When I arrived at house, I was told house wasnâ€™t cooling anymore. I started at condenser and opened up cabinet of all electrical components. I had no power to condenser unit, so I went to breaker panel. Breaker panel had breaker inside In tripped position. I flipped breaker back on and went to do a amp draw. Hooked up my amp probe and system was working at 29 amps. Exceeding max amp draw of 27 amps. Itâ€™ll keep tripping breaker when compressor gets over worked. I showed issue to owner and he is aware of his compressor. Owner will reach out if he wants to continue with replacement. For today, Iâ€™m charging for diagnostic only.