Great service as always.
Very nice and knowledgeable, answered all my questions and took time to help me understand. Will be using again!
Always great service from Charlie’s Air Heating and Air Conditioning
Was great from beginning to end! Technicians were friendly and completed job in one day. Would definitely recommend Charlie’s air conditioning and heating service for a job well done.
Phil has always been good.
Complaint a/c not keeping up Cause of the issue is bad txv. Need to replace txv and weigh in correct amount of Puron. Quoted $505.00 plus service call. Replaced txv and charged the system with R-410A. System operating normally at this time.
NO cooling, another company removed control board and blower, looked up parts, replaced board, blower. Fired up ac found compressor and fan wired incorrectly. Wired right, fan motor was hot and loud, damage was done to motor, replaced condenser motor tested ac system is cooling
AC Not Keeping Up/ 2021 AC Check Up Cause of the issue was dead capacitor on outdoor coil. Replaced capacitor and added 1 lb of R-22. Everything else was clean and checked out well. System operating normally at this time.
Behavioral health side raising in temperature No cooling unit 3, found compressor locked up, condenser fan motor broken. Unit needs a new compressor and ecm fan motor. Spoke with Keith, wants us to check warranty. Replaced compressor under warranty, fan motor under warranty. Pressure tested and evacuated system, charged unit, system is cooling
No cooling, washed condenser, checked charge, added 2 lbs r22, system is cooling
Start new 2021 PCSA AC MAINTENANCE Capacitor on outdoor coil needed replaced. Capacitor on blower motor needed replaced. Customer wanted new thermostat. Everything else was clean and checked out well. System operating normally at this time.
Bad a/h board. Low on R-22 compressor wonâ€™t pump set up est.
Cause of the issue was dead capacitor. System is operating. Temp drop inside is about 15 degrees or so.
Complaint no a/c rooftop unit found condenser fan motor locked up, compressor overheated. Spoke with Keith, coming back this afternoon with motor and to see if compressor has cooled down Returned in afternoon, compressor had cooled down and reset. Replaced condenser fan motor with capacitor, tested ac system is cooling
PCSA 2021 Prepaid AC Maintenance Everything was clean and checked out well. System operating normally at this time.
Wired fan to run continuous, opened up side of unit to add more return, checked charge, replaced capacitor system is cooling
No cooling, found burnt up outdoor capacitor. Replaced capacitor, checked charge, coil is very dirty, no hose hookup available. System was cooling but further attention is needed
AC Not Cooling replaced burnt parts
AC MAINTENANCE Switched from 1 time to pcsa Replaced single run cap Filter clean All other checks good
Complaint a/c not cooling washed condenser