Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Joseph was very skilled and carefully reviewed my home’s unique situation. He was caring and engaging. I would highly recommend him!
⭐️⭐️⭐️⭐️⭐️ Chris was professional and understood my needs as well as circumstances, took the time to explain options
Performed Precision Heating Tune Up/Inspection on Amana Gas Furnace. Replaced 16x25x1 Air Filter. Inspected electrical components and downloaded update to control board. Inspected Burners and Heat Exchanger. Put system in operation and tested in Low Stage Heat and High Stage Heat. Measured Gas Pressures in each Heat Stage and performed Combustion Analysis. Measured Supply and return air temperatures. System operating within manufacturer standards upon completion. Visually inspected Water Heater and performed Combustion Analysis on Water Heater. Found no signs of water leakage at this time. Water Heater is 10 Years old. Will follow up with estimate for the replacement of the water heater. Completed Inspection Form and returned Form to Main Office upon completion.
Performed Precision Heating Tune Up on Gas Fired York Furnace. Replaced 14x24x1 Air Filter. Cleaned and serviced Humidifier. Tested operation of Humidifier and set control to 35%. Inspected Burners and Heat Exchanger on Furnace. Inspected Electrical Components. Blower Motor Capacitor is testing within rating, but is at its lowest recommended rating. The Blower Capacitor was replaced about 3 Years ago. This could b indicating that the Blower Motor is working harder to operate and is wearing. Cleaned Drain Line and Condensation Pump. Put system in operation and performed Combustion Analysis on system. System is operating, but do to age and overall condition, would recommend replacement of the Gas Furnace and upgrading the zone panels and zone dampers at the same time before any issue occur with the Furnace.
Arrived onsite to perform Six Month Inspection of Amana Gas Furnace. Upon arrival, homeowner informed me that they were not comfortable with anyone being in the home due to the COVID cases rising. Was informed that the system was operating well with no issues.
Performed Precision Heating Tune Up on Lennox Gas Furnace System. Replaced 16x25x4 High Efficient Air Filter. Tested Electrical Components on Furnace. Inspected Burner Assembly and Heat Exchanger. Removed and cleaned Flame Sensor. Cleaned all Furnace Tubing and hoses. Inspected Blower Compartment. Checked Gas Fittings at Water Heater for leaks. Performed Combustion Analysis on Furnace and measured Air Temperature readings. Also performed Visual Inspection of Hot Water Heater. Performed Combustion Analysis on Water Heater. Water Heater is 8 Years old and is operational with no visible signs of leakage. Would recommend begin planning for replacement of Water Heater before any issues occur. Completed Greene Countries Village Inspection Form Report and delivered in after hours mail slot at office. Included copy of the Form to customer with Tune Up.
Installed hardstart kit with potential relay per schematic and got homeowner to cycled on a/c for left side of house. Running amps was 7.9 amps. Start up amp draw was 23 amps. Also checked incoming voltage was 239 volts. A/c is starting and running correctly at time of service.
Found oil pump is making a wining noise when it runs. Bearings are starting to wear some. Boiler is almost 20 years old. Bearings are not grinding at all yet but homeowner is going to decide weather or not to replace oil pump now or later she will call us back when she decides what she wants to do from here.
Performed precision oil tune up on Columbia oil boiler. Replaced rf1 oil filter and .65x80 b nozzle. Bleed oil lines and vacuumed and brushed out boiler. Performed smoke and combustion test. Oil boiler is working fine at time of inspection.
Installation of a Customer supplied Aprilaire 1850 Dehumidifier to replace the Dehumidifier that was previously installed but was damaged when the basement flooded recently. Collect balance upon completion. Install customer purchased Dehumidifier in same location next to the Furnace. Install in Drain Pan with Float Switch. Duct Dehumidifier to the main ductwork with 8" Flex, and also to pull from the basement using TEE Fittings. Unit is gravity drain into a sump pump. Test operation of Dehumidifier upon completion. Customer would also like us to look at the basement/garage space to see if there are any other options for conditioning the space. Customer is concerned about water that is appearing on the drywall ceiling. 8/28/20. Installed Aprilaire dehumidifier in 30x30 metal drain pan with float switch. Put dehumidifier up on pump up legs. Installed condensation drain with pvc trap to sump pit. Installed 2 10â€ tees with dampers to pull air from basement and from whole house duct w
Follow Up Visit to replace 16x25x1 Air Filter. Showed homeowner how to replace Air Filter and installed a new 16x25x1 Filter. Homeowner would like to start the Service Membership in April for the AC Tune Up. Checked Thermostat to ensure the Filter reminder was cleared. The office will contact to schedule the AC Tune Up/Service Membership.
Assessed ductwork that was run through slab and moisture damage to hardwood floors. Need to research sealant and protective finish for duct system. Recommended Mold and More for duct cleaning.
Checked dehumidifier not working, found that dehumidifier was under water from a flood. Dehumidifier display is blank and is bad can not check further but motors and controls may be damaged. Recommend replacing dehumidifier.
Installed new amana 2 stage gas furnace with single stage 3 1/2 ton a/c system. Installed furnace on legs with new 24x10 return drop. Adapted to metal supply plenum. Sealed exsisting condensate hole in cement. Added condensation pump and pumped water into wash sink next to furnace. Installed new reme halo in supply plenum. Tested furnace in both heating and cooling modes. System is working fine at time of install.
Service call that the Indoor Coil was freezing and the system was not cooling. Homeowner shut AC off for the night and ran the fan to defrost the indoor coil. Inspected coil to ensure it was free of ice. Put system in operation to test. Measured a 7 degree temperature split between Supply air and Return Air. Measured refrigerant charge which was low and below the freezing point. Added 2lbs of R-22 Refrigerant to system charging by Superheat standards. Recommended Superheat was 18 degrees, charge system to a 7 Degree Superheat. Supply Air and Return Air split increased to 18 degrees. Checked Condensation Drain Line and blew through. Poured 1 Cup bleach through drain line to help clean. Refrigerant was added to system 2 months ago, indicating that the leak is starting the increase. Recommend replacement of the full Furnace/AC system before any further issues. Joe will follow up to review the original proposal for system replacement that was provided.
Found a/c to not be a ductless system, but a thru the wall a/c very close to a window unit. Told homeowner we donâ€™t service theses units but I can check for power at the outlet to see if this is why unit in not coming on. Checked for voltage and found 243 volts going to unit. Homeowner had un plugged about 12 times yesterday and nothing came on. While I was there unit came on and display came on and started Cooling . Told homeowner that the display or board inside unit may be going bad and told her the a/c will probably shut off again and she should just replace the unit do to theses units are not worth repairing. Performed maintenance on system. Checked temperature split, and wasable filter was just cleaned. There is no model # on system that is visible. Homeowner is probably going to try to find the unit online and replace themselves if other issues occur.
Service call that the AC was not working. Upon arrival found Outdoor Fan was running and the compressor was trying to start and would shut down immediately. Found a burnt wire from the Contactor to the Capacitor. Tested the start Capacitor which had previously been noted to be replaced. The Start capacitor was testing well below its rating range. Installed a new 88-108 Mfd Start Capacitor with starting relay and wired into the system. Repaired the damaged wire from the Contactor to the Dual Capacitor. Put system in operation to test. Measured Amp draw on the compressor at startup and during runtime. Measured voltage across Contactor. Took a refrigerant measurement and measured Supply and return air temperatures. If system continues to have issues the recommendation will be to replace the AC system. If the compressor wires are burning up this is due to the compressor drawing higher amps during startup and run. Due to age and overall condition of the AC would recommend to begin plannin