Came home to find our air was not working. Called Perfect Service and within 45 mins Mr. Buddy was here. Had to get a part for the air unit and came back to put it on when he could have told us he would be back in the morning. Love Perfect Service.
Great service! Buddy is very knowledgeable and informative. Rates are very reasonable and we purchased an annual maintenance contract. We will definitely recommend to people and look forward to a long relationship with Perfect Service!
CLEAN AND CHECK A/C. CHECK THERMOSTAT, CHECK FREON LEVELS, CHECK AIR FLOW, CHECK CONDENSER COIL, CHECK ALL ELECTRICAL CONNECTIONS. ADJUST BLOWER COMPONENTS, LUBRICATE ALL NECESSARY MOVING PARTS. EVERYTHING IS RUNNING GREAT.
CLEAN AND CHECK CONDENSER COIL. CHECK ALL ELECTRICAL CONNECTIONS, CHECK FREON LEVELS, CHECK THERMOSTAT. ADJUST BLOWER COMPONENTS, LUBRICATE ALL NECESSARY MOVING PARTS. CHECK AIR FLOW. EVERYTHING IS RUNNING GREAT.
Service work completed for the Heil 2015 air condensing unit with heat pump.
Service work completed for 2011 Heil air conditioning unit with heat pump, cleaned air filters, and adjusted blower motors.
Service work performed for the Heil air conditioning unit with Zep con-coil cleaner. Adjusted blower motor, checked condensation drain.
Checked ducts for the build-up, cleaned condensation drain and condensing coil.
Service agreement maintained with regular cleaning.
Service work performed for the Heil 2013 air condensing unit with Zep con-coil cleaner, no repairs needed.
Installed the 2013 UV light system.
Installed new 3ton package unit with 12 yr warranty on parts and labor.
Cleaned condenser coil for 2005 Air conditioning unit with Zep con-coil cleaner, no repairs needed, also checked ducts for buildup and cleaned air filters.
HVAC service on a 5-year-old American Standard. Found bad condenser pump and replaced. A dirty coil will cause the unit to run longer, and bring on the backup heat more often, which will cost you more money.
Check and clean on a 5-year-old Bryant. Check heat exchanger, a heat exchanger can develop cracks with age. If they exist, there is a risk of serious illness from the toxic fumes emitted.
3-year-old Ameristar check and clean. Check and clean condenser coil. Foreign material on the condenser coil reduces the system capacity to remove heat from the house.
Air Conditioning service. Diagnose, clean and perform annual AC maintenance and tune-up on Heil Cooling System. Cleaned condenser coil, check Freon pressures, cleared drain lines, oiled necessary moving parts, on 3 year old HVAC system with R-410a. Heating and cooling maintenance complete which will help lower cooling cost for this residential customer. Cooling system is now ready for spring and summer weather.