Brian did a great job of going over the plan and offering the best value project for my budget and goals.
Tested heating gas pressure. Removed the second stage from the thermostat settings. Found disconnected supply duct supplying the upstairs bedroom and bathroom near the thermostat. Found and removed large blockage in the master bedroom supply grille. Cleaned the filter.
Collected a $600 deposit. Balance due will be 5501
Performed Furnace diagnostic on 1990 Rheem system. Upon my diagnostic system was experiencing intermittent behavior. 1. Found that circuitboard had Multiple burns and heat marks this could be an indication of a faulty board although cannot confirm it until new board is installed 2. Indoor blower motor has leaking oil from bearing and is over amp due to this, This can lead to the motor either locking up or overheating 3. Secondary motor control is becoming weak due to high amperage of fan 4. Condensate line are plumbed in correctly with the wrong material. 5. Duct work is not sealed correctly, This can cause lower Airflow and air Leakage 6. Static pressure was 0.90, Static pressure is the airflow of the system due to this being so high this Can cause complications with the heat exchanger overheating and Began to form cracks Recommendations- 1. After market Circuit board Is installed to solve intermittent behavior issue 2. Indoor blower motor is replaced due to oil leakage in high ampe
A.c. maintenance in Santa Margarita
Installing new ac fan blade and fan motor on lennox ac unit
Doing an air conditioner maintenance in Rancho Santa Margarita
Estimate on system