Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
We removed old tankless water heater and all connections to it. Including the cabinet surrounding it, flu pipes and gas lines and water lines. We installed and new concentric metal flu and adapted to new water heater. Reconnected existing water and gas lines, tested for leaks on both. Installed longer power cord to new water heater to reach power outlet. Re-installed cabinet surrounding the water heater after making a few modifications to make it fit right. Tested out and went over install with customer.
Found that as soon as oil boiler went To fire soot blew out everywhere. Recommend we need to clean the boiler thought. Told homeowner just to clean the boiler could be almost 4 hrs. Will let office know to schedule in work.
Tankless Water heater not working some times, up on arrival customer advised that was working, open up hot water faucet and water heater came on producing hot water, check water pressure reading 90 psi usually is about 60 psi, new pressure reducing valve is needed, also did not found expansion tank installed, check flame sensor and if ignition cleaned both parts, check venting ok, water heater has a interior problem with the electronics,
Performed Precision a heating Tune Up on Payne Gas Furnace. Checked 20x22x1 Air Filter. Filter was clean and did not need changing. Tested electrical components on system. Found Blower Motor Capacitor was testing below rating. Recommend replacement of the Capacitor. Inspected Burners and Heat Exchanger. Cleaned Flame Sensor and measured resistance on Ignitor. Put system in operation and performed Combustion Analysis on Furnace.
Performed Precision Heating Tune Up on the York System for the Back office area. Replaced Air Filters. Inspected and tested electrical components. Removed Covers and inspected Heat Exchanger. Cleaned Flame Sensor and Spark Ignitor. Put system into operation and performed Combustion Analysis on Furnace and measured Air Temperature readings. Performed Precision Tune Up for the Carrier Gas Furnace for the Front Office Area. Replaced Air filters and inspected Blower Belt for proper tension. Found Burners and Heat Exchanger were extremely rusted. Also found Inducer Motor Assembly and Wheel were very rusted. Rust is falling off of the components and around the Heat Exchanger. Removed panels to inspect Heat Exchanger. Along one of the Heat Exchanger Tubes found a crack running along the bottom seam of the Heat Exchanger. Also found a hole at the heat exchanger near the burner entry. The heat exchanger has failed and the system is not safe to run. Locked out the system at the outdoor breake
Performed heating maintenance, replaced media filter with supplied filter. Serviced humidifier, cleaned and replaced water panel. Started air humidifier. Cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches. Performed combustion test. Checked operation and temperature rise
Service call that the Heat for the Back office area was not working. Upon arrival put system in heating mode to test operation. Proceeded to the unit outside to troubleshoot. Found Inducer Motor coming on and Spark Ignitor running but no flame was present. Removed Pilot tubing from gas valve and gas was present. Blew through the Pilot tubing to clear the blockage in the line. Reassembled Pilot tubing and put system back in operation. System fired up immediately with no issue. Turned system off and cleaned Flame Sensor and Spark Assembly. Cycled system several times to ensure it was firing properly. Performed Combustion Test on unit. Checked filters which are getting dirty and will need to be replaced when we return for the maintenance visit on Monday 11/23.
Performed gas boiler tune up on Weil McLain 80% gas boiler. Pulled of smoke pipe and inspected heat exchanger and chimney base , both were clear. Inspected burners and pilot assembly. Tested each zone valve and checked each baseboard to make sure everything was getting hot. Tested circulator pump and checked boiler pressure. Gas boiler is working fine at time of inspection.
Performed AC Tune Up on Payne system. Replaced 20x22x1 Air Filter. Tested components and found the Blower Motor Capacitor was testing below rating. Also found Dual capacitor testing low. The single Poe Contactor is worn and pitted, and a voltage drop was measured across the coil indicating the Contactor is wearing. Also found condensation drain pipe was clogged and the coil pan was overflowing. Cleared drain line and tested. The floor drain the condensation pipe empties into is backing up and also appears to be clogged. Measured refrigerant and found system to be low on charge. It appears as if a drop in replacement refrigerant was used on the system at one time. System is only cooling with a 12-13 Degree temperature split and if ran the indoor coil may freeze up. There are two refrigerants hand written on the outdoor unit, so the exact refrigerant is not known and the refrigerants cannot be mixed. Would recommend replacement of the Gas Furnace/AC system due to overall poor condition
Performed AC tune Up on both package units. Replaced Air Filters in both systems. Inspected and tested electrical components. TheYork system which supplies the back office area, the Outdoor Fan Capacitor was testing in rating but was rusted and had signs of oil. This indicates that the capacitor is starting to fail. Would recommend replacement of the capacitor before failure occurs. Also noted the presence of water in the bottom of the control panel area. The condensation drain is broken and no trap exists. Water could be penetrating the unit from elsewhere, or it could be an issue with improper drainage. Measured refrigerant charge on both systems. Checked belt tension on the system for the front office area. The front office unit could not find any access to the drain line to inspect or Cleanout. Refrigerant levels were to standard on both systems. The Front office system had been previously diagnosed as having a restriction. This could be an intermittent issue. During testing the re
Performed cooling maintenance on first floor air conditioner, , cleaned first floor filter. Cleaned condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioners, checked refrigerant charge on both. Checked operation and temperature drop across coil. Finished up cooling maintenance on second floor a/c system. Replaced 14x24x1 air filter. Blew out condensate drain. Checked all electrical conections and components. Tested capacitor at outdoor unit. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at time of inspection.
Performed quality check, checked media filter. Shut off humidifier for summer. Tested condensate pump and water safety checked furnace set up. Cycled furnace, checked low and high fire fuel pressures. Started air conditioner, measured refrigerant charge. Checked operation and temperature drop across coil.
Water leak from saddle valve for humidifier, found valve leaking at the seat between gasket and valve, replace valve and check for leaks no leaks test humidifier ok adjust water flow, recommended adding more ventilation to mechanical room
Performed Quality Assurance on Amana Gas Furnace/AC System. Reviewed installation with homeowner. Completed Checklist Form in system.
Reclaimed and removed old ac unit . Removed old heater and coil. Installed a new amana gas heater. Fixed flue piping that was falling out the wall and recemented the pipe in the wall. Adapted all duct work as needed . Installed a new HE filter on to the return. Taped and sealed all duct work. Ran a new counter strike gas line. Ran a new condensate drain with a ez trap wired in the furnace. Installed a new Aprilaire humidifier and ran new copper water line over to hot water heater piping. Ran new vinyl tbing over to discharge sink. Ran a new electrical box with a new switch and outlet. Ran new copper lines from inside coil to new amana ac unit. Unit is on a new plastic pad with rocks underneath. A new disconnect box and electrical whip to unit. Installed a t10 thermostat and set up setting. Ran lineset threw finished portion of house and came down brick with linehide and ran lineset on side of house to ac unit .brazed and leak checked with soapy bubbles and 300 psi of nitro. Tested syst