Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Technicians were fantastic. Very neat and professional. I would recommend them to everyone
I have used several different companies over the years and I think DiBiase is the best. The techs have a degree of knowledge that I have not seen before and they do not try to sell you stuff that you don't need.
Kurt and Paul were great. They walked me through the problem and how they were going to fix it.
Had them out twice so far. Don’t pressure to upsell, explain things so you can understand, prompt, friendly
Performed 6 month check, replaced standard air filter, tested water safetyâ€™s. Tested condensate pump. Reviewed set up. Checked voltage, amperage and electrical connections. Started air conditioner, checked refrigerant charge and temperature drop across coil. $189.00 per year maintenance
Performed cooling maintenance, replaced standard air filter. Inspected cooling coil. Cleaned condensate drain and pump, blew out condensate trap. Checked voltage, amperage and electrical connections. Measured capacitor values ok. Started heat pump, checked refrigerant charge and temperature drop across coil.
Gave Mike the proposal for replacing his air conditioner and coil, he also wants to install a humidifier on his 1st floor system. He said he is not in the situation replace more than just the unit that is not working at this time.
Performed two ac check ups, check electrical low and high replace both filters, clean both pumps, test pumps, both blower capacitors are low recommend replacing both capacitors, check outdoor unit first floor 410 pressures, ok capacitor is little low rated 35 reading 31,, on second floor unit found open winding common could not reset overload also system is flat on refrigerant due to condition and high price to repairs recommend replacing ac unit
Installed single stage amana heat pump system. Tested condensate with water. Installed new Honeywell t 6 thermostat. Vacuumed down line set to 352microns and soap checked for leaks. Ran heat pump system in heating and cooling. System is running to manufacture specifications.
Performed precision ac tune up on 2 trane ac. Replaced both 20x25x5 filters (homeowner provided) checked all electrical components and connections. Blew out both condensate lines and tested with water. Checked refrigerant pressures and temperatures at indoor and outdoor units. Both ac systems working fine at time of service.
From talking to homeowner thermostat seems to be in accurate also indoor coil is very dirty. Cleaned indoor coil and replaced thermostat with t4 programable thermostat. Also performed precision ac tune up on Bryant ac. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. Ac working fine at time of service.
Checked cooling complaint, customer stated that the breaker tripped. Got to outdoor unit, found fan running slow. Checked run Capacitor ok, checked compressor, found short in compress windings. Recommend replacing due to age vs repairing. Need sales to call
Performed two ac tune ups, check electrical low and high replace filter 16x25x1 and 16x20x1 flushed drains ok check split ok, outdoor units r22 ok first floor contactor and cap ok, on second floor unit found weak capacitor 35/5 reading 27/4.5 also fan motor is running at .65 amps rated at .5 amps, informed customer about situation and recommend repairs would recommend getting estimate to replace ac unit due to age Office to follow up with customer
Performed cooling maintenance on 3 ton heat pump, checked washable air filter. Checked voltage, amperage and electrical connections. Inspected coil and drain pan tested water safety's. Blew out condensate trap. Measured compressor capacitor values. Started het pump in cooling mode, measured refrigerant charge. Checked operation and temperature drop across coil.
Upon arrival we noticed with customer water leaking from exhaust we replaced the section of piping that was leaking and took pictures we also replaced the air filter to a 20x25x4 the humidistat was falling out of duct work and sitting on top of unit we re attached the humidistat with duct board tape. Delta t downstairs 17 degreesEverything was then alright for downstairs system the upstairs heat pump filter was dirty and I washed that and put it back in. The condensate was unprotected and didnâ€™t have any pitch in the drain and was level recommend a ez trap for condensate and wet switch for pan customer will hold off. Delta t for upstairs 18 degrees.
Performed precision ac tune up on Lennox ac. Replaced 20x25x1 air filter. They also have a larger filter rack and we're using 2 filters, told homeowner to only use on or the other for both is to restrictive. Blew out condensate drain and tested operation of condensate pump. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. System working well at time of service.
Performed ac check up on first floor unit replace filter, flush drain test pump ok electrical low and high ok per customer added refrigerant 1 1/5 lb of 410a outdoor electrical ok cycle unit ok, on second floor unit is low on refrigerant, customer declined leak search on both units, added 2 1/5 lbs to second floor, both systems, are working at correct pressures,
Replace indoor thermal expansion valve (txv) removed old valve and installed new valve, pressure test system at 300 psi no leaks, triple evacuation ok down to 500 microns, after repairs tested system pressures ok put system running and check 410 pressure ok pressure are 260/125 with 9 super heat and 7 sub cooling, split ok supply 48 return 70, performed ac inspection during visit, flushed drain ok filter ok check outdoor unit 410 and electrical ok installed surge protectors ecm for blower and zebra pack in outdoor unit, cycle unit ok
Comfort problem, found outdoor unit not running, open on low pressure switch, test switch opens at 50 and closes at 100, standing pressures 160\80 remove low pressure from circuit to test unit, as soon the unit starts head pressure goes up to 350 and low pressure side down to 20 psig, there is a restriction in the high side, system has. 2 year warranty labor, repair is under warranty will order new txv for air handler and return to installed once we get part