Did an AC maintenance check-up on a 24 -year Ruud unit in Talladega Al. Check all electrical connections.
Did an HT maintenance check-up in Talladega Al on a 23 year Carrier unit. Adjust blower components. No need for system replacement.
Did an HT maintenance check-up on a 4 year Payne unit in Talladega Al. Check manifold gas pressure and for proper venting. Replaced capacitor under warranty.
Came out to Talladega, AL for a/c maintenance tune-up on a 23-year-old Lennox system. Check thermostat, air filter, and airflow.
Cleaned condensation drain checked ducts for build up, lubricated all moving parts. Checked voltage. No repairs.
Service work performed for 2008 Air conditioning unit with heat pump, cleaned condensation drain condensing coil with Zep con-coil cleaner.