Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
The DiBiase crew did an excellent job on a very difficult installation.
I really like this company. They know what they are doing and do not try to sell you things you don't need. I have been calling them for the last 2 years to service my heater and air conditioner and wish I has found them sooner. It is easy to schedule a call and they send a text with a picture of the person that is coming to your door.
Technicians were fantastic. Very neat and professional. I would recommend them to everyone
I have used several different companies over the years and I think DiBiase is the best. The techs have a degree of knowledge that I have not seen before and they do not try to sell you stuff that you don't need.
Kurt and Paul were great. They walked me through the problem and how they were going to fix it.
Had them out twice so far. Don’t pressure to upsell, explain things so you can understand, prompt, friendly
Performed oil cleaning on a boiler, check low and high cleared exchanger and chimney base, replace nozzle and adjust electrodes, clean cad cell replace oil canister and also added a fusible shut off valve before filter for easy excess to filter, check for oil leaks and purge line ok started boiler and performed smoke test and combustion test cycle boiler ok check water pressure and temp ok at this time boiler is working on good condition
Performed precision heat tune up on arcoaire heatpump. Replaced 20x22x1 air filter. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. Cleaned dirty evaporator coil with chemical cleaner. Heat pump system is working fine at time of service. Found very dirty evaporator coil
Performed precision heat tune up on amana gas furnace. Aprilaire 413 air filter is still ok. Checked all electrical conections and components. Checked temperature rise. Checked gas pressure and performed combustion test. Blew out condensate drain and tested pump. Performed service on humidifier, replaced Aprilaire 35 pad. Found 115 v condensate pump very gunked up. After cleaning tested pump and found it not pumping very well. Recommend we replace it . Replaced pump and tested. System is working fine now at time of service.
Performed Quality Assurance Inspection on Amana AC/Air Handler System. Tested EZ Trap and Wet Switch Safety Devices. Completed Checklist Form in System. Reviewed Installation with Homeowners.
Performed leak search on air conditioner, found leak on indoor coil right side bottom front. Found no other leaks. Started air conditioner, checked refrigerant charge ok. Signed up for maintenance plan, wants to start with heating maintenance. Also will wait until spring to replace cooling coil. Will need to quote in spring due to coil price changes.
Checked no cooling complaint, set thermostat to cooling, blower came on but no outdoor, checked voltage ok, found open dual run capacitor. Replaced dual run capacitor, started air conditioner, checked refrigerant charge and temperature drop across coil.
Checked no cooling complaint, indoor coil iced up, checked coil itâ€™s free of ice, checked air filter ok. Started air conditioner, checked blower on, checked refrigerant charge, found low on charge. Topped off refrigerant charge, balanced by superheat, checked operation and temperature drop across coil Canâ€™t guaranty charge there is a leak. Recommend replacing air conditioner.
Performed cooling maintenance, checked air filter ok. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started heat pump, checked refrigerant charge, found system low on charge. Topped off refrigerant charge and balanced by superheat. Checked operation and temperature drop across coil.
Performed ac check up check electrical low and high flushed drain test pump ok check filter ok check split ok, airflow ok outdoor unit 410 pressures ok capacitor and contactor ok cycle unit ok recommended surge protectors for indoor and outdoor unit emailed quote
Performed 6 month inspection on heat pump, check electrical low and high ok filter 20x22x1 ok flushed drain test pump ok check split outdoor unit 410 pressures ok sub cooling and super heat ok system working up to manufacturer specifications
Performed ac check up, check electrical low and high ok flushed drain test pump ok check 201 filter ok split 17 supply 50 return 67 check fan speed at 1000 cfm 2 1/2 ac outdoor installed ecm protector for blower motor, check outdoor unit r22 pressures subccoling and super heat ok capacitor and contactor ok cycle unit ok
Installed amana ac system. Flushed and adapted to 7/8 3/8 lineset. Leak checked and vacuumed down system to 380 microns. Tested condensate drain and pump with water. Checked delta t at air handler it was 19 degrees. Checked refrigerant pressures and temperatures at outdoor unit. System is working at manufacture specifications.
Checked no cooling complaint, found unit set to cooling and the blower is running, checked outdoor unit, found locked out on head pressure, reset and heat pump came on and ran in heating. Found no 24 volts from inside. Added jumper at outdoor unit. Need to diagnose in the fall when we can go up into the attic Need to diagnose no 24 volts to O At the outdoor unit in cooling mode.
Performed cooling maintenance on 2 air conditioners, replaced standard air filters. Cleaned condensate drain. Inspected cooling coils. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioners, checked refrigerant charge and temperature drop across coils
No ac, second floor unit, found system running upon arrival, check indoor unit filter ok supply and return temp ok, noticed no ez trap or wet switch, customer aware of not having safetyâ€™s, check outdoor unit r22 pressures amp draw and motor and compressor ok did not find any issues at this moment with ac unit told customer is he has same problem to come out side and check operation on outdoor unit if unit runs