Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Great company with great service ! the tech was above and beyond excellent service with excellent advice Regarding my heating system Great job Brian Five star thank you
I have been calling DiBiase for a few years now, Their prices are fair, their technicians are always knowledgeable and they are a bunch of friendly people.
Great communication, knowledgeable and friendly.
great service, knowledgeable technicians, everyone is very pleasant
Both Kurt and Zac were professional and honest. Great customer experience.
Performed heating maintenance, replaced standard air. Cleaned burners and flame sensor. Inspected heat exchanger, found the 3 middle chambers with heavy rust across the tops. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started gas furnace, measured fuel pressures. Performed combustion test. Checked operation and temperature rise across coil.
Performed heating maintenance, replaced air filter. Cleaned burners and flame sensor, inspected heat exchanger. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches. Checked operation and temperature rise.
Heat tune up on Bryant gas furnace. Replaced Aprilaire 501 filters and humidifier pads all provided by homeowner. All electrical components within spec except for blower capacitor. Replaced blower capacitor. 55F temp rise. Combustion test proves integrity of heat exchanger; efficiency is 92%. System is performing/operating well at this time.
Found first floor propane gas furnace with inducer motor running proving pressure switch and send 120 volts to hot surface igniter but igniter was not glowing. Found very rusted and corroded heat exchanger. Furnace is about 15 years old recommended that beacause of condition of gas furnace, to replace system. Also explained to homeowner that it is also beneficial to replace the a/c with the furnace at the same time. Also gave customer a price on replacement of the hot surface igniter. Was not able to perform a combustion test due to system being down. Set up appointment with office for 10:30 am Monday to give an estimate on system replacement.
Checked no hot water, found water heater locked out on pressure switch. Found inducer running. Checked pressures, found a restriction in the vent pipe. Checked pipe, found a dead mouse in the vent termination. Cleared vent pipe. Reset lockout. Started water heater and checked operation.
Performed heating maintenance, checked media filter ok. Tested electric back up heaters. Checked voltage, amperage and electrical connections, measured capacitor values. Started heat pump, calculated btu output. Tested defrost cycle. Checked operation and temperature rise across coil.
Service call that there was an odor coming from the unit. Customer noted that the smell seems to be stronger at night. Proceeded to Air Handler to inspect unit. Found Air Filter was dirty. Inspection of the Indoor Coil shows that there is a large amount of buildup and dirt on the inside of the Coil. Removed the Electric Heat Kit and found a dead mouse inside the unit. Removed Mouse and installed a new 20x24x1 Air Filter. Put system in operation to test for smell. Turned system up so the Electric Heat would also run. After system ran customer noted that she could not smell any odors. The coil being dirty could also be causing the Smell. This will also effect the performance of the system. In addition to the Coil cleaning, also recommending a REME Air Purifier be installed on the system which can help reduce odors and particulates in the Air and in duct system. Included an estimate for the Coil Cleaning and REME installation.
Performed heating maintenance, checked media air filter ok. Serviced humidifier, cleaned and replaced water panel. Started humidifier, checked operation ok. Cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches. Performed combustion test. Checked operation and temperature rise.
Performed heating maintenance, checked media air filter ok. Cleaned burners and flame sensor, inspected heat exchanger. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches. Measured fuel pressures. Performed combustion test. Checked operation and temperature rise.
Performed cooling maintenance on air conditioner. Checked air filter ok. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil. Cycled electric heaters. Rabah Would like a quote on replacing the 2 ton outdoor unit with a heat pump, there is already 9 conductors thermostat wire run to the thermostat and outdoor units. Also wants options on replacing a oil boiler with a summer/winter domestic water heater.
Replace thermostat with pro T6 WiFi, cycle heat pump test emergency and regular heat ok helped customer set up app and went trough settings system is running to standards
Performed precision heat tune up on thermopride oil furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Replaced garbar oil filter. Replaced nozzle. Checked pump screen. Checked temperature rise. Brushed and vacuumed soot from smoke pipe and heat exchanger. Sealed up chimney base. Performed smoke and combustion test. Oil furnace is working fine at time of inspection.
Performed gas heat tune up on attic upon arrival spoke to customer I was informed about a water leak Congress possibly from attic unit, unit check electrical low and high ok found furnace trap leaking into auxiliary pan, and auxiliary pan leaking onto ceiling, found drain hose not completely attached to trap, blower made customer aware where was the source coming from check blower motor and cap cap is reading below manufacture specifications, blower wheel and motor needs to be taken out of furnace to be cleaned, dirty wheel, also found igniter reading weak, informed customer about findings and email proposal,
Performed Quality Assurance inspection on a newly installed Naiven tankless and NOVO water treatment system. No leaks found. Customer did say about a slight humming noise. Normally is caused by a dirty water filter. Shutdown system and checked water filter. Is a little dirty. Cleaned filter and reinstalled. Turned system back on. Noise seemed to go away.
Performed two propane gas heaters check ups, check electrical low and high replaced filters, and also service humidifiers check manifold gas pressures combustion test ok cleaned flame sensor test humidifiers cycle both furnaces ok