Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed heating maintenance, replaced media air filter with supplied filter. Serviced humidifier and replaced water panel with supplied water panel. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches. Measured fuel pressures and performed combustion test.
Performed precision heat tune up on Weil McLain 80% natural gas boiler. Checked burners, burners are clean. Checked chimney base for debris. Checked all electrical conections and components. Cycled on boiler and tested 2 zone head valves. Tested circular pump. Checked expansion tank. Gas boiler is working fine at time of service, no recommendations at this time.
Customer has two system basement and attic, attic thermostat sometimes goes blank after hours come back on, attic unit has wet switch, thermostat come on by itself no need to reset power, asked customer if he had to reset wet switch his answer was no, never see water or tripped wet switch, check wiring next thermostat has common and 24 volts going to base, would recommended replacement of next thermostat no issues found with wiring.
No ac found no indoor or outdoor unit running, thermostat calling for cool but no signal to indoor board, found defective thermostat quoted for new thermostat and also check operation of system,,,,,customer will replace its own thermostat
Performed cooling maintenance, checked media air filter ok. Cleaned eztrap and drain, cleaned voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Performed cooling maintenance, checked air filter ok. Cleaned condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge, checked operation and temperature drop across coil. Canâ€™t find anything reason for poor cooling
installed ez traps on both 1st and 2nd floor systems. Also performed precision a/c tune up on 2 Payne a/c systems. Replaced 14x24x1 air filter, and cleaned wasable filter. Checked all electrical conections and components. Blew out condensate drain. Flushed with water. Checked temperature split at air handlers. Checked refrigerant pressures and temperatures at indoor and outdoor units.
Performed cooling maintenance, cleaned eac prefilters. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioners, checked refrigerant charge, found first floor air conditioner low on charge. Topped off refrigerant charge, balanced charge by superheat. Checked operation and temperature drop across coils.
Checked pool pak not dehumidifying, found a call for the compressor to run but no operation, checked refrigerant pressures, have static pressure. Not familiar with this unit and found a not that said the compressors were just changed. Recommend a commercial company to look at pool pak. Checked exhaust fan, found belt broke. Replaced belt, cleaned up old belt debris. Started exhaust fan and checked operation.
Checked saddle valve leaking, tighten both saddle screws and packaging nut. Checked for leaks, tighten water heater cold fill packing nut.
Performed oil heat tune up, furnace is from, 1999, cleaned heat exchanger and flue pipe, check all electrical connections low and high voltage ok, replaced oil filter and nozzle, noticed furnace was running but it was flame was not within specifications, after cleaning performed smoke and combustion test, some parts are wearing out, would recommend replacing burner pump, primary control sometimes cuts out, will have to be modified since itâ€™s very hard to get that part emailed proposal to do repairs would recommend upgrading oil furnace for safety purposes, some parts heat exchanger are Heavily covered with a lot of rust the overall integrity of heat exchanger is in poor condition
We removed old tankless water heater and all connections to it. Including the cabinet surrounding it, flu pipes and gas lines and water lines. We installed and new concentric metal flu and adapted to new water heater. Reconnected existing water and gas lines, tested for leaks on both. Installed longer power cord to new water heater to reach power outlet. Re-installed cabinet surrounding the water heater after making a few modifications to make it fit right. Tested out and went over install with customer.
Found that as soon as oil boiler went To fire soot blew out everywhere. Recommend we need to clean the boiler thought. Told homeowner just to clean the boiler could be almost 4 hrs. Will let office know to schedule in work.
Tankless Water heater not working some times, up on arrival customer advised that was working, open up hot water faucet and water heater came on producing hot water, check water pressure reading 90 psi usually is about 60 psi, new pressure reducing valve is needed, also did not found expansion tank installed, check flame sensor and if ignition cleaned both parts, check venting ok, water heater has a interior problem with the electronics,
Performed Precision a heating Tune Up on Payne Gas Furnace. Checked 20x22x1 Air Filter. Filter was clean and did not need changing. Tested electrical components on system. Found Blower Motor Capacitor was testing below rating. Recommend replacement of the Capacitor. Inspected Burners and Heat Exchanger. Cleaned Flame Sensor and measured resistance on Ignitor. Put system in operation and performed Combustion Analysis on Furnace.