I have had in the past couple years 3 different technicians from Charlie’s Air Conditioning and Heating and they have all been professional, on time, very knowledgeable, prepare anything needed right away and have all acted like they have my best interest at heart. I have recommended them to all of my friends and families.
Very pleased with the work done
Would recommend Charlie’s to anyone who needs heating and A/C services.
went right to work on outside unit. showed my granddaughter the faulty part and was on his way.
Always please w/CH&A…very professional courteous helpful
Justin was friendly quick and thorough All of Charlie’s staff are very friendly and helpful
You don’t me want to
Phil did his usual good service and also gave me some good advise on replacing. My AC and furance.
Charlie’s is so professional and Daniel is a great technician
Justin was outstanding! Very professional and thorough.
These folks have taken care of us since we moved into the area. Always feel good about prices and the way my systems are operating when they leave.
Daniel was very professional & explained things to me & did a great job.
NO AC - Unit blowing warm air. Replaced capacitor.
Complaint strange smell. Inspected furnaces and indoor coils. Didn’t see any signs of trouble or anything that would cause a smell. Continued to inspect utility room and found the possible origin of the smell to be the emergency battery for a pump. Battery was overheating and putting off an overwhelming odor. Maintenance removed battery from the room and will monitor for any changes in the smell.
PCSA 2022 PREPAID AC CHECK UP .forgot appointment System checks out good at this time, coil is clean, filter is changed, drain is flushed. System was low on refrigerant, charged with 1 pound of 410A. Need to monitor on next visit to see if it gets worse or not.
PCSA 2022 a/c check up renewal. System is running efficiently at this time, filter is routinely changed by customer, drain is flushed. Outdoor coil was dirty with dust and debris, cleaned thoroughly for optimal efficiency.
Motor quit - NO AC.Recleaned pump changed filter.
Just bought this house and wants 2 ac units checked out. One system on south side of house was not running due to bad capacitor, replaced and verified operation. Found that system was also 2 pounds low on R22, charged system and Verified operation. Filters need to be changed and customer said she will change them this week. North side system isn’t running efficiently at this time.
Replaced aluminum A/coil
TXV for M6 dropped off with James
Drain line was completely clogged in garage with a combination of rust and some sort of paste. Thoroughly cleaned drain line and added pan treatment to help prevent this from reoccurring. Customer will monitor system and let us know of any changes. System is operating normally at this time.
Breaker is bad. Swapped out a 20 amp double pole with another 20 amp double pole that was no longer in use, their electric water heater had been swapped with a gas water heater years ago. Customer will buy a breaker in the correct style and replace breaker. System cooling at this time
Performed leak search and found the leak to be in the outdoor coil. It appeared the outdoor coil was recently bumped by a lawnmower causing one of the end loops to crack. Found and fixed the leak and added another pound of R-410A to the system to put Puron levels back into operating range. System is operating normally at this time.
We need to order an evap coil for this and remove the filter drier outside currently there are two liquid line filter driers. Leave the one at the air handler and cut out and re pipe the one in the unit with just copper The best time to do this coil would be a Wednesday or Friday
Complaint no a/c not keeping up, found unit working great except there is no return air for that room, as soon as you open a door all the cool air gets pulled from the room and into the main mall. Waiting for a decent day to get on the roof and try to gameplan return air for the room. Until then its working as well as it can, suggest leaving doors closed as much as possible until then
Cleaned drain pan and A/coil. Rabbi changed filter
Quoted 4 ton heat pump replacement