Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
DiBiase Heating and Cooling is a knowledgable and very honest and fair organization. I needed a completely new unit and Bill Duffy from sales was knowledgable and gave us four options and helped us decide. I would not hesitate to recommend DiBiase for your air conditioning needs.
A year on from choosing DiBiase to install a new HVAC system and sign up for the annual service agreement. We have not been disappointed. Dealing with DiBiase to schedule or make adjustments to appointments is so easy. Their system to keep you informed before and after any event is excellent. We had to make a last minute change to today’s maintenance and the Dibiase team were great in accommodating. Our service tech Luis arrived as scheduled. It is great to have experienced techs that know our system return each time. Luis is professional friendly and very knowledgeable, a pleasure to have him work with us. I would recommend Luis and DiBiase for HVAC systems and service without hesitation.
Lois was great to deal with. He explains the problem and told me what it takes to repair the problem.
I have used other companies in the past and I like DiBiase the best. There service is excellent and their servicemen are very knowledgeable and friendly. Luis has come to my house a few times now and I really like him,
Kurt figured out the issue with sensors and got system up and running in short period of time.
Both technicians were great to deal with and worked quickly to complete the job. Kurt was very helpful and thoroughly explained all that was needed.
I have been using DiBiase HVAC service for sometime. I really like how they care about their customers. I recently got my heating furnace replaced and I couldn’t have asked for a better service. DiBiase is my go to service for all my hvac needs.
Great company with great service ! the tech was above and beyond excellent service with excellent advice Regarding my heating system Great job Brian Five star thank you
Performed precision heat tune up on carrier heat pump and Lennox gas furnace system. Wasable air filter is clean, replaced 20x25x4 ( homeowner provided filter) checked all electrical components and connections. Found bad condenser fan motor and capacitor on 18 year old carrier heat pump. Let homeowner know to replace the motor would be around $1,000 , but we also donâ€™t know if the charge is good. Recommend replacing the heat pump, homeowner went with the best option. Cleaned flame sensor on gas furnace. Blew out condensate drain. Checked temperature rise, and performed combustion test. Gas furnace is working fine at time of inspection.
Arrived at house and made call for heat. Uploaded available CoolCloud updates. ECM motor started ok but stopped and then ramped down attempting to ramp back up. System shut off on Error Code E6. Blower. Followed CoolCloud steps for trouble shooting. Checked filter; ok. Checked high voltage pin of ECM; ok. Checked 24V pin during a call For fan only meter read 0V. Checked for 24V between G and C at control during call for fan: 24V. Used SupCo ECM pro tool to provide constant 24v (from transformer) to low voltage pin of ECM motor. Motor ran well. Board needs to be replaced. Warranty. Ordered board from HVAC Distributors. Scheduled arrival tomorrow 10/22/21 (shop). Office will contact to schedule repair. URGENT: Blower motor is not operating. No Charge. Under Warranty.
Performed precision oil boiler tune up on peerless oil boiler. Replaced.85x80b nozzle. Replaced rf1 oil filter. Checked all electrical conections and components. Tested all three zone valves. Vacuumed out soot from smoke pipe and heat exchanger. Performed smoke and combustion test. Replaced caddy cell due to lens distortion from heating oil spray back. Oil boiler is working fine at time of inspection, no further recommendations at this time.
Heat pump not working, found system off upon arrival, asked customer to set thermostat regular heat 5 degrees higher than room temperature, check indoor air handler and did not started, check power and no power between Y and C thermostat showing heating, manually test heat pump and back up 15 kw electric heat system works ok by jumping the thermostat, also noticed contactor in bad shape, quoted to replace thermostat and customer approved repairs for T6 and replacement of contactor, after repairs check operation on heat pump refrigerant pressures ok electric heat back up ok.
Performed precision oil heater tune up on thermopride oil furnace. Replaced 16x24x1 air filter. Replaced garbar oil filter. Replaced oil nozzle. Vaccumed out smoke pipe and heat exchanger. Checked all electrical conections and components. Performed smoke and combustion test. Oil furnace is working fine at time of service. Oil tank is rusted and getting old recommended replacement of oil tank, sent estimate.
Heat Tune Up 40K BTU Natural Gas Furnace. Made call for heat from thermostat. Cleaned flame sensor. Checked hot surface ignitor ohms and condition. Checked pressure switches and tubing. Checked all field and manufacturer wiring. Checked all electric motors and components. Checked gas pressure. Measured temp rise. Performed combustion test. Set digital humidistat to â€œ4â€ and opened bypass damper. Completed Gas Furnace Inspection Form Furnace is operating safely at design conditions at the time of this maintenance.
2 Heat Tune UPS under plan maintenances. Cycled both furnaces to HEAT at thermostats. Changed filters. Measured temp rises. Visually inspected heat exchanger and burners. Measured hot surface ignitor ohms. Cleaned flame sensors. Checked gas pressures. Checked field and manufacturer wiring. Checked all electric motors and components. Performed combustion tests. Recommended REMEs Provided estimate for install Recommended Bypass Humidifiers Provided estimate Installed water alarm near hot water heater. Completed Gas Furnace Inspection Forms Both Furnaces are operating well at the time of this maintenance.
Performed Quality Assurance on Amana Gas Furnace/AC System. Completed Checklist Form in system. Reviewed installation with homeowner. Tested Water Safeties on system. This install passed the QA: two points are 1.) AC was setup to 2-Stage on cool cloud 2.) Outdoor unit pad could have been leveled more and unit centered on the pad. Spoke with Homeowner about replacing the 2 Air Filters for the Second Floor system. She is going to order more filters and replace them.
Found oil tank is currently a 275 gallon tank with a supply and return lines made of 3/8â€ copper coming out of the top of the oil tank. Fill is 1 1/2â€ and vent is 1â€ black iron. Provided estimate to replace oil tank. There is an outside entrance to remove and replace oil tank.
Heat Pump Tune Up, check electrical low and high voltage connections ok change filter, 16x20x1 test back up heaters check amp draw on Elements ok, airflow ok, check pump added tabs to pump to maintain clean pump, check outdoor unit refrigerant pressures capacitor and contactor found run capacitor reading 0/4.9 rated 30/5 compressor gas hard start relay and start capacitor this is why unit is still starting informed customer about findings emailed proposal.
Six month inspection for 60K btu natural gas furnace. Aprilaire 413 filter ok. Checked drain and collector box tubing as well as EZ trap. Checked burners and heat exchanger. Checked flame sensor. Checked hot surface ignitor and measured resistance. Checked temp rise. Checked LO Fire and Hi Fire gas pressure. Combustion test good. Completed Gas Furnace Inspection Form Furnace is operating safely at design conditions at the time of six month inspection.
Performed two gas heat tune up, check electrical low and high voltage check connections, cleaned flame sensor and burners ok gas pressure ok performed combustion test check supply and return temperature replaced both filter would recommended replacement of hvac systems or at least second floor system.
Performed heating maintenance, checked air filter ok. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections. Cleaned burners and flame sensor, inspected heat exchanger. Serviced humidifier, cleaned and replaced water panel. Started gas furnace, tested limit and safety switches. Measured fuel pressures performed combustion test.
Performed Quality Assurance on Amana AC/Air Handler. Reviewed installation with Homeowner. Setup up the Thermostat for Wifi with the Homeowner and setup multiple accounts for his wife and son. Completed Checklist Form in system. Homeowner said he completed all of the Finance Paperwork online. He said he was having problems completing it because his email was not being accepted. This install passed the QA Inspection: Outdoor Unit was not level. Had to tape around some of the supply connection where tape was peeling off.
Installed Amana gas furnace and outdoor ac unit for second floor. Recovered old refrigerant and flushed line set with chemicals. Leveled new pad and leveled new outdoor condenser. Replaced old disconnect and electrical whip with new. Installed TXV onto the coil and tightened all connections. Connected gas line to new gas furnace installed ez trap and connected to existing pvc drainage. Connected and taped return and supply back on and brazed copper connections. Pressure tested and put on vacuum until under 500 microns and then pulled so we could crack the lines. Added what refrigerant was needed to system. Installed new Honeywell T4 thermostat and programmed to system. Tested out and recorded in service titan.