Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Nathan Pitner and Dan Swenson were courteous and professional. Did a great job in a very timely manner. Also loved the advance text message with the technicians photo. We will highly recommend DiBiase Heating and Cooling Company to our family and friends.
Perform AC tuneup check electrical low and high voltage connections flush drain test pump check supply and return air temperature blower motor and cap OK check outdoor unit refrigerant pressures capacitor contactor cycle unit noticed capacitor is just below the rating inform customer and recommend a replacement customer will think about repairs also recommended adding whole house air filtration system reme halo and air cleaner emailed proposal for recommendations
Found after going over System checked refrigerant pressures, 410a pressures were 225/112 at 64 degrees. Also checked temperature split, found temperature split to be 20 degrees which is good. Also checked to see if any water damage was done to the duct work or system itself, found no water damage to duct work or equipment. After looking over System found that where we capped off the the return duct, there was still a few returns we had missed to include during installation. This is not helping the thermostat active temperature. Thermostat is set to 70 degrees and is only achieving 76 degrees. Now at this point there is de- humidifiers running and creating extra heat in the house to dry out from water leak. We will need to return and reconnect these returns with panning in order to create more draw on the first floor.
Duct cleaning by Mold and More. DiBiase subcontracted them for the service. Job was completed and Customer was satisfied with the service.
Performed Quality Assurance Inspection on Amana System. Reviewed installation with homeowner. Homeowner has several concerns that she thought were supposed to be part of the Installation (See notes in checklist). Need to speak to Tony and have him follow up with the customer. Addressed and corrected any issues that were found during the Inspection. Completed checklist form in system. Collected customers PPL information to process any eligible rebates.
New install today customer has no heat upon arrival found thermostat calling for heat and unit running, check unit previous history codes, no errors were showing on heat pump or furnace side, cycle unit couple times ok test condensation pump ok, went all settings on unit ok thermostat is set to one heat one cool, found no issues at this time, system is working
Reclaimed and removed old heat pump. Removed old coil and heater. Installed a new amana gas heater and converted it to propane. Installed a new amana coil on top of furnace. Modified supply ductwork as needed and taped and sealed all joints. Modified a piece of thermo pan to shut return bay and foamed it closed. Flushed lineset and brazed and leak checked with nitro and soapy bubbles. Installed new amana heatpump on a new plastic pad and snow feet underneath. New disconnect box and electrical wiring to unit. Installed a new condensate drain with an ez trap wired in. Ran new condensate vinyl tubing out where water softener drain into front of house. Installed a new filter rack in the unit with a 16/25/1 filter. Installed a t10 thermostat and tested unit in heating and heatpump mode.
Service call that the Gas Furnace was not working. Upon arrival spoke with customer about issue. Was informed that the system went through several attempts to start and run and then began to run later. Turned heat up to test operation. Found inducer motor running but pressure switch was not closing. Found a bees nest in Intake Vent Pipe at burner box screen. Removed and blew through Intake and Exhaust Piping and removed another bees nest from the intake pipe. Exhaust Vent pipe had a lot of water that had accumulated. Found the Exposed Exhaust Pipe is pitched the wrong way in one section. This could be causing water to pool and not drain properly which could also cause pressure switch problems in the future. Cycled system multiple times and measured pressure across the Switch. Pressure switch was rated for 1.4â€ WC and was testing at 1.7-1.8â€ WC upon completion. Burners on unit are very rusted. Also found Heat Exchanger was very rusted. Cleaned Flame Sensor and performed a combustion
Performed heating maintenance, checked air filter. Ok. Blew out condensate trap and drain. Cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections, measured capacitor values. Started gas furnace, tested limit and safety switches. Maintenance fuel pressures. Performed combustion test. Checked operation and temperature rise.
Performed heating maintenance, checked air filter. Blew out condensate trap. Checked voltage, amperage and electrical connections, measured capacitor values. Cleaned burners and flame sensor, inspected heat exchanger. Started furnace, tested limit and safety switches, measured fuel pressures. Performed combustion test. Checked operation and temperature rise.
Performed both heat and a/c tune up on carrier propane gas and a/c system. 16x25x1 air filter is clean. Checked all electrical conections and components.blew out condensate drain. Checked gas pressure. Performed combustion test. Checked refrigerant pressures and temperatures at indoor and outdoor units. Both gas furnace and a/c are working fine at time of inspection. Found flame sensor worn almost entirely thru. Called distributer for price and availability. 4/22/20. Installed flame sensor and checked flame signal. Had a reading of 5 micro amps . Furnace is functioning correctly at time of service.
Performed ac tune up check electrical low and high ok replace air filter, flushed drain and test pump ok added tabs, check temp split ok check outdoor unit refrigerant pressures capacitor and contactor ok noticed locked rotor amps are over 100 with potential relay and start capacitor only draws 26 amps informed customer and recommended converting to cscr customer will think on that option
Performed precision heat tune up on comandaire geothermal. Replaced Aprilaire 213 air filter. Checked all electrical conections and components. Did have some corrosion around loop circulator pump, but no water leaks. Checked air temperature rise which was 22 degrees. Also had a 7 degree water delta t . Which is good. Checked compressor amp draw, it was within specs. Geothermal is older but is working fine at time of service.
Performed LP gas heater check up, check electrical clean filter test pump ok recommended replacing flame rod and blower cap, customer ok with pricing blower cap reading 12.5 rated at 15" and rod is in bad shape cycle ht gas pressures combustion test ok, recommend replacing burners lot of rust on the end cones, and carry over,
Tested hot water heater pressure at 80psi and house pressure is 50psi. Expansion tank is good . Relief valve needs to be replaced. Replaced relief valve and tested out . Checked for water leaks around new relief valve . Relief Valve never opened after water heater satisfied. Tested temperature, pressure and full operation of water heater and Water heater is running to standards.
Tested hot water heater pressure at 80psi and house pressure is 50psi. Expansion tank is good . Relief valve needs to be replaced.