Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
He and dave did great professional job and explained everything we asked
This company added a heating and cooling system to our second floor. They were very professional and so easy to work with. They came up with a great HVAC system for our major home renovation. Their work was excellent and they tailored the stages of the job to work perfectly with the other professionals who were here working as well. Their workers are very polite and clean up meticulously. My husband and I are really pleased and impressed with the job they completed.
Performed Six Month Heating Inspection on Amana Gas Furnace. Replaced 16x20x1 Air Filter. Cleaned Condensation Pump, refilled, and tested operation. Inspected Wiring on Control Board and verified Blower Speeds. Performed Combustion Analysis, measured Gas Pressure, and Supply/Return Air Temperatures. System is operating to standards at this time. Humidifier is operating and set properly. Homeowner is going to replace Water Panel for the Humidifier.
Replaced old steam humidifier with new aprilaire model 800 steam humidifier. Replaced existing hose with copper and rubber up to duct and replaced steam distribution pipe. Installed new inline filter and new drain.
Performed heat pump check up check electrical low and high ok replace filter service humidifier test electric heat back up ok check split blower wheel and coil ok outdoor unit pressures 410 capacitor and contactor ok cycle and test defrost ok
Replacement of the Drain Spud for the Humidifier Drain Line On System #2. The Drain Spud is broken and the Vinyl Tubing Drain Line is very loosely connected due to having a very small connection. Replace the Drain Spud and install a new piece of Vinyl Tubing from the Drain Spud to the PVC Drain. Replaced ignitor on Weil McLain boiler. Cycled boiler and checked operation. Went to replace spud drain on craw space heat pump, found that the craw space flooded from yesterdayâ€™s rain. Need time for craw space to dry to access humidifier. Collected balance need to return to replace humidifier spud drain.
Performed heating maintenance, replaced and cleaned air filters. Serviced humidifiers, cleaned and replaced water panels. Found craw space humidifier need a spud drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Tested heat pump electric back up heaters. Started heat pumps, measured btu output. Checked operation and temperature rise across coils. Tested defrost cycles. Serviced gas furnace cleaned boiler heat exchanger, found ignitor failing on boiler. Inspected furnace heat exchanger. Blew out condensate trap. Cleaned flame sensor. Started gas furnace, tested limit and safety switches, performed combustion test. Checked operation and temperature rise.
Service call and Quality Assurance for new system installation. Water was in the Auxiliary Drain Pan and caused the Wet Switch to Shut the System down. Found the Condensation Drain Pipe was piped into the Secondary Drain Line. This was causing the water to overflow and leak out the Primary Drain Plug. Repiped the EZ Trap and Drain Line to the Primary Drain. Poured water through the Trap to test. Reset Wet Switch and placed on paper towel in pan. Completed Quality Assurance and reviewed installation and water leak with homeowner. Completed Checklist Form in System. Corrected any issues that were found.
We will install a new return duct in the hallway wall and run a new duct to connect to the main return in basement and pan off the necessary area to connect. We will relocate the 2 supply registers on the first floor in the kitchen area and connect to the main supply duct. The airflow to each register will be measured. We will run new ducting for the dehumidifier to connect the dehumidifier to the existing duct system. Tees will be installed with dampers so the airflow can be adjusted to pull air from the basement or the main house. We will install a new supply duct for the first floor laundry room/bathroom that will be a wall type register and run a new duct in the basement and connect with a collar with balancing damper.
Installed new attic air handler and 7 flex runs. Cut in supply grills. Cut in new central return. Ran new thermostat wire and installed thermostat. Ran lineset and tied into new outdoor heat pump. Leveled pad. Brazed in with nitrogen and evacuated to 170 microns. Ran electric circuits from panel to air handler and condenser. Ran new condensate pipe with ez trap and wet switch in Auxiliary pan. Installed linehide down side of house. Connected 4 flex runs in crawlspace. Installed dehumidifier in return drop of first floor system. Adjusted refrigerant charge and tested. System operating perfectly at time of install. Delta t28.
Found great room and second floor capacitors weak, replaced both capacitors.
Performed Quality Assurance Inspection on recently Installed Amana Gas Furnace/AC system. Reviewed Installation with Homeowner. Completed Checklist Form in System.
Reclaimed and removed old equipment. Installed new pad, disconnect, whip, and outdoor condenser. Ran new line-set and low volt wire. Brazed in outdoor unit with nitrogen. Installed new gas furnace and evaporator. Modified and reconnected ductwork. Reconnected venting, gas, electric and condensate. Leak checked gas. Installed new pump and ez trap. Brazed in line set to evaporator. Pressure tested to 300 and leak checked, no leaks found. Evacuated down to 246 microns. Ran vinyl to discharge line. Replaced air filter. Tested unit and adjusted charge. System working properly at time of install. Delta t 21.
Performed cooling maintenance, checked washable air filter ok. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started heat pump, checked refrigerant charge and temperature drop across coil.
Performed precision a/c tune up on a/c systems. 3 mini splits, one with 2 indoor heads. Washable filters were clean. Performed a/c tune ups on 4 trane a/c systems. Replaced 3 Aprilaire 213 air filters and 1 16x25x1 air filter. Blew out all condensate drains and tested pumps. Also checked all electrical conections and components. Checked refrigerant pressures and temperatures, all systems working fine at this time.
Performed ac check up, check electrical low and high voltage ok replce filter, flushed drain ok add tabs, check outdoor unit 410 pressures ok contactor and capacitor ok, cycle heat pump ok installed ecm motor protector indoor and on outdoor unit,
Current system is, heat pump with electric heat backup, talked to customer about situation, he thinks leak is coming from unit, went to roof and inspect unit, found lower side of roof line uncovered not sealed, check return and supply ok, silicone all lower part of unit curve, unit is sealed completely all way around,