Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Woke up to a temp of 58 degrees. Heater not working. Prompt response to my service call to replace the igniter on the same day. Very professional and trustworthy company.
Kurt and Mike were extremely courteous and resolved our problem efficiently
Luis was very professional and efficient in his work! I am giving this service call a five-star rating assuming that my furnace issue has been resolved and will not require any return visits.
On time, pleasant and good service.
Serviced my central AC unit. Everything was done to my satisfaction. Was able to schedule my appointment quickly. Received photo of Tech that was coming out and reminder of appointment. Brian and Zach were friendly and very professional. Spoke with Chris on the phone and he gave me some very useful information about my system. Would very definitely recommend DIBIASE. The best I've run across in many years as a homeowner.
Everything went well.
Chris and Alex performed the Quality Assurance Review of our recent HVAC installation. Their review was very thorough, and all of my concerns/questions were addressed to my satisfaction.
Paul, Mike and Andy were courteous, respectful and efficient in the installation of our new HVAC system.
Customer stated they furnace was not working this morning, upon arrival found thermostat satisfied at temperature test furnace for over 30 mins twin system, both furnaces come on with no issues, both units come on and off based on thermostat demand, both heaters are working could not find any issues, would recommend setting thermostat at fixed setting to see if problem was about thermostat scheduling,
No heat, customer stopped working last night, found heater running upon arrival, did not find any error codes on control, check heater operation cycle couple times clean sensor and check ignition, did noticed inducer making noise during initial start up, also noticed some white discoloring on the igniter, heater is working but has an intermittent problem with ignition during a call for heat, also noticed expansion tank from water heater is full of water water heater age is 16 years old, would recommend replacement
Removed old furnace and coil . Installed a new American standard gas heater. Installed a new american standard coil on top of furnace. Reconnected gas piping. Installed a new ez trap with a new condensate drain and pump, discharged in sewer line. Installed new Aprilaire 600 humidifier with new humidistat, saddle valve and new copper water line, install pvc humidifier drain to condensate pump. Ran new line set and thermostat wire. Installed a new American standard ac unit on top of a plastic pad. Put in a new disconnect box and whip to the unit. Brazed and leak checked all joints and tested with 300 psi of nitro and spray bubbles. Adapted all duct work as needed taped and sealed all connections. Caulked and sealed all penetrations into the house. Reconnected flue piping and performed and combustion test. Temp rise is 40. Installed a new Aprilaire He filter, and Filter size is 413
Performed precision heat tune up on trane gas furnace. Homeowner to replace Honeywell rp2200 air filter. Checked all electrical conections and components. Found inducer motor bearings sounding rough when starting. Also found transition piece leaking water behind inducer motor. Recommend for the price to replace these parts entire furnace should be replaced and a/c. Cleaned flame sensor and blew out condensate drain. Checked gas pressure and performed combustion test. Set up appointment with office to look at replacement.
found inducer motor running, and pressure switch proving but igniter not glowing. Had 124v going to igniter but not coming on. Found break in igniter. Had a replacement igniter on truck. Replaced white Rodgers igniter and performed combustion test. Also had a 45 degree temperature rise. Recommend due to age to start thinking about replacement of entire system, at this point homeowner is thinking more closer to spring time.
Tested temperature rise it was high, furnace was cutting off on high limit, so we then checked filter and realized it was clogged up. So we Replaced Aprilaire 413 filter. Verified new zone panel wiring. Adjusted dip switch and thermostat settings and rechecked temp rise. 50 degree split. Customer will advise us on any comfort issues.
Homeowner had the codes written down that he had recorded. Looked them up and the cof code which is constant air flow beacause of thermostat being in fan on. Then the tp5 is fan speed code. Checked over gas fitting for gas leaks, no leaks found. Ran furnace several times an could no get it to simulate the sound. Found supply plenum when you flexted it made a loud thud sound, this could have been the sound so added some bracing with s-cleat to brace supply plenum and added two pieces on return plenum to help brace duct. Also found 16x25x1 air filter pretty dirty, this does not help with the duct noise. System is working fine at time of inspection.
No heat for multipurpose room, twining units, both are in the attic, found one unit cycling on and off on low power coming in, by passed twining control and starts fine, went and check other unit found no power to unit, getting 115 and transformer reducing power to 24 volt, but board not responding check and touch wires, and unit came on, inspect back side of board and seen black marks recommended replacing board quoted for repairs customer ok repairs installed new oem control board and add 3 amp fuse after repair cycle and test both units performed combustion test on both units ok co 25 and 21
Performed precision heat tune up on 80% trane gas furnace. Checked all electrical conections and components. Cleaned flame sensor. Checked gas pressure. Performed combustion test. Gas furnace is working fine at time of service.
Performed precision heat tune up on amana 80% gas furnace. Replaced 20x25x1 air filter. Checked all electrical conections and components. Cleaned flame sensor. Checked gas pressure, and performed combustion test. Gas furnace is working fine at time of service. Humidifier pad is clean. Tested operation.
Performed precision heat tune up on trane gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Cleaned flame sensor. Checked gas pressure and performed combustion test. Gas furnace is working fine at time of service. Also serviced Aprilaire humidifier with #35 humidifier pad.
Found motor getting 120v but will not run. Blower motor is bad. Will need to return tomorrow with motor and mount. Will complete tune up when we return. 12/3/19. Returned to install new blower motor and performed precision heat tune up on 80% carrier gas furnace. Replaced very dirty air filter 16x25x1. Checked all electrical conections and components. Cleaned flame sensor. Blew out pressure switch tubing. Checked gas pressure and performed combustion test. Gas furnace is working fine at time of service.
Checked noise, checked air filter ok. Started gas furnace, cycled thru low and high fire, let blower ramp up, only noise was from a return grill.
Performed precision heat tune up on carrier gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Cleaned flame sensor. Cycled on both zones. Checked gas pressure, performed combustion test. Carrier 80% gas furnace is working fine at time of service.
Performed gas heat check up check electrical low and high ok filter ok clean sensor and burners ok gas pressures low an high ok combustion test cycle furnace ok replace humidifier pad and performed service check feed tube and orifice ok good water flow, all electrical connections are nice and tight, blower connector had some play, was able to clip it correctly