Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Joseph was very skilled and carefully reviewed my home’s unique situation. He was caring and engaging. I would highly recommend him!
⭐️⭐️⭐️⭐️⭐️ Chris was professional and understood my needs as well as circumstances, took the time to explain options
Found system vibration was caused by just being an older builders grade system. System is a 2003. Put isolators under system to test if it would help with vibratiOn. This did help. Homeowner doesnâ€™t want to put any money towards this system since it is older. Recommend to homeowner to set up a membership to have the system completely checked out. Homeowner signed up for maintenance plan. Recommend that he starts to think about replacement of the a/c system. Will need to schedule a time to return to complete a/c tune up. Checked refrigerant pressures are ok.
Service call that the AC was not working. Upon arrival found indoor temperature at 83 Degrees and unit was set to 73 Degrees in cooling. The blower motor was running but the outdoor unit was not on. Found broken wiring at the indoor unit control board which was not allowing the voltage to go to the outdoor unit. Repaired wiring and put system in operation. Found 16x20x1 Air Filter was very dirty, replaced Air Filter. Measured refrigerant charge and Air Temperature readings. Measured Amp draw on the compressor which was running with high Amos. Compressor is rated for 16 RLA and was running close to 14 Amps. Also found Contactor on outdoor unit working but very worn and pitted. Also measured a voltage drop across the coil of the Contactor. Outdoor coil has some damage to the fins and some dirt buildup in the coil. Would recommend replacing the Outdoor Capacitor, Contactor, adding a Hard Start Kit, and cleaning the Condenser Coil. The AC system is at least 20 Years old. Due to age and ove
Core sense diagnostic module reading 4 flashes. Locked rotor lockot 45-5 MFD capacitor reading under tolerance. Replaced capacitor. Cycled system. Outdoor coil was dirty. Cleaned outdoor coil.
Performed cooling maintenance, replaced standard air filter. Blew out condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil. Set both thermostats to permanent hold.
Checked thermostat not shutting off. Found thermostat in recovery. Cycled air conditioner it shuts off.
Performed cooling maintenance, replaced standard air. Cleaned eztrap and drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil.
No ac found system off upon arrival set thermostat to call for ac and system was running on heat Reversing valve not getting power, check wiring on stat and found wiring issues connect orange wire into o and white into w terminal check operation ok supply and 60 return air 93 pressure 350/160
Found water heater pilot out again. There is definitely an issue with the water heater gas control valve and or thermopile. These items should be replaced together. Repair would easily be $700-$800. Water heater is 9 years old recommended replacement of the water heater. Told homeowner that it is probably going to go out again and recommended replacement of the tank very soon. Homeowner will let us know her next move.
Light pilot on water heater, set thermostat to b setting.
PECO Heat Pump Tune Up. 24F temp rise. Filter ok. Strip heater amps ok. 20x21x1 filter ok. Thermostat was programmed for a convention forced air system. I reprogrammed stat to heat pump settings with a 4F droop. Compressor amps/outdoor voltage ok. Capacitors ok. Verified condensate pump operation. System is operating well at the time of this maintenance/tune up. Will provide prices estimate for membership in email.
Performed heating maintenance, cleaned eac pre filter. Checked voltage, amperage and electrical connections, measured capacitor values. Tested electric back up heaters. Started heat pump, calculated btu output. Tested defrost cycle. Checked operation and temperature rise across coil.
Performed gas heat tune up, check electrical low and high, filter ok, cleaned flame sensor, check gas pressures performed combustion test check blower motor and cap, check airflow ok, check heat exchanger integrity found lot of rust inside heat exchanger, cycle furnace furnace is working but would recommended upgrading system
Performed Precision Heating Tune Up and Inspection on Gas Furnace. Replaced 14x20x1 Air Filter. Inspected and tested electrical components on furnace. Cleaned Flame Sensor and Spark Ignitor. Inspected Burners and Heat Exchanger Chambers. Cleaned Pressure switch tubing and exercised switch. Leak tested Gas Fittings directly at the Gas Furnace and directly at the Hot Water Heater. Inspected Water Heater for signs of water leakage. Performed a Combustion Test on Gas Furnace and Water Heater. Combustion readings were normal for both the Water Heater and Gas Furnace at this time. Completed Association Inspection Form and dropped form of at main office.
Performed Precision Heating Tune Up/Inspection on Amana Gas Furnace. Replaced 16x25x1 Air Filter. Inspected electrical components and downloaded update to control board. Inspected Burners and Heat Exchanger. Put system in operation and tested in Low Stage Heat and High Stage Heat. Measured Gas Pressures in each Heat Stage and performed Combustion Analysis. Measured Supply and return air temperatures. System operating within manufacturer standards upon completion. Visually inspected Water Heater and performed Combustion Analysis on Water Heater. Found no signs of water leakage at this time. Water Heater is 10 Years old. Will follow up with estimate for the replacement of the water heater. Completed Inspection Form and returned Form to Main Office upon completion.
Performed Precision Heating Tune Up on Gas Fired York Furnace. Replaced 14x24x1 Air Filter. Cleaned and serviced Humidifier. Tested operation of Humidifier and set control to 35%. Inspected Burners and Heat Exchanger on Furnace. Inspected Electrical Components. Blower Motor Capacitor is testing within rating, but is at its lowest recommended rating. The Blower Capacitor was replaced about 3 Years ago. This could b indicating that the Blower Motor is working harder to operate and is wearing. Cleaned Drain Line and Condensation Pump. Put system in operation and performed Combustion Analysis on system. System is operating, but do to age and overall condition, would recommend replacement of the Gas Furnace and upgrading the zone panels and zone dampers at the same time before any issue occur with the Furnace.