Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Technicians very knowledgeable
Highly Recommend DiBiase for their service. Their technicians are very knowledgeable and professional. They prepared a proposal before the work was completed so we knew the cost upfront. The technicians were on time and friendly and we liked getting a text knowing they were on the way.
From the first phone call to DiBiase to the tech’s house call, this has been an excellent experience.
This is the first time that Brian, the technician serviced some rental property heaters, as part of the maintenance plan. There are no surprises, and a lot of communication before, during and after the appointment. DiBiase wants to know that the customer is satisfied....and I am!
Excellent technician, on time and very polite.
Performed precision heat tune up on 80% amana gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Checked gas pressure and performed combustion test. Heating is uneven in certain parts of the home recommend ecobee 4 with room sensor. Gas furnace is working fine at time of service.
Performed heating maintenance, checked air filter ok. Found electric heated cycle on limit and no blower. Found thermostat is not calling for electric heat, found electric heater relay stuck closed. Replaced electric heat relay. Tested electric back up heaters. Started heat pump, measured btu output. Tested defrost cycle. Checked operation and temperature rise across coil. Serviced humidifier and replaced water panels. Started and checked operation. Set humidistat to 35% rh.
No heat, found unit on lock out upon arrival, pressure switch problem, noticed a blockage on pressure switch tubing, and also flame sensor is dirty, quoted for repairs, customer ok the required repairs for today to get heater running, however the inducer motor is making loud noise, and indication the bearings might be failing, and also blower run capacitor is reading 2.8 taped at 5 talked to land lord and explained situation and she only wants the required repairs for today, and donâ€™t want to change blower capacitor, there will be a service charge if we have to come back for blower issue, cycle heater after todayâ€™s repairs and also combustion test heater is running at this time, emailed land lord estimate for capacitor and inducer filter should get replace immediately and also every 30 days
No heat two system house two gas heaters and 2 ac units found both furnaces in the off position also gas off to heaters, start heaters and performed combustion test co levels within good range inspect both heat exchangers, smoke test and also performed heat exchanger test with blower on and off, during visual inspection did found lot of corrosion around the plate rings, and also on the back part, did not see any visual cracks but on my results with blower, there was change on oxygen and excess air when blower came on, and also oxygen went up by 2.5 percent, with this results shows that some air is getting into chamber, attention is needed on both furnaces, no visual cracks were found, but both heat exchangers showing change on oxygen and excess air, carbon monoxide in the exhaust is 43 for one and 18 on the other informed customer about situation, joe to come out tomorrow between 2 and 4 pm for house evaluation for proper system replacement proposal
Performed precision heat tune up on crown oil boiler . Replaced.85 45b nozzle. Replaced rf1 oil filter. Cleaned out boiler and brushed out smoke pipe. Performed combustion test on boiler. Cycled thermostat to heating, and made sure pipes were getting hot. Oil furnace is working fine at time of service.
Performed heating maintenance, checked media air filters. Serviced humidifiers, cleaned and replaced water panels. Checked operation. Set humidistat to 40% rh. Serviced gas furnaces, cleaned burners and flame sensors, inspected heat exchangers. Blew out condensate traps. Checked voltage, amperage and electrical connections. Started gas furnaces, measured fuel pressures. Tested limit and safety switches. Performed combustion test. Checked operation and temperature rise.
Service call that the AC was not working. Was informed that they experienced lightning and a partial power outage. Arrived onsite and found the Thermostat set to 70 Degrees and the Indoor Temperature was at 74. Proceeded to the Attic Air Handler to troubleshoot. The Fuse on the Air Handler has blown. Tested system with a resettable Fuse and determined that the Wet Switch Safety Device had shorted internally and this was causing the Fuse to blow. Installed a new Wet Switch Safety Device and a new Fuse for the Air Handler. Put system back in operation and tested. Tested Voltages and Amp Readings on System. Measured Refrigerant Charge and Inspected Wiring. System is operating to standards. No Charge for the replacement of the Fuse.
Drained 2nd floor boiler loop. Removed bathroom hydronic baseboard. Capped off loop to baseboard in basement boiler room. Removed and replaced leaking 3/4 elbow with new progress fittings. Refilled and purged air from boiler as well as possible without radiator in place. 9/27/19 installed 2 ft baseboard and purged air from loop. Everything is getting hot, no leaks.
Replaced power vented 50 gallon natural gas water heater with pan and water alarm 6 year tank/parts 2 year labor. Installed new expansion tank. Tested water temperature. Performed heat tune up. Replaced filter. Installed intake vent drain kit. Found evidence of water coming through it. Piped into existing condensate line. Tested gas pressures and combustion. Everything working well at time of service.
Went over job with homeowner. Homeowner is going to get bathroom remodeled . Existing basebord in room now is around 7 feet long. Bathroom is 7 ft by 6 ft. Homeowner would like a price to replace baseboard with a 2 ft piece of baseboard. He whould like an email sent to him with a picture of the baseboard we would install. Also would like one 3/4 90 that is corroded on a piece of baseboard. Talked to homeowner about outdoor reset and replacing the 2 exsisting air bleeders. Office to get back with quote.
Customer has oil boiler, two zones, baseboard heat, both loops have some joints that are leaking, and also wants to replace and add some baseboard in some areas, customer wants pricing on replacing baseboard and moving other baseboard
Performed Quality Assurance On Amana AC and Air Handler. Replaced 24x24x1 Air Filter. Reviewed Installation with Homeowners son. Reviewed and tested system based on the Sons questions/concerns, and corrected any issues that were found. Completed Checklist Form in System.
System not cooling. Found blower motor running. Liquid line extremely hot. Checked condenser and found fan not running. Checked capacitor, measured ok. Bad condenser fan. Installed rescue motor and new 45/5 capacitor. Tested system. Checked r22 pressures. Measured 184/69. System operating as it should.
Performed two peco heat pump check ups, check electrical low and high ok both filters ok coils are clean capacitor and contactor ok pressures 410 ok flushed drain ok attic unit does not have ez trap recommend ez trap customer want to hold on ez trap at this moment, customer has ductless heat pump that is not working correctly quoted to trouble shoot unit customer also wants to wait on the troubleshooting for mini split Both units are 18 000 btus
Installed new air handler and ac unit, along with a new ez trap and wet switch with a new pan the plenum sure were re attached and sealed. The outdoor was set on concrete deck with new pad whip disconnect . We flushed the line sets and brazed with nitrogen. Pressure tested to 352 for 20 minutes triple evacuated and pumped down to 342 microns and held for 10 minutes added 13 ounces for charge system was running great. When we come back we need to put in a new 24x24x1 filter I didnâ€™t have a new one on the truck. NEEDS 24x24x1 filter