Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
From the first phone call to DiBiase to the tech’s house call, this has been an excellent experience.
This is the first time that Brian, the technician serviced some rental property heaters, as part of the maintenance plan. There are no surprises, and a lot of communication before, during and after the appointment. DiBiase wants to know that the customer is satisfied....and I am!
Excellent technician, on time and very polite.
Went over job with homeowner. Homeowner is going to get bathroom remodeled . Existing basebord in room now is around 7 feet long. Bathroom is 7 ft by 6 ft. Homeowner would like a price to replace baseboard with a 2 ft piece of baseboard. He whould like an email sent to him with a picture of the baseboard we would install. Also would like one 3/4 90 that is corroded on a piece of baseboard. Talked to homeowner about outdoor reset and replacing the 2 exsisting air bleeders. Office to get back with quote.
Customer has oil boiler, two zones, baseboard heat, both loops have some joints that are leaking, and also wants to replace and add some baseboard in some areas, customer wants pricing on replacing baseboard and moving other baseboard
Performed Quality Assurance On Amana AC and Air Handler. Replaced 24x24x1 Air Filter. Reviewed Installation with Homeowners son. Reviewed and tested system based on the Sons questions/concerns, and corrected any issues that were found. Completed Checklist Form in System.
System not cooling. Found blower motor running. Liquid line extremely hot. Checked condenser and found fan not running. Checked capacitor, measured ok. Bad condenser fan. Installed rescue motor and new 45/5 capacitor. Tested system. Checked r22 pressures. Measured 184/69. System operating as it should.
Performed two peco heat pump check ups, check electrical low and high ok both filters ok coils are clean capacitor and contactor ok pressures 410 ok flushed drain ok attic unit does not have ez trap recommend ez trap customer want to hold on ez trap at this moment, customer has ductless heat pump that is not working correctly quoted to trouble shoot unit customer also wants to wait on the troubleshooting for mini split Both units are 18 000 btus
Installed new air handler and ac unit, along with a new ez trap and wet switch with a new pan the plenum sure were re attached and sealed. The outdoor was set on concrete deck with new pad whip disconnect . We flushed the line sets and brazed with nitrogen. Pressure tested to 352 for 20 minutes triple evacuated and pumped down to 342 microns and held for 10 minutes added 13 ounces for charge system was running great. When we come back we need to put in a new 24x24x1 filter I didnâ€™t have a new one on the truck. NEEDS 24x24x1 filter
Performed heating maintenance on gas furnace, replaced air filter, inspected heat exchanger. Cleaned burners and pilot burners. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started gas furnace, performed combustion test. Tested limit and safety switchâ€™s. Checked operation and temperature rise.
Performed heating maintenance on gas boiler, checked expansion tank, checked boiler pressure. Cleaned burners and pilot burner. Inspected heat exchanger. Started gas boiler, tested limit and safety switch, measured fuel pressure, performed combustion test. Paid for on work order 13232
Checked no cooling complaint, found indoor coil iced up, thawed coil, checked refrigerant charge, found low on charge. Topped off refrigerant charge, checked operation and temperature drop across coil.
Performed precision ac tune up on older American standard system. Replaced 20x25x1 air filter. Checked all electrical conections and components.found a lot of gunk in drain line recommended ez trap to protect drain line.Blew out condensate drain and tested pump with water. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is getting older but still working at theme of service.
Checked condensate leak, removed cover and accessed pan, found no drain connected to the drain. Checked below and see no drain run. Also there is thermostat wire used as high voltage to indoor heads. Would need to remove heads to run condensate drain and replace line voltage between heads and outdoor. Recommend replacing vs repaired due to condition of the heads.
Performed precision ac tune up on Lennox ac. Replaced 20x24x1 air filter. Checked all electrical conections and components. Blew out condensate drain and tested with water. Checked refrigerant pressures and temperatures at indoor and outdoor units. Found weak indoor blower capacitor recommended replacement. System is working at time of service.
Estimate for Crawl Space which is experiencing high humidity. Spoke with homeowner upon arrival and reviewed Crawl Space and Duct. Took pictures and recorded measurements in the notes. Told homeowner we will follow up with an estimate for repairs.
Performed cooling maintenance on 2 air conditioners, replaced 2 rp413 media filters. Cleaned condensate drain and pump. Inspected cooling coils. Checked voltage, amperage and electrical connections, measured capacitor values. Found second floor air conditioner capacitor rating below rated value. Replaced second floor run capacitor. Checked air conditioners refrigerant charge and temperature drop across coils.
Performed ac check up, check electrical low and high ok replace filter, flushed drain ok test pump check split ok outdoor unit 410 pressures capacitor and contactor ok cycle unit ok noticed water heater is old recommend replacing with new one quoted for new one