Complaint no a/c blowing warm air. Cause of the issue was dead capacitor on outdoor coil and stuck sequencer on indoor air handler causing one of the heaters to never shut off. Replaced capacitor and sequencer. Fan motor on outdoor coil was newer and set in reverse. Switched wires on fan motor so that it spins the right direction. Puron levels look good. System is operating normally at this time.