Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Great communication, knowledgeable and friendly.
great service, knowledgeable technicians, everyone is very pleasant
Both Kurt and Zac were professional and honest. Great customer experience.
The DiBiase crew did an excellent job on a very difficult installation.
I really like this company. They know what they are doing and do not try to sell you things you don't need. I have been calling them for the last 2 years to service my heater and air conditioner and wish I has found them sooner. It is easy to schedule a call and they send a text with a picture of the person that is coming to your door.
Performed precision heat pump tune up on amana heat pump system. Replaced Aprilaire 413 air filter. Checked all electrical conections and components. Blew out condensate drain. Checked temperature rise at air handler. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at time of inspection.
Found a/c not running. Found blower running in attic and thermostat calling for cooling but no 24 volts at contactor. Went up to Honeywell t-6 thermostat and pulled off the wall and jumped out wires, a/c unit came on , bad thermostat not picking up y relay at thermostat. Replaced thermostat under warranty and checked refrigerant pressures. System is working fine at time of service.
Found that after talking to homeowner after the power went out the Honeywell t-6 thermostat got switched to the schedule function when I arrived it was on temporary hold and then it would automatically switch to a set temperature from 72 degrees to the program of 85 degrees. Went into installer programming and made the thermostat a non programmable thermostat. Now you can just go up and down with your temperature, showed homeowner how to do this. Also checked 410a refrigerant pressures they were ok. System is working fine at time of service.
Reclaimed and removed old equipment. Install Ed new American standard condenser on pad. Installed new disconnect and whip. Flushed lineset and brazed in with nitrogen. Installed new American standard air handler in drip pan elevated on snow feet. Brazed in with nitrogen and pressure tested to 300. Evacuated down to 210 microns. Installed new April air filter and sealed return. Reconnected supply and sealed. Installed ez trap and wet switch and ran condensate to existing drain. Broke r with safteys. Tested system in cool and adjusted charge. System working great at time of install.
Performed Quality Assurance inspection on a newly installed gas furnace and air conditioning system. Checked over entire system. System running great at time of QA.
Checked no cooling complaint, found thermostat set to heat. Set to cooling, set temporary holt to permit hold. Set thermostat to 70. Heat pump came on. Checked refrigerant charge and temperature drop across coil. Explained thermostat and hold.
Closed off king valves at condenser unit just in case a joint would break open during flexing of lineset. Pulled down lineset clamps and flexed lineset back into cavity where it can now be drywalled. No joints or lines broke open during this process. Re secured clamps on lineset back into place and checked 410a refrigerant pressures on Payne a/c system. Pressures were 305/119 at 77 degrees. System is back in operation again.
Reclaimed and removed old equipment. Installed new leveled pad, disconnect, whip, and flushed lineset. Placed new Amana condenser on pad and brazed in lineset with nitrogen. Wired in high and low volt connections. Installed new Amana high efficiency gas furnace and evaporator coil. Secured new April aire filter and sealed return and adapted supply ductwork and sealed. Ran new vents to exterior of home and tied into furnace. Brazed in coil with nitrogen and pressure tested to 300 psi then evacuated down to 129 microns. Installed new ez trap and condensate pump. Ran vinyl tubing to discharge line. Installed new humidifier and routed drain to pump. Wired safetyâ€™s to break r. Reconnected gas and leak checked. Installed new switch and receptacle. Wired all high and low volt connections. Installed horizontal drain kit on intake vent. Tested operation in heating and cooling. Adjusted refrigerant charge and txv and adjusted gas pressures. Performed combustion test. System working great at
Performed cooling maintenance, checked media air filter ok. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started heat pump, checked refrigerant charge and temperature drop across coil.
Performed precision a/c tune up on Goodman a/c system. Recommend getting a heating and cooling membership plan, also beacause furnace did not have a hole in the exahaust pipe for a combustion test. 16x25x1 air filter is clean. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. Checked temperature split at indoor coil. System is working fine at time of inspection.
Returned to site to charge system. Put system in operation and added 2lbs of R-22 Refrigerant to system, charging by Superheat standards. Charged system to recommended superheat of 22 Degrees. Supply temperature was 61 and return temperature was 81 after adding refrigerant. Office will contact on Monday to verify installation date/time.
Found 20 year old r-22 carrier a/c system low on charge. Pressures were 256/48. System is low on charge. Do not recommend just adding charge to the system, outdoor unit is not in good shape . Lot of fins smashed in and lot of rust. Recommend replacing the a/c and gas furnace due to age of the furnace. System is only getting a 11 degree temperature. Set up appointment with office for 5 to 7pm. To have someone come out to give a quote on full system replacement.
Performed Quality Assurance inspection on a newly installed heat pump system. Checked over entire system. No air leaks, all penetrations sealed. Wiring proper and secure. Everything looks great. System running great at time of QA. Inside temp split of 50/70.
Found system low on charge. R-22 pressures were 152/38. Gave homeowner 3 options. Option 1 add r22 to the system and leak dye to find the refrigerant leak. Option 2 . Add r-22 to the system. Option 3 replacement of the system. Homeowner wanted to just add charge to the system. So added exactly 2 lbs of r22 to the system. Pressures are now 188/75 at 86 degrees outside temp. Had a 23 degree temperature split at indoor coil. Told homeowner that we donâ€™t know the longevity of just adding r-22 to the system. System is working fine at time of service.
Performed precision a/c tune up on arcoaire a/c system. Replaced 20x22x1 air filter. Checked all electrical conections and components. Blew out condensate drain and tested condensation pump. Checked temperature split at indoor unit. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at time of inspection.