Charlie’s, excellent service; friendly, accommodating office staff; personable, knowledgeable techs; convenient scheduling. Charlie’s has been our heating/cooling contractor for years, and we have trusted them to fulfill our needs. Daniel provided excellent service today, as he always does.
Extremely personable and knowledgeable about how our system works!
Daniel, was above and beyond, please send him anytime we need service
On time, professional, patient and great attitude!
These people have never disappointed me. They listen, evaluate, and solve my problems.
PCSA 2021 heating maintenance renewal Thermostat buttons were unresponsive. New thermostat was needed. Contactor on outdoor coil is a little worn but still operating normally. Everything else was clean and checked out well. System is operating normally at this time.
2 System PCSA heating maintenance Need to comcome back out and replace board once itâ€™s in Replaced blown dual run cap under parts and labor warranty Will take pics of cabinet upon return 10/19 Board replaced Pictures taken Customer advised to get carbon monoxide detector in house
All back up coming on 15 kw Checked defrost Checked SH and SC in air conditioning Both coils clean Filters clean All checks good
Meal Worms M2-returned and replaced suction and liquid line filter driers. Unit had a badly burnt up compressor, this step is an industry standard to ensure all acid has been removed from system. Pressure tested, evacuated to 500 microns, recharged system. Tested heat and cool, run checks ok
Completed pm humidifier 30%
10 kw equipped and all coming on Checked defrost Contactor and cap check good Customer included a check for something else I will give to Kyle Customer would like invoice mailed
Burners not lighting across Cleaned burners and flame sensor Checks good
2021 PCSA heating maintenance renewal . Completed fall PM cleared codes on board. Ck filter in spring
Complaint not cooling Cause of the issue was bad blower motor. Installed temporary motor until replacement motor arrives.
AC Not Cooling. Need est. asap
PCSA 2021 RENEWAL - Heating Check Up Completed fall ck all in good order.
Checked system slight noise in condenser motor. Will recheck inspring new filter flushed pump.
Complaint lines are frosting up Cause of the issue was a leak in outdoor coil. Added 7 lbs of R-410A and leak stop until part arrives.
Complaint outside unit making noise . Wrong capacitor in condenser replaced with 35/7.5. Need to ck motor speed & size 1075 1/3 hp. Checked on motor, size and capacitor are correct
PCSA Prepaid Heating 2021 Check Up 2 Systems Everything was clean and checked out well. Both systems are operating normally at this time.