Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Nathan Pitner and Dan Swenson were courteous and professional. Did a great job in a very timely manner. Also loved the advance text message with the technicians photo. We will highly recommend DiBiase Heating and Cooling Company to our family and friends.
Performed precision a/c tune up on carrier a/c system. 16x25x1 air filter is clean. Checked all electrical conections and components. Blew out condensate drain. Added new capacitor and hard start kit. Checked temperature split at indoor unit. Checked refrigerant pressures and temperatures at indoor and outdoor units. A/c system is working fine at time of service.
Performed six month quality, checked air filter ok. Tested water safetyâ€™s. Cycled furnace. Started heat pump, checked btu output. Tested defrost cycle. Checked operation and temperature rise across coil.
Replaced burners and pilot assembly. Checked for gas leaks, no leaks found. Performed combustion test. Package gas furnace is working fine again at time of service.
Found system to be firing intermittently burners are extremely corroded and pilot assembly is also corroded. Recommend replacing both burners and pilot assembly.
Found open condensate safety. Pump is constantly energized. Length of vinyl tubing is frozen outside. Hard piped to 1â€ PVC with appropriate bushings and fittings. System is operating well at the time of this service.
Performed QA on American Standard Furnace/Heat Pump install. Completed checklist form in system. Reviewed install with homeowner. Tested system in all heating modes and tested static pressures and temperature splits. Adjusted heating fan speeds for gas furnace. This install did not Pass the QA. Addressed all issues that were found. Please see my notes below from Checklist: Thermostat was not secured to the wall and they did not put any anchors in the screws so it was just pulling off of the wall. Also the top screw wasnâ€™t even holding the wiring terminals plate. Wiring at the outdoor unit needed to be corrected. The wire nuts were too small for the high voltage and there was exposed wiring. Put larger wire nuts and taped. Also taped and secured the low voltage wiring. Condensation Vinyl Tubing and thermostat wiring were just hanging loose in the two closets in the basement. Secured the vinyl tubing and wire. The lineset hole outside was not sealed at all. Sealed around L
Installed new American standard furnace and coil. Installed new heat pump on new leveled pad. Ran new 7/8 lineset. Installed new supply plenum and return drop. Installed new condensate pump and vinyl tubing. Ran new 8 wire to thermostat. Adapted to existing flue and intake. Adapted to existing gas line. Installed new Lp kit. Installed new switch an outlet. Tested system in heating and aux heat. Tested condensate system. System running properly. Payment collected.
Performed propane gas furnace check up, check electrical low and high voltage connections, check air filter ok, check burners and pilot assembly, inspect heat exchanger, performed combustion test check blower motor and cap, check temperature split supply and return ok, cycle gas furnace ok would recommended system replacement current system is from 2001
Performed heating maintenance, replaced air filter, blew out condensate trap and drain. Cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections, measured capacitor values. Started gas furnace, tested limit and safety,performed combustion test. Checked operation and temperature rise.
No Heat 80K BTU Propane Furnace with electronic spark ignition/smart valve. Cleared pilot tuning. Cleaned senor and ignitor of pilot assembly. Cycled furnace several times. Burners and heat exchanger ok. Electrical components ok. Combustion test:passed. Homeowner became plan member. Furnace is operating safely at design conditions at the time of this service.
Performed Six Month Heating Inspection on Amana Gas Furnace System. Replaced 16x25x1 Air Filter. Cleaned and tested Condensation Pump. Insulated the 2â€ PVC Exhaust Pipe on the exterior of the home. Performed Update on Control Board and put system into operation. Performed Combustion Analysis on Furnace and measured Supply and Return Air Temperatures.
Performed 6 month inspection on recently installed propane furnace, check all settings electrical connections low and high ok, replaced filter, test pump check supply and return airflow/temp ok check manifold pressure on 50% and 100% performed combustion test cycle furnace ok.
Performed quality assurance on recently installed furnace and ac, check all electrical wiring ok, check condensation drain, pump and ez trap ok, test pump, ran furnace and ac, check supply and rerun air for ac mode 74/55 made little repairs on drain kit for intake, nothing big. Check settings on cool cloud ok check outdoor unit, disconnect and whip going to unit ok overall installation look good, we keep unsung cable ties to strap txv bulb, also exhaust run about 10 feet after wall termination not sure if we have to insulate exhaust, will be management decision to insulate 2 in pvc exhaust
Removed existing 60k furnace. Installed new Amana furnace and air conditioner. Installed new return drop and adapted to existing supply. Installed new lineset and linehide. Installed new switch and outlet combo. Installed new ez trap condensate pump and vinyl tubing to indoor discharge. Pressure tested and evacetued below 500 microns. Tested system in heating and cooling. System working properly. System install went over with customer. Payment collected
Customer has open loop carrier geothermal, water coil is leaking check water piping in and out no sign of connections leaking, water is coming from water coil, new water coil is needed, we will contact customer for repairs.