Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Installers were great
Kurt came to repair my heating system. He was prompt, courteous, and resolved the issue we were having with our heating/ cooling system.
He and dave did great professional job and explained everything we asked
This company added a heating and cooling system to our second floor. They were very professional and so easy to work with. They came up with a great HVAC system for our major home renovation. Their work was excellent and they tailored the stages of the job to work perfectly with the other professionals who were here working as well. Their workers are very polite and clean up meticulously. My husband and I are really pleased and impressed with the job they completed.
Caulk seal around new filtered grill in lower floor. No charge for this visit.
Performed Quality Assurance inspection on a newly installed gas furnace and air conditioning system. System was running while doing QA. Inside temp split of 50/70. Running great at time of QA. All wiring proper and secure. No leaks on gas line connections. No leaks on condensate drain. Outdoor unit level and proper. Disconnect off level but looks like they matched it up to cover unpainted wall area behind. System looks great. Installed filtered return grill on wall. Need to swing by one day and caulk around new return grill I installed. Did not have white caulk.
Reclaimed and removed old equipment. Installed new leveled pad, disconnect, whip, and American standard condenser. Cut open wall between studs and Ran new lineset in 3 pieces, used zoom lock fittings and brazed in with nitrogen. Installed new American standard furnace. Placed new coil on top and brazed in with nitrogen. Pressure tested to 300 psi and evacuated down to 135 microns. Fabricated a plenum and sealed all ductwork. Reconnected gas and leak checked. Installed new ez trap and pump and ran condensate piping. Ran new vinyl to discharge. Reconnected Flue piping. Installed new receptacle and switch and reconnected electric. Wired in low volt. Tested all functions. Found stand pipe was clogged and blew out with gallon gun and tested. Performed combustion test and adjusted gas pressures. Charged unit to specifications. System running great at time of install.
Checked no cooling complaint on carrier heat pump, found outdoor fan not running. Checked run capacitor, found open capacitor. Replaced dual run capacitor. Started air conditioner, checked operation and refrigerant charge ok.
Add ac renew to lubricate all internal parts of the refrigeration system, compressor, compressor valves, indoor and outdoor txv and also reversing valve, will improve compressor efficiency and lower compressor noise
Performed quality check, checked air filter ok. Checked voltage, amperage and electrical connections, tested electric back up heaters. Started heat pump, tested defrost cycle, measured refrigerant charge in cooling mode. Checked operation and temperature drop across coil. Jeannine Will contact us when she is ready to finish the garage.
Performed four split ac units check ups, check electrical low an high ok replace filters (3) 213 and one 16x25x1 Flushed drain and test pump ok tuned off humidifiers, check splits ok outdoor unit refrigerant pressures and electrical components ok capacitor and contactor ok cycle all four units ok, recommend adding ac renew for unit 1 and 2 compressor is making noise, adding ac renew will lubricate all internal moving parts will work more efficient and will help prevent any compressor damage, also air handler 2 has mold informed customer and recommended adding uv light treatment,,,,also performed ac tune up on mini splits units each unit has two indoor units one is straight ac and other one is heat pump both duct less units checked out ok clean all filters and inspect indoor and outdoor coils ok, emailed proposal for units 1 and 2
Performed precision a/c tune up on trane heat pump system. Replaced 20x22x1 air filter. Checked all electrical conections and components. Blew out condensate drain. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at time of service.
Found contacter burned and pitted. Replaced 1 1/2 pole contactor. Also performed precision heat tune and a/c tune up on Bryant hybrid system. 16x20x1 air filter is clean. Checked all electrical conections and components. Cleaned flame sensor. Blew out condensate drain and pressure switch tubing. Checked operation of heat pump in heating mode. Tested condensate pump. Performed combustion test. Checked heat pump in a/c mode. System is working fine at time of service.
Found locked up 1/2 hp psc blower motor. Found 123 volts going to blower motor but motor is tight and locked up. Gave homeowner option to ethier replace furnace or blower motor. Homeowner wanted to replace blower motor for now so replaced motor and system is a hybrid. Heat pump with propane back up so checked temperature rise in heat pump mode. Temperature rise was 18 degrees in heat pump mode. Customer is a new customer so suggested they sign up for a service contract to have the savings on the repair. Homeowner signed up for membership, system is back up and working fine.
Performed precision peco heat tune up on carrier heat pump. Replaced 18x20x1 air filter. Found dirty evaporator coil. Cleaned with coil brush and evaporator coil cleaner. Checked all electrical conections and components. Blew out condensate drain. Checked operation of emergency heat. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at time of service.
Found alert code on thermostat was just a 3 month filter reminder. Checked air filter and it was very dirty 20x20x1 air filter is dirty from construction dust. Homeowner to replace. Removed filter for now to test out system. Also where air filter is located it can be moved to other bedroom location but then it is also far away from where the stair case rises up for cooling season and may pre- maturely shut off in a/c time. Homeowner wants to keep the thermostat where it is at for now. Started up heat pump system. Heat pump went into a/c mode when it was supposed to be in heating mode. Disconnected orange wire for reversing valve at outdoor heat pump and system went into heating mode. Went up in attic and had 24v at o wire. Went into settings on t6 thermostat and found everything was set up correctly, and wired correctly at base. Replaced t-6 thermostat head and put into heat pump mode. Now have 22 degree tempature rise and pressures were 285/80 410a. This will make a big difference for
Replaced spud drain on craw space humidifier, removed broken spud drain and installed new spud drain, connected. Started and checked operation.
Performed Six Month Heating Inspection on Amana Gas Furnace. Replaced 16x20x1 Air Filter. Cleaned Condensation Pump, refilled, and tested operation. Inspected Wiring on Control Board and verified Blower Speeds. Performed Combustion Analysis, measured Gas Pressure, and Supply/Return Air Temperatures. System is operating to standards at this time. Humidifier is operating and set properly. Homeowner is going to replace Water Panel for the Humidifier.
Replaced old steam humidifier with new aprilaire model 800 steam humidifier. Replaced existing hose with copper and rubber up to duct and replaced steam distribution pipe. Installed new inline filter and new drain.