Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Luis was excellent in checking my air conditioner. He showed me the old filter and the new one he was putting in. He was careful of my floors by wearing booties over his shoes. Appreciate him adjusting the thermostat and fixing the times I want it to go on etc. Very pleased. Thank you
My window was 8:00am to 10:00 am which with most other Co. that means ether 10:30am or we get a call there running late but with Lois the door bell rang at 8:01am. He was very professional and very polite. Explained everything he did to were I could understand what he was saying. I hope to see him again.
The service was were efficient and Good! We were satisfied
DiBiase team is organized and makes scheduling and rescheduling service appointments a breeze. They email a pic of the technician for peace of mind - nice touch. Techs are respectful and knowledgeable.
Service man was on time, throughly experienced, and very helpful
Very polite and neat, explain everything they are doing. They leave the place cleaner then they found it.
I came home from work to a cold house on a January night, determined the heating system wasn't working, called DiBiase, and the dispatcher scheduled a technician to arrive within the hour. He arrived in good time, replaced a failed igniter and stayed long enough to ensure the system was heating the house properly. I put my kids to bed in a warm house that same night.
As a new customer, I called with an small emergency situation and they sent someone out quickly to help. So courteous and professional & knowledgeable - great to deal with! Highly recommend!
Installed new ac and coil with new whip ez trap and condensate pump, ran new vinyl to discharge line added junction box and ran new power wire for outlet. Ran new refrigerant lines and new thermostat wire for outside,Triple evacuated and pressure tested vacuumed down to 267 microns added 15 ounces of 410a. System checked out ok!
Performed ac 6 month inspection check electrical low and ok new filter, flushed drain check split ok outdoor unit 410 pressures ok 6 sub cooling system ok cycle unit ok
Replace current mercury thermostats with t4 pro non programmable thermostats test and cycle both thermostats ok left user instructions on kitchen table, double AA batteries should get replace about every 2 years on thermostats
Performed ac check up, check electrical low and high ok replace 413 filter, flushed drain ok check split, check outdoor unit 410 pressures capacitor and contactor ok cycle unit ok
Performed precision ac tune up on amana ac system. Replaced Aprilaire 413 air filter. Blew out condensate drain and tested pump with water. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. Ac is running at manufacture specifications at time of service.
Performed precision ac tune up on trane ac. Replaced 16x25x1 air filter. Blew out condensate drain and tested with water. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor outdoor unit. System is working fine at time of service.
Performed cooling maintenance, checked air filter ok. Inspected cooling coil, blew out condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Performed ac check up, check electrical low and high ok replace filter flushed drain ok check split ok check outdoor unit contactor and capacitor ok added 1 lb of r22 pressures ok good super heat and sub cooling would recommend replacing system
Performed two ac check ups, second floor and first floor, check electrical low and high ok replace filter 14x25x1 second floor, 413 for first floor ok, check split, outdoor unit r22 pressures capacitor and contactor ok, first floor unit 410 pressures capacitor and contactor ok, cycle units ok recommend installing an ez trap and an ecm motor protector for first floor
Replace blower motor and also new capacitor cycle and test blower ok amp draw 8.5 amps on blower motor, start ac unit, found breaker was tripped to outdoor unit, reset breaker and noticed ac unit slowly came up to speed, compressor did not start right away took seconds to start would recommend replace unit,
Performed cooling maintenance, checked air filter, inspected cooling coil. Checked voltage, amperage and electrical connections, measured capacitor values ok. Cleaned condensate drain. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Checked no cooling on second floor air conditioner, first showed the basement and found that it is the first floor system, went to attic and found second floor air conditioner. Found thermostat reading replace batteries, replaced and no change. Replaced thermostat. Got call for cooling, found blower motor has bad bearings. Pulled blower found 1 hp blower motor. Need a 1 hp blower motor for York model P3URC20N09501C serial EMGM477317 customer has no cooling on second floor. Need to price up and quote customer.
Installed 80% amana gas furnace and 13 seer ac. Kept existing thermostats. Installed new 16x25x1 air filter. Adapted to metal plenum. Adapted to gas line, exsisting high and low voltage. Tested system in heating and cooling and performed combustion test. Ac and gas furnace system working at manufacture specifications.
We will replace current water heater, drain and dispose old tank, install new 50 gallon Bradford white water heater with new expansion tank. Pan and water alarm inside pan 3 in flue pipe installed new water heater Bradford white 50 gallon atmospheric vented new pan and water sensor also installed new expansion tank, check for leaks on work performed no leaks, also on gas connections we worked on ok no leaks, purge all air from pipes and cycle water heater ok cycle water heater ok
Performed cooling maintenance on 3.5 ton air conditioner , replaced standard air filter. Cleaned condensate drain. Checked voltage, amperage and electrical connections. Measured capacitor values. Started air conditioner, measured refrigerant charge, found slightly low on charge. Checked operation and temperature drop across coil