. Performed Combustion Analysis on Furnace and measured Air Temperatures. Combustion results and air temperature readings were within standards.
Performed gas steam boiler cleaning, check and clean burners, ok check electrical low and high voltage ok gas pressure ok check and test low water cutoff ok c(eco water level, also clean and flushed pigtail performed combustion test cycle boiler ok
Arrived at customers home and spoke to them about what they were experiencing. Proceeded to the thermostat and set for cooling. Heard blower come on. Proceeded to the outdoor unit and not coming on. Opened up outdoor unit electrical panel and pushed in contractor. Unit started. Checked voltage and proper line voltage. Checked wire nut connections and looked ok. Went back down to basement and opened up furnace and checked low voltage wiring. Connections good and proper. Checked low voltage readings with meter and getting 24v to outdoor unit. Checked outside at outdoor unit and losing 24v. Proceeded to check low voltage wiring from furnace to outdoor unit and found a break in wiring. Repaired broken wiring. Tested system again in cooling. Indoor and outdoor unit now running. Ran system for 15 minutes and checked pressures and temps. Getting inside split of 53/72. Pressures are 124/273. Superheat of 9 and sub-cool of 7.8. System running good in cooling. Tested heating. Getting temp split
Perform gas heat tuneup check electrical low and high voltage clean flame sensor checked burners check low and high stage gas pressures perform a combustion test cycle unit test condensation pump replace air filter and service humidifier
Performed heat pump inspection check electrical low and high voltage ok check filter ok test back up heat ok check temp rise ok check outdoor unit refrigerant pressures capacitor and contactor ok test defrost and cycle unit installed surge protector on indoor unit, unit is from 1997 would recommend starting to get pricing to upgrade unit
Performed Precision Heating tune up on the First Floor and Second Floor systems. Replaced high Efficiency Air Filters provided by homeowner for each system. Inspected all electrical components and cleaned accessible furnace drain lines and hoses. The attic system drain ties in with the first floor system drain and empties into the foundation. Would recommend installing EZ Traps for each AC drain Aline and a condensation Pump for the first floor system to alleviate the foundation drainage. While inspecting units also found both systems flame sensors testing ok but both were starting to become pitted. Cleaned flame sensors and tested. Would recommend replacement of both OEM Flame Sensors. Performed Combustion Testing on both systems. Spoke with homeowner about installing a Bypass Humidifier for the first floor system.
Replace heat thermostat and removed outdoor unit casing and cleaned coil with water and coil cleaner to Improve efficiency and better heat transfer
Performed gas heat steam boiler check up check electrical low and high ok cleaned pig tail, and burners, check manifold gas pressure ok check water level ok combustion test cycle boiler, check inducer motor ok, inspect all components for any leaks no leaks found cycle unit from thermostat ok performed visual inspection on electric water heater, water heater is from 2009
Reclaimed and removed old ac, coil and heater. Installed a new American standard heater with an American standard coil on top. Adapted all supply ducting as needed and taped and sealed all duct. Ran new copper lines and brazed and leak checked with nitro and soapy bubbles. Installed a new condensate drain with an ez trap wired in. New condensate pump with new vinyl tubing ran over to discharge. Adapted flue piping as needed . Adapted gas piping. Ran a new electrical outlet and switch to unit, installed a new American standard ac unit on a new plastic pad. New disconnect box and electrical wiring to unit. Tested unit in all modes.
Performed heating maintenance, cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections, measured capacitor values ok. Found only 9 psi in boiler, open fast fill and auto fill regulated pressures from 9 psi to 15 psi. Val was stuck. Tested expansion tank ok. Checked circulator ok. Started boiler, performed combustion test. Tested 3 zones 2 heating and 1 domestic hot water. All work.
Performed Precision Heating Tune Up on an Amana Heat Pump system. Replaced 20x20x1 Air Filter. Inspected Electrical Components on Air Handler and Outdoor Unit. Put system in Heating Mode and measured Refrigerant charge on system. Tested system in Heating Mode and with Auxiliary Heat running. Measured 19.1 Amps on Heating Elements for Heat Kit. System operating to standards at this time.
Drain down, disconnect, and remove existing water heater. Install new Bradford White 50 Gallon Powervented Natural Gas Water Heater in an Auxiliary Drain Pan elevated on bricks. Install Water Alarm in Auxiliary Drain Pan. Adapt Piping to the new Water Heater with Expansion Tank. Adapt Gas Piping and Vent Piping to new Water Heater. Fill Water Heater and purge system of Air. Set thermostat to "Hot" Setting and measure Water Temperature and Water Pressure.